Program Version:EnergyPlus, Version 9.3.0-64d91887f6, YMD=2020.09.18 19:55
Tabular Output Report in Format: HTML
Building: Building
Environment: RUNPERIOD 1 ** Pittsburgh Allegheny Co Ap PA USA TMY3 WMO#=725205
Simulation Timestamp: 2020-09-18 19:55:49
Report: Annual Building Utility Performance Summary
For: Entire Facility
Timestamp: 2020-09-18 19:55:49
Values gathered over 2184.00 hours| Total Energy [GJ] | Energy Per Total Building Area [MJ/m2] | Energy Per Conditioned Building Area [MJ/m2] | |
| Total Site Energy | 61.95 | 66.82 | 66.82 |
| Net Site Energy | 61.95 | 66.82 | 66.82 |
| Total Source Energy | 196.20 | 211.60 | 211.60 |
| Net Source Energy | 196.20 | 211.60 | 211.60 |
| Site=>Source Conversion Factor | |
| Electricity | 3.167 |
| Natural Gas | 1.084 |
| District Cooling | 1.056 |
| District Heating | 3.613 |
| Steam | 0.300 |
| Gasoline | 1.050 |
| Diesel | 1.050 |
| Coal | 1.050 |
| Fuel Oil #1 | 1.050 |
| Fuel Oil #2 | 1.050 |
| Propane | 1.050 |
| Other Fuel 1 | 1.000 |
| Other Fuel 2 | 1.000 |
| Area [m2] | |
| Total Building Area | 927.20 |
| Net Conditioned Building Area | 927.20 |
| Unconditioned Building Area | 0.00 |
| Electricity [GJ] | Natural Gas [GJ] | Gasoline [GJ] | Diesel [GJ] | Coal [GJ] | Fuel Oil No 1 [GJ] | Fuel Oil No 2 [GJ] | Propane [GJ] | Other Fuel 1 [GJ] | Other Fuel 2 [GJ] | District Cooling [GJ] | District Heating [GJ] | Water [m3] | |
| Heating | 15.84 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | 4.30 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 26.29 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 8.65 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 6.87 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total End Uses | 61.95 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Subcategory | Electricity [GJ] | Natural Gas [GJ] | Gasoline [GJ] | Diesel [GJ] | Coal [GJ] | Fuel Oil No 1 [GJ] | Fuel Oil No 2 [GJ] | Propane [GJ] | Other Fuel 1 [GJ] | Other Fuel 2 [GJ] | District Cooling [GJ] | District Heating [GJ] | Water [m3] | |
| Heating | General | 15.84 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | General | 4.30 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | GeneralLights | 26.29 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | General | 8.65 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | General | 6.87 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Electricity Intensity [MJ/m2] | Natural Gas Intensity [MJ/m2] | Gasoline Intensity [MJ/m2] | Diesel Intensity [MJ/m2] | Coal Intensity [MJ/m2] | Fuel Oil No 1 Intensity [MJ/m2] | Fuel Oil No 2 Intensity [MJ/m2] | Propane Intensity [MJ/m2] | Other Fuel 1 Intensity [MJ/m2] | Other Fuel 2 Intensity [MJ/m2] | District Cooling Intensity [MJ/m2] | District Heating Intensity [MJ/m2] | Water Intensity [m3/m2] | |
| Lighting | 28.35 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| HVAC | 29.13 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Other | 9.33 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total | 66.82 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Electricity Intensity [MJ/m2] | Natural Gas Intensity [MJ/m2] | Gasoline Intensity [MJ/m2] | Diesel Intensity [MJ/m2] | Coal Intensity [MJ/m2] | Fuel Oil No 1 Intensity [MJ/m2] | Fuel Oil No 2 Intensity [MJ/m2] | Propane Intensity [MJ/m2] | Other Fuel 1 Intensity [MJ/m2] | Other Fuel 2 Intensity [MJ/m2] | District Cooling Intensity [MJ/m2] | District Heating Intensity [MJ/m2] | Water Intensity [m3/m2] | |
| Lighting | 28.35 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| HVAC | 29.13 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Other | 9.33 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total | 66.82 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Electricity [GJ] | Percent Electricity [%] | |
| Fuel-Fired Power Generation | 0.000 | 0.00 |
| High Temperature Geothermal* | 0.000 | 0.00 |
| Photovoltaic Power | 0.000 | 0.00 |
| Wind Power | 0.000 | 0.00 |
| Power Conversion | 0.000 | 0.00 |
| Net Decrease in On-Site Storage | 0.000 | 0.00 |
| Total On-Site Electric Sources | 0.000 | 0.00 |
| Electricity Coming From Utility | 61.951 | 100.00 |
| Surplus Electricity Going To Utility | 0.000 | 0.00 |
| Net Electricity From Utility | 61.951 | 100.00 |
| Total On-Site and Utility Electric Sources | 61.951 | 100.00 |
| Total Electricity End Uses | 61.951 | 100.00 |
| Heat [GJ] | Percent Heat [%] | |
| Water-Side Heat Recovery | 0.00 | |
| Air to Air Heat Recovery for Cooling | 0.00 | |
| Air to Air Heat Recovery for Heating | 0.00 | |
| High-Temperature Geothermal* | 0.00 | |
| Solar Water Thermal | 0.00 | |
| Solar Air Thermal | 0.00 | |
| Total On-Site Thermal Sources | 0.00 |
| Water [m3] | Percent Water [%] | |
| Rainwater Collection | 0.00 | - |
| Condensate Collection | 0.00 | - |
| Groundwater Well | 0.00 | - |
| Total On Site Water Sources | 0.00 | - |
| - | - | - |
