Program Version:EnergyPlus, Version 8.8.0-7c3bbe4830, YMD=2018.03.11 14:48
Tabular Output Report in Format: HTML
Building: Building
Environment: SUMMERDAY ** jiaozuo Henan CHN CSWD WMO#=570830
Simulation Timestamp: 2018-03-11 14:48:12
Report: Annual Building Utility Performance Summary
For: Entire Facility
Timestamp: 2018-03-11 14:48:12
Values gathered over 8784.00 hours| Total Energy [GJ] | Energy Per Total Building Area [MJ/m2] | Energy Per Conditioned Building Area [MJ/m2] | |
| Total Site Energy | 212.66 | 229.36 | 229.36 |
| Net Site Energy | 212.66 | 229.36 | 229.36 |
| Total Source Energy | 579.55 | 625.06 | 625.06 |
| Net Source Energy | 579.55 | 625.06 | 625.06 |
| Site=>Source Conversion Factor | |
| Electricity | 3.167 |
| Natural Gas | 1.084 |
| District Cooling | 1.056 |
| District Heating | 3.613 |
| Steam | 0.300 |
| Gasoline | 1.050 |
| Diesel | 1.050 |
| Coal | 1.050 |
| Fuel Oil #1 | 1.050 |
| Fuel Oil #2 | 1.050 |
| Propane | 1.050 |
| Other Fuel 1 | 1.000 |
| Other Fuel 2 | 1.000 |
| Area [m2] | |
| Total Building Area | 927.20 |
| Net Conditioned Building Area | 927.20 |
| Unconditioned Building Area | 0.00 |
| Electricity [GJ] | Natural Gas [GJ] | Additional Fuel [GJ] | District Cooling [GJ] | District Heating [GJ] | Water [m3] | |
| Heating | 0.00 | 45.10 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | 23.18 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 81.54 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 47.85 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 3.10 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 9.06 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 2.83 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total End Uses | 167.56 | 45.10 | 0.00 | 0.00 | 0.00 | 0.00 |
| Subcategory | Electricity [GJ] | Natural Gas [GJ] | Additional Fuel [GJ] | District Cooling [GJ] | District Heating [GJ] | Water [m3] | |
| Heating | Boiler | 0.00 | 45.10 | 0.00 | 0.00 | 0.00 | 0.00 |
| Boiler Parasitic | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Cooling | General | 23.18 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | GeneralLights | 81.54 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | General | 47.85 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | Transformer | 3.10 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | General | 9.06 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | General | 2.83 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Electricity Intensity [MJ/m2] | Natural Gas Intensity [MJ/m2] | Additional Fuel Intensity [MJ/m2] | District Cooling Intensity [MJ/m2] | District Heating Intensity [MJ/m2] | Water Intensity [m3/m2] | |
| Lighting | 87.94 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| HVAC | 37.83 | 48.64 | 0.00 | 0.00 | 0.00 | 0.00 |
| Other | 54.95 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total | 180.72 | 48.64 | 0.00 | 0.00 | 0.00 | 0.00 |
| Electricity Intensity [MJ/m2] | Natural Gas Intensity [MJ/m2] | Additional Fuel Intensity [MJ/m2] | District Cooling Intensity [MJ/m2] | District Heating Intensity [MJ/m2] | Water Intensity [m3/m2] | |
| Lighting | 87.94 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| HVAC | 37.83 | 48.64 | 0.00 | 0.00 | 0.00 | 0.00 |
| Other | 54.95 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total | 180.72 | 48.64 | 0.00 | 0.00 | 0.00 | 0.00 |
| Electricity [GJ] | Percent Electricity [%] | |
| Fuel-Fired Power Generation | 0.000 | 0.00 |
| High Temperature Geothermal* | 0.000 | 0.00 |
| Photovoltaic Power | 0.000 | 0.00 |
| Wind Power | 0.000 | 0.00 |
| Power Conversion | 0.000 | 0.00 |
| Net Decrease in On-Site Storage | 0.000 | 0.00 |
| Total On-Site Electric Sources | 0.000 | 0.00 |
| Electricity Coming From Utility | 167.561 | 100.00 |
| Surplus Electricity Going To Utility | 0.000 | 0.00 |
| Net Electricity From Utility | 167.561 | 100.00 |
| Total On-Site and Utility Electric Sources | 167.561 | 100.00 |
| Total Electricity End Uses | 167.561 | 100.00 |
| Heat [GJ] | Percent Heat [%] | |
| Water-Side Heat Recovery | 0.00 | |
| Air to Air Heat Recovery for Cooling | 0.00 | |
| Air to Air Heat Recovery for Heating | 0.00 | |
| High-Temperature Geothermal* | 0.00 | |
| Solar Water Thermal | 0.00 | |
| Solar Air Thermal | 0.00 | |
| Total On-Site Thermal Sources | 0.00 |
| Water [m3] | Percent Water [%] | |
| Rainwater Collection | 0.00 | - |
| Condensate Collection | 0.00 | - |
| Groundwater Well | 0.00 | - |
| Total On Site Water Sources | 0.00 | - |
| - | - | - |
| Initial Storage | 0.00 | - |
| Final Storage | 0.00 | - |
| Change in Storage | 0.00 | - |
| - | - | - |
| Water Supplied by Utility | 0.00 | - |
| - | - | - |
| Total On Site, Change in Storage, and Utility Water Sources | 0.00 | - |
| Total Water End Uses | 0.00 | - |
| Degrees [deltaC] | |
| Tolerance for Zone Heating Setpoint Not Met Time | 0.20 |
| Tolerance for Zone Cooling Setpoint Not Met Time | 0.20 |
| Facility [Hours] | |
| Time Setpoint Not Met During Occupied Heating | 0.00 |
| Time Setpoint Not Met During Occupied Cooling | 151.75 |
| Time Not Comfortable Based on Simple ASHRAE 55-2004 | 36.75 |
Table of Contents
TopReport: Input Verification and Results Summary
For: Entire Facility
Timestamp: 2018-03-11 14:48:12
General| Value | |
| Program Version and Build | EnergyPlus, Version 8.8.0-7c3bbe4830, YMD=2018.03.11 14:48 |
| RunPeriod | SUMMERDAY |
| Weather File | jiaozuo Henan CHN CSWD WMO#=570830 |
| Latitude [deg] | 35.21 |
| Longitude [deg] | 113.27 |
| Elevation [m] | 110.40 |
| Time Zone | 8.00 |
| North Axis Angle [deg] | 30.00 |
| Rotation for Appendix G [deg] | 0.00 |
| Hours Simulated [hrs] | 8784.00 |
| Total | North (315 to 45 deg) | East (45 to 135 deg) | South (135 to 225 deg) | West (225 to 315 deg) | |
| Gross Wall Area [m2] | 274.20 | 91.50 | 45.60 | 91.50 | 45.60 |
| Above Ground Wall Area [m2] | 274.20 | 91.50 | 45.60 | 91.50 | 45.60 |
| Window Opening Area [m2] | 60.90 | 20.85 | 9.12 | 21.81 | 9.12 |
| Gross Window-Wall Ratio [%] | 22.21 | 22.79 | 20.00 | 23.84 | 20.00 |
| Above Ground Window-Wall Ratio [%] | 22.21 | 22.79 | 20.00 | 23.84 | 20.00 |
| Total | North (315 to 45 deg) | East (45 to 135 deg) | South (135 to 225 deg) | West (225 to 315 deg) | |
| Gross Wall Area [m2] | 274.20 | 91.50 | 45.60 | 91.50 | 45.60 |
| Above Ground Wall Area [m2] | 274.20 | 91.50 | 45.60 | 91.50 | 45.60 |
| Window Opening Area [m2] | 60.90 | 20.85 | 9.12 | 21.81 | 9.12 |
| Gross Window-Wall Ratio [%] | 22.21 | 22.79 | 20.00 | 23.84 | 20.00 |
| Above Ground Window-Wall Ratio [%] | 22.21 | 22.79 | 20.00 | 23.84 | 20.00 |
| Total | |
| Gross Roof Area [m2] | 463.60 |
| Skylight Area [m2] | 0.00 |
| Skylight-Roof Ratio [%] | 0.00 |
| Area [m2] | Conditioned (Y/N) | Part of Total Floor Area (Y/N) | Volume [m3] | Multipliers | Above Ground Gross Wall Area [m2] | Underground Gross Wall Area [m2] | Window Glass Area [m2] | Opening Area [m2] | Lighting [W/m2] | People [m2 per person] | Plug and Process [W/m2] | |
| PLENUM-1 | 463.60 | Yes | Yes | 283.20 | 1.00 | 54.84 | 0.00 | 0.00 | 0.00 | 0.0000 | 0.0000 | |
| SPACE1-1 | 99.16 | Yes | Yes | 239.25 | 1.00 | 73.20 | 0.00 | 21.81 | 21.81 | 15.9742 | 9.01 | 10.6495 |
| SPACE2-1 | 42.73 | Yes | Yes | 103.31 | 1.00 | 36.48 | 0.00 | 9.12 | 9.12 | 16.0056 | 8.55 | 10.6704 |
| SPACE3-1 | 96.48 | Yes | Yes | 239.25 | 1.00 | 73.20 | 0.00 | 20.85 | 20.85 | 16.4179 | 8.77 | 10.9453 |
| SPACE4-1 | 42.73 | Yes | Yes | 103.31 | 1.00 | 36.48 | 0.00 | 9.12 | 9.12 | 16.0056 | 8.55 | 10.6704 |
| SPACE5-1 | 182.49 | Yes | Yes | 447.68 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 16.2420 | 9.12 | 10.8280 |
| Total | 927.20 | 1416.00 | 274.20 | 0.00 | 60.90 | 60.90 | 8.0889 | 17.83 | 5.3926 | |||
| Conditioned Total | 927.20 | 1416.00 | 274.20 | 0.00 | 60.90 | 60.90 | 8.0889 | 17.83 | 5.3926 | |||
| Unconditioned Total | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | ||||||
| Not Part of Total | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
Report: Demand End Use Components Summary
For: Entire Facility
Timestamp: 2018-03-11 14:48:12
End Uses| Electricity [W] | Natural Gas [W] | Propane [W] | District Cooling [W] | Steam [W] | Water [m3/s] | |
| Time of Peak | 30-JUL-14:00 | 07-JAN-06:15 | - | - | - | - |
| Heating | 0.00 | 32104.24 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | 8600.92 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 7500.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 4000.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 250.97 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 700.27 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 541.93 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total End Uses | 21594.09 | 32104.24 | 0.00 | 0.00 | 0.00 | 0.00 |
| Subcategory | Electricity [W] | Natural Gas [W] | Propane [W] | District Cooling [W] | Steam [W] | Water [m3/s] | |
| Heating | Boiler | 0.00 | 32104.24 | 0.00 | 0.00 | 0.00 | 0.00 |
| Boiler Parasitic | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Cooling | General | 8600.92 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | GeneralLights | 7500.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | General | 4000.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | Transformer | 250.97 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | General | 700.27 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | General | 541.93 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
Report: Source Energy End Use Components Summary
For: Entire Facility
Timestamp: 2018-03-11 14:48:12
Values gathered over 8784.00 hours| Source Electricity [GJ] | Source Natural Gas [GJ] | Source Additional Fuel [GJ] | Source District Cooling [GJ] | Source District Heating [GJ] | |
| Heating | 0.00 | 48.89 | 0.00 | 0.00 | 0.00 |
| Cooling | 73.40 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 258.23 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 151.53 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 9.82 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 28.71 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 8.98 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total Source Energy End Use Components | 530.66 | 48.89 | 0.00 | 0.00 | 0.00 |
| Source Electricity [MJ/m2] | Source Natural Gas [MJ/m2] | Source Additional Fuel [MJ/m2] | Source District Cooling [MJ/m2] | Source District Heating [MJ/m2] | |
| Heating | 0.00 | 52.73 | 0.00 | 0.00 | 0.00 |
| Cooling | 79.16 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 278.50 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 163.42 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 10.60 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 30.96 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 9.68 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total Source Energy End Use Components | 572.33 | 52.73 | 0.00 | 0.00 | 0.00 |
| Source Electricity [MJ/m2] | Source Natural Gas [MJ/m2] | Source Additional Fuel [MJ/m2] | Source District Cooling [MJ/m2] | Source District Heating [MJ/m2] | |
| Heating | 0.00 | 52.73 | 0.00 | 0.00 | 0.00 |
| Cooling | 79.16 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 278.50 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 163.42 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 10.60 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 30.96 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 9.68 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total Source Energy End Use Components | 572.33 | 52.73 | 0.00 | 0.00 | 0.00 |
Report: Climatic Data Summary
For: Entire Facility
Timestamp: 2018-03-11 14:48:12
SizingPeriod:DesignDay| Maximum Dry Bulb [C] | Daily Temperature Range [deltaC] | Humidity Value | Humidity Type | Wind Speed [m/s] | Wind Direction | |
| CHICAGO_IL_USA ANNUAL HEATING 99% DESIGN CONDITIONS DB | -17.30 | 0.00 | -17.30 | Wetbulb [C] | 4.90 | 270.00 |
| CHICAGO_IL_USA ANNUAL COOLING 1% DESIGN CONDITIONS DB/MCWB | 31.50 | 10.70 | 23.00 | Wetbulb [C] | 5.30 | 230.00 |
| Value | |
| None |
Report: Envelope Summary
For: Entire Facility
Timestamp: 2018-03-11 14:48:12
Opaque Exterior| Construction | Reflectance | U-Factor with Film [W/m2-K] | U-Factor no Film [W/m2-K] | Gross Area [m2] | Net Area [m2] | Azimuth [deg] | Tilt [deg] | Cardinal Direction | |
| WALL-1PF | WALL-1 | 0.22 | 0.384 | 0.408 | 18.30 | 18.30 | 210.00 | 90.00 | S |
| WALL-1PR | WALL-1 | 0.22 | 0.384 | 0.408 | 9.12 | 9.12 | 120.00 | 90.00 | E |
| WALL-1PB | WALL-1 | 0.22 | 0.384 | 0.408 | 18.30 | 18.30 | 30.00 | 90.00 | N |
| WALL-1PL | WALL-1 | 0.22 | 0.384 | 0.408 | 9.12 | 9.12 | 300.00 | 90.00 | W |
| TOP-1 | ROOF-1 | 0.35 | 0.271 | 0.282 | 463.60 | 463.60 | 210.00 | 0.00 | |
| FRONT-1 | WALL-1 | 0.22 | 0.384 | 0.408 | 73.20 | 51.39 | 210.00 | 90.00 | S |
| F1-1 | FLOOR-SLAB-1 | 0.35 | 4.174 | 12.894 | 99.16 | 99.16 | 30.00 | 180.00 | |
| RIGHT-1 | WALL-1 | 0.22 | 0.384 | 0.408 | 36.48 | 27.36 | 120.00 | 90.00 | E |
| F2-1 | FLOOR-SLAB-1 | 0.35 | 4.174 | 12.894 | 42.73 | 42.73 | 300.00 | 180.00 | |
| BACK-1 | WALL-1 | 0.22 | 0.384 | 0.408 | 73.20 | 52.35 | 30.00 | 90.00 | N |
| F3-1 | FLOOR-SLAB-1 | 0.35 | 4.174 | 12.894 | 96.48 | 96.48 | 74.22 | 180.00 | |