| Initial Storage | 0.00 | - |
| Final Storage | 0.00 | - |
| Change in Storage | 0.00 | - |
| - | - | - |
| Water Supplied by Utility | 0.00 | - |
| - | - | - |
| Total On Site, Change in Storage, and Utility Water Sources | 0.00 | - |
| Total Water End Uses | 0.00 | - |
| Degrees [deltaC] | |
| Tolerance for Zone Heating Setpoint Not Met Time | 0.20 |
| Tolerance for Zone Cooling Setpoint Not Met Time | 0.20 |
| Facility [Hours] | |
| Time Setpoint Not Met During Occupied Heating | 207.00 |
| Time Setpoint Not Met During Occupied Cooling | 126.75 |
| Time Not Comfortable Based on Simple ASHRAE 55-2004 | 289.25 |
Table of Contents
TopReport: Input Verification and Results Summary
For: Entire Facility
Timestamp: 2020-09-18 19:55:49
General| Value | |
| Program Version and Build | EnergyPlus, Version 9.3.0-64d91887f6, YMD=2020.09.18 19:55 |
| RunPeriod | RUNPERIOD 1 |
| Weather File | Pittsburgh Allegheny Co Ap PA USA TMY3 WMO#=725205 |
| Latitude [deg] | 40.35 |
| Longitude [deg] | -79.9 |
| Elevation [m] | 380.00 |
| Time Zone | -5.0 |
| North Axis Angle [deg] | 30.00 |
| Rotation for Appendix G [deg] | 0.00 |
| Hours Simulated [hrs] | 2184.00 |
| Total | North (315 to 45 deg) | East (45 to 135 deg) | South (135 to 225 deg) | West (225 to 315 deg) | |
| Gross Wall Area [m2] | 274.20 | 91.50 | 45.60 | 91.50 | 45.60 |
| Above Ground Wall Area [m2] | 274.20 | 91.50 | 45.60 | 91.50 | 45.60 |
| Window Opening Area [m2] | 60.90 | 20.85 | 9.12 | 21.81 | 9.12 |
| Gross Window-Wall Ratio [%] | 22.21 | 22.79 | 20.00 | 23.84 | 20.00 |
| Above Ground Window-Wall Ratio [%] | 22.21 | 22.79 | 20.00 | 23.84 | 20.00 |
| Total | North (315 to 45 deg) | East (45 to 135 deg) | South (135 to 225 deg) | West (225 to 315 deg) | |
| Gross Wall Area [m2] | 274.20 | 91.50 | 45.60 | 91.50 | 45.60 |
| Above Ground Wall Area [m2] | 274.20 | 91.50 | 45.60 | 91.50 | 45.60 |
| Window Opening Area [m2] | 60.90 | 20.85 | 9.12 | 21.81 | 9.12 |
| Gross Window-Wall Ratio [%] | 22.21 | 22.79 | 20.00 | 23.84 | 20.00 |
| Above Ground Window-Wall Ratio [%] | 22.21 | 22.79 | 20.00 | 23.84 | 20.00 |
| Total | |
| Gross Roof Area [m2] | 463.60 |
| Skylight Area [m2] | 0.00 |
| Skylight-Roof Ratio [%] | 0.00 |
| Area [m2] | Conditioned (Y/N) | Part of Total Floor Area (Y/N) | Volume [m3] | Multipliers | Above Ground Gross Wall Area [m2] | Underground Gross Wall Area [m2] | Window Glass Area [m2] | Opening Area [m2] | Lighting [W/m2] | People [m2 per person] | Plug and Process [W/m2] | |
| PLENUM-1 | 463.60 | Yes | Yes | 283.20 | 1.00 | 54.84 | 0.00 | 0.00 | 0.00 | 0.0000 | 0.0000 | |
| SPACE1-1 | 99.16 | Yes | Yes | 239.25 | 1.00 | 73.20 | 0.00 | 21.81 | 21.81 | 15.9742 | 9.01 | 10.6495 |
| SPACE2-1 | 42.73 | Yes | Yes | 103.31 | 1.00 | 36.48 | 0.00 | 9.12 | 9.12 | 16.0056 | 8.55 | 10.6704 |
| SPACE3-1 | 96.48 | Yes | Yes | 239.25 | 1.00 | 73.20 | 0.00 | 20.85 | 20.85 | 16.4179 | 8.77 | 10.9453 |
| SPACE4-1 | 42.73 | Yes | Yes | 103.31 | 1.00 | 36.48 | 0.00 | 9.12 | 9.12 | 16.0056 | 8.55 | 10.6704 |
| SPACE5-1 | 182.49 | Yes | Yes | 447.68 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 16.2420 | 9.12 | 10.8280 |
| Total | 927.20 | 1416.00 | 274.20 | 0.00 | 60.90 | 60.90 | 8.0889 | 17.83 | 5.3926 | |||
| Conditioned Total | 927.20 | 1416.00 | 274.20 | 0.00 | 60.90 | 60.90 | 8.0889 | 17.83 | 5.3926 | |||
| Unconditioned Total | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | ||||||
| Not Part of Total | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
Report: Demand End Use Components Summary
For: Entire Facility
Timestamp: 2020-09-18 19:55:49
End Uses| Electricity [W] | Natural Gas [W] | Gasoline [W] | Diesel [W] | Coal [W] | Fuel Oil #1 [W] | Fuel Oil #2 [W] | Propane [W] | Other Fuel 1 [W] | Other Fuel 2 [W] | District Cooling [W] | Steam [W] | Water [m3/s] | |
| Time of Peak | 05-JAN-08:30 | - | - | - | - | - | - | - | - | - | - | - | - |
| Heating | 9451.16 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | 3630.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 7500.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 2500.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 1839.25 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total End Uses | 24920.41 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Subcategory | Electricity [W] | Natural Gas [W] | Gasoline [W] | Diesel [W] | Coal [W] | Fuel Oil #1 [W] | Fuel Oil #2 [W] | Propane [W] | Other Fuel 1 [W] | Other Fuel 2 [W] | District Cooling [W] | Steam [W] | Water [m3/s] | |
| Heating | General | 9451.16 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | General | 3630.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | GeneralLights | 7500.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | General | 2500.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | General | 1839.25 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
Report: Source Energy End Use Components Summary
For: Entire Facility