| LEFT-1 | WALL-1 | 0.22 | 0.384 | 0.408 | 36.48 | 27.36 | 300.00 | 90.00 | W |
| F4-1 | FLOOR-SLAB-1 | 0.35 | 4.174 | 12.894 | 42.73 | 42.73 | 120.00 | 180.00 | |
| F5-1 | FLOOR-SLAB-1 | 0.35 | 4.174 | 12.894 | 182.49 | 182.49 | 30.00 | 180.00 |
| Construction | Glass Area [m2] | Frame Area [m2] | Divider Area [m2] | Area of One Opening [m2] | Area of Multiplied Openings [m2] | Glass U-Factor [W/m2-K] | Glass SHGC | Glass Visible Transmittance | Frame Conductance [W/m2-K] | Divider Conductance [W/m2-K] | Shade Control | Parent Surface | Azimuth [deg] | Tilt [deg] | Cardinal Direction | |
| WF-1 | DBL CLR 3MM/13MM AIR | 16.56 | 0.00 | 0.00 | 16.56 | 16.56 | 2.720 | 0.764 | 0.812 | No | FRONT-1 | 210.00 | 90.00 | S | ||
| DF-1 | SGL GREY 3MM | 5.25 | 0.00 | 0.00 | 5.25 | 5.25 | 5.894 | 0.716 | 0.611 | No | FRONT-1 | 210.00 | 90.00 | S | ||
| WR-1 | DBL CLR 3MM/13MM AIR | 9.12 | 0.00 | 0.00 | 9.12 | 9.12 | 2.720 | 0.764 | 0.812 | No | RIGHT-1 | 120.00 | 90.00 | E | ||
| WB-1 | DBL CLR 3MM/13MM AIR | 16.44 | 0.00 | 0.00 | 16.44 | 16.44 | 2.720 | 0.764 | 0.812 | No | BACK-1 | 30.00 | 90.00 | N | ||
| DB-1 | SGL GREY 3MM | 4.41 | 0.00 | 0.00 | 4.41 | 4.41 | 5.894 | 0.716 | 0.611 | No | BACK-1 | 30.00 | 90.00 | N | ||
| WL-1 | DBL CLR 3MM/13MM AIR | 9.12 | 0.00 | 0.00 | 9.12 | 9.12 | 2.720 | 0.764 | 0.812 | No | LEFT-1 | 300.00 | 90.00 | W | ||
| Total or Average | 60.90 | 3.223 | 0.756 | 0.780 | ||||||||||||
| North Total or Average | 20.85 | 3.391 | 0.754 | 0.769 | ||||||||||||
| Non-North Total or Average | 40.05 | 3.136 | 0.757 | 0.785 |
| Construction | Area of One Opening [m2] | Area of Openings [m2] | Glass U-Factor [W/m2-K] | Glass SHGC | Glass Visible Transmittance | Parent Surface | |
| Total or Average | 0.00 | - | - | - |
| Construction | U-Factor with Film [W/m2-K] | U-Factor no Film [W/m2-K] | Gross Area [m2] | Parent Surface | |
| None |
Report: Shading Summary
For: Entire Facility
Timestamp: 2018-03-11 14:48:12
Sunlit Fraction| March 21 9am | March 21 noon | March 21 3pm | June 21 9am | June 21 noon | June 21 3pm | December 21 9am | December 21 noon | December 21 3pm | |
| WF-1 | 0.00 | 0.00 | 0.17 | 0.00 | 0.00 | 0.00 | 0.00 | 0.27 | 0.67 |
| DF-1 | 0.00 | 0.24 | 0.47 | 0.00 | 0.02 | 0.22 | 0.98 | 0.65 | 0.87 |
| WR-1 | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 0.00 |
| WB-1 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| DB-1 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| WL-1 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 |
| Name | Type | Shaded Construction | Control | Glare Control | |
| None |
Report: Lighting Summary
For: Entire Facility
Timestamp: 2018-03-11 14:48:12
Interior Lighting| Zone | Lighting Power Density [W/m2] | Zone Area [m2] | Total Power [W] | End Use Subcategory | Schedule Name | Scheduled Hours/Week [hr] | Hours/Week > 1% [hr] | Full Load Hours/Week [hr] | Return Air Fraction | Conditioned (Y/N) | Consumption [GJ] | |
| SPACE1-1 LIGHTS 1 | SPACE1-1 | 15.9742 | 99.16 | 1584.00 | GeneralLights | LIGHTS-1 | 57.70 | 168.00 | 57.76 | 0.2000 | Y | 17.22 |
| SPACE2-1 LIGHTS 1 | SPACE2-1 | 16.0056 | 42.73 | 684.00 | GeneralLights | LIGHTS-1 | 57.70 | 168.00 | 57.76 | 0.2000 | Y | 7.44 |
| SPACE3-1 LIGHTS 1 | SPACE3-1 | 16.4179 | 96.48 | 1584.00 | GeneralLights | LIGHTS-1 | 57.70 | 168.00 | 57.76 | 0.2000 | Y | 17.22 |
| SPACE4-1 LIGHTS 1 | SPACE4-1 | 16.0056 | 42.73 | 684.00 | GeneralLights | LIGHTS-1 | 57.70 | 168.00 | 57.76 | 0.2000 | Y | 7.44 |
| SPACE5-1 LIGHTS 1 | SPACE5-1 | 16.2420 | 182.49 | 2964.00 | GeneralLights | LIGHTS-1 | 57.70 | 168.00 | 57.76 | 0.2000 | Y | 32.22 |
| Interior Lighting Total | 16.1777 | 463.60 | 7500.00 | 81.54 |
| Zone | Control Name | Daylighting Method | Control Type | Fraction Controlled | Lighting Installed in Zone [W] | Lighting Controlled [W] | |
| None |
| Total Watts | Astronomical Clock/Schedule | Schedule Name | Scheduled Hours/Week [hr] | Hours/Week > 1% [hr] | Full Load Hours/Week [hr] | Consumption [GJ] | |
| Exterior Lighting Total | 0.00 | 0.00 |
Report: Equipment Summary
For: Entire Facility
Timestamp: 2018-03-11 14:48:12
Central Plant| Type | Nominal Capacity [W] | Nominal Efficiency [W/W] | IPLV in SI Units [W/W] | IPLV in IP Units [Btu/W-h] | |
| CENTRAL BOILER | Boiler:HotWater | 27475.23 | 0.80 | ||
| CENTRAL CHILLER | Chiller:Electric | 35614.09 | 3.20 |
| Type | Design Coil Load [W] | Nominal Total Capacity [W] | Nominal Sensible Capacity [W] | Nominal Latent Capacity [W] | Nominal Sensible Heat Ratio | Nominal Efficiency [W/W] | Nominal Coil UA Value [W/C] | Nominal Coil Surface Area [m2] | |
| OA COOLING COIL 1 | Coil:Cooling:Water | 11420.22 | 8857.93 | 5619.75 | 3238.19 | 0.63 | - | 879.19 | 8.92 |
| MAIN COOLING COIL 1 | Coil:Cooling:Water | 12774.24 | 17920.27 | 12949.38 | 4970.89 | 0.72 | - | 1489.74 | 15.11 |
| DX Cooling Coil Type | Standard Rated Net Cooling Capacity [W] | Standard Rated Net COP [W/W] | EER [Btu/W-h] | SEER [Btu/W-h] | IEER [Btu/W-h] | |
| None |
| DX Cooling Coil Type | Rated Net Cooling Capacity Test A [W] | Rated Electric Power Test A [W] | Rated Net Cooling Capacity Test B [W] | Rated Electric Power Test B [W] | Rated Net Cooling Capacity Test C [W] | Rated Electric Power Test C [W] | Rated Net Cooling Capacity Test D [W] | Rated Electric Power Test D [W] | |
| None |
| DX Heating Coil Type | High Temperature Heating (net) Rating Capacity [W] | Low Temperature Heating (net) Rating Capacity [W] | HSPF [Btu/W-h] | Region Number | |
| None |
| Type | Design Coil Load [W] | Nominal Total Capacity [W] | Nominal Efficiency [W/W] | |
| SPACE1-1 ZONE COIL | Coil:Heating:Water | 4624.10 | 3704.71 | - |
| SPACE2-1 ZONE COIL | Coil:Heating:Water | 1984.29 | 1994.75 | - |
| SPACE3-1 ZONE COIL | Coil:Heating:Water | 4495.10 | 3778.87 | - |
| SPACE4-1 ZONE COIL | Coil:Heating:Water | 2039.35 | 2050.51 | - |
| SPACE5-1 ZONE COIL | Coil:Heating:Water | 3570.75 | 3222.73 | - |
| OA HEATING COIL 1 | Coil:Heating:Water | 6877.10 | 4553.72 | - |
| MAIN HEATING COIL 1 | Coil:Heating:Water | 3498.65 | 3080.17 | - |
| Type | Total Efficiency [W/W] | Delta Pressure [pa] | Max Air Flow Rate [m3/s] | Rated Electric Power [W] | Rated Power Per Max Air Flow Rate [W-s/m3] | Motor Heat In Air Fraction | End Use | |
| SUPPLY FAN 1 | Fan:VariableVolume | 0.70 | 600.00 | 1.05 | 902.71 | 857.14 | 1.00 | General |
| Type | Control | Head [pa] | Water Flow [m3/s] | Electric Power [W] | Power Per Water Flow Rate [W-s/m3] | Motor Efficiency [W/W] | |
| HW CIRC PUMP | Pump:VariableSpeed | Intermittent | 179352.00 | 0.000595 | 151.93 | 255487.18 | 0.90 |
| CW CIRC PUMP | Pump:VariableSpeed | Intermittent | 179352.00 | 0.002121 | 541.93 | 255487.18 | 0.90 |
| Type | Storage Volume [m3] | Input [W] | Thermal Efficiency [W/W] | Recovery Efficiency [W/W] | Energy Factor | |
| None |
Report: HVAC Sizing Summary
For: Entire Facility
Timestamp: 2018-03-11 14:48:12
Zone Sensible Cooling| Calculated Design Load [W] | User Design Load [W] | User Design Load per Area [W/m2] | Calculated Design Air Flow [m3/s] | User Design Air Flow [m3/s] | Design Day Name | Date/Time Of Peak {TIMESTAMP} | Thermostat Setpoint Temperature at Peak Load [C] | Indoor Temperature at Peak Load [C] | Indoor Humidity Ratio at Peak Load [kgWater/kgAir] | Outdoor Temperature at Peak Load [C] | Outdoor Humidity Ratio at Peak Load [kgWater/kgAir] | Minimum Outdoor Air Flow Rate [m3/s] | Heat Gain Rate from DOAS [W] | |
| SPACE1-1 | 2584.90 | 2584.90 | 26.07 | 0.215 | 0.215 | CHICAGO_IL_USA ANNUAL COOLING 1% DESIGN CONDITIONS DB/MCWB | 7/21 15:45:00 | 23.90 | 23.90 | 0.00981 | 31.02 | 0.01459 | 0.056 | 0.00 |
| SPACE2-1 | 2175.40 | 2175.40 | 50.90 | 0.181 | 0.181 | CHICAGO_IL_USA ANNUAL COOLING 1% DESIGN CONDITIONS DB/MCWB | 7/21 10:30:00 | 23.90 | 23.90 | 0.00943 | 28.24 | 0.01459 | 0.025 | 0.00 |
| SPACE3-1 | 2779.15 | 2779.15 | 28.81 | 0.231 | 0.231 | CHICAGO_IL_USA ANNUAL COOLING 1% DESIGN CONDITIONS DB/MCWB | 7/21 10:00:00 | 23.90 | 23.90 | 0.00975 | 27.43 | 0.01459 | 0.055 | 0.00 |
| SPACE4-1 | 2508.90 | 2508.90 | 58.71 | 0.209 | 0.209 | CHICAGO_IL_USA ANNUAL COOLING 1% DESIGN CONDITIONS DB/MCWB | 7/21 18:00:00 | 23.90 | 23.90 | 0.00937 | 28.93 | 0.01459 | 0.025 | 0.00 |
| SPACE5-1 | 2608.28 | 2608.28 | 14.29 | 0.217 | 0.217 | CHICAGO_IL_USA ANNUAL COOLING 1% DESIGN CONDITIONS DB/MCWB | 7/21 15:00:00 | 23.90 | 23.90 | 0.01038 | 31.50 | 0.01459 | 0.103 | 0.00 |
| Calculated Design Load [W] | User Design Load [W] | User Design Load per Area [W/m2] | Calculated Design Air Flow [m3/s] | User Design Air Flow [m3/s] | Design Day Name | Date/Time Of Peak {TIMESTAMP} | Thermostat Setpoint Temperature at Peak Load [C] | Indoor Temperature at Peak Load [C] | Indoor Humidity Ratio at Peak Load [kgWater/kgAir] | Outdoor Temperature at Peak Load [C] | Outdoor Humidity Ratio at Peak Load [kgWater/kgAir] | Minimum Outdoor Air Flow Rate [m3/s] | Heat Gain Rate from DOAS [W] | |
| SPACE1-1 | 3860.76 | 3860.76 | 38.93 | 0.115 | 0.115 | CHICAGO_IL_USA ANNUAL HEATING 99% DESIGN CONDITIONS DB | 1/21 24:00:00 | 22.20 | 22.20 | 0.00377 | -17.30 | 0.00084 | 0.056 | 0.00 |
| SPACE2-1 | 1625.15 | 1625.15 | 38.03 | 0.049 | 0.049 | CHICAGO_IL_USA ANNUAL HEATING 99% DESIGN CONDITIONS DB | 1/21 24:00:00 | 22.20 | 22.20 | 0.00377 | -17.30 | 0.00084 | 0.025 | 0.00 |
| SPACE3-1 | 3753.07 | 3753.07 | 38.90 | 0.112 | 0.112 | CHICAGO_IL_USA ANNUAL HEATING 99% DESIGN CONDITIONS DB | 1/21 24:00:00 | 22.20 | 22.20 | 0.00377 | -17.30 | 0.00084 | 0.055 | 0.00 |
| SPACE4-1 | 1625.15 | 1625.15 | 38.03 | 0.049 | 0.049 | CHICAGO_IL_USA ANNUAL HEATING 99% DESIGN CONDITIONS DB | 1/21 24:00:00 | 22.20 | 22.20 | 0.00377 | -17.30 | 0.00084 | 0.025 | 0.00 |
| SPACE5-1 | 2981.57 | 2981.57 | 16.34 | 0.089 | 0.103 | CHICAGO_IL_USA ANNUAL HEATING 99% DESIGN CONDITIONS DB | 1/21 24:00:00 | 22.20 | 22.20 | 0.00349 | -17.30 | 0.00084 | 0.103 | 0.00 |
| Calculated cooling [m3/s] | User cooling [m3/s] | Calculated heating [m3/s] | User heating [m3/s] | |
| VAV SYS 1 | 1.05 | 1.05 | 0.43 | 0.43 |
| Previous Design Volume Flow Rate [m3/s] | Algorithm Volume Flow Rate [m3/s] | Coincident Design Volume Flow Rate [m3/s] | Coincident Size Adjusted | Peak Sizing Period Name | Peak Day into Period {TIMESTAMP}[day] | Peak Hour Of Day {TIMESTAMP}[hr] | Peak Step Start Minute {TIMESTAMP}[min] | |
| None |
Report: System Summary
For: Entire Facility
Timestamp: 2018-03-11 14:48:12
Economizer| High Limit Shutoff Control | Minimum Outdoor Air [m3/s] | Maximum Outdoor Air [m3/s] | Return Air Temp Limit | Return Air Enthalpy Limit | Outdoor Air Temperature Limit [C] | Outdoor Air Enthalpy Limit [C] | |
| None |
| Controller:MechanicalVentilation Name | Outdoor Air Per Person [m3/s-person] | Outdoor Air Per Area [m3/s-m2] | Outdoor Air Per Zone [m3/s] | Outdoor Air ACH [ach] | Outdoor Air Method | Outdoor Air Schedule Name | Air Distribution Effectiveness in Cooling Mode | Air Distribution Effectiveness in Heating Mode | Air Distribution Effectiveness Schedule Name | |
| None |
| Winter Clothes [hr] | Summer Clothes [hr] | Summer or Winter Clothes [hr] | |
| SPACE1-1 | 565.75 | 1682.00 | 36.25 |
| SPACE2-1 | 823.50 | 1702.75 | 16.75 |
| SPACE3-1 | 672.25 | 1734.25 | 29.75 |
| SPACE4-1 | 743.75 | 1844.50 | 22.75 |
| SPACE5-1 | 0.75 | 2500.75 | 0.25 |
| PLENUM-1 | 0.00 | 0.00 | 0.00 |
| Facility | 1031.75 | 2511.25 | 36.75 |
| During Heating [hr] | During Cooling [hr] | During Occupied Heating [hr] | During Occupied Cooling [hr] | |
| SPACE1-1 | 105.75 | 148.50 | 0.00 | 148.50 |
| SPACE2-1 | 82.75 | 0.00 | 0.00 | 0.00 |
| SPACE3-1 | 98.00 | 0.00 | 0.00 | 0.00 |
| SPACE4-1 | 84.00 | 68.25 | 0.00 | 3.50 |
| SPACE5-1 | 121.00 | 6.00 | 0.00 | 6.00 |
| PLENUM-1 | 0.00 | 0.00 | 0.00 | 0.00 |
| Facility | 122.50 | 216.50 | 0.00 | 151.75 |
Report: Outdoor Air Summary
For: Entire Facility
Timestamp: 2018-03-11 14:48:12
Average Outdoor Air During Occupied Hours| Average Number of Occupants | Nominal Number of Occupants | Zone Volume [m3] | Mechanical Ventilation [ach] | Infiltration [ach] | AFN Infiltration [ach] | Simple Ventilation [ach] | |
| SPACE1-1 | 9.50 | 11.00 | 239.25 | 0.900 | 0.029 | 0.000 | 0.000 |
| SPACE2-1 | 4.32 | 5.00 | 103.31 | 1.389 | 0.030 | 0.000 | 0.000 |
| SPACE3-1 | 9.50 | 11.00 | 239.25 | 0.880 | 0.029 | 0.000 | 0.000 |
| SPACE4-1 | 4.32 | 5.00 | 103.31 | 1.522 | 0.030 | 0.000 | 0.000 |
| SPACE5-1 | 17.27 | 20.00 | 447.68 | 0.543 | 0.030 | 0.000 | 0.000 |
| Average Number of Occupants | Nominal Number of Occupants | Zone Volume [m3] | Mechanical Ventilation [ach] | Infiltration [ach] | AFN Infiltration [ach] | Simple Ventilation [ach] | |
| SPACE1-1 | 9.50 | 11.00 | 239.25 | 0.522 | 0.000 | 0.000 | 0.000 |
| SPACE2-1 | 4.32 | 5.00 | 103.31 | 0.712 | 0.000 | 0.000 | 0.000 |
| SPACE3-1 | 9.50 | 11.00 | 239.25 | 0.448 | 0.000 | 0.000 | 0.000 |
| SPACE4-1 | 4.32 | 5.00 | 103.31 | 0.785 | 0.000 | 0.000 | 0.000 |
| SPACE5-1 | 17.27 | 20.00 | 447.68 | 0.299 | 0.000 | 0.000 | 0.000 |
Report: Object Count Summary
For: Entire Facility
Timestamp: 2018-03-11 14:48:12
Surfaces by Class| Total | Outdoors | |
| Wall | 24 | 8 |
| Floor | 10 | 5 |
| Roof | 6 | 1 |
| Internal Mass | 0 | 0 |
| Building Detached Shading | 0 | 0 |
| Fixed Detached Shading | 0 | 0 |
| Window | 6 | 6 |