Timestamp: 2020-09-18 19:55:49
Values gathered over 2184.00 hours| Source Electricity [GJ] | Source Natural Gas [GJ] | Source Gasoline [GJ] | Source Diesel [GJ] | Source Coal [GJ] | Source Fuel Oil No 1 [GJ] | Source Fuel Oil No 2 [GJ] | Source Propane [GJ] | Source Other Fuel 1 [GJ] | Source Other Fuel 2 [GJ] | Source District Cooling [GJ] | Source District Heating [GJ] | |
| Heating | 50.17 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | 13.61 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 83.26 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 27.39 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 21.77 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total Source Energy End Use Components | 196.20 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Source Electricity [MJ/m2] | Source Natural Gas [MJ/m2] | Source Gasoline [MJ/m2] | Source Diesel [MJ/m2] | Source Coal [MJ/m2] | Source Fuel Oil No 1 [MJ/m2] | Source Fuel Oil No 2 [MJ/m2] | Source Propane [MJ/m2] | Source Other Fuel 1 [MJ/m2] | Source Other Fuel 2 [MJ/m2] | Source District Cooling [MJ/m2] | Source District Heating [MJ/m2] | |
| Heating | 54.11 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | 14.68 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 89.80 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 29.54 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 23.48 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total Source Energy End Use Components | 211.60 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Source Electricity [MJ/m2] | Source Natural Gas [MJ/m2] | Source Gasoline [MJ/m2] | Source Diesel [MJ/m2] | Source Coal [MJ/m2] | Source Fuel Oil No 1 [MJ/m2] | Source Fuel Oil No 2 [MJ/m2] | Source Propane [MJ/m2] | Source Other Fuel 1 [MJ/m2] | Source Other Fuel 2 [MJ/m2] | Source District Cooling [MJ/m2] | Source District Heating [MJ/m2] | |
| Heating | 54.11 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | 14.68 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 89.80 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 29.54 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 23.48 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total Source Energy End Use Components | 211.60 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
Report: Component Sizing Summary
For: Entire Facility
Timestamp: 2020-09-18 19:55:49
AirTerminal:SingleDuct:VAV:Reheat| Design Size Maximum Air Flow Rate [m3/s] | Design Size Constant Minimum Air Flow Fraction | User-Specified Constant Minimum Air Flow Fraction | Design Size Minimum Air Flow Rate [m3/s] | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | Design Size Maximum Flow Fraction during Reheat [] | |
| SPACE1-1 VAV REHEAT | 0.614593 | 0.200000 | 0.100000 | 0.061459 | 0.000620 | 0.100000 |
| SPACE2-1 VAV REHEAT | 0.498195 | 0.200000 | 0.100000 | 0.049820 | 0.001166 | 0.100000 |
| SPACE3-1 VAV REHEAT | 0.659641 | 0.200000 | 0.100000 | 0.065964 | 0.000684 | 0.100000 |
| SPACE4-1 VAV REHEAT | 0.534015 | 0.200000 | 0.100000 | 0.053401 | 0.001250 | 0.100000 |
| SPACE5-1 VAV REHEAT | 0.703283 | 0.200000 | 0.100000 | 0.070328 | 0.000385 | 0.100000 |
| Design Size Nominal Capacity [W] | |
| SPACE1-1 ZONE COIL | 5430.27 |
| SPACE2-1 ZONE COIL | 2292.57 |
| SPACE3-1 ZONE COIL | 5269.13 |
| SPACE4-1 ZONE COIL | 2292.57 |
| SPACE5-1 ZONE COIL | 4015.23 |
| MAIN HEATING COIL 1 | 9262.13 |
| Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | Sum of Air Terminal Maximum Flow Rates [m3/s] | Adjusted Heating Design Air Flow Rate [m3/s] | Adjusted Cooling Design Air Flow Rate [m3/s] | Adjusted Main Design Air Flow Rate [m3/s] | User Heating Air Flow Ratio [] | Calculated Heating Air Flow Ratio [] | Design Supply Air Flow Rate [m3/s] | |
| VAV SYS 1 | 0.300973 | 0.300973 | 3.01 | 0.974355 | 3.01 | 3.01 | 1.00 | 0.323735 | 3.01 |
| Maximum Outdoor Air Flow Rate [m3/s] | Minimum Outdoor Air Flow Rate [m3/s] | |
| OA CONTROLLER 1 | 3.01 | 0.480949 |
| Design Size High Speed Rated Air Flow Rate [m3/s] | Design Size High Speed Gross Rated Total Cooling Capacity [W] | Design Size High Speed Rated Sensible Heat Ratio | Design Size Low Speed Rated Air Flow Rate [m3/s] | Design Size Low Speed Gross Rated Total Cooling Capacity [W] | Design Size Low Speed Gross Rated Sensible Heat Ratio | |
| MAIN COOLING COIL 1 | 3.01 | 57773.44 | 0.789052 | 1.00 | 19255.89 | 0.789052 |
| Design Size Maximum Flow Rate [m3/s] | |
| SUPPLY FAN 1 | 3.01 |
Report: Surface Shadowing Summary
For: Entire Facility
Timestamp: 2020-09-18 19:55:49
Surfaces (Walls, Roofs, etc) that may be Shadowed by Other Surfaces| Possible Shadow Receivers | |
| MAIN SOUTH OVERHANG | FRONT-1 | |
| Mir-MAIN SOUTH OVERHANG | SOUTH DOOR OVERHANG | WALL-1PF | FRONT-1 | |
| SOUTH DOOR OVERHANG | WALL-1PF | |
| Mir-SOUTH DOOR OVERHANG | WALL-1PF | |
| WALL-1PF | SOUTH DOOR OVERHANG | |
| FRONT-1 | MAIN SOUTH OVERHANG | SOUTH DOOR OVERHANG | |