| Door | 0 | 0 |
| Glass Door | 2 | 2 |
| Shading | 4 | 4 |
| Overhang | 0 | 0 |
| Fin | 0 | 0 |
| Tubular Daylighting Device Dome | 0 | 0 |
| Tubular Daylighting Device Diffuser | 0 | 0 |
| Count | |
| HVAC Air Loops | 1 |
| Conditioned Zones | 6 |
| Unconditioned Zones | 0 |
| Supply Plenums | 0 |
| Return Plenums | 1 |
| Count | |
| IDF Objects | 322 |
| Defaulted Fields | 67 |
| Fields with Defaults | 764 |
| Autosized Fields | 82 |
| Autosizable Fields | 93 |
| Autocalculated Fields | 7 |
| Autocalculatable Fields | 113 |
Report: Energy Meters
For: Entire Facility
Timestamp: 2018-03-11 14:48:12
Annual and Peak Values - Electricity| Electricity Annual Value [GJ] | Electricity Minimum Value [W] | Timestamp of Minimum {TIMESTAMP} | Electricity Maximum Value [W] | Timestamp of Maximum {TIMESTAMP} | |
| Electricity:Facility | 0.67 | 515.26 | 07-JUL-00:15 | 17163.02 | 07-JUL-15:00 |
| Electricity:Building | 0.45 | 475.00 | 07-JUL-00:15 | 12000.00 | 07-JUL-10:15 |
| Electricity:Zone:SPACE1-1 | 0.09 | 100.32 | 07-JUL-00:15 | 2534.40 | 07-JUL-10:15 |
| InteriorLights:Electricity | 0.30 | 375.00 | 07-JUL-00:15 | 7500.00 | 07-JUL-10:15 |
| InteriorLights:Electricity:Zone:SPACE1-1 | 0.06 | 79.20 | 07-JUL-00:15 | 1584.00 | 07-JUL-10:15 |
| GeneralLights:InteriorLights:Electricity | 0.30 | 375.00 | 07-JUL-00:15 | 7500.00 | 07-JUL-10:15 |
| Electricity:Zone:SPACE2-1 | 0.04 | 43.32 | 07-JUL-00:15 | 1094.40 | 07-JUL-10:15 |
| InteriorLights:Electricity:Zone:SPACE2-1 | 0.03 | 34.20 | 07-JUL-00:15 | 684.00 | 07-JUL-10:15 |
| Electricity:Zone:SPACE3-1 | 0.09 | 100.32 | 07-JUL-00:15 | 2534.40 | 07-JUL-10:15 |
| InteriorLights:Electricity:Zone:SPACE3-1 | 0.06 | 79.20 | 07-JUL-00:15 | 1584.00 | 07-JUL-10:15 |
| Electricity:Zone:SPACE4-1 | 0.04 | 43.32 | 07-JUL-00:15 | 1094.40 | 07-JUL-10:15 |
| InteriorLights:Electricity:Zone:SPACE4-1 | 0.03 | 34.20 | 07-JUL-00:15 | 684.00 | 07-JUL-10:15 |
| Electricity:Zone:SPACE5-1 | 0.18 | 187.72 | 07-JUL-00:15 | 4742.40 | 07-JUL-10:15 |
| InteriorLights:Electricity:Zone:SPACE5-1 | 0.12 | 148.20 | 07-JUL-00:15 | 2964.00 | 07-JUL-10:15 |
| InteriorEquipment:Electricity | 0.15 | 100.00 | 07-JUL-00:15 | 4500.00 | 07-JUL-09:15 |
| InteriorEquipment:Electricity:Zone:SPACE1-1 | 0.03 | 21.12 | 07-JUL-00:15 | 950.40 | 07-JUL-09:15 |
| General:InteriorEquipment:Electricity | 0.15 | 100.00 | 07-JUL-00:15 | 4500.00 | 07-JUL-09:15 |
| InteriorEquipment:Electricity:Zone:SPACE2-1 | 0.01 | 9.12 | 07-JUL-00:15 | 410.40 | 07-JUL-09:15 |
| InteriorEquipment:Electricity:Zone:SPACE3-1 | 0.03 | 21.12 | 07-JUL-00:15 | 950.40 | 07-JUL-09:15 |
| InteriorEquipment:Electricity:Zone:SPACE4-1 | 0.01 | 9.12 | 07-JUL-00:15 | 410.40 | 07-JUL-09:15 |
| InteriorEquipment:Electricity:Zone:SPACE5-1 | 0.06 | 39.52 | 07-JUL-00:15 | 1778.40 | 07-JUL-09:15 |
| Electricity:HVAC | 0.03 | 40.26 | 07-JUL-00:15 | 710.29 | 07-JUL-15:00 |
| ExteriorEquipment:Electricity | 0.01 | 40.26 | 07-JUL-00:15 | 273.17 | 07-JUL-10:15 |
| Transformer:ExteriorEquipment:Electricity | 0.01 | 40.26 | 07-JUL-00:15 | 273.17 | 07-JUL-10:15 |
| ElectricityPurchased:Facility | 0.67 | 515.26 | 07-JUL-00:15 | 17163.02 | 07-JUL-15:00 |
| ElectricityPurchased:Plant | 0.67 | 515.26 | 07-JUL-00:15 | 17163.02 | 07-JUL-15:00 |
| Cogeneration:ElectricityPurchased | 0.67 | 515.26 | 07-JUL-00:15 | 17163.02 | 07-JUL-15:00 |
| ElectricitySurplusSold:Facility | 0.00 | 0.00 | 07-JUL-00:15 | 0.00 | 07-JUL-00:15 |
| ElectricitySurplusSold:Plant | 0.00 | 0.00 | 07-JUL-00:15 | 0.00 | 07-JUL-00:15 |
| Cogeneration:ElectricitySurplusSold | 0.00 | 0.00 | 07-JUL-00:15 | 0.00 | 07-JUL-00:15 |
| ElectricityNet:Facility | 0.67 | 515.26 | 07-JUL-00:15 | 17163.02 | 07-JUL-15:00 |
| ElectricityNet:Plant | 0.67 | 515.26 | 07-JUL-00:15 | 17163.02 | 07-JUL-15:00 |
| Cogeneration:ElectricityNet | 0.67 | 515.26 | 07-JUL-00:15 | 17163.02 | 07-JUL-15:00 |
| Fans:Electricity | 0.02 | 0.00 | 07-JUL-00:15 | 459.32 | 07-JUL-15:00 |
| General:Fans:Electricity | 0.02 | 0.00 | 07-JUL-00:15 | 459.32 | 07-JUL-15:00 |
| Electricity:Plant | 0.19 | 0.00 | 07-JUL-00:15 | 4972.57 | 07-JUL-15:45 |
| Heating:Electricity | 0.00 | 0.00 | 07-JUL-00:15 | 0.00 | 07-JUL-00:15 |
| Boiler Parasitic:Heating:Electricity | 0.00 | 0.00 | 07-JUL-00:15 | 0.00 | 07-JUL-00:15 |
| Cooling:Electricity | 0.17 | 0.00 | 07-JUL-00:15 | 4485.07 | 07-JUL-15:45 |
| General:Cooling:Electricity | 0.17 | 0.00 | 07-JUL-00:15 | 4485.07 | 07-JUL-15:45 |
| Pumps:Electricity | 0.02 | 0.00 | 07-JUL-00:15 | 488.52 | 07-JUL-16:00 |
| Gas Annual Value [GJ] | Gas Minimum Value [W] | Timestamp of Minimum {TIMESTAMP} | Gas Maximum Value [W] | Timestamp of Maximum {TIMESTAMP} | |
| Gas:Facility | 0.05 | 0.00 | 07-JUL-00:15 | 11160.58 | 07-JUL-06:15 |
| Gas:Plant | 0.05 | 0.00 | 07-JUL-00:15 | 11160.58 | 07-JUL-06:15 |
| Heating:Gas | 0.05 | 0.00 | 07-JUL-00:15 | 11160.58 | 07-JUL-06:15 |
| Boiler:Heating:Gas | 0.05 | 0.00 | 07-JUL-00:15 | 11160.58 | 07-JUL-06:15 |
| Cooling Annual Value [GJ] | Cooling Minimum Value [W] | Timestamp of Minimum {TIMESTAMP} | Cooling Maximum Value [W] | Timestamp of Maximum {TIMESTAMP} | |
| PlantLoopCoolingDemand:Facility | 0.68 | 0.00 | 07-JUL-00:15 | 18173.67 | 07-JUL-15:00 |
| PlantLoopCoolingDemand:HVAC | 0.68 | 0.00 | 07-JUL-00:15 | 18173.67 | 07-JUL-15:00 |
| CoolingCoils:PlantLoopCoolingDemand | 0.68 | 0.00 | 07-JUL-00:15 | 18173.67 | 07-JUL-15:00 |
| Annual Value [m3] | Minimum Value [m3/s] | Timestamp of Minimum {TIMESTAMP} | Maximum Value [m3/s] | Timestamp of Maximum {TIMESTAMP} | |
| None |
| Annual Value [kg] | Minimum Value [kg/s] | Timestamp of Minimum {TIMESTAMP} | Maximum Value [kg/s] | Timestamp of Maximum {TIMESTAMP} | |
| Carbon Equivalent:Facility | 0.00 | 0.000 | 07-JUL-00:15 | 0.000 | 07-JUL-00:15 |
| CarbonEquivalentEmissions:Carbon Equivalent | 0.00 | 0.000 | 07-JUL-00:15 | 0.000 | 07-JUL-00:15 |
| Annual Value [m3] | Minimum Value [m3/s] | Timestamp of Minimum {TIMESTAMP} | Maximum Value [m3/s] | Timestamp of Maximum {TIMESTAMP} | |
| None |
| Annual Value [L] | Minimum Value [L] | Timestamp of Minimum {TIMESTAMP} | Maximum Value [L] | Timestamp of Maximum {TIMESTAMP} | |
| None |
| Annual Value [GJ] | Minimum Value [W] | Timestamp of Minimum {TIMESTAMP} | Maximum Value [W] | Timestamp of Maximum {TIMESTAMP} | |
| EnergyTransfer:Facility | 2.60 | 0.00 | 07-JUL-20:15 | 67689.21 | 07-JUL-15:00 |
| EnergyTransfer:Building | 0.28 | 0.00 | 07-JUL-20:15 | 7901.86 | 07-JUL-15:00 |
| EnergyTransfer:Zone:PLENUM-1 | 0.02 | 0.00 | 07-JUL-00:15 | 1197.99 | 07-JUL-09:30 |
| Heating:EnergyTransfer | 0.03 | 0.00 | 07-JUL-15:30 | 3710.90 | 07-JUL-06:15 |
| Heating:EnergyTransfer:Zone:PLENUM-1 | 0.02 | 0.00 | 07-JUL-00:15 | 1197.99 | 07-JUL-09:30 |
| Cooling:EnergyTransfer | 0.25 | 0.00 | 07-JUL-00:15 | 7874.75 | 07-JUL-15:00 |
| Cooling:EnergyTransfer:Zone:PLENUM-1 | 0.00 | 0.00 | 07-JUL-00:15 | 724.03 | 07-JUL-19:45 |
| EnergyTransfer:Zone:SPACE1-1 | 0.06 | 0.00 | 07-JUL-20:15 | 1736.01 | 07-JUL-15:00 |
| Heating:EnergyTransfer:Zone:SPACE1-1 | 0.00 | 0.00 | 07-JUL-08:15 | 806.09 | 07-JUL-06:15 |
| Cooling:EnergyTransfer:Zone:SPACE1-1 | 0.05 | 0.00 | 07-JUL-00:15 | 1736.01 | 07-JUL-15:00 |
| EnergyTransfer:Zone:SPACE2-1 | 0.03 | 0.00 | 07-JUL-20:15 | 934.55 | 07-JUL-15:00 |
| Heating:EnergyTransfer:Zone:SPACE2-1 | 0.00 | 0.00 | 07-JUL-08:15 | 386.22 | 07-JUL-06:15 |
| Cooling:EnergyTransfer:Zone:SPACE2-1 | 0.03 | 0.00 | 07-JUL-00:15 | 934.55 | 07-JUL-15:00 |
| EnergyTransfer:Zone:SPACE3-1 | 0.06 | 0.00 | 07-JUL-20:15 | 2036.37 | 07-JUL-15:00 |
| Heating:EnergyTransfer:Zone:SPACE3-1 | 0.00 | 0.00 | 07-JUL-08:15 | 855.46 | 07-JUL-06:15 |
| Cooling:EnergyTransfer:Zone:SPACE3-1 | 0.06 | 0.00 | 07-JUL-00:15 | 2036.37 | 07-JUL-15:00 |
| EnergyTransfer:Zone:SPACE4-1 | 0.03 | 0.00 | 07-JUL-20:15 | 979.42 | 07-JUL-15:30 |
| Heating:EnergyTransfer:Zone:SPACE4-1 | 0.00 | 0.00 | 07-JUL-08:15 | 384.15 | 07-JUL-06:15 |
| Cooling:EnergyTransfer:Zone:SPACE4-1 | 0.03 | 0.00 | 07-JUL-00:15 | 979.42 | 07-JUL-15:30 |
| EnergyTransfer:Zone:SPACE5-1 | 0.08 | 0.00 | 07-JUL-20:15 | 2218.61 | 07-JUL-15:00 |
| Heating:EnergyTransfer:Zone:SPACE5-1 | 0.01 | 0.00 | 07-JUL-08:15 | 1256.89 | 07-JUL-06:15 |
| Cooling:EnergyTransfer:Zone:SPACE5-1 | 0.07 | 0.00 | 07-JUL-00:15 | 2218.61 | 07-JUL-15:00 |
| EnergyTransfer:HVAC | 0.72 | 0.00 | 07-JUL-00:15 | 18173.67 | 07-JUL-15:00 |
| HeatingCoils:EnergyTransfer | 0.04 | 0.00 | 07-JUL-00:15 | 6813.64 | 07-JUL-06:15 |
| PlantLoopHeatingDemand:Facility | 0.04 | 0.00 | 07-JUL-00:15 | 6813.64 | 07-JUL-06:15 |
| PlantLoopHeatingDemand:HVAC | 0.04 | 0.00 | 07-JUL-00:15 | 6813.64 | 07-JUL-06:15 |
| HeatingCoils:PlantLoopHeatingDemand | 0.04 | 0.00 | 07-JUL-00:15 | 6813.64 | 07-JUL-06:15 |
| CoolingCoils:EnergyTransfer | 0.68 | 0.00 | 07-JUL-00:15 | 18173.67 | 07-JUL-15:00 |
| EnergyTransfer:Plant | 1.60 | 0.00 | 07-JUL-00:15 | 41617.34 | 07-JUL-15:45 |
| Boilers:EnergyTransfer | 0.04 | 0.00 | 07-JUL-00:15 | 8928.47 | 07-JUL-06:15 |
| Chillers:EnergyTransfer | 0.70 | 0.00 | 07-JUL-00:15 | 18572.58 | 07-JUL-15:00 |
| HeatRejection:EnergyTransfer | 0.86 | 0.00 | 07-JUL-00:15 | 23051.20 | 07-JUL-15:45 |
Report: Sensible Heat Gain Summary
For: Entire Facility
Timestamp: 2018-03-11 14:48:12
Annual Building Sensible Heat Gain Components| HVAC Zone Eq & Other Sensible Air Heating [GJ] | HVAC Zone Eq & Other Sensible Air Cooling [GJ] | HVAC Terminal Unit Sensible Air Heating [GJ] | HVAC Terminal Unit Sensible Air Cooling [GJ] | HVAC Input Heated Surface Heating [GJ] | HVAC Input Cooled Surface Cooling [GJ] | People Sensible Heat Addition [GJ] | Lights Sensible Heat Addition [GJ] | Equipment Sensible Heat Addition [GJ] | Window Heat Addition [GJ] | Interzone Air Transfer Heat Addition [GJ] | Infiltration Heat Addition [GJ] | Opaque Surface Conduction and Other Heat Addition [GJ] | Equipment Sensible Heat Removal [GJ] | Window Heat Removal [GJ] | Interzone Air Transfer Heat Removal [GJ] | Infiltration Heat Removal [GJ] | Opaque Surface Conduction and Other Heat Removal [GJ] | |
| SPACE1-1 | 0.000 | 0.000 | 4.340 | -13.196 | 0.000 | 0.000 | 7.078 | 17.221 | 10.105 | 22.092 | 0.000 | 0.000 | 0.001 | 0.000 | -13.238 | 0.000 | -0.956 | -33.446 |
| SPACE2-1 | 0.000 | 0.000 | 2.029 | -7.859 | 0.000 | 0.000 | 3.248 | 7.436 | 4.364 | 13.262 | 0.000 | 0.000 | 0.001 | 0.000 | -4.430 | 0.000 | -0.418 | -17.633 |
| SPACE3-1 | 0.000 | 0.000 | 4.353 | -12.716 | 0.000 | 0.000 | 7.119 | 17.221 | 10.105 | 17.516 | 0.000 | 0.000 | 0.001 | 0.000 | -12.536 | 0.000 | -0.937 | -30.126 |
| SPACE4-1 | 0.000 | 0.000 | 2.075 | -8.205 | 0.000 | 0.000 | 3.292 | 7.436 | 4.364 | 13.419 | 0.000 | 0.000 | 0.000 | 0.000 | -4.563 | 0.000 | -0.412 | -17.406 |
| SPACE5-1 | 0.000 | 0.000 | 3.389 | -15.741 | 0.000 | 0.000 | 12.653 | 32.224 | 18.909 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | -1.913 | -49.520 |
| PLENUM-1 | 15.361 | -4.490 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | -10.871 |
| Total Facility | 15.361 | -4.490 | 16.186 | -57.716 | 0.000 | 0.000 | 33.391 | 81.537 | 47.845 | 66.288 | 0.000 | 0.000 | 0.004 | 0.000 | -34.766 | 0.000 | -4.635 | -159.001 |
| Time of Peak {TIMESTAMP} | HVAC Zone Eq & Other Sensible Air Heating [W] | HVAC Zone Eq & Other Sensible Air Cooling [W] | HVAC Terminal Unit Sensible Air Heating [W] | HVAC Terminal Unit Sensible Air Cooling [W] | HVAC Input Heated Surface Heating [W] | HVAC Input Cooled Surface Cooling [W] | People Sensible Heat Addition [W] | Lights Sensible Heat Addition [W] | Equipment Sensible Heat Addition [W] | Window Heat Addition [W] | Interzone Air Transfer Heat Addition [W] | Infiltration Heat Addition [W] | Opaque Surface Conduction and Other Heat Addition [W] | Equipment Sensible Heat Removal [W] | Window Heat Removal [W] | Interzone Air Transfer Heat Removal [W] | Infiltration Heat Removal [W] | Opaque Surface Conduction and Other Heat Removal [W] | |
| SPACE1-1 | 18-SEP-16:15 | 0.00 | 0.00 | 0.00 | -3042.47 | 0.00 | 0.00 | 721.96 | 1584.00 | 528.00 | 4918.69 | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | 0.00 | 0.00 | -4710.18 |
| SPACE2-1 | 02-SEP-11:00 | 0.00 | 0.00 | 0.00 | -1880.94 | 0.00 | 0.00 | 348.39 | 684.00 | 410.40 | 3161.63 | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | 0.00 | 0.00 | -2723.48 |
| SPACE3-1 | 30-JUL-14:00 | 0.00 | 0.00 | 0.00 | -2954.78 | 0.00 | 0.00 | 613.14 | 1425.60 | 950.40 | 3579.99 | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | 0.00 | 0.00 | -3614.35 |
| SPACE4-1 | 29-JUL-18:08 | 0.00 | 0.00 | 0.00 | -2750.77 | 0.00 | 0.00 | 167.82 | 410.40 | 136.80 | 4617.88 | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | 0.00 | 0.00 | -2582.13 |
| SPACE5-1 | 01-AUG-15:00 | 0.00 | 0.00 | 0.00 | -2637.05 | 0.00 | 0.00 | 1393.54 | 2964.00 | 1580.80 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | 0.00 | 0.00 | -3301.29 |
| PLENUM-1 | 19-JUN-16:00 | 0.00 | -3277.64 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 3277.64 | 0.00 | -0.00 | 0.00 | 0.00 | 0.00 |
| Total Facility | 19-JUN-16:00 | 0.00 | -3277.64 | 0.00 | -11739.43 | 0.00 | 0.00 | 3619.29 | 7500.00 | 3500.00 | 11792.19 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -11394.42 |
| Time of Peak {TIMESTAMP} | HVAC Zone Eq & Other Sensible Air Heating [W] | HVAC Zone Eq & Other Sensible Air Cooling [W] | HVAC Terminal Unit Sensible Air Heating [W] | HVAC Terminal Unit Sensible Air Cooling [W] | HVAC Input Heated Surface Heating [W] | HVAC Input Cooled Surface Cooling [W] | People Sensible Heat Addition [W] | Lights Sensible Heat Addition [W] | Equipment Sensible Heat Addition [W] | Window Heat Addition [W] | Interzone Air Transfer Heat Addition [W] | Infiltration Heat Addition [W] | Opaque Surface Conduction and Other Heat Addition [W] | Equipment Sensible Heat Removal [W] | Window Heat Removal [W] | Interzone Air Transfer Heat Removal [W] | Infiltration Heat Removal [W] | Opaque Surface Conduction and Other Heat Removal [W] | |
| SPACE1-1 | 04-JAN-06:02 | 0.00 | 0.00 | 3606.22 | -0.00 | 0.00 | 0.00 | 0.00 | 79.20 | 21.12 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -1464.74 | 0.00 | -133.39 | -2108.40 |
| SPACE2-1 | 04-JAN-06:02 | 0.00 | 0.00 | 1900.56 | -0.00 | 0.00 | 0.00 | 0.00 | 34.20 | 9.12 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -523.61 | 0.00 | -58.91 | -1361.36 |
| SPACE3-1 | 04-JAN-06:02 | 0.00 | 0.00 | 3673.26 | -0.00 | 0.00 | 0.00 | 0.00 | 79.20 | 21.12 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -1416.58 | 0.00 | -133.43 | -2223.57 |
| SPACE4-1 | 04-JAN-06:02 | 0.00 | 0.00 | 1941.56 | -0.00 | 0.00 | 0.00 | 0.00 | 34.20 | 9.12 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -523.33 | 0.00 | -58.91 | -1402.64 |
| SPACE5-1 | 04-JAN-06:02 | 0.00 | 0.00 | 3007.94 | -0.00 | 0.00 | 0.00 | 0.00 | 148.20 | 39.52 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | 0.00 | -276.90 | -2918.76 |
| PLENUM-1 | 07-JAN-08:08 | 3511.81 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | 0.00 | 0.00 | -3511.81 |
| Total Facility | 07-JAN-06:15 | 1871.96 | 0.00 | 13405.56 | 0.00 | 0.00 | 0.00 | 0.00 | 375.00 | 100.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -4379.65 | 0.00 | 0.00 | -11372.87 |
Report: Standard 62.1 Summary
For: Entire Facility
Timestamp: 2018-03-11 14:48:12
System Ventilation Requirements for Cooling| Sum of Zone Primary Air Flow - Vpz-sum [m3/s] | System Population - Ps | Sum of Zone Population - Pz-sum | Occupant Diversity - D | Uncorrected Outdoor Air Intake Airflow - Vou [m3/s] | System Primary Airflow - Vps [m3/s] | Average Outdoor Air Fraction - Xs | System Ventilation Efficiency - Ev | Outdoor Air Intake Flow - Vot [m3/s] | Percent Outdoor Air - %OA | |
| VAV SYS 1 | 1.053 | 52.00 | 52.00 | 1.00 | 0.2641 | 1.053 | 0.251 | 1.000 | 0.2641 | 0.25 |
| Sum of Zone Primary Air Flow - Vpz-sum [m3/s] | System Population - Ps | Sum of Zone Population - Pz-sum | Occupant Diversity - D | Uncorrected Outdoor Air Intake Airflow - Vou [m3/s] | System Primary Airflow - Vps [m3/s] | Average Outdoor Air Fraction - Xs | System Ventilation Efficiency - Ev | Outdoor Air Intake Flow Vot [m3/s] | Percent Outdoor Air - %OA | |
| VAV SYS 1 | 0.428 | 52.00 | 52.00 | 1.00 | 0.2641 | 0.428 | 1.000 | 1.000 | 0.2641 | 0.62 |
| AirLoop Name | People Outdoor Air Rate - Rp [m3/s-person] | Zone Population - Pz | Area Outdoor Air Rate - Ra [m3/s-m2] | Zone Floor Area - Az [m2] | Breathing Zone Outdoor Airflow - Vbz [m3/s] | Cooling Zone Air Distribution Effectiveness - Ez-clg | Cooling Zone Outdoor Airflow - Voz-clg [m3/s] | Heating Zone Air Distribution Effectiveness - Ez-htg | Heating Zone Outdoor Airflow - Voz-htg [m3/s] | |
| SPACE1-1 | VAV SYS 1 | 0.002360 | 11.00 | 0.000305 | 99.16 | 0.0562 | 1.000 | 0.0562 | 1.000 | 0.0562 |
| SPACE2-1 | VAV SYS 1 | 0.002360 | 5.00 | 0.000305 | 42.73 | 0.0248 | 1.000 | 0.0248 | 1.000 | 0.0248 |
| SPACE3-1 | VAV SYS 1 | 0.002360 | 11.00 | 0.000305 | 96.48 | 0.0554 | 1.000 | 0.0554 | 1.000 | 0.0554 |
| SPACE4-1 | VAV SYS 1 | 0.002360 | 5.00 | 0.000305 | 42.73 | 0.0248 | 1.000 | 0.0248 | 1.000 | 0.0248 |
| SPACE5-1 | VAV SYS 1 | 0.002360 | 20.00 | 0.000305 | 182.49 | 0.1029 | 1.000 | 0.1029 | 1.000 | 0.1029 |
| People Outdoor Air Rate - Rp [m3/s-person] | Sum of Zone Population - Pz-sum | Area Outdoor Air Rate - Ra [m3/s-m2] | Sum of Zone Floor Area - Az-sum [m2] | Breathing Zone Outdoor Airflow - Vbz [m3/s] | Cooling Zone Outdoor Airflow - Voz-clg [m3/s] | Heating Zone Outdoor Airflow - Voz-htg [m3/s] | |
| VAV SYS 1 | 0.002360 | 52.00 | 0.000305 | 463.60 | 0.2641 | 0.2641 | 0.2641 |
| AirLoop Name | Box Type | Zone Primary Airflow - Vpz [m3/s] | Zone Discharge Airflow - Vdz [m3/s] | Minimum Zone Primary Airflow - Vpz-min [m3/s] | Zone Outdoor Airflow Cooling - Voz-clg [m3/s] | Primary Outdoor Air Fraction - Zpz | Primary Air Fraction - Ep | Secondary Recirculation Fraction- Er | Supply Air Fraction- Fa | Mixed Air Fraction - Fb | Outdoor Air Fraction - Fc | Zone Ventilation Efficiency - Evz | |
| SPACE1-1 | VAV SYS 1 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.215 | 0.2151 | 0.0756 | 0.0562 | 0.000 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| SPACE2-1 | VAV SYS 1 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.181 | 0.1810 | 0.0362 | 0.0248 | 0.000 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| SPACE3-1 | VAV SYS 1 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.231 | 0.2313 | 0.0735 | 0.0554 | 0.000 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| SPACE4-1 | VAV SYS 1 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.209 | 0.2088 | 0.0418 | 0.0248 | 0.000 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| SPACE5-1 | VAV SYS 1 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.217 | 0.2170 | 0.1391 | 0.1029 | 0.000 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| Sum of Zone Primary Airflow - Vpz-sum [m3/s] | System Primary Airflow - Vps [m3/s] | Sum of Zone Discharge Airflow - Vdz-sum [m3/s] | Sum of Min Zone Primary Airflow - Vpz-min [m3/s] | Zone Outdoor Airflow Cooling - Voz-clg [m3/s] | Zone Ventilation Efficiency - Evz-min | |
| VAV SYS 1 | 1.05 | 1.053 | 1.05 | 0.3661 | 0.2641 | 1.000 |
| AirLoop Name | Box Type | Zone Primary Airflow - Vpz [m3/s] | Zone Discharge Airflow - Vdz [m3/s] | Minimum Zone Primary Airflow - Vpz-min [m3/s] | Zone Outdoor Airflow Heating - Voz-htg [m3/s] | Primary Outdoor Air Fraction - Zpz | Primary Air Fraction - Ep | Secondary Recirculation Fraction- Er | Supply Air Fraction- Fa | Mixed Air Fraction - Fb | Outdoor Air Fraction - Fc | Zone Ventilation Efficiency - Evz | |
| SPACE1-1 | VAV SYS 1 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.115 | 0.115 | 0.115 | 0.0562 | 0.487 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| SPACE2-1 | VAV SYS 1 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.049 | 0.049 | 0.049 | 0.0248 | 0.511 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| SPACE3-1 | VAV SYS 1 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.112 | 0.112 | 0.112 | 0.0554 | 0.494 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| SPACE4-1 | VAV SYS 1 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.049 | 0.049 | 0.049 | 0.0248 | 0.511 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| SPACE5-1 | VAV SYS 1 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.103 | 0.103 | 0.103 | 0.1029 | 1.000 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| Sum of Zone Primary Airflow - Vpz-sum [m3/s] | System Primary Airflow - Vps [m3/s] | Sum of Zone Discharge Airflow - Vdz-sum [m3/s] | Sum of Min Zone Primary Airflow - Vpz-min [m3/s] | Zone Outdoor Airflow Heating - Voz-htg [m3/s] | Zone Ventilation Efficiency - Evz-min | |
| VAV SYS 1 | 0.43 | 0.428 | 0.43 | 0.43 | 0.2641 | 1.000 |
Report: LEED Summary
For: Entire Facility
Timestamp: 2018-03-11 14:48:12
Sec1.1A-General Information| Data | |
| Weather File | SUMMERDAY ** jiaozuo Henan CHN CSWD WMO#=570830 |
| Total gross floor area [m2] | 927.20 |
| Principal Heating Source | Natural Gas |
| Space Area [m2] | Regularly Occupied Area [m2] | Unconditioned Area [m2] | Typical Hours/Week in Operation [hr/wk] | |
| SPACE1-1 | 99.16 | 99.16 | 0.00 | 77.00 |
| SPACE2-1 | 42.73 | 42.73 | 0.00 | 77.00 |
| SPACE3-1 | 96.48 | 96.48 | 0.00 | 77.00 |
| SPACE4-1 | 42.73 | 42.73 | 0.00 | 77.00 |
| SPACE5-1 | 182.49 | 182.49 | 0.00 | 77.00 |
| PLENUM-1 | 463.60 | 463.60 | 0.00 | 0.00 |
| Totals | 927.20 | 927.20 | 0.00 |
| Data | |
| Number of hours heating loads not met | 0.00 |
| Number of hours cooling loads not met | 151.75 |
| Number of hours not met | 151.75 |
| Utility Rate | Virtual Rate [$/unit energy] | Units of Energy | Units of Demand | |
| None |
| Electric Energy Use [GJ] | Electric Demand [W] | Natural Gas Energy Use [GJ] | Natural Gas Demand [W] | Additional Fuel Use [GJ] | Additional Fuel Demand [W] | District Cooling Use [GJ] | District Cooling Demand [W] | District Heating Use [GJ] | District Heating Demand [W] | |
| Heating -- Boiler | 0.00 | 0.00 | 45.10 | 32104.24 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heating -- Boiler Parasitic | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling -- General | 23.18 | 8868.72 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting -- GeneralLights | 81.54 | 7500.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting -- Not Subdivided | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment -- General | 47.85 | 4500.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment -- Transformer | 3.10 | 273.17 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans -- General | 9.06 | 780.99 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps -- Not Subdivided | 2.83 | 555.98 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection -- Not Subdivided | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification -- Not Subdivided | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery -- Not Subdivided | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems -- Not Subdivided | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration -- Not Subdivided | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators -- Not Subdivided | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Process Subtotal [GJ] | Total Energy Use [GJ] | |
| Electricity | 47.85 | 167.56 |
| Natural Gas | 0.00 | 45.10 |
| Additional | 0.00 | 0.00 |
| Total | 47.85 | 212.66 |
| Process Subtotal [$] | Total Energy Cost [$] | |
| Electricity | 0.00 | |
| Natural Gas | 0.00 | |
| Additional | 0.00 | |
| Total | 0.00 |
| Rated Capacity [kW] | Annual Energy Generated [GJ] | |
| Photovoltaic | 0.00 | 0.00 |
| Wind | 0.00 | 0.00 |
| Electricty [MJ/m2] | |
| Interior Lighting (All) | 87.94 |
| Space Heating | 0.00 |
| Space Cooling | 25.00 |
| Fans (All) | 9.78 |
| Service Water Heating | 0.00 |
| Receptacle Equipment | 51.60 |
| Miscellaneous (All) | 180.72 |
| Subtotal | 180.72 |
| Natural Gas [MJ/m2] | |
| Space Heating | 48.64 |
| Service Water Heating | 0.00 |
| Miscellaneous (All) | 48.64 |
| Subtotal | 48.64 |
| Additional [MJ/m2] | |
| Subtotal | 0.00 |
| Miscellaneous | 0.00 |
| Percent [%] | |
| Interior Lighting (All) | 38.34 |
| Space Heating | 21.21 |
| Space Cooling | 10.90 |
| Fans (All) | 4.26 |
| Service Water Heating | 0.00 |
| Receptacle Equipment | 22.50 |
| Miscellaneous | 2.79 |
| Equivalent Full Load Hours of Operation Per Year [hr] | Hours > 1% [hr] | |
| OCCUPY-1 | 2479. | 2871. |
| LIGHTS-1 | 3009. | 8760. |
| EQUIP-1 | 2650. | 8760. |
| INFIL-SCH | 3624. | 3624. |
| SHADETRANSSCH | 0. | 0. |
| MIN OA SCHED | 3756. | 8760. |
| FANAVAILSCHED | 6202. | 6202. |
| COOLINGCOILAVAILSCHED | 3654. | 3654. |
| COOLINGPUMPAVAILSCHED | 8760. | 8760. |
| REHEATCOILAVAILSCHED | 6202. | 6202. |
| PLANTONSCHED | 8760. | 8760. |
| ALWAYS ON | 8760. | 8760. |
| First Object Used | Month Assumed | 11am First Wednesday [C] | Days with Same 11am Value | 11pm First Wednesday [C] | Days with Same 11pm Value | |
| HTG-SETP-SCH | HEATINGSETPOINT | January | 22.20 | 365 | 16.70 | 365 |
| PLENUMHTG-SETP-SCH | PLENUMHEATINGSETPOINT | January | 12.80 | 365 | 12.80 | 365 |
| CLG-SETP-SCH | COOLINGSETPOINT | July | 23.90 | 365 | 29.40 | 365 |
| PLENUMCLG-SETP-SCH | PLENUMCOOLINGSETPOINT | July | 40.00 | 365 | 40.00 | 365 |
Report: Component Sizing Summary
For: Entire Facility
Timestamp: 2018-03-11 14:48:12
AirTerminal:SingleDuct:VAV:Reheat| Design Size Maximum Air Flow Rate [m3/s] | Design Size Constant Minimum Air Flow Fraction | User-Specified Constant Minimum Air Flow Fraction | Design Size Minimum Air Flow Rate [m3/s] | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | Design Size Maximum Flow Fraction during Reheat [] | Design Size Maximum Reheat Water Flow Rate [m3/s] | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | |
| SPACE1-1 VAV REHEAT | 0.215093 | 0.351290 | 0.300000 | 0.064528 | 0.000651 | 0.300000 | 0.000102 | 0.115416 | 16.70 | 0.008000 |
| SPACE2-1 VAV REHEAT | 0.181010 | 0.200000 | 0.300000 | 0.054303 | 0.001271 | 0.300000 | 0.000044 | 0.054303 | 16.70 | 0.008000 |
| SPACE3-1 VAV REHEAT | 0.231263 | 0.317897 | 0.300000 | 0.069379 | 0.000719 | 0.300000 | 0.000099 | 0.112197 | 16.70 | 0.008000 |
| SPACE4-1 VAV REHEAT | 0.208758 | 0.200000 | 0.300000 | 0.062628 | 0.001465 | 0.300000 | 0.000045 | 0.062628 | 16.70 | 0.008000 |
| SPACE5-1 VAV REHEAT | 0.217039 | 0.640701 | 0.300000 | 0.065112 | 0.000357 | 0.300000 | 0.000079 | 0.089133 | 16.70 | 0.008000 |
| Design Size Rated Capacity [W] | Design Size Maximum Water Flow Rate [m3/s] | Design Size U-Factor Times Area Value [W/K] | |