| Possible Shadow Receivers | |
| FRONT-1 | WF-1 | DF-1 | |
| RIGHT-1 | WR-1 | |
| BACK-1 | WB-1 | DB-1 | |
| LEFT-1 | WL-1 | |
Report: Adaptive Comfort Summary
For: Entire Facility
Timestamp: 2020-09-18 19:55:49
Time Not Meeting the Adaptive Comfort Models during Occupied Hours| ASHRAE55 90% Acceptability Limits [Hours] | ASHRAE55 80% Acceptability Limits [Hours] | CEN15251 Category I Acceptability Limits [Hours] | CEN15251 Category II Acceptability Limits [Hours] | CEN15251 Category III Acceptability Limits [Hours] |
Report: Initialization Summary
For: Entire Facility
Timestamp: 2020-09-18 19:55:49
Version| Version ID | |
| 1 | 9.3 |
| #TimeSteps | Minutes per TimeStep {minutes} | |
| 1 | 4 | 15 |
| Minimum System TimeStep {minutes} | Max HVAC Iterations | Minimum Plant Iterations | Maximum Plant Iterations | |
| 1 | 1 | 20 | 2 | 8 |
| Do Zone Sizing | Do System Sizing | Do Plant Sizing | Do Design Days | Do Weather Simulation | Do HVAC Sizing Simulation | |
| 1 | Yes | Yes | No | No | Yes | No |
| Use Coil Direct Simulation | Zone Radiant Exchange Algorithm | Override Mode | Number of Timestep In Hour | Force Euler Method | Minimum Number of Warmup Days | Force Suppress All Begin Environment Resets | MaxZoneTempDiff | |
| 1 | No | ScriptF | Normal | 4 | No | 1 | No | 0.300 |
| Tolerance for Time Heating Setpoint Not Met | Tolerance for Zone Cooling Setpoint Not Met Time | |
| 1 | 0.200 | 0.200 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | 20.03 | 20.03 | 20.13 | 20.30 | 20.43 | 20.52 | 20.62 | 20.77 | 20.78 | 20.55 | 20.44 | 20.20 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | 2.10 | 1.21 | 2.79 | 5.27 | 11.76 | 16.77 | 20.14 | 21.17 | 19.42 | 15.53 | 10.34 | 5.52 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 |
| Jan{dimensionless} | Feb{dimensionless} | Mar{dimensionless} | Apr{dimensionless} | May{dimensionless} | Jun{dimensionless} | Jul{dimensionless} | Aug{dimensionless} | Sep{dimensionless} | Oct{dimensionless} | Nov{dimensionless} | Dec{dimensionless} | |
| 1 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 |
| Normal | Daylighting {dimensionless} | |
| 1 | 1.000 | 1.000 |
| Jan{dimensionless} | Feb{dimensionless} | Mar{dimensionless} | Apr{dimensionless} | May{dimensionless} | Jun{dimensionless} | Jul{dimensionless} | Aug{dimensionless} | Sep{dimensionless} | Oct{dimensionless} | Nov{dimensionless} | Dec{dimensionless} | |
| 1 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 |
| Jan{dimensionless} | Feb{dimensionless} | Mar{dimensionless} | Apr{dimensionless} | May{dimensionless} | Jun{dimensionless} | Jul{dimensionless} | Aug{dimensionless} | Sep{dimensionless} | Oct{dimensionless} | Nov{dimensionless} | Dec{dimensionless} | |
| 1 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 |
| Wind Sensor Height Above Ground {m} | Wind Speed Profile Exponent {} | Wind Speed Profile Boundary Layer Thickness {m} | Air Temperature Sensor Height Above Ground {m} | Wind Speed Modifier Coefficient-Internal | Temperature Modifier Coefficient-Internal | |
| 1 | 10.000 | 0.140 | 270.000 | 1.500 | 1.586 | 9.750E-003 |
| Location Name | Latitude {N+/S- Deg} | Longitude {E+/W- Deg} | Time Zone Number {GMT+/-} | Elevation {m} | Standard Pressure at Elevation {Pa} | Standard RhoAir at Elevation | |
| 1 | Pittsburgh Allegheny Co Ap PA USA TMY3 WMO#=725205 | 40.35 | -79.92 | -5.00 | 380.00 | 96842 | 1.1510 |
| Calculation Method{} | Water Mains Temperature Schedule Name{} | Annual Average Outdoor Air Temperature{C} | Maximum Difference In Monthly Average Outdoor Air Temperatures{deltaC} | Fixed Default Water Mains Temperature{C} | |
| 1 | FixedDefault | NA | NA | NA | 10.0 |
| Building Name | North Axis {deg} | Terrain | Loads Convergence Tolerance Value | Temperature Convergence Tolerance Value | Solar Distribution | Maximum Number of Warmup Days | Minimum Number of Warmup Days | |
| 1 | Building | 30.000 | City | 4.00000E-002 | 0.40000 | FullExterior | 25 | 6 |
| Algorithm {Simple TARP CeilingDiffuser AdaptiveConvectionAlgorithm} |
|
| 1 | Simple |
| Algorithm {SimpleCombined TARP MoWitt DOE-2 AdaptiveConvectionAlgorithm} |
|
| 1 | SimpleCombined |
| Value {Anisotropic} | |
| 1 | Anisotropic |
| Value {ThirdOrderBackwardDifference AnalyticalSolution EulerMethod} |
|
| 1 | ThirdOrderBackwardDifference |
| Simulation {Yes/No} | Carbon Dioxide Concentration | |
| 1 | No | N/A |
| Simulation {Yes/No} | Generic Contaminant Concentration | |
| 1 | No | N/A |
| Enforce Mass Balance |
Adjust Zone Mixing |
Adjust Zone Infiltration {AddInfiltration AdjustInfiltration None} |
Infiltration Zones {MixingSourceZonesOnly AllZones} |
|
| 1 | No | N/A | N/A | N/A |
| Value {RegulaFalsi Bisection BisectionThenRegulaFalsi RegulaFalsiThenBisection} |
|
| 1 | RegulaFalsi |
| Wind Speed Profile Exponent {} | Wind Speed Profile Boundary Layer Thickness {m} | Air Temperature Gradient Coefficient {K/m} | |
| 1 | 0.330 | 460.000 | 6.500000E-003 |
| Starting Corner | Vertex Input Direction | Coordinate System | Daylight Reference Point Coordinate System | Rectangular (Simple) Surface Coordinate System | |
| 1 | UpperLeftCorner | Counterclockwise | RelativeCoordinateSystem | RelativeCoordinateSystem | RelativeToZoneOrigin |
| Value {CTF - ConductionTransferFunction EMPD - MoisturePenetrationDepthConductionTransferFunction CondFD - ConductionFiniteDifference HAMT - CombinedHeatAndMoistureFiniteElement} - Description |
Inside Surface Max Temperature Limit{C} |
Surface Convection Coefficient Lower Limit {W/m2-K} |
Surface Convection Coefficient Upper Limit {W/m2-K} |
|
| 1 | CTF - ConductionTransferFunction | 200 | 0.10 | 1000.0 |
| Number of Fixed Detached Shades | Number of Building Detached Shades | Number of Attached Shades | |
| 1 | 0 | 0 | 4 |
| Number of Zones | Number of Zone Surfaces | Number of SubSurfaces | |
| 1 | 6 | 46 | 6 |
| Zone Name | North Axis {deg} | Origin X-Coordinate {m} | Origin Y-Coordinate {m} | Origin Z-Coordinate {m} | Centroid X-Coordinate {m} | Centroid Y-Coordinate {m} | Centroid Z-Coordinate {m} | Type | Zone Multiplier | Zone List Multiplier | Minimum X {m} | Maximum X {m} | Minimum Y {m} | Maximum Y {m} | Minimum Z {m} | Maximum Z {m} | Ceiling Height {m} | Volume {m3} | Zone Inside Convection Algorithm {Simple-Detailed-CeilingDiffuser-TrombeWall} | Zone Outside Convection Algorithm {Simple-Detailed-Tarp-MoWitt-DOE-2-BLAST} | Floor Area {m2} | Exterior Gross Wall Area {m2} | Exterior Net Wall Area {m2} | Exterior Window Area {m2} | Number of Surfaces | Number of SubSurfaces | Number of Shading SubSurfaces | Part of Total Building Area | |
| 1 | PLENUM-1 | 0.0 | 0.00 | 0.00 | 0.00 | 17.01 | -1.04 | 2.70 | 1 | 1 | 1 | 0.00 | 34.01 | -15.25 | 13.16 | 2.40 | 3.00 | 0.61 | 283.20 | Simple | Simple | 463.60 | 54.84 | 54.84 | 0.00 | 10 | 0 | 0 | Yes |
| 2 | SPACE1-1 | 0.0 | 0.00 | 0.00 | 0.00 | 14.06 | -6.15 | 1.20 | 1 | 1 | 1 | 0.00 | 26.41 | -15.25 | 1.35 | 0.00 | 2.40 | 2.44 | 239.25 | Simple | Simple | 99.16 | 73.20 | 51.39 | 21.81 | 6 | 2 | 4 | Yes |
| 3 | SPACE2-1 | 0.0 | 0.00 | 0.00 | 0.00 | 28.88 | -7.88 | 1.20 | 1 | 1 | 1 | 25.06 | 34.01 | -15.25 | -2.09 | 0.00 | 2.40 | 2.44 | 103.31 | Simple | Simple | 42.74 | 36.48 | 27.36 | 9.12 | 6 | 1 | 0 | Yes |
| 4 | SPACE3-1 | 0.0 | 0.00 | 0.00 | 0.00 | 19.98 | 4.10 | 1.20 | 1 | 1 | 1 | 7.60 | 34.01 | -3.35 | 13.16 | 0.00 | 2.40 | 2.44 | 239.25 | Simple | Simple | 96.48 | 73.20 | 52.35 | 20.85 | 6 | 2 | 0 | Yes |
| 5 | SPACE4-1 | 0.0 | 0.00 | 0.00 | 0.00 | 5.15 | 5.82 | 1.20 | 1 | 1 | 1 | 0.00 | 9.00 | 0.00 | 13.16 | 0.00 | 2.40 | 2.44 | 103.31 | Simple | Simple | 42.74 | 36.48 | 27.36 | 9.12 | 6 | 1 | 0 | Yes |
| 6 | SPACE5-1 | 0.0 | 0.00 | 0.00 | 0.00 | 17.03 | -1.00 | 1.20 | 1 | 1 | 1 | 5.05 | 29.01 | -10.20 | 8.20 | 0.00 | 2.40 | 2.44 | 447.68 | Simple | Simple | 182.49 | 0.00 | 0.00 | 0.00 | 6 | 0 | 0 | Yes |
| Zone Name | Floor Area {m2} | # Occupants | Area per Occupant {m2/person} | Occupant per Area {person/m2} | Interior Lighting {W/m2} | Electric Load {W/m2} | Gas Load {W/m2} | Other Load {W/m2} | Hot Water Eq {W/m2} | Steam Equipment {W/m2} | Sum Loads per Area {W/m2} | Outdoor Controlled Baseboard Heat | |
| 1 | PLENUM-1 | 463.60 | 0.0 | N/A | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | No |
| 2 | SPACE1-1 | 99.16 | 11.0 | 9.015 | 0.111 | 15.974 | 10.649 | 0.000 | 0.000 | 0.000 | 0.000 | 26.624 | No |
| 3 | SPACE2-1 | 42.74 | 5.0 | 8.547 | 0.117 | 16.006 | 10.670 | 0.000 | 0.000 | 0.000 | 0.000 | 26.676 | No |
| 4 | SPACE3-1 | 96.48 | 11.0 | 8.771 | 0.114 | 16.418 | 10.945 | 0.000 | 0.000 | 0.000 | 0.000 | 27.363 | No |
| 5 | SPACE4-1 | 42.74 | 5.0 | 8.547 | 0.117 | 16.006 | 10.670 | 0.000 | 0.000 | 0.000 | 0.000 | 26.676 | No |
| 6 | SPACE5-1 | 182.49 | 20.0 | 9.125 | 0.110 | 16.242 | 10.828 | 0.000 | 0.000 | 0.000 | 0.000 | 27.070 | No |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Number of People {} | People/Floor Area {person/m2} | Floor Area per person {m2/person} | Fraction Radiant | Fraction Convected | Sensible Fraction Calculation | Activity level | ASHRAE 55 Warnings | Carbon Dioxide Generation Rate | Nominal Minimum Number of People | Nominal Maximum Number of People | MRT Calculation Type | Work Efficiency | Clothing Insulation Calculation Method | Clothing Insulation Calculation Method Schedule | Clothing | Air Velocity | Fanger Calculation | Pierce Calculation | KSU Calculation | |
| 1 | SPACE1-1 PEOPLE 1 | OCCUPY-1 | SPACE1-1 | 99.16 | 11.0 | 11.0 | 0.111 | 9.015 | 0.300 | 0.700 | AutoCalculate | ACTSCHD | No | 3.8200E-008 | 0 | 11 | Zone Averaged | WORKEFFSCH | Dynamic Clothing Model ASHRAE55 | N/A | Constant-1.0 | AIRVELOCITYSCH | Yes | No | No |
| 2 | SPACE2-1 PEOPLE 1 | OCCUPY-1 | SPACE2-1 | 42.74 | 5.0 | 5.0 | 0.117 | 8.547 | 0.300 | 0.700 | AutoCalculate | ACTSCHD | No | 3.8200E-008 | 0 | 5 | Zone Averaged | WORKEFFSCH | Dynamic Clothing Model ASHRAE55 | N/A | Constant-1.0 | AIRVELOCITYSCH | Yes | No | No |