| SPACE1-1 ZONE COIL | 4702.63 | 0.000102 | 113.24 |
| SPACE2-1 ZONE COIL | 2017.99 | 0.000044 | 46.69 |
| SPACE3-1 ZONE COIL | 4571.44 | 0.000099 | 110.08 |
| SPACE4-1 ZONE COIL | 2073.98 | 0.000045 | 46.05 |
| SPACE5-1 ZONE COIL | 3631.39 | 0.000079 | 87.44 |
| OA HEATING COIL 1 | 6877.10 | 0.000149 | 85.63 |
| MAIN HEATING COIL 1 | 3498.65 | 0.000076 | 56.49 |
| Design Supply Air Flow Rate [m3/s] | |
| VAV SYS 1 | 1.05 |
| Maximum Outdoor Air Flow Rate [m3/s] | Minimum Outdoor Air Flow Rate [m3/s] | |
| OA CONTROLLER 1 | 1.05 | 0.264118 |
| Maximum Actuated Flow [m3/s] | |
| OA HC CONTROLLER 1 | 0.000149 |
| OA CC CONTROLLER 1 | 0.001360 |
| CENTRAL COOLING COIL CONTROLLER 1 | 0.000761 |
| CENTRAL HEATING COIL CONTROLLER 1 | 0.000076 |
| Design Size Design Coil Load [W] | Design Size Design Water Flow Rate [m3/s] | Design Size Design Air Flow Rate [m3/s] | Design Size Design Inlet Air Temperature [C] | Design Size Design Inlet Water Temperature [C] | Design Size Design Outlet Air Temperature [C] | Design Size Design Inlet Air Humidity Ratio | Design Size Design Outlet Air Humidity Ratio | |
| OA COOLING COIL 1 | 11420.22 | 0.001360 | 0.264118 | 29.44 | 7.00 | 11.00 | 0.014595 | 0.008000 |
| MAIN COOLING COIL 1 | 12774.24 | 0.000761 | 0.888342 | 20.87 | 7.00 | 12.80 | 0.009237 | 0.008386 |
| Design Size Maximum Flow Rate [m3/s] | |
| SUPPLY FAN 1 | 1.05 |
| Maximum Loop Flow Rate [m3/s] | Plant Loop Volume [m3] | |
| HOT WATER LOOP | 0.000595 | 0.071361 |
| CHILLED WATER LOOP | 0.002121 | 0.254538 |
| Design Flow Rate [m3/s] | Design Power Consumption [W] | |
| HW CIRC PUMP | 0.000595 | 151.93 |
| CW CIRC PUMP | 0.002121 | 541.93 |
| Design Size Nominal Capacity [W] | Design Size Design Water Flow Rate [m3/s] | |
| CENTRAL BOILER | 27475.23 | 0.000595 |
| Design Size Nominal Capacity [W] | Design Size Design Chilled Water Flow Rate [m3/s] | User-Specified Design Condenser Water Flow Rate [m3/s] | |
| CENTRAL CHILLER | 35614.09 | 0.002121 | 0.001100 |
Report: Surface Shadowing Summary
For: Entire Facility
Timestamp: 2018-03-11 14:48:12
Surfaces (Walls, Roofs, etc) that may be Shadowed by Other Surfaces| Possible Shadow Receivers | |
| MAIN SOUTH OVERHANG | FRONT-1 | |
| Mir-MAIN SOUTH OVERHANG | SOUTH DOOR OVERHANG | WALL-1PF | FRONT-1 | |
| SOUTH DOOR OVERHANG | WALL-1PF | |
| Mir-SOUTH DOOR OVERHANG | WALL-1PF | |
| WALL-1PF | SOUTH DOOR OVERHANG | |
| FRONT-1 | MAIN SOUTH OVERHANG | SOUTH DOOR OVERHANG | |
| Possible Shadow Receivers | |
| FRONT-1 | WF-1 | DF-1 | |
| RIGHT-1 | WR-1 | |
| BACK-1 | WB-1 | DB-1 | |
| LEFT-1 | WL-1 | |
Report: Adaptive Comfort Summary
For: Entire Facility
Timestamp: 2018-03-11 14:48:12
Time Not Meeting the Adaptive Comfort Models during Occupied Hours| ASHRAE55 90% Acceptability Limits [Hours] | ASHRAE55 80% Acceptability Limits [Hours] | CEN15251 Category I Acceptability Limits [Hours] | CEN15251 Category II Acceptability Limits [Hours] | CEN15251 Category III Acceptability Limits [Hours] |
Report: Initialization Summary
For: Entire Facility
Timestamp: 2018-03-11 14:48:12
Version| Version ID | |
| 1 | 8.8 |
| #TimeSteps | Minutes per TimeStep {minutes} | |
| 1 | 4 | 15 |
| Minimum System TimeStep {minutes} | Max HVAC Iterations | Minimum Plant Iterations | Maximum Plant Iterations | |
| 1 | 1 | 20 | 2 | 8 |
| Do Zone Sizing | Do System Sizing | Do Plant Sizing | Do Design Days | Do Weather Simulation | Do HVAC Sizing Simulation | |
| 1 | Yes | Yes | Yes | No | Yes | No |
| Tolerance for Time Heating Setpoint Not Met | Tolerance for Zone Cooling Setpoint Not Met Time | |
| 1 | 0.200 | 0.200 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | 20.03 | 20.03 | 20.13 | 20.30 | 20.43 | 20.52 | 20.62 | 20.77 | 20.78 | 20.55 | 20.44 | 20.20 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | 4.15 | 3.11 | 4.94 | 7.81 | 15.30 | 21.08 | 24.98 | 26.16 | 24.14 | 19.65 | 13.66 | 8.09 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 |
| Jan{dimensionless} | Feb{dimensionless} | Mar{dimensionless} | Apr{dimensionless} | May{dimensionless} | Jun{dimensionless} | Jul{dimensionless} | Aug{dimensionless} | Sep{dimensionless} | Oct{dimensionless} | Nov{dimensionless} | Dec{dimensionless} | |
| 1 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 |
| Normal | Daylighting {dimensionless} | |
| 1 | 1.000 | 1.000 |
| Jan{dimensionless} | Feb{dimensionless} | Mar{dimensionless} | Apr{dimensionless} | May{dimensionless} | Jun{dimensionless} | Jul{dimensionless} | Aug{dimensionless} | Sep{dimensionless} | Oct{dimensionless} | Nov{dimensionless} | Dec{dimensionless} | |
| 1 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 |
| Jan{dimensionless} | Feb{dimensionless} | Mar{dimensionless} | Apr{dimensionless} | May{dimensionless} | Jun{dimensionless} | Jul{dimensionless} | Aug{dimensionless} | Sep{dimensionless} | Oct{dimensionless} | Nov{dimensionless} | Dec{dimensionless} | |
| 1 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 |
| Wind Sensor Height Above Ground {m} | Wind Speed Profile Exponent {} | Wind Speed Profile Boundary Layer Thickness {m} | Air Temperature Sensor Height Above Ground {m} | Wind Speed Modifier Coefficient-Internal | Temperature Modifier Coefficient-Internal | |
| 1 | 10.000 | 0.140 | 270.000 | 1.500 | 1.586 | 9.750E-003 |
| Location Name | Latitude {N+/S- Deg} | Longitude {E+/W- Deg} | Time Zone Number {GMT+/-} | Elevation {m} | Standard Pressure at Elevation {Pa} | Standard RhoAir at Elevation | |
| 1 | jiaozuo Henan CHN CSWD WMO#=570830 | 35.21 | 113.27 | 8.00 | 110.40 | 100006 | 1.1886 |
| Building Name | North Axis {deg} | Terrain | Loads Convergence Tolerance Value | Temperature Convergence Tolerance Value | Solar Distribution | Maximum Number of Warmup Days | Minimum Number of Warmup Days | |
| 1 | Building | 30.000 | City | 4.00000E-002 | 0.40000 | FullExterior | 25 | 6 |
| Algorithm {Simple TARP CeilingDiffuser AdaptiveConvectionAlgorithm} |
|
| 1 | Simple |
| Algorithm {SimpleCombined TARP MoWitt DOE-2 AdaptiveConvectionAlgorithm} |
|
| 1 | SimpleCombined |
| Value {Anisotropic} | |
| 1 | Anisotropic |
| Value {ThirdOrderBackwardDifference AnalyticalSolution EulerMethod} |
|
| 1 | ThirdOrderBackwardDifference |
| Simulation {Yes/No} | Carbon Dioxide Concentration | |
| 1 | No | N/A |
| Simulation {Yes/No} | Generic Contaminant Concentration | |
| 1 | No | N/A |
| Enforce Mass Balance |
Adjust Zone Mixing |
Adjust Zone Infiltration {AddInfiltration AdjustInfiltration None} |
Infiltration Zones {MixingSourceZonesOnly AllZones} |
|
| 1 | No | N/A | N/A | N/A |
| Value {RegulaFalsi Bisection BisectionThenRegulaFalsi RegulaFalsiThenBisection} |
|
| 1 | RegulaFalsi |
| Wind Speed Profile Exponent {} | Wind Speed Profile Boundary Layer Thickness {m} | Air Temperature Gradient Coefficient {K/m} | |
| 1 | 0.330 | 460.000 | 6.500000E-003 |
| Starting Corner | Vertex Input Direction | Coordinate System | Daylight Reference Point Coordinate System | Rectangular (Simple) Surface Coordinate System | |
| 1 | UpperLeftCorner | Counterclockwise | RelativeCoordinateSystem | RelativeCoordinateSystem | RelativeToZoneOrigin |
| Value {CTF - ConductionTransferFunction EMPD - MoisturePenetrationDepthConductionTransferFunction CondFD - ConductionFiniteDifference HAMT - CombinedHeatAndMoistureFiniteElement} - Description |
Inside Surface Max Temperature Limit{C} |
Surface Convection Coefficient Lower Limit {W/m2-K} |
Surface Convection Coefficient Upper Limit {W/m2-K} |
|
| 1 | CTF - ConductionTransferFunction | 200 | 0.10 | 1000.0 |
| Number of Fixed Detached Shades | Number of Building Detached Shades | Number of Attached Shades | |
| 1 | 0 | 0 | 4 |
| Number of Zones | Number of Zone Surfaces | Number of SubSurfaces | |
| 1 | 6 | 46 | 6 |
| Zone Name | North Axis {deg} | Origin X-Coordinate {m} | Origin Y-Coordinate {m} | Origin Z-Coordinate {m} | Centroid X-Coordinate {m} | Centroid Y-Coordinate {m} | Centroid Z-Coordinate {m} | Type | Zone Multiplier | Zone List Multiplier | Minimum X {m} | Maximum X {m} | Minimum Y {m} | Maximum Y {m} | Minimum Z {m} | Maximum Z {m} | Ceiling Height {m} | Volume {m3} | Zone Inside Convection Algorithm {Simple-Detailed-CeilingDiffuser-TrombeWall} | Zone Outside Convection Algorithm {Simple-Detailed-Tarp-MoWitt-DOE-2-BLAST} | Floor Area {m2} | Exterior Gross Wall Area {m2} | Exterior Net Wall Area {m2} | Exterior Window Area {m2} | Number of Surfaces | Number of SubSurfaces | Number of Shading SubSurfaces | Part of Total Building Area | |
| 1 | PLENUM-1 | 0.0 | 0.00 | 0.00 | 0.00 | 17.01 | -1.04 | 2.70 | 1 | 1 | 1 | 0.00 | 34.01 | -15.25 | 13.16 | 2.40 | 3.00 | 0.61 | 283.20 | Simple | Simple | 463.60 | 54.84 | 54.84 | 0.00 | 10 | 0 | 0 | Yes |
| 2 | SPACE1-1 | 0.0 | 0.00 | 0.00 | 0.00 | 14.06 | -6.15 | 1.20 | 1 | 1 | 1 | 0.00 | 26.41 | -15.25 | 1.35 | 0.00 | 2.40 | 2.44 | 239.25 | Simple | Simple | 99.16 | 73.20 | 51.39 | 21.81 | 6 | 2 | 4 | Yes |
| 3 | SPACE2-1 | 0.0 | 0.00 | 0.00 | 0.00 | 28.88 | -7.88 | 1.20 | 1 | 1 | 1 | 25.06 | 34.01 | -15.25 | -2.09 | 0.00 | 2.40 | 2.44 | 103.31 | Simple | Simple | 42.74 | 36.48 | 27.36 | 9.12 | 6 | 1 | 0 | Yes |
| 4 | SPACE3-1 | 0.0 | 0.00 | 0.00 | 0.00 | 19.98 | 4.10 | 1.20 | 1 | 1 | 1 | 7.60 | 34.01 | -3.35 | 13.16 | 0.00 | 2.40 | 2.44 | 239.25 | Simple | Simple | 96.48 | 73.20 | 52.35 | 20.85 | 6 | 2 | 0 | Yes |
| 5 | SPACE4-1 | 0.0 | 0.00 | 0.00 | 0.00 | 5.15 | 5.82 | 1.20 | 1 | 1 | 1 | 0.00 | 9.00 | 0.00 | 13.16 | 0.00 | 2.40 | 2.44 | 103.31 | Simple | Simple | 42.74 | 36.48 | 27.36 | 9.12 | 6 | 1 | 0 | Yes |
| 6 | SPACE5-1 | 0.0 | 0.00 | 0.00 | 0.00 | 17.03 | -1.00 | 1.20 | 1 | 1 | 1 | 5.05 | 29.01 | -10.20 | 8.20 | 0.00 | 2.40 | 2.44 | 447.68 | Simple | Simple | 182.49 | 0.00 | 0.00 | 0.00 | 6 | 0 | 0 | Yes |
| Zone Name | Floor Area {m2} | # Occupants | Area per Occupant {m2/person} | Occupant per Area {person/m2} | Interior Lighting {W/m2} | Electric Load {W/m2} | Gas Load {W/m2} | Other Load {W/m2} | Hot Water Eq {W/m2} | Steam Equipment {W/m2} | Sum Loads per Area {W/m2} | Outdoor Controlled Baseboard Heat | |
| 1 | PLENUM-1 | 463.60 | 0.0 | N/A | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | No |
| 2 | SPACE1-1 | 99.16 | 11.0 | 9.015 | 0.111 | 15.974 | 10.649 | 0.000 | 0.000 | 0.000 | 0.000 | 26.624 | No |
| 3 | SPACE2-1 | 42.74 | 5.0 | 8.547 | 0.117 | 16.006 | 10.670 | 0.000 | 0.000 | 0.000 | 0.000 | 26.676 | No |
| 4 | SPACE3-1 | 96.48 | 11.0 | 8.771 | 0.114 | 16.418 | 10.945 | 0.000 | 0.000 | 0.000 | 0.000 | 27.363 | No |
| 5 | SPACE4-1 | 42.74 | 5.0 | 8.547 | 0.117 | 16.006 | 10.670 | 0.000 | 0.000 | 0.000 | 0.000 | 26.676 | No |
| 6 | SPACE5-1 | 182.49 | 20.0 | 9.125 | 0.110 | 16.242 | 10.828 | 0.000 | 0.000 | 0.000 | 0.000 | 27.070 | No |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Number of People {} | People/Floor Area {person/m2} | Floor Area per person {m2/person} | Fraction Radiant | Fraction Convected | Sensible Fraction Calculation | Activity level | ASHRAE 55 Warnings | Carbon Dioxide Generation Rate | Nominal Minimum Number of People | Nominal Maximum Number of People | |
| 1 | SPACE1-1 PEOPLE 1 | OCCUPY-1 | SPACE1-1 | 99.16 | 11.0 | 11.0 | 0.111 | 9.015 | 0.300 | 0.700 | AutoCalculate | ACTSCHD | No | 3.8200E-008 | 0 | 11 |
| 2 | SPACE2-1 PEOPLE 1 | OCCUPY-1 | SPACE2-1 | 42.74 | 5.0 | 5.0 | 0.117 | 8.547 | 0.300 | 0.700 | AutoCalculate | ACTSCHD | No | 3.8200E-008 | 0 | 5 |
| 3 | SPACE3-1 PEOPLE 1 | OCCUPY-1 | SPACE3-1 | 96.48 | 11.0 | 11.0 | 0.114 | 8.771 | 0.300 | 0.700 | AutoCalculate | ACTSCHD | No | 3.8200E-008 | 0 | 11 |
| 4 | SPACE4-1 PEOPLE 1 | OCCUPY-1 | SPACE4-1 | 42.74 | 5.0 | 5.0 | 0.117 | 8.547 | 0.300 | 0.700 | AutoCalculate | ACTSCHD | No | 3.8200E-008 | 0 | 5 |
| 5 | SPACE5-1 PEOPLE 1 | OCCUPY-1 | SPACE5-1 | 182.49 | 20.0 | 20.0 | 0.110 | 9.125 | 0.300 | 0.700 | AutoCalculate | ACTSCHD | No | 3.8200E-008 | 0 | 20 |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Lighting Level {W} | Lights/Floor Area {W/m2} | Lights per person {W/person} | Fraction Return Air | Fraction Radiant | Fraction Short Wave | Fraction Convected | Fraction Replaceable | End-Use Category | Nominal Minimum Lighting Level {W} | Nominal Maximum Lighting Level {W} | |
| 1 | SPACE1-1 LIGHTS 1 | LIGHTS-1 | SPACE1-1 | 99.16 | 11.0 | 1584.000 | 15.974 | 144.000 | 0.200 | 0.590 | 0.200 | 1.000E-002 | 0.000 | GeneralLights | 79.200 | 1584.000 |
| 2 | SPACE2-1 LIGHTS 1 | LIGHTS-1 | SPACE2-1 | 42.74 | 5.0 | 684.000 | 16.006 | 136.800 | 0.200 | 0.590 | 0.200 | 1.000E-002 | 0.000 | GeneralLights | 34.200 | 684.000 |
| 3 | SPACE3-1 LIGHTS 1 | LIGHTS-1 | SPACE3-1 | 96.48 | 11.0 | 1584.000 | 16.418 | 144.000 | 0.200 | 0.590 | 0.200 | 1.000E-002 | 0.000 | GeneralLights | 79.200 | 1584.000 |
| 4 | SPACE4-1 LIGHTS 1 | LIGHTS-1 | SPACE4-1 | 42.74 | 5.0 | 684.000 | 16.006 | 136.800 | 0.200 | 0.590 | 0.200 | 1.000E-002 | 0.000 | GeneralLights | 34.200 | 684.000 |
| 5 | SPACE5-1 LIGHTS 1 | LIGHTS-1 | SPACE5-1 | 182.49 | 20.0 | 2964.000 | 16.242 | 148.200 | 0.200 | 0.590 | 0.200 | 1.000E-002 | 0.000 | GeneralLights | 148.200 | 2964.000 |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Equipment Level {W} | Equipment/Floor Area {W/m2} | Equipment per person {W/person} | Fraction Latent | Fraction Radiant | Fraction Lost | Fraction Convected | End-Use SubCategory | Nominal Minimum Equipment Level {W} | Nominal Maximum Equipment Level {W} | |