| 3 | SPACE3-1 PEOPLE 1 | OCCUPY-1 | SPACE3-1 | 96.48 | 11.0 | 11.0 | 0.114 | 8.771 | 0.300 | 0.700 | AutoCalculate | ACTSCHD | No | 3.8200E-008 | 0 | 11 | Zone Averaged | WORKEFFSCH | Dynamic Clothing Model ASHRAE55 | N/A | Constant-1.0 | AIRVELOCITYSCH | Yes | No | No |
| 4 | SPACE4-1 PEOPLE 1 | OCCUPY-1 | SPACE4-1 | 42.74 | 5.0 | 5.0 | 0.117 | 8.547 | 0.300 | 0.700 | AutoCalculate | ACTSCHD | No | 3.8200E-008 | 0 | 5 | Zone Averaged | WORKEFFSCH | Dynamic Clothing Model ASHRAE55 | N/A | Constant-1.0 | AIRVELOCITYSCH | Yes | No | No |
| 5 | SPACE5-1 PEOPLE 1 | OCCUPY-1 | SPACE5-1 | 182.49 | 20.0 | 20.0 | 0.110 | 9.125 | 0.300 | 0.700 | AutoCalculate | ACTSCHD | No | 3.8200E-008 | 0 | 20 | Zone Averaged | WORKEFFSCH | Dynamic Clothing Model ASHRAE55 | N/A | Constant-1.0 | AIRVELOCITYSCH | Yes | No | No |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Lighting Level {W} | Lights/Floor Area {W/m2} | Lights per person {W/person} | Fraction Return Air | Fraction Radiant | Fraction Short Wave | Fraction Convected | Fraction Replaceable | End-Use Category | Nominal Minimum Lighting Level {W} | Nominal Maximum Lighting Level {W} | |
| 1 | SPACE1-1 LIGHTS 1 | LIGHTS-1 | SPACE1-1 | 99.16 | 11.0 | 1584.000 | 15.974 | 144.000 | 0.200 | 0.590 | 0.200 | 1.000E-002 | 0.000 | GeneralLights | 79.200 | 1584.000 |
| 2 | SPACE2-1 LIGHTS 1 | LIGHTS-1 | SPACE2-1 | 42.74 | 5.0 | 684.000 | 16.006 | 136.800 | 0.200 | 0.590 | 0.200 | 1.000E-002 | 0.000 | GeneralLights | 34.200 | 684.000 |
| 3 | SPACE3-1 LIGHTS 1 | LIGHTS-1 | SPACE3-1 | 96.48 | 11.0 | 1584.000 | 16.418 | 144.000 | 0.200 | 0.590 | 0.200 | 1.000E-002 | 0.000 | GeneralLights | 79.200 | 1584.000 |
| 4 | SPACE4-1 LIGHTS 1 | LIGHTS-1 | SPACE4-1 | 42.74 | 5.0 | 684.000 | 16.006 | 136.800 | 0.200 | 0.590 | 0.200 | 1.000E-002 | 0.000 | GeneralLights | 34.200 | 684.000 |
| 5 | SPACE5-1 LIGHTS 1 | LIGHTS-1 | SPACE5-1 | 182.49 | 20.0 | 2964.000 | 16.242 | 148.200 | 0.200 | 0.590 | 0.200 | 1.000E-002 | 0.000 | GeneralLights | 148.200 | 2964.000 |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Equipment Level {W} | Equipment/Floor Area {W/m2} | Equipment per person {W/person} | Fraction Latent | Fraction Radiant | Fraction Lost | Fraction Convected | End-Use SubCategory | Nominal Minimum Equipment Level {W} | Nominal Maximum Equipment Level {W} | |
| 1 | SPACE1-1 ELECEQ 1 | EQUIP-1 | SPACE1-1 | 99.16 | 11.0 | 1056.000 | 10.649 | 96.000 | 0.000 | 0.300 | 0.000 | 0.700 | General | 21.120 | 528.000 |
| 2 | SPACE2-1 ELECEQ 1 | EQUIP-1 | SPACE2-1 | 42.74 | 5.0 | 456.000 | 10.670 | 91.200 | 0.000 | 0.300 | 0.000 | 0.700 | General | 9.120 | 228.000 |
| 3 | SPACE3-1 ELECEQ 1 | EQUIP-1 | SPACE3-1 | 96.48 | 11.0 | 1056.000 | 10.945 | 96.000 | 0.000 | 0.300 | 0.000 | 0.700 | General | 21.120 | 528.000 |
| 4 | SPACE4-1 ELECEQ 1 | EQUIP-1 | SPACE4-1 | 42.74 | 5.0 | 456.000 | 10.670 | 91.200 | 0.000 | 0.300 | 0.000 | 0.700 | General | 9.120 | 228.000 |
| 5 | SPACE5-1 ELECEQ 1 | EQUIP-1 | SPACE5-1 | 182.49 | 20.0 | 1976.000 | 10.828 | 98.800 | 0.000 | 0.300 | 0.000 | 0.700 | General | 39.520 | 988.000 |
| Shading Calculation Method | Shading Calculation Update Frequency Method | Shading Calculation Update Frequency {days} | Maximum Figures in Shadow Overlap Calculations {} | Polygon Clipping Algorithm | Pixel Counting Resolution | Sky Diffuse Modeling Algorithm | Output External Shading Calculation Results | Disable Self-Shading Within Shading Zone Groups | Disable Self-Shading From Shading Zone Groups to Other Zones | |
| 1 | PolygonClipping | Periodic | 20 | 15000 | SutherlandHodgman | 512 | SimpleSkyDiffuseModeling | No | No | No |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Design Volume Flow Rate {m3/s} | Volume Flow Rate/Floor Area {m3/s-m2} | Volume Flow Rate/Exterior Surface Area {m3/s-m2} | ACH - Air Changes per Hour | Equation A - Constant Term Coefficient {} | Equation B - Temperature Term Coefficient {1/C} | Equation C - Velocity Term Coefficient {s/m} | Equation D - Velocity Squared Term Coefficient {s2/m2} | |
| 1 | SPACE1-1 INFIL 1 | INFIL-SCH | SPACE1-1 | 99.16 | 11.0 | 1.670E-002 | 1.684E-004 | 2.281E-004 | 0.251 | 0.000 | 0.000 | 0.224 | 0.000 |
| 2 | SPACE2-1 INFIL 1 | INFIL-SCH | SPACE2-1 | 42.74 | 5.0 | 7.170E-003 | 1.678E-004 | 1.965E-004 | 0.250 | 0.000 | 0.000 | 0.224 | 0.000 |
| 3 | SPACE3-1 INFIL 1 | INFIL-SCH | SPACE3-1 | 96.48 | 11.0 | 1.670E-002 | 1.731E-004 | 2.281E-004 | 0.251 | 0.000 | 0.000 | 0.224 | 0.000 |
| 4 | SPACE4-1 INFIL 1 | INFIL-SCH | SPACE4-1 | 42.74 | 5.0 | 7.170E-003 | 1.678E-004 | 1.965E-004 | 0.250 | 0.000 | 0.000 | 0.224 | 0.000 |
| 5 | SPACE5-1 INFIL 1 | INFIL-SCH | SPACE5-1 | 182.49 | 20.0 | 3.109E-002 | 1.704E-004 | N/A | 0.250 | 0.000 | 0.000 | 0.224 | 0.000 |
| Simple | |
| 1 | Simple |
| Zone Name | Mixing/Mundt/UCSDDV/UCSDCV/UCSDUFI/UCSDUFE/User Defined | |
| 1 | PLENUM-1 | Mixing/Well-Stirred |
| 2 | SPACE1-1 | Mixing/Well-Stirred |
| 3 | SPACE2-1 | Mixing/Well-Stirred |
| 4 | SPACE3-1 | Mixing/Well-Stirred |
| 5 | SPACE4-1 | Mixing/Well-Stirred |
| 6 | SPACE5-1 | Mixing/Well-Stirred |
| No Multizone or Distribution/Multizone with Distribution/Multizone without Distribution/Multizone with Distribution only during Fan Operation | |
| 1 | NoMultizoneOrDistribution |
| Sensible Heat Capacity Multiplier | Moisture Capacity Multiplier | Carbon Dioxide Capacity Multiplier | Generic Contaminant Capacity Multiplier | |
| 1 | 1.000 | 1.000 | 1.000 | 1.000 |
| Value | |
| 1 | 4 |
| Sizing Factor ID | Value | |
| 1 | Global | 1.3000 |
| 2 | Zone SPACE1-1 | 1.3000 |
| 3 | Zone SPACE2-1 | 1.3000 |
| 4 | Zone SPACE3-1 | 1.3000 |
| 5 | Zone SPACE4-1 | 1.3000 |
| 6 | Zone SPACE5-1 | 1.3000 |
| Sizing Factor ID | Value | |
| 1 | Global | 1.3000 |
| 2 | Zone SPACE1-1 | 1.3000 |
| 3 | Zone SPACE2-1 | 1.3000 |
| 4 | Zone SPACE3-1 | 1.3000 |
| 5 | Zone SPACE4-1 | 1.3000 |
| 6 | Zone SPACE5-1 | 1.3000 |
| Zone Name | Load Type | Calc Des Load {W} | User Des Load {W} | Calc Des Air Flow Rate {m3/s} | User Des Air Flow Rate {m3/s} | Design Day Name | Date/Time of Peak | Temperature at Peak {C} | Humidity Ratio at Peak {kgWater/kgDryAir} | Floor Area {m2} | # Occupants | Calc Outdoor Air Flow Rate {m3/s} | Calc DOAS Heat Addition Rate {W} | |
| 1 | SPACE1-1 | Cooling | 4390.53312 | 5707.69305 | 0.47276 | 0.61459 | PITTSBURGH ALLEGHENY CO AP ANN CLG .4% CONDNS DB=>MWB | 7/21 16:30:00 | 31.21000 | 1.39781E-002 | 99.16000 | 11.00000 | 0.10229 | 0.00000 |
| 2 | SPACE1-1 | Heating | 3415.47763 | 4440.12092 | 0.21088 | 0.27415 | PITTSBURGH ALLEGHENY CO AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | -15.40000 | 1.02482E-003 | 99.16000 | 11.00000 | 0.10229 | 0.00000 |
| 3 | SPACE2-1 | Cooling | 3559.07282 | 4626.79466 | 0.38323 | 0.49820 | PITTSBURGH ALLEGHENY CO AP ANN CLG .4% CONDNS DB=>MWB | 7/21 09:45:00 | 28.01725 | 1.39724E-002 | 42.73500 | 5.00000 | 4.53094E-002 | 0.00000 |
| 4 | SPACE2-1 | Heating | 1441.95505 | 1874.54157 | 8.90315E-002 | 0.11574 | PITTSBURGH ALLEGHENY CO AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | -15.40000 | 1.02482E-003 | 42.73500 | 5.00000 | 4.53094E-002 | 0.00000 |
| 5 | SPACE3-1 | Cooling | 4713.20691 | 6127.16898 | 0.50742 | 0.65964 | PITTSBURGH ALLEGHENY CO AP ANN CLG .4% CONDNS DB=>MWB | 7/21 09:00:00 | 26.75500 | 1.39701E-002 | 96.48000 | 11.00000 | 0.10093 | 0.00000 |
| 6 | SPACE3-1 | Heating | 3314.13068 | 4308.36988 | 0.20463 | 0.26601 | PITTSBURGH ALLEGHENY CO AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | -15.40000 | 1.02482E-003 | 96.48000 | 11.00000 | 0.10093 | 0.00000 |
| 7 | SPACE4-1 | Cooling | 3814.89077 | 4959.35800 | 0.41078 | 0.53401 | PITTSBURGH ALLEGHENY CO AP ANN CLG .4% CONDNS DB=>MWB | 7/21 17:30:00 | 30.31900 | 1.39765E-002 | 42.73500 | 5.00000 | 4.53094E-002 | 0.00000 |
| 8 | SPACE4-1 | Heating | 1441.95505 | 1874.54157 | 8.90315E-002 | 0.11574 | PITTSBURGH ALLEGHENY CO AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | -15.40000 | 1.02482E-003 | 42.73500 | 5.00000 | 4.53094E-002 | 0.00000 |
| 9 | SPACE5-1 | Cooling | 5023.92775 | 6531.10607 | 0.54099 | 0.70328 | PITTSBURGH ALLEGHENY CO AP ANN CLG .4% CONDNS DB=>MWB | 7/21 16:45:00 | 31.01200 | 1.39778E-002 | 182.49000 | 20.00000 | 0.18710 | 0.00000 |
| 10 | SPACE5-1 | Heating | 2525.46766 | 3283.10795 | 0.15593 | 0.20271 | PITTSBURGH ALLEGHENY CO AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | -15.40000 | 1.02482E-003 | 182.49000 | 20.00000 | 0.18710 | 0.00000 |
| System Name | Load Type | Peak Load Kind | User Design Capacity | Calc Des Air Flow Rate [m3/s] | User Des Air Flow Rate [m3/s] | Design Day Name | Date/Time of Peak | |
| 1 | VAV SYS 1 | Cooling | Sensible | 46146.52 | 3.00973 | 3.00973 | PITTSBURGH ALLEGHENY CO AP ANN CLG .4% CONDNS DB=>MWB | 7/21 00:00:00 |
| 2 | VAV SYS 1 | Heating | Sensible | 16761.65 | 0.97435 | 0.97435 | PITTSBURGH ALLEGHENY CO AP ANN HTG 99.6% CONDNS DB | 1/21 09:15:00 |
| Component Type | Component Name | Input Field Description | Value | |
| 1 | AirTerminal:SingleDuct:VAV:Reheat | SPACE1-1 VAV REHEAT | Design Size Maximum Air Flow Rate [m3/s] | 0.61459 |
| 2 | AirTerminal:SingleDuct:VAV:Reheat | SPACE1-1 VAV REHEAT | Design Size Constant Minimum Air Flow Fraction | 0.20000 |
| 3 | AirTerminal:SingleDuct:VAV:Reheat | SPACE1-1 VAV REHEAT | User-Specified Constant Minimum Air Flow Fraction | 0.10000 |
| 4 | AirTerminal:SingleDuct:VAV:Reheat | SPACE1-1 VAV REHEAT | Design Size Minimum Air Flow Rate [m3/s] | 6.14593E-002 |
| 5 | AirTerminal:SingleDuct:VAV:Reheat | SPACE1-1 VAV REHEAT | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 6.19800E-004 |
| 6 | AirTerminal:SingleDuct:VAV:Reheat | SPACE1-1 VAV REHEAT | Design Size Maximum Flow Fraction during Reheat [] | 0.10000 |
| 7 | Coil:Heating:Electric | SPACE1-1 ZONE COIL | Design Size Nominal Capacity [W] | 5430.26572 |