| 1 | SPACE1-1 ELECEQ 1 | EQUIP-1 | SPACE1-1 | 99.16 | 11.0 | 1056.000 | 10.649 | 96.000 | 0.000 | 0.300 | 0.000 | 0.700 | General | 21.120 | 950.400 |
| 2 | SPACE2-1 ELECEQ 1 | EQUIP-1 | SPACE2-1 | 42.74 | 5.0 | 456.000 | 10.670 | 91.200 | 0.000 | 0.300 | 0.000 | 0.700 | General | 9.120 | 410.400 |
| 3 | SPACE3-1 ELECEQ 1 | EQUIP-1 | SPACE3-1 | 96.48 | 11.0 | 1056.000 | 10.945 | 96.000 | 0.000 | 0.300 | 0.000 | 0.700 | General | 21.120 | 950.400 |
| 4 | SPACE4-1 ELECEQ 1 | EQUIP-1 | SPACE4-1 | 42.74 | 5.0 | 456.000 | 10.670 | 91.200 | 0.000 | 0.300 | 0.000 | 0.700 | General | 9.120 | 410.400 |
| 5 | SPACE5-1 ELECEQ 1 | EQUIP-1 | SPACE5-1 | 182.49 | 20.0 | 1976.000 | 10.828 | 98.800 | 0.000 | 0.300 | 0.000 | 0.700 | General | 39.520 | 1778.400 |
| Calculation Method | Value {days} | Allowable Number Figures in Shadow Overlap {} | Polygon Clipping Algorithm | Sky Diffuse Modeling Algorithm | |
| 1 | AverageOverDaysInFrequency | 20 | 15000 | SutherlandHodgman | SimpleSkyDiffuseModeling |
| Surface Name | Outside Model Assignment | Outside Area [m2] | Outside Perimeter [m] | Outside Height [m] | Inside Model Assignment | Inside Height [cm] | Inside Perimeter Envelope [m] | Inside Hydraulic Diameter [m] | Window Wall Ratio [ ] | Window Location [ ] | Near Radiant [Yes/No] | Has Active HVAC [Yes/No] | |
| 1 | WALL-1PF | 0 | 91.50 | 67.00 | 3.00 | 0 | 0.61 | 91.40 | 14.85 | 0.00 | 0 | No | No |
| 2 | WALL-1PR | 0 | 45.60 | 80.55 | 3.00 | 0 | 0.61 | 91.40 | 14.85 | 0.00 | 0 | No | No |
| 3 | WALL-1PB | 0 | 91.50 | 80.55 | 3.00 | 0 | 0.61 | 91.40 | 14.85 | 0.00 | 0 | No | No |
| 4 | WALL-1PL | 0 | 45.60 | 36.40 | 3.00 | 0 | 0.61 | 91.40 | 14.85 | 0.00 | 0 | No | No |
| 5 | C1-1P | 0 | 0.00 | 0.00 | 0.00 | 0 | 0.61 | 91.40 | 14.85 | 0.00 | 0 | No | No |
| 6 | C2-1P | 0 | 0.00 | 0.00 | 0.00 | 0 | 0.61 | 91.40 | 14.85 | 0.00 | 0 | No | No |
| 7 | C3-1P | 0 | 0.00 | 0.00 | 0.00 | 0 | 0.61 | 91.40 | 14.85 | 0.00 | 0 | No | No |
| 8 | C4-1P | 0 | 0.00 | 0.00 | 0.00 | 0 | 0.61 | 91.40 | 14.85 | 0.00 | 0 | No | No |
| 9 | C5-1P | 0 | 0.00 | 0.00 | 0.00 | 0 | 0.61 | 91.40 | 14.85 | 0.00 | 0 | No | No |
| 10 | TOP-1 | 0 | 463.60 | 91.40 | 0.00 | 0 | 0.61 | 91.40 | 14.85 | 0.00 | 0 | No | No |
| 11 | FRONT-1 | 0 | 91.50 | 67.00 | 3.00 | 0 | 2.44 | 30.50 | 4.61 | 0.30 | 4 | No | No |
| 12 | WF-1 | 0 | 91.50 | 67.00 | 3.00 | 0 | 2.44 | 30.50 | 4.61 | 0.30 | 2 | No | No |
| 13 | DF-1 | 0 | 91.50 | 67.00 | 3.00 | 0 | 2.44 | 30.50 | 4.61 | 0.30 | 1 | No | No |
| 14 | SB12 | 0 | 0.00 | 0.00 | 0.00 | 0 | 2.44 | 30.50 | 4.61 | 0.30 | 0 | No | No |
| 15 | SB14 | 0 | 0.00 | 0.00 | 0.00 | 0 | 2.44 | 30.50 | 4.61 | 0.30 | 0 | No | No |
| 16 | SB15 | 0 | 0.00 | 0.00 | 0.00 | 0 | 2.44 | 30.50 | 4.61 | 0.30 | 0 | No | No |
| 17 | F1-1 | 0 | 0.00 | 0.00 | 0.00 | 0 | 2.44 | 30.50 | 4.61 | 0.30 | 0 | No | No |
| 18 | C1-1 | 0 | 0.00 | 0.00 | 0.00 | 0 | 2.44 | 30.50 | 4.61 | 0.30 | 0 | No | No |
| 19 | RIGHT-1 | 0 | 45.60 | 80.55 | 3.00 | 0 | 2.44 | 15.20 | 3.86 | 0.25 | 3 | No | No |
| 20 | WR-1 | 0 | 45.60 | 80.55 | 3.00 | 0 | 2.44 | 15.20 | 3.86 | 0.25 | 2 | No | No |
| 21 | SB21 | 0 | 0.00 | 0.00 | 0.00 | 0 | 2.44 | 15.20 | 3.86 | 0.25 | 0 | No | No |
| 22 | SB23 | 0 | 0.00 | 0.00 | 0.00 | 0 | 2.44 | 15.20 | 3.86 | 0.25 | 0 | No | No |
| 23 | SB25 | 0 | 0.00 | 0.00 | 0.00 | 0 | 2.44 | 15.20 | 3.86 | 0.25 | 0 | No | No |
| 24 | F2-1 | 0 | 0.00 | 0.00 | 0.00 | 0 | 2.44 | 15.20 | 3.86 | 0.25 | 0 | No | No |
| 25 | C2-1 | 0 | 0.00 | 0.00 | 0.00 | 0 | 2.44 | 15.20 | 3.86 | 0.25 | 0 | No | No |
| 26 | BACK-1 | 0 | 91.50 | 80.55 | 3.00 | 0 | 2.44 | 30.50 | 4.49 | 0.28 | 4 | No | No |
| 27 | WB-1 | 0 | 91.50 | 80.55 | 3.00 | 0 | 2.44 | 30.50 | 4.49 | 0.28 | 2 | No | No |
| 28 | DB-1 | 0 | 91.50 | 80.55 | 3.00 | 0 | 2.44 | 30.50 | 4.49 | 0.28 | 1 | No | No |
| 29 | SB32 | 0 | 0.00 | 0.00 | 0.00 | 0 | 2.44 | 30.50 | 4.49 | 0.28 | 0 | No | No |
| 30 | SB34 | 0 | 0.00 | 0.00 | 0.00 | 0 | 2.44 | 30.50 | 4.49 | 0.28 | 0 | No | No |
| 31 | SB35 | 0 | 0.00 | 0.00 | 0.00 | 0 | 2.44 | 30.50 | 4.49 | 0.28 | 0 | No | No |
| 32 | F3-1 | 0 | 0.00 | 0.00 | 0.00 | 0 | 2.44 | 30.50 | 4.49 | 0.28 | 0 | No | No |
| 33 | C3-1 | 0 | 0.00 | 0.00 | 0.00 | 0 | 2.44 | 30.50 | 4.49 | 0.28 | 0 | No | No |
| 34 | LEFT-1 | 0 | 45.60 | 36.40 | 3.00 | 0 | 2.44 | 15.20 | 3.86 | 0.25 | 3 | No | No |
| 35 | WL-1 | 0 | 45.60 | 36.40 | 3.00 | 0 | 2.44 | 15.20 | 3.86 | 0.25 | 2 | No | No |
| 36 | SB41 | 0 | 0.00 | 0.00 | 0.00 | 0 | 2.44 | 15.20 | 3.86 | 0.25 | 0 | No | No |
| 37 | SB43 | 0 | 0.00 | 0.00 | 0.00 | 0 | 2.44 | 15.20 | 3.86 | 0.25 | 0 | No | No |
| 38 | SB45 | 0 | 0.00 | 0.00 | 0.00 | 0 | 2.44 | 15.20 | 3.86 | 0.25 | 0 | No | No |
| 39 | F4-1 | 0 | 0.00 | 0.00 | 0.00 | 0 | 2.44 | 15.20 | 3.86 | 0.25 | 0 | No | No |
| 40 | C4-1 | 0 | 0.00 | 0.00 | 0.00 | 0 | 2.44 | 15.20 | 3.86 | 0.25 | 0 | No | No |
| 41 | SB51 | 0 | 0.00 | 0.00 | 0.00 | 0 | 2.44 | 0.00 | 8.62 | -999.00 | 0 | No | No |
| 42 | SB52 | 0 | 0.00 | 0.00 | 0.00 | 0 | 2.44 | 0.00 | 8.62 | -999.00 | 0 | No | No |
| 43 | SB53 | 0 | 0.00 | 0.00 | 0.00 | 0 | 2.44 | 0.00 | 8.62 | -999.00 | 0 | No | No |
| 44 | SB54 | 0 | 0.00 | 0.00 | 0.00 | 0 | 2.44 | 0.00 | 8.62 | -999.00 | 0 | No | No |
| 45 | F5-1 | 0 | 0.00 | 0.00 | 0.00 | 0 | 2.44 | 0.00 | 8.62 | -999.00 | 0 | No | No |
| 46 | C5-1 | 0 | 0.00 | 0.00 | 0.00 | 0 | 2.44 | 0.00 | 8.62 | -999.00 | 0 | No | No |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Design Volume Flow Rate {m3/s} | Volume Flow Rate/Floor Area {m3/s/m2} | Volume Flow Rate/Exterior Surface Area {m3/s/m2} | ACH - Air Changes per Hour | Equation A - Constant Term Coefficient {} | Equation B - Temperature Term Coefficient {1/C} | Equation C - Velocity Term Coefficient {s/m} | Equation D - Velocity Squared Term Coefficient {s2/m2} | |
| 1 | SPACE1-1 INFIL 1 | INFIL-SCH | SPACE1-1 | 99.16 | 11.0 | 3.200E-002 | 3.227E-004 | 4.372E-004 | 0.482 | 0.000 | 0.000 | 0.224 | 0.000 |
| 2 | SPACE2-1 INFIL 1 | INFIL-SCH | SPACE2-1 | 42.74 | 5.0 | 1.400E-002 | 3.276E-004 | 3.838E-004 | 0.488 | 0.000 | 0.000 | 0.224 | 0.000 |
| 3 | SPACE3-1 INFIL 1 | INFIL-SCH | SPACE3-1 | 96.48 | 11.0 | 3.200E-002 | 3.317E-004 | 4.372E-004 | 0.482 | 0.000 | 0.000 | 0.224 | 0.000 |
| 4 | SPACE4-1 INFIL 1 | INFIL-SCH | SPACE4-1 | 42.74 | 5.0 | 1.400E-002 | 3.276E-004 | 3.838E-004 | 0.488 | 0.000 | 0.000 | 0.224 | 0.000 |
| 5 | SPACE5-1 INFIL 1 | INFIL-SCH | SPACE5-1 | 182.49 | 20.0 | 6.200E-002 | 3.397E-004 | N/A | 0.499 | 0.000 | 0.000 | 0.224 | 0.000 |
| Simple | |
| 1 | Simple |
| Zone Name | Mixing/Mundt/UCSDDV/UCSDCV/UCSDUFI/UCSDUFE/User Defined | |
| 1 | PLENUM-1 | Mixing/Well-Stirred |
| 2 | SPACE1-1 | Mixing/Well-Stirred |
| 3 | SPACE2-1 | Mixing/Well-Stirred |
| 4 | SPACE3-1 | Mixing/Well-Stirred |
| 5 | SPACE4-1 | Mixing/Well-Stirred |
| 6 | SPACE5-1 | Mixing/Well-Stirred |
| No Multizone or Distribution/Multizone with Distribution/Multizone without Distribution/Multizone with Distribution only during Fan Operation | |
| 1 | NoMultizoneOrDistribution |
| Sensible Heat Capacity Multiplier | Moisture Capacity Multiplier | Carbon Dioxide Capacity Multiplier | Generic Contaminant Capacity Multiplier | |
| 1 | 1.000 | 1.000 | 1.000 | 1.000 |
| Value | |
| 1 | 4 |
| Sizing Factor ID | Value | |
| 1 | Global | 1.0000 |
| Sizing Factor ID | Value | |
| 1 | Global | 1.0000 |
| Zone Name | Load Type | Calc Des Load {W} | User Des Load {W} | Calc Des Air Flow Rate {m3/s} | User Des Air Flow Rate {m3/s} | Design Day Name | Date/Time of Peak | Temperature at Peak {C} | Humidity Ratio at Peak {kgWater/kgDryAir} | Floor Area {m2} | # Occupants | Calc Outdoor Air Flow Rate {m3/s} | Calc DOAS Heat Addition Rate {W} | |
| 1 | SPACE1-1 | Cooling | 2584.89730 | 2584.89730 | 0.21509 | 0.21509 | CHICAGO_IL_USA ANNUAL COOLING 1% DESIGN CONDITIONS DB/MCWB | 7/21 15:45:00 | 31.01850 | 1.45947E-002 | 99.16000 | 11.00000 | 5.62038E-002 | 0.00000 |
| 2 | SPACE1-1 | Heating | 3860.76475 | 3860.76475 | 0.11542 | 0.11542 | CHICAGO_IL_USA ANNUAL HEATING 99% DESIGN CONDITIONS DB | 1/21 24:00:00 | -17.30000 | 8.38927E-004 | 99.16000 | 11.00000 | 5.62038E-002 | 0.00000 |
| 3 | SPACE2-1 | Cooling | 2175.39518 | 2175.39518 | 0.18101 | 0.18101 | CHICAGO_IL_USA ANNUAL COOLING 1% DESIGN CONDITIONS DB/MCWB | 7/21 10:30:00 | 28.23650 | 1.45947E-002 | 42.73500 | 5.00000 | 2.48342E-002 | 0.00000 |
| 4 | SPACE2-1 | Heating | 1625.14886 | 1625.14886 | 4.85834E-002 | 4.85834E-002 | CHICAGO_IL_USA ANNUAL HEATING 99% DESIGN CONDITIONS DB | 1/21 24:00:00 | -17.30000 | 8.38927E-004 | 42.73500 | 5.00000 | 2.48342E-002 | 0.00000 |
| 5 | SPACE3-1 | Cooling | 2779.14891 | 2779.14891 | 0.23126 | 0.23126 | CHICAGO_IL_USA ANNUAL COOLING 1% DESIGN CONDITIONS DB/MCWB | 7/21 10:00:00 | 27.43400 | 1.45947E-002 | 96.48000 | 11.00000 | 5.53864E-002 | 0.00000 |
| 6 | SPACE3-1 | Heating | 3753.06885 | 3753.06885 | 0.11220 | 0.11220 | CHICAGO_IL_USA ANNUAL HEATING 99% DESIGN CONDITIONS DB | 1/21 24:00:00 | -17.30000 | 8.38927E-004 | 96.48000 | 11.00000 | 5.53864E-002 | 0.00000 |
| 7 | SPACE4-1 | Cooling | 2508.89829 | 2508.89829 | 0.20876 | 0.20876 | CHICAGO_IL_USA ANNUAL COOLING 1% DESIGN CONDITIONS DB/MCWB | 7/21 18:00:00 | 28.93200 | 1.45947E-002 | 42.73500 | 5.00000 | 2.48342E-002 | 0.00000 |
| 8 | SPACE4-1 | Heating | 1625.14886 | 1625.14886 | 4.85834E-002 | 4.85834E-002 | CHICAGO_IL_USA ANNUAL HEATING 99% DESIGN CONDITIONS DB | 1/21 24:00:00 | -17.30000 | 8.38927E-004 | 42.73500 | 5.00000 | 2.48342E-002 | 0.00000 |
| 9 | SPACE5-1 | Cooling | 2608.28090 | 2608.28090 | 0.21704 | 0.21704 | CHICAGO_IL_USA ANNUAL COOLING 1% DESIGN CONDITIONS DB/MCWB | 7/21 15:00:00 | 31.50000 | 1.45947E-002 | 182.49000 | 20.00000 | 0.10286 | 0.00000 |
| 10 | SPACE5-1 | Heating | 2981.56778 | 2981.56778 | 8.91327E-002 | 0.10286 | CHICAGO_IL_USA ANNUAL HEATING 99% DESIGN CONDITIONS DB | 1/21 24:00:00 | -17.30000 | 8.38927E-004 | 182.49000 | 20.00000 | 0.10286 | 0.00000 |
| System Name | Load Type | Peak Load Kind | User Design Capacity | Calc Des Air Flow Rate [m3/s] | User Des Air Flow Rate [m3/s] | Design Day Name | Date/Time of Peak | |
| 1 | VAV SYS 1 | Cooling | Sensible | 16796.85 | 1.05316 | 1.05316 | CHICAGO_IL_USA ANNUAL COOLING 1% DESIGN CONDITIONS DB/MCWB | 7/21 00:00:00 |
| 2 | VAV SYS 1 | Heating | Sensible | 9621.54 | 0.42764 | 0.42764 | CHICAGO_IL_USA ANNUAL HEATING 99% DESIGN CONDITIONS DB | 1/21 01:00:00 |
| Component Type | Component Name | Input Field Description | Value | |
| 1 | AirTerminal:SingleDuct:VAV:Reheat | SPACE1-1 VAV REHEAT | Design Size Maximum Air Flow Rate [m3/s] | 0.21509 |
| 2 | AirTerminal:SingleDuct:VAV:Reheat | SPACE1-1 VAV REHEAT | Design Size Constant Minimum Air Flow Fraction | 0.35129 |
| 3 | AirTerminal:SingleDuct:VAV:Reheat | SPACE1-1 VAV REHEAT | User-Specified Constant Minimum Air Flow Fraction | 0.30000 |
| 4 | AirTerminal:SingleDuct:VAV:Reheat | SPACE1-1 VAV REHEAT | Design Size Minimum Air Flow Rate [m3/s] | 6.45278E-002 |
| 5 | AirTerminal:SingleDuct:VAV:Reheat | SPACE1-1 VAV REHEAT | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 6.50744E-004 |
| 6 | AirTerminal:SingleDuct:VAV:Reheat | SPACE1-1 VAV REHEAT | Design Size Maximum Flow Fraction during Reheat [] | 0.30000 |
| 7 | AirTerminal:SingleDuct:VAV:Reheat | SPACE1-1 VAV REHEAT | Design Size Maximum Reheat Water Flow Rate [m3/s] | 1.02164E-004 |
| 8 | AirTerminal:SingleDuct:VAV:Reheat | SPACE1-1 VAV REHEAT | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | 0.11542 |
| 9 | AirTerminal:SingleDuct:VAV:Reheat | SPACE1-1 VAV REHEAT | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | 16.70000 |
| 10 | AirTerminal:SingleDuct:VAV:Reheat | SPACE1-1 VAV REHEAT | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | 8.00000E-003 |
| 11 | Coil:Heating:Water | SPACE1-1 ZONE COIL | Design Size Rated Capacity [W] | 4702.63045 |
| 12 | Coil:Heating:Water | SPACE1-1 ZONE COIL | Design Size Maximum Water Flow Rate [m3/s] | 1.02164E-004 |
| 13 | Coil:Heating:Water | SPACE1-1 ZONE COIL | Design Size U-Factor Times Area Value [W/K] | 113.24397 |
| 14 | AirTerminal:SingleDuct:VAV:Reheat | SPACE2-1 VAV REHEAT | Design Size Maximum Air Flow Rate [m3/s] | 0.18101 |
| 15 | AirTerminal:SingleDuct:VAV:Reheat | SPACE2-1 VAV REHEAT | Design Size Constant Minimum Air Flow Fraction | 0.20000 |
| 16 | AirTerminal:SingleDuct:VAV:Reheat | SPACE2-1 VAV REHEAT | User-Specified Constant Minimum Air Flow Fraction | 0.30000 |
| 17 | AirTerminal:SingleDuct:VAV:Reheat | SPACE2-1 VAV REHEAT | Design Size Minimum Air Flow Rate [m3/s] | 5.43029E-002 |
| 18 | AirTerminal:SingleDuct:VAV:Reheat | SPACE2-1 VAV REHEAT | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 1.27069E-003 |
| 19 | AirTerminal:SingleDuct:VAV:Reheat | SPACE2-1 VAV REHEAT | Design Size Maximum Flow Fraction during Reheat [] | 0.30000 |
| 20 | AirTerminal:SingleDuct:VAV:Reheat | SPACE2-1 VAV REHEAT | Design Size Maximum Reheat Water Flow Rate [m3/s] | 4.38405E-005 |
| 21 | AirTerminal:SingleDuct:VAV:Reheat | SPACE2-1 VAV REHEAT | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | 5.43029E-002 |
| 22 | AirTerminal:SingleDuct:VAV:Reheat | SPACE2-1 VAV REHEAT | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | 16.70000 |
| 23 | AirTerminal:SingleDuct:VAV:Reheat | SPACE2-1 VAV REHEAT | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | 8.00000E-003 |
| 24 | Coil:Heating:Water | SPACE2-1 ZONE COIL | Design Size Rated Capacity [W] | 2017.99168 |
| 25 | Coil:Heating:Water | SPACE2-1 ZONE COIL | Design Size Maximum Water Flow Rate [m3/s] | 4.38405E-005 |
| 26 | Coil:Heating:Water | SPACE2-1 ZONE COIL | Design Size U-Factor Times Area Value [W/K] | 46.69485 |
| 27 | AirTerminal:SingleDuct:VAV:Reheat | SPACE3-1 VAV REHEAT | Design Size Maximum Air Flow Rate [m3/s] | 0.23126 |
| 28 | AirTerminal:SingleDuct:VAV:Reheat | SPACE3-1 VAV REHEAT | Design Size Constant Minimum Air Flow Fraction | 0.31790 |
| 29 | AirTerminal:SingleDuct:VAV:Reheat | SPACE3-1 VAV REHEAT | User-Specified Constant Minimum Air Flow Fraction | 0.30000 |
| 30 | AirTerminal:SingleDuct:VAV:Reheat | SPACE3-1 VAV REHEAT | Design Size Minimum Air Flow Rate [m3/s] | 6.93789E-002 |
| 31 | AirTerminal:SingleDuct:VAV:Reheat | SPACE3-1 VAV REHEAT | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 7.19102E-004 |
| 32 | AirTerminal:SingleDuct:VAV:Reheat | SPACE3-1 VAV REHEAT | Design Size Maximum Flow Fraction during Reheat [] | 0.30000 |
| 33 | AirTerminal:SingleDuct:VAV:Reheat | SPACE3-1 VAV REHEAT | Design Size Maximum Reheat Water Flow Rate [m3/s] | 9.93137E-005 |
| 34 | AirTerminal:SingleDuct:VAV:Reheat | SPACE3-1 VAV REHEAT | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | 0.11220 |
| 35 | AirTerminal:SingleDuct:VAV:Reheat | SPACE3-1 VAV REHEAT | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | 16.70000 |
| 36 | AirTerminal:SingleDuct:VAV:Reheat | SPACE3-1 VAV REHEAT | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | 8.00000E-003 |
| 37 | Coil:Heating:Water | SPACE3-1 ZONE COIL | Design Size Rated Capacity [W] | 4571.44120 |
| 38 | Coil:Heating:Water | SPACE3-1 ZONE COIL | Design Size Maximum Water Flow Rate [m3/s] | 9.93137E-005 |
| 39 | Coil:Heating:Water | SPACE3-1 ZONE COIL | Design Size U-Factor Times Area Value [W/K] | 110.08471 |
| 40 | AirTerminal:SingleDuct:VAV:Reheat | SPACE4-1 VAV REHEAT | Design Size Maximum Air Flow Rate [m3/s] | 0.20876 |
| 41 | AirTerminal:SingleDuct:VAV:Reheat | SPACE4-1 VAV REHEAT | Design Size Constant Minimum Air Flow Fraction | 0.20000 |
| 42 | AirTerminal:SingleDuct:VAV:Reheat | SPACE4-1 VAV REHEAT | User-Specified Constant Minimum Air Flow Fraction | 0.30000 |
| 43 | AirTerminal:SingleDuct:VAV:Reheat | SPACE4-1 VAV REHEAT | Design Size Minimum Air Flow Rate [m3/s] | 6.26275E-002 |
| 44 | AirTerminal:SingleDuct:VAV:Reheat | SPACE4-1 VAV REHEAT | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 1.46549E-003 |
| 45 | AirTerminal:SingleDuct:VAV:Reheat | SPACE4-1 VAV REHEAT | Design Size Maximum Flow Fraction during Reheat [] | 0.30000 |
| 46 | AirTerminal:SingleDuct:VAV:Reheat | SPACE4-1 VAV REHEAT | Design Size Maximum Reheat Water Flow Rate [m3/s] | 4.50569E-005 |
| 47 | AirTerminal:SingleDuct:VAV:Reheat | SPACE4-1 VAV REHEAT | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | 6.26275E-002 |
| 48 | AirTerminal:SingleDuct:VAV:Reheat | SPACE4-1 VAV REHEAT | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | 16.70000 |
| 49 | AirTerminal:SingleDuct:VAV:Reheat | SPACE4-1 VAV REHEAT | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | 8.00000E-003 |
| 50 | Coil:Heating:Water | SPACE4-1 ZONE COIL | Design Size Rated Capacity [W] | 2073.98336 |
| 51 | Coil:Heating:Water | SPACE4-1 ZONE COIL | Design Size Maximum Water Flow Rate [m3/s] | 4.50569E-005 |
| 52 | Coil:Heating:Water | SPACE4-1 ZONE COIL | Design Size U-Factor Times Area Value [W/K] | 46.04886 |
| 53 | AirTerminal:SingleDuct:VAV:Reheat | SPACE5-1 VAV REHEAT | Design Size Maximum Air Flow Rate [m3/s] | 0.21704 |
| 54 | AirTerminal:SingleDuct:VAV:Reheat | SPACE5-1 VAV REHEAT | Design Size Constant Minimum Air Flow Fraction | 0.64070 |
| 55 | AirTerminal:SingleDuct:VAV:Reheat | SPACE5-1 VAV REHEAT | User-Specified Constant Minimum Air Flow Fraction | 0.30000 |
| 56 | AirTerminal:SingleDuct:VAV:Reheat | SPACE5-1 VAV REHEAT | Design Size Minimum Air Flow Rate [m3/s] | 6.51118E-002 |
| 57 | AirTerminal:SingleDuct:VAV:Reheat | SPACE5-1 VAV REHEAT | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 3.56797E-004 |
| 58 | AirTerminal:SingleDuct:VAV:Reheat | SPACE5-1 VAV REHEAT | Design Size Maximum Flow Fraction during Reheat [] | 0.30000 |
| 59 | AirTerminal:SingleDuct:VAV:Reheat | SPACE5-1 VAV REHEAT | Design Size Maximum Reheat Water Flow Rate [m3/s] | 7.88913E-005 |
| 60 | AirTerminal:SingleDuct:VAV:Reheat | SPACE5-1 VAV REHEAT | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | 8.91327E-002 |
| 61 | AirTerminal:SingleDuct:VAV:Reheat | SPACE5-1 VAV REHEAT | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | 16.70000 |
| 62 | AirTerminal:SingleDuct:VAV:Reheat | SPACE5-1 VAV REHEAT | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | 8.00000E-003 |
| 63 | Coil:Heating:Water | SPACE5-1 ZONE COIL | Design Size Rated Capacity [W] | 3631.39093 |
| 64 | Coil:Heating:Water | SPACE5-1 ZONE COIL | Design Size Maximum Water Flow Rate [m3/s] | 7.88913E-005 |
| 65 | Coil:Heating:Water | SPACE5-1 ZONE COIL | Design Size U-Factor Times Area Value [W/K] | 87.44388 |
| 66 | AirLoopHVAC | VAV SYS 1 | Design Supply Air Flow Rate [m3/s] | 1.05316 |
| 67 | Controller:OutdoorAir | OA CONTROLLER 1 | Maximum Outdoor Air Flow Rate [m3/s] | 1.05316 |
| 68 | Controller:OutdoorAir | OA CONTROLLER 1 | Minimum Outdoor Air Flow Rate [m3/s] | 0.26412 |
| 69 | Coil:Heating:Water | OA HEATING COIL 1 | Design Size Rated Capacity [W] | 6877.10488 |
| 70 | Coil:Heating:Water | OA HEATING COIL 1 | Design Size Maximum Water Flow Rate [m3/s] | 1.49404E-004 |
| 71 | Coil:Heating:Water | OA HEATING COIL 1 | Design Size U-Factor Times Area Value [W/K] | 85.63289 |
| 72 | Controller:WaterCoil | OA HC CONTROLLER 1 | Maximum Actuated Flow [m3/s] | 1.49404E-004 |
| 73 | Coil:Cooling:Water | OA COOLING COIL 1 | Design Size Design Coil Load [W] | 11420.22119 |
| 74 | Coil:Cooling:Water | OA COOLING COIL 1 | Design Size Design Water Flow Rate [m3/s] | 1.36034E-003 |
| 75 | Coil:Cooling:Water | OA COOLING COIL 1 | Design Size Design Air Flow Rate [m3/s] | 0.26412 |
| 76 | Coil:Cooling:Water | OA COOLING COIL 1 | Design Size Design Inlet Air Temperature [C] | 29.43888 |
| 77 | Coil:Cooling:Water | OA COOLING COIL 1 | Design Size Design Inlet Water Temperature [C] | 7.00000 |
| 78 | Coil:Cooling:Water | OA COOLING COIL 1 | Design Size Design Outlet Air Temperature [C] | 11.00000 |
| 79 | Coil:Cooling:Water | OA COOLING COIL 1 | Design Size Design Inlet Air Humidity Ratio | 1.45947E-002 |
| 80 | Coil:Cooling:Water | OA COOLING COIL 1 | Design Size Design Outlet Air Humidity Ratio | 8.00000E-003 |
| 81 | Controller:WaterCoil | OA CC CONTROLLER 1 | Maximum Actuated Flow [m3/s] | 1.36034E-003 |
| 82 | Coil:Cooling:Water | MAIN COOLING COIL 1 | Design Size Design Coil Load [W] | 12774.24176 |
| 83 | Coil:Cooling:Water | MAIN COOLING COIL 1 | Design Size Design Water Flow Rate [m3/s] | 7.60811E-004 |
| 84 | Coil:Cooling:Water | MAIN COOLING COIL 1 | Design Size Design Air Flow Rate [m3/s] | 0.88834 |
| 85 | Coil:Cooling:Water | MAIN COOLING COIL 1 | Design Size Design Inlet Air Temperature [C] | 20.87496 |
| 86 | Coil:Cooling:Water | MAIN COOLING COIL 1 | Design Size Design Inlet Water Temperature [C] | 7.00000 |
| 87 | Coil:Cooling:Water | MAIN COOLING COIL 1 | Design Size Design Outlet Air Temperature [C] | 12.80000 |
| 88 | Coil:Cooling:Water | MAIN COOLING COIL 1 | Design Size Design Inlet Air Humidity Ratio | 9.23737E-003 |
| 89 | Coil:Cooling:Water | MAIN COOLING COIL 1 | Design Size Design Outlet Air Humidity Ratio | 8.38649E-003 |
| 90 | Coil:Heating:Water | MAIN HEATING COIL 1 | Design Size Rated Capacity [W] | 3498.65156 |
| 91 | Coil:Heating:Water | MAIN HEATING COIL 1 | Design Size Maximum Water Flow Rate [m3/s] | 7.60076E-005 |
| 92 | Coil:Heating:Water | MAIN HEATING COIL 1 | Design Size U-Factor Times Area Value [W/K] | 56.48962 |
| 93 | Fan:VariableVolume | SUPPLY FAN 1 | Design Size Maximum Flow Rate [m3/s] | 1.05316 |
| 94 | Controller:WaterCoil | CENTRAL COOLING COIL CONTROLLER 1 | Maximum Actuated Flow [m3/s] | 7.60811E-004 |
| 95 | Controller:WaterCoil | CENTRAL HEATING COIL CONTROLLER 1 | Maximum Actuated Flow [m3/s] | 7.60076E-005 |
| 96 | PlantLoop | HOT WATER LOOP | Maximum Loop Flow Rate [m3/s] | 5.94678E-004 |
| 97 | PlantLoop | HOT WATER LOOP | Plant Loop Volume [m3] | 7.13613E-002 |
| 98 | Pump:VariableSpeed | HW CIRC PUMP | Design Flow Rate [m3/s] | 5.94678E-004 |
| 99 | Pump:VariableSpeed | HW CIRC PUMP | Design Power Consumption [W] | 151.93252 |
| 100 | Boiler:HotWater | CENTRAL BOILER | Design Size Nominal Capacity [W] | 27475.23034 |
| 101 | Boiler:HotWater | CENTRAL BOILER | Design Size Design Water Flow Rate [m3/s] | 5.94678E-004 |
| 102 | PlantLoop | CHILLED WATER LOOP | Maximum Loop Flow Rate [m3/s] | 2.12115E-003 |
| 103 | PlantLoop | CHILLED WATER LOOP | Plant Loop Volume [m3] | 0.25454 |
| 104 | Pump:VariableSpeed | CW CIRC PUMP | Design Flow Rate [m3/s] | 2.12115E-003 |
| 105 | Pump:VariableSpeed | CW CIRC PUMP | Design Power Consumption [W] | 541.92612 |
| 106 | Chiller:Electric | CENTRAL CHILLER | Design Size Nominal Capacity [W] | 35614.09027 |
| 107 | Chiller:Electric | CENTRAL CHILLER | Design Size Design Chilled Water Flow Rate [m3/s] | 2.12115E-003 |
| 108 | Chiller:Electric | CENTRAL CHILLER | User-Specified Design Condenser Water Flow Rate [m3/s] | 1.10000E-003 |
| Component Type | Name | Nominal Total Capacity {W} | |
| 1 | Coil:Heating:Water | SPACE1-1 ZONE COIL | 3704.71 |
| 2 | Coil:Heating:Water | SPACE2-1 ZONE COIL | 1994.75 |
| 3 | Coil:Heating:Water | SPACE3-1 ZONE COIL | 3778.87 |
| 4 | Coil:Heating:Water | SPACE4-1 ZONE COIL | 2050.51 |
| 5 | Coil:Heating:Water | SPACE5-1 ZONE COIL | 3222.73 |
| 6 | Coil:Heating:Water | OA HEATING COIL 1 | 4553.72 |
| 7 | Coil:Heating:Water | MAIN HEATING COIL 1 | 3080.17 |
| Component Type | Name | Nominal Total Capacity {W} | Nominal Sensible Capacity {W} | Nominal Latent Capacity {W} | Nominal Sensible Heat Ratio | Nominal Coil UA Value {W/C} | Nominal Coil Surface Area {m2} | |
| 1 | Coil:Cooling:Water | OA COOLING COIL 1 | 8857.93 | 5619.75 | 3238.19 | 0.63 | 879.19 | 8.92 |
| 2 | Coil:Cooling:Water | MAIN COOLING COIL 1 | 17920.27 | 12949.38 | 4970.89 | 0.72 | 1489.74 | 15.11 |
| Zone Name | # Surfaces | |
| 1 | PLENUM-1 | 10 |
| 2 | SPACE1-1 | 8 |
| 3 | SPACE2-1 | 7 |
| 4 | SPACE3-1 | 8 |
| 5 | SPACE4-1 | 7 |
| 6 | SPACE5-1 | 6 |
| Number of Shading Surfaces | # Surfaces | |
| 1 | Number of Shading Surfaces | 4 |
| Surface Name | Surface Class | Base Surface | Heat Transfer Algorithm | Construction | Nominal U (w/o film coefs) {W/m2-K} | Nominal U (with film coefs) {W/m2-K} | Solar Diffusing | Area (Net) {m2} | Area (Gross) {m2} | Area (Sunlit Calc) {m2} | Azimuth {deg} | Tilt {deg} | ~Width {m} | ~Height {m} | Reveal {m} | ExtBoundCondition | ExtConvCoeffCalc | IntConvCoeffCalc | SunExposure | WindExposure | ViewFactorToGround | ViewFactorToSky | ViewFactorToGround-IR | ViewFactorToSky-IR | #Sides | |
| 1 | WALL-1PF | Wall | CTF - ConductionTransferFunction | WALL-1 | 0.408 | 0.384 | 18.30 | 18.30 | 18.30 | 210.00 | 90.00 | 30.50 | 0.60 | 0.00 | ExternalEnvironment | ASHRAESimple | ASHRAESimple | SunExposed | WindExposed | 0.50 | 0.50 | 0.52 | 0.48 | 4 | ||
| 2 | WALL-1PR | Wall | CTF - ConductionTransferFunction | WALL-1 | 0.408 | 0.384 | 9.12 | 9.12 | 9.12 | 120.00 | 90.00 | 15.20 | 0.60 | 0.00 | ExternalEnvironment | ASHRAESimple | ASHRAESimple | SunExposed | WindExposed | 0.50 | 0.50 | 0.50 | 0.50 | 4 | ||
| 3 | WALL-1PB | Wall | CTF - ConductionTransferFunction | WALL-1 | 0.408 | 0.384 | 18.30 | 18.30 | 18.30 | 30.00 | 90.00 | 30.50 | 0.60 | 0.00 | ExternalEnvironment | ASHRAESimple | ASHRAESimple | SunExposed | WindExposed | 0.50 | 0.50 | 0.50 | 0.50 | 4 | ||
| 4 | WALL-1PL | Wall | CTF - ConductionTransferFunction | WALL-1 | 0.408 | 0.384 | 9.12 | 9.12 | 9.12 | 300.00 | 90.00 | 15.20 | 0.60 | 0.00 | ExternalEnvironment | ASHRAESimple | ASHRAESimple | SunExposed | WindExposed | 0.50 | 0.50 | 0.50 | 0.50 | 4 | ||
| 5 | C1-1P | Floor | CTF - ConductionTransferFunction | CLNG-1 | 1.533 | 1.117 | 99.16 | 99.16 | 99.16 | 30.00 | 180.00 | 30.50 | 5.23 | 0.00 | C1-1 | Other/Same Surface Int Conv | ASHRAESimple | NoSun | NoWind | 0.00 | 0.00 | 1.00 | 0.00 | 4 | ||
| 6 | C2-1P | Floor | CTF - ConductionTransferFunction | CLNG-1 | 1.533 | 1.117 | 42.74 | 42.74 | 42.74 | 300.00 | 180.00 | 15.20 | 5.16 | 0.00 | C2-1 | Other/Same Surface Int Conv | ASHRAESimple | NoSun | NoWind | 0.00 | 0.00 | 1.00 | 0.00 | 4 | ||
| 7 | C3-1P | Floor | CTF - ConductionTransferFunction | CLNG-1 | 1.533 | 1.117 | 96.48 | 96.48 | 96.48 | 74.22 | 180.00 | 5.16 | 23.10 | 0.00 | C3-1 | Other/Same Surface Int Conv | ASHRAESimple | NoSun | NoWind | 0.00 | 0.00 | 1.00 | 0.00 | 4 | ||
| 8 | C4-1P | Floor | CTF - ConductionTransferFunction | CLNG-1 | 1.533 | 1.117 | 42.74 | 42.74 | 42.74 | 120.00 | 180.00 | 15.20 | 5.23 | 0.00 | C4-1 | Other/Same Surface Int Conv | ASHRAESimple | NoSun | NoWind | 0.00 | 0.00 | 1.00 | 0.00 | 4 | ||
| 9 | C5-1P | Floor | CTF - ConductionTransferFunction | CLNG-1 | 1.533 | 1.117 | 182.49 | 182.49 | 182.49 | 30.00 | 180.00 | 23.10 | 7.90 | 0.00 | C5-1 | Other/Same Surface Int Conv | ASHRAESimple | NoSun | NoWind | 0.00 | 0.00 | 1.00 | 0.00 | 4 | ||
| 10 | TOP-1 | Roof | CTF - ConductionTransferFunction | ROOF-1 | 0.282 | 0.268 | 463.60 | 463.60 | 463.60 | 210.00 | 0.00 | 30.50 | 15.20 | 0.00 | ExternalEnvironment | ASHRAESimple | ASHRAESimple | SunExposed | WindExposed | 0.00 | 1.00 | 0.00 | 1.00 | 4 | ||
| 11 | FRONT-1 | Wall | CTF - ConductionTransferFunction | WALL-1 | 0.408 | 0.384 | 51.39 | 73.20 | 51.39 | 210.00 | 90.00 | 30.50 | 2.40 | 0.00 | ExternalEnvironment | ASHRAESimple | ASHRAESimple | SunExposed | WindExposed | 0.50 | 0.50 | 0.61 | 0.39 | 4 | ||
| 12 | WF-1 | Window | FRONT-1 | Window5 Detailed Fenestration | DBL CLR 3MM/13MM AIR | N/A | 2.720 | No | 16.56 | 16.56 | 16.56 | 210.00 | 90.00 | 13.80 | 1.20 | 0.00 | ExternalEnvironment | ASHRAESimple | ASHRAESimple | SunExposed | WindExposed | 0.50 | 0.50 | 0.78 | 0.22 | 4 |
| 13 | DF-1 | Window | FRONT-1 | Window5 Detailed Fenestration | SGL GREY 3MM | N/A | 5.894 | No | 5.25 | 5.25 | 5.25 | 210.00 | 90.00 | 2.50 | 2.10 | 0.00 | ExternalEnvironment | ASHRAESimple | ASHRAESimple | SunExposed | WindExposed | 0.50 | 0.50 | 0.66 | 0.34 | 4 |
| 14 | SB12 | Wall | CTF - ConductionTransferFunction | INT-WALL-1 | 2.811 | 1.978 | 12.56 | 12.56 | 12.56 | 75.00 | 90.00 | 5.23 | 2.40 | 0.00 | SB21 | Other/Same Surface Int Conv | ASHRAESimple | NoSun | NoWind | 0.00 | 0.50 | 0.50 | 0.50 | 4 | ||
| 15 | SB14 | Wall | CTF - ConductionTransferFunction | INT-WALL-1 | 2.811 | 1.978 | 12.56 | 12.56 | 12.56 | 345.00 | 90.00 | 5.23 | 2.40 | 0.00 | SB41 | Other/Same Surface Int Conv | ASHRAESimple | NoSun | NoWind | 0.00 | 0.50 | 0.50 | 0.50 | 4 | ||
| 16 | SB15 | Wall | CTF - ConductionTransferFunction | INT-WALL-1 | 2.811 | 1.978 | 55.44 | 55.44 | 55.44 | 30.00 | 90.00 | 23.10 | 2.40 | 0.00 | SB51 | Other/Same Surface Int Conv | ASHRAESimple | NoSun | NoWind | 0.00 | 0.50 | 0.50 | 0.50 | 4 | ||
| 17 | F1-1 | Floor | CTF - ConductionTransferFunction | FLOOR-SLAB-1 | 12.894 | 3.119 | 99.16 | 99.16 | 99.16 | 30.00 | 180.00 | 30.50 | 5.23 | 0.00 | Ground | N/A-Ground | ASHRAESimple | NoSun | NoWind | 0.00 | 0.00 | 1.00 | 0.00 | 4 | ||
| 18 | C1-1 | Roof | CTF - ConductionTransferFunction | CLNG-1 | 1.533 | 1.189 | 99.16 | 99.16 | 99.16 | 210.00 | 0.00 | 30.50 | 5.23 | 0.00 | C1-1P | Other/Same Surface Int Conv | ASHRAESimple | NoSun | NoWind | 0.00 | 1.00 | 0.00 | 1.00 | 4 | ||
| 19 | RIGHT-1 | Wall | CTF - ConductionTransferFunction | WALL-1 | 0.408 | 0.384 | 27.36 | 36.48 | 27.36 | 120.00 | 90.00 | 15.20 | 2.40 | 0.00 | ExternalEnvironment | ASHRAESimple | ASHRAESimple | SunExposed | WindExposed | 0.50 | 0.50 | 0.50 | 0.50 | 4 | ||
| 20 | WR-1 | Window | RIGHT-1 | Window5 Detailed Fenestration | DBL CLR 3MM/13MM AIR | N/A | 2.720 | No | 9.12 | 9.12 | 9.12 | 120.00 | 90.00 | 7.60 | 1.20 | 0.00 | ExternalEnvironment | ASHRAESimple | ASHRAESimple | SunExposed | WindExposed | 0.50 | 0.50 | 0.50 | 0.50 | 4 |
| 21 | SB21 | Wall | CTF - ConductionTransferFunction | INT-WALL-1 | 2.811 | 1.978 | 12.56 | 12.56 | 12.56 | 255.00 | 90.00 | 5.23 | 2.40 | 0.00 | SB12 | Other/Same Surface Int Conv | ASHRAESimple | NoSun | NoWind | 0.00 | 0.50 | 0.50 | 0.50 | 4 | ||
| 22 | SB23 | Wall | CTF - ConductionTransferFunction | INT-WALL-1 | 2.811 | 1.978 | 12.39 | 12.39 | 12.39 | 345.78 | 90.00 | 5.16 | 2.40 | 0.00 | SB32 | Other/Same Surface Int Conv | ASHRAESimple | NoSun | NoWind | 0.00 | 0.50 | 0.50 | 0.50 | 4 | ||
| 23 | SB25 | Wall | CTF - ConductionTransferFunction | INT-WALL-1 | 2.811 | 1.978 | 18.96 | 18.96 | 18.96 | 300.00 | 90.00 | 7.90 | 2.40 | 0.00 | SB52 | Other/Same Surface Int Conv | ASHRAESimple | NoSun | NoWind | 0.00 | 0.50 | 0.50 | 0.50 | 4 | ||
| 24 | F2-1 | Floor | CTF - ConductionTransferFunction | FLOOR-SLAB-1 | 12.894 | 3.119 | 42.74 | 42.74 | 42.74 | 300.00 | 180.00 | 15.20 | 5.16 | 0.00 | Ground | N/A-Ground | ASHRAESimple | NoSun | NoWind | 0.00 | 0.00 | 1.00 | 0.00 | 4 | ||
| 25 | C2-1 | Roof | CTF - ConductionTransferFunction | CLNG-1 | 1.533 | 1.189 | 42.74 | 42.74 | 42.74 | 120.00 | 0.00 | 15.20 | 5.23 | 0.00 | C2-1P | Other/Same Surface Int Conv | ASHRAESimple | NoSun | NoWind | 0.00 | 1.00 | 0.00 | 1.00 | 4 | ||
| 26 | BACK-1 | Wall | CTF - ConductionTransferFunction | WALL-1 | 0.408 | 0.384 | 52.35 | 73.20 | 52.35 | 30.00 | 90.00 | 30.50 | 2.40 | 0.00 | ExternalEnvironment | ASHRAESimple | ASHRAESimple | SunExposed | WindExposed | 0.50 | 0.50 | 0.50 | 0.50 | 4 | ||
| 27 | WB-1 | Window | BACK-1 | Window5 Detailed Fenestration | DBL CLR 3MM/13MM AIR | N/A | 2.720 | No | 16.44 | 16.44 | 16.44 | 30.00 | 90.00 | 13.70 | 1.20 | 0.00 | ExternalEnvironment | ASHRAESimple | ASHRAESimple | SunExposed | WindExposed | 0.50 | 0.50 | 0.50 | 0.50 | 4 |
| 28 | DB-1 | Window | BACK-1 | Window5 Detailed Fenestration | SGL GREY 3MM | N/A | 5.894 | No | 4.41 | 4.41 | 4.41 | 30.00 | 90.00 | 2.10 | 2.10 | 0.00 | ExternalEnvironment | ASHRAESimple | ASHRAESimple | SunExposed | WindExposed | 0.50 | 0.50 | 0.50 | 0.50 | 4 |
| 29 | SB32 | Wall | CTF - ConductionTransferFunction | INT-WALL-1 | 2.811 | 1.978 | 12.39 | 12.39 | 12.39 | 165.78 | 90.00 | 5.16 | 2.40 | 0.00 | SB23 | Other/Same Surface Int Conv | ASHRAESimple | NoSun | NoWind | 0.00 | 0.50 | 0.50 | 0.50 | 4 | ||
| 30 | SB34 | Wall | CTF - ConductionTransferFunction | INT-WALL-1 | 2.811 | 1.978 | 12.39 | 12.39 | 12.39 | 254.22 | 90.00 | 5.16 | 2.40 | 0.00 | SB43 | Other/Same Surface Int Conv | ASHRAESimple | NoSun | NoWind | 0.00 | 0.50 | 0.50 | 0.50 | 4 | ||
| 31 | SB35 | Wall | CTF - ConductionTransferFunction | INT-WALL-1 | 2.811 | 1.978 | 55.44 | 55.44 | 55.44 | 210.00 | 90.00 | 23.10 | 2.40 | 0.00 | SB53 | Other/Same Surface Int Conv | ASHRAESimple | NoSun | NoWind | 0.00 | 0.50 | 0.50 | 0.50 | 4 | ||
| 32 | F3-1 | Floor | CTF - ConductionTransferFunction | FLOOR-SLAB-1 | 12.894 | 3.119 | 96.48 | 96.48 | 96.48 | 74.22 | 180.00 | 5.16 | 23.10 | 0.00 | Ground | N/A-Ground | ASHRAESimple | NoSun | NoWind | 0.00 | 0.00 | 1.00 | 0.00 | 4 | ||
| 33 | C3-1 | Roof | CTF - ConductionTransferFunction | CLNG-1 | 1.533 | 1.189 | 96.48 | 96.48 | 96.48 | 254.22 | 0.00 | 5.16 | 30.50 | 0.00 | C3-1P | Other/Same Surface Int Conv | ASHRAESimple | NoSun | NoWind | 0.00 | 1.00 | 0.00 | 1.00 | 4 | ||
| 34 | LEFT-1 | Wall | CTF - ConductionTransferFunction | WALL-1 | 0.408 | 0.384 | 27.36 | 36.48 | 27.36 | 300.00 | 90.00 | 15.20 | 2.40 | 0.00 | ExternalEnvironment | ASHRAESimple | ASHRAESimple | SunExposed | WindExposed | 0.50 | 0.50 | 0.50 | 0.50 | 4 | ||
| 35 | WL-1 | Window | LEFT-1 | Window5 Detailed Fenestration | DBL CLR 3MM/13MM AIR | N/A | 2.720 | No | 9.12 | 9.12 | 9.12 | 300.00 | 90.00 | 7.60 | 1.20 | 0.00 | ExternalEnvironment | ASHRAESimple | ASHRAESimple | SunExposed | WindExposed | 0.50 | 0.50 | 0.50 | 0.50 | 4 |
| 36 | SB41 | Wall | CTF - ConductionTransferFunction | INT-WALL-1 | 2.811 | 1.978 | 12.56 | 12.56 | 12.56 | 165.00 | 90.00 | 5.23 | 2.40 | 0.00 | SB14 | Other/Same Surface Int Conv | ASHRAESimple | NoSun | NoWind | 0.00 | 0.50 | 0.50 | 0.50 | 4 | ||
| 37 | SB43 | Wall | CTF - ConductionTransferFunction | INT-WALL-1 | 2.811 | 1.978 | 12.39 | 12.39 | 12.39 | 74.22 | 90.00 | 5.16 | 2.40 | 0.00 | SB34 | Other/Same Surface Int Conv | ASHRAESimple | NoSun | NoWind | 0.00 | 0.50 | 0.50 | 0.50 | 4 | ||
| 38 | SB45 | Wall | CTF - ConductionTransferFunction | INT-WALL-1 | 2.811 | 1.978 | 18.96 | 18.96 | 18.96 | 120.00 | 90.00 | 7.90 | 2.40 | 0.00 | SB54 | Other/Same Surface Int Conv | ASHRAESimple | NoSun | NoWind | 0.00 | 0.50 | 0.50 | 0.50 | 4 | ||
| 39 | F4-1 | Floor | CTF - ConductionTransferFunction | FLOOR-SLAB-1 | 12.894 | 3.119 | 42.74 | 42.74 | 42.74 | 120.00 | 180.00 | 15.20 | 5.23 | 0.00 | Ground | N/A-Ground | ASHRAESimple | NoSun | NoWind | 0.00 | 0.00 | 1.00 | 0.00 | 4 | ||
| 40 | C4-1 | Roof | CTF - ConductionTransferFunction | CLNG-1 | 1.533 | 1.189 | 42.74 | 42.74 | 42.74 | 300.00 | 0.00 | 15.20 | 5.16 | 0.00 | C4-1P | Other/Same Surface Int Conv | ASHRAESimple | NoSun | NoWind | 0.00 | 1.00 | 0.00 | 1.00 | 4 | ||
| 41 | SB51 | Wall | CTF - ConductionTransferFunction | INT-WALL-1 | 2.811 | 1.978 | 55.44 | 55.44 | 55.44 | 210.00 | 90.00 | 23.10 | 2.40 | 0.00 | SB15 | Other/Same Surface Int Conv | ASHRAESimple | NoSun | NoWind | 0.00 | 0.50 | 0.50 | 0.50 | 4 | ||
| 42 | SB52 | Wall | CTF - ConductionTransferFunction | INT-WALL-1 | 2.811 | 1.978 | 18.96 | 18.96 | 18.96 | 120.00 | 90.00 | 7.90 | 2.40 | 0.00 | SB25 | Other/Same Surface Int Conv | ASHRAESimple | NoSun | NoWind | 0.00 | 0.50 | 0.50 | 0.50 | 4 | ||
| 43 | SB53 | Wall | CTF - ConductionTransferFunction | INT-WALL-1 | 2.811 | 1.978 | 55.44 | 55.44 | 55.44 | 30.00 | 90.00 | 23.10 | 2.40 | 0.00 | SB35 | Other/Same Surface Int Conv | ASHRAESimple | NoSun | NoWind | 0.00 | 0.50 | 0.50 | 0.50 | 4 | ||
| 44 | SB54 | Wall | CTF - ConductionTransferFunction | INT-WALL-1 | 2.811 | 1.978 | 18.96 | 18.96 | 18.96 | 300.00 | 90.00 | 7.90 | 2.40 | 0.00 | SB45 | Other/Same Surface Int Conv | ASHRAESimple | NoSun | NoWind | 0.00 | 0.50 | 0.50 | 0.50 | 4 | ||
| 45 | F5-1 | Floor | CTF - ConductionTransferFunction | FLOOR-SLAB-1 | 12.894 | 3.119 | 182.49 | 182.49 | 182.49 | 30.00 | 180.00 | 23.10 | 7.90 | 0.00 | Ground | N/A-Ground | ASHRAESimple | NoSun | NoWind | 0.00 | 0.00 | 1.00 | 0.00 | 4 | ||
| 46 | C5-1 | Roof | CTF - ConductionTransferFunction | CLNG-1 | 1.533 | 1.189 | 182.49 | 182.49 | 182.49 | 210.00 | 0.00 | 23.10 | 7.90 | 0.00 | C5-1P | Other/Same Surface Int Conv | ASHRAESimple | NoSun | NoWind | 0.00 | 1.00 | 0.00 | 1.00 | 4 |
| Surface Name | Surface Class | Base Surface | Heat Transfer Algorithm | Transmittance Schedule | Min Schedule Value | Max Schedule Value | Solar Diffusing | Area (Net) {m2} | Area (Gross) {m2} | Area (Sunlit Calc) {m2} | Azimuth {deg} | Tilt {deg} | ~Width {m} | ~Height {m} | Reveal {m} | ExtBoundCondition | ExtConvCoeffCalc | IntConvCoeffCalc | SunExposure | WindExposure | ViewFactorToGround | ViewFactorToSky | ViewFactorToGround-IR | ViewFactorToSky-IR | #Sides | |
| 1 | MAIN SOUTH OVERHANG | Shading | FRONT-1 | None | SHADETRANSSCH | 0.00 | 0.00 | 25.74 | 25.74 | 25.74 | 210.00 | 180.00 | 19.80 | 1.30 | 4 | |||||||||||
| 2 | Mir-MAIN SOUTH OVERHANG | Shading | FRONT-1 | None | SHADETRANSSCH | 0.00 | 0.00 | 25.74 | 25.74 | 25.74 | 30.00 | 0.00 | 19.80 | 1.30 | 4 | |||||||||||
| 3 | SOUTH DOOR OVERHANG | Shading | FRONT-1 | None | SHADETRANSSCH | 0.00 | 0.00 | 6.20 | 6.20 | 6.20 | 210.00 | 180.00 | 3.10 | 2.00 | 4 | |||||||||||
| 4 | Mir-SOUTH DOOR OVERHANG | Shading | FRONT-1 | None | SHADETRANSSCH | 0.00 | 0.00 | 6.20 | 6.20 | 6.20 | 30.00 | 0.00 | 3.10 | 2.00 | 4 |
| Environment Name | Environment Type | Start Date | End Date | Start DayOfWeek | Duration {#days} | Source:Start DayOfWeek | Use Daylight Saving | Use Holidays | Apply Weekend Holiday Rule | Use Rain Values | Use Snow Values | |
| 1 | WINTERDAY | WeatherFileRunPeriod | 01/01 | 12/31 | Tuesday | 365 | Use RunPeriod Specified Day | Yes | Yes | No | Yes | Yes |
| 2 | SUMMERDAY | WeatherFileRunPeriod | 07/07 | 07/07 | Tuesday | 1 | Use RunPeriod Specified Day | Yes | Yes | No | Yes | Yes |
| Daylight Saving Indicator | Source | Start Date | End Date | |
| 1 | No | |||
| 2 | No |
| NumberofWarmupDays | |
| 1 | 6 |
| 2 | 6 |
| Zone Name | Environment Type/Name | Average Warmup Temperature Difference {deltaC} | Std Dev Warmup Temperature Difference {deltaC} | Max Temperature Pass/Fail Convergence | Min Temperature Pass/Fail Convergence | Average Warmup Load Difference {W} | Std Dev Warmup Load Difference {W} | Heating Load Pass/Fail Convergence | Cooling Load Pass/Fail Convergence | |
| 1 | PLENUM-1 | RunPeriod: WINTERDAY | 0.1318224329 | 6.9887074723E-002 | Pass | Pass | 7.2832516834E-002 | 0.1630443956 | Pass | Pass |
| 2 | SPACE1-1 | RunPeriod: WINTERDAY | 0.1171363517 | 0.2987196663 | Pass | Pass | 0.9512883474 | 3.4731303052 | Pass | Pass |
| 3 | SPACE2-1 | RunPeriod: WINTERDAY | 0.1083691636 | 0.3161189509 | Pass | Pass | 0.5913481412 | 2.3576327757 | Pass | Pass |
| 4 | SPACE3-1 | RunPeriod: WINTERDAY | 0.1155392562 | 0.3047718005 | Pass | Pass | 0.6254835164 | 2.1242943509 | Pass | Pass |
| 5 | SPACE4-1 | RunPeriod: WINTERDAY | 0.1088309022 | 0.3176656892 | Pass | Pass | 0.6323708234 | 2.6948511001 | Pass | Pass |
| 6 | SPACE5-1 | RunPeriod: WINTERDAY | 0.1172979544 | 0.1815227235 | Pass | Pass | 0.2742888643 | 1.3129285361 | Pass | Pass |
| 7 | PLENUM-1 | RunPeriod: SUMMERDAY | 9.1918852337E-002 | 9.4143007793E-002 | Pass | Pass | 0.3315168666 | 0.9968243476 | Pass | Pass |
| 8 | SPACE1-1 | RunPeriod: SUMMERDAY | 6.1395228054E-002 | 0.1154761827 | Pass | Pass | 0.2086424418 | 0.9556705228 | Pass | Pass |
| 9 | SPACE2-1 | RunPeriod: SUMMERDAY | 7.0376058735E-002 | 0.1155826075 | Pass | Pass | 0.2129404999 | 0.9918985493 | Pass | Pass |
| 10 | SPACE3-1 | RunPeriod: SUMMERDAY | 6.2216143452E-002 | 0.1192079831 | Pass | Pass | 0.2195868684 | 0.9614072133 | Pass | Pass |
| 11 | SPACE4-1 | RunPeriod: SUMMERDAY | 7.0364748269E-002 | 0.1083649981 | Pass | Pass | 0.2112080447 | 0.9628234089 | Pass | Pass |
| 12 | SPACE5-1 | RunPeriod: SUMMERDAY | 5.8219597342E-002 | 0.1252216049 | Pass | Pass | 0.1875534353 | 0.7605392517 | Pass | Pass |