| 8 | AirTerminal:SingleDuct:VAV:Reheat | SPACE2-1 VAV REHEAT | Design Size Maximum Air Flow Rate [m3/s] | 0.49820 |
| 9 | AirTerminal:SingleDuct:VAV:Reheat | SPACE2-1 VAV REHEAT | Design Size Constant Minimum Air Flow Fraction | 0.20000 |
| 10 | AirTerminal:SingleDuct:VAV:Reheat | SPACE2-1 VAV REHEAT | User-Specified Constant Minimum Air Flow Fraction | 0.10000 |
| 11 | AirTerminal:SingleDuct:VAV:Reheat | SPACE2-1 VAV REHEAT | Design Size Minimum Air Flow Rate [m3/s] | 4.98195E-002 |
| 12 | AirTerminal:SingleDuct:VAV:Reheat | SPACE2-1 VAV REHEAT | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 1.16578E-003 |
| 13 | AirTerminal:SingleDuct:VAV:Reheat | SPACE2-1 VAV REHEAT | Design Size Maximum Flow Fraction during Reheat [] | 0.10000 |
| 14 | Coil:Heating:Electric | SPACE2-1 ZONE COIL | Design Size Nominal Capacity [W] | 2292.56616 |
| 15 | AirTerminal:SingleDuct:VAV:Reheat | SPACE3-1 VAV REHEAT | Design Size Maximum Air Flow Rate [m3/s] | 0.65964 |
| 16 | AirTerminal:SingleDuct:VAV:Reheat | SPACE3-1 VAV REHEAT | Design Size Constant Minimum Air Flow Fraction | 0.20000 |
| 17 | AirTerminal:SingleDuct:VAV:Reheat | SPACE3-1 VAV REHEAT | User-Specified Constant Minimum Air Flow Fraction | 0.10000 |
| 18 | AirTerminal:SingleDuct:VAV:Reheat | SPACE3-1 VAV REHEAT | Design Size Minimum Air Flow Rate [m3/s] | 6.59641E-002 |
| 19 | AirTerminal:SingleDuct:VAV:Reheat | SPACE3-1 VAV REHEAT | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 6.83707E-004 |
| 20 | AirTerminal:SingleDuct:VAV:Reheat | SPACE3-1 VAV REHEAT | Design Size Maximum Flow Fraction during Reheat [] | 0.10000 |
| 21 | Coil:Heating:Electric | SPACE3-1 ZONE COIL | Design Size Nominal Capacity [W] | 5269.13343 |
| 22 | AirTerminal:SingleDuct:VAV:Reheat | SPACE4-1 VAV REHEAT | Design Size Maximum Air Flow Rate [m3/s] | 0.53401 |
| 23 | AirTerminal:SingleDuct:VAV:Reheat | SPACE4-1 VAV REHEAT | Design Size Constant Minimum Air Flow Fraction | 0.20000 |
| 24 | AirTerminal:SingleDuct:VAV:Reheat | SPACE4-1 VAV REHEAT | User-Specified Constant Minimum Air Flow Fraction | 0.10000 |
| 25 | AirTerminal:SingleDuct:VAV:Reheat | SPACE4-1 VAV REHEAT | Design Size Minimum Air Flow Rate [m3/s] | 5.34015E-002 |
| 26 | AirTerminal:SingleDuct:VAV:Reheat | SPACE4-1 VAV REHEAT | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 1.24960E-003 |
| 27 | AirTerminal:SingleDuct:VAV:Reheat | SPACE4-1 VAV REHEAT | Design Size Maximum Flow Fraction during Reheat [] | 0.10000 |
| 28 | Coil:Heating:Electric | SPACE4-1 ZONE COIL | Design Size Nominal Capacity [W] | 2292.56616 |
| 29 | AirTerminal:SingleDuct:VAV:Reheat | SPACE5-1 VAV REHEAT | Design Size Maximum Air Flow Rate [m3/s] | 0.70328 |
| 30 | AirTerminal:SingleDuct:VAV:Reheat | SPACE5-1 VAV REHEAT | Design Size Constant Minimum Air Flow Fraction | 0.20000 |
| 31 | AirTerminal:SingleDuct:VAV:Reheat | SPACE5-1 VAV REHEAT | User-Specified Constant Minimum Air Flow Fraction | 0.10000 |
| 32 | AirTerminal:SingleDuct:VAV:Reheat | SPACE5-1 VAV REHEAT | Design Size Minimum Air Flow Rate [m3/s] | 7.03283E-002 |
| 33 | AirTerminal:SingleDuct:VAV:Reheat | SPACE5-1 VAV REHEAT | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 3.85382E-004 |
| 34 | AirTerminal:SingleDuct:VAV:Reheat | SPACE5-1 VAV REHEAT | Design Size Maximum Flow Fraction during Reheat [] | 0.10000 |
| 35 | Coil:Heating:Electric | SPACE5-1 ZONE COIL | Design Size Nominal Capacity [W] | 4015.22917 |
| 36 | AirLoopHVAC | VAV SYS 1 | Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | 0.30097 |
| 37 | AirLoopHVAC | VAV SYS 1 | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | 0.30097 |
| 38 | AirLoopHVAC | VAV SYS 1 | Sum of Air Terminal Maximum Flow Rates [m3/s] | 3.00973 |
| 39 | AirLoopHVAC | VAV SYS 1 | Adjusted Heating Design Air Flow Rate [m3/s] | 0.97435 |
| 40 | AirLoopHVAC | VAV SYS 1 | Adjusted Cooling Design Air Flow Rate [m3/s] | 3.00973 |
| 41 | AirLoopHVAC | VAV SYS 1 | Adjusted Main Design Air Flow Rate [m3/s] | 3.00973 |
| 42 | AirLoopHVAC | VAV SYS 1 | User Heating Air Flow Ratio [] | 1.00000 |
| 43 | AirLoopHVAC | VAV SYS 1 | Calculated Heating Air Flow Ratio [] | 0.32374 |
| 44 | AirLoopHVAC | VAV SYS 1 | Design Supply Air Flow Rate [m3/s] | 3.00973 |
| 45 | Controller:OutdoorAir | OA CONTROLLER 1 | Maximum Outdoor Air Flow Rate [m3/s] | 3.00973 |
| 46 | Controller:OutdoorAir | OA CONTROLLER 1 | Minimum Outdoor Air Flow Rate [m3/s] | 0.48095 |
| 47 | Coil:Cooling:DX:TwoSpeed | MAIN COOLING COIL 1 | Design Size High Speed Rated Air Flow Rate [m3/s] | 3.00973 |
| 48 | Coil:Cooling:DX:TwoSpeed | MAIN COOLING COIL 1 | Design Size High Speed Gross Rated Total Cooling Capacity [W] | 57773.44221 |
| 49 | Coil:Cooling:DX:TwoSpeed | MAIN COOLING COIL 1 | Design Size High Speed Rated Sensible Heat Ratio | 0.78905 |
| 50 | Coil:Cooling:DX:TwoSpeed | MAIN COOLING COIL 1 | Design Size Low Speed Rated Air Flow Rate [m3/s] | 1.00314 |
| 51 | Coil:Cooling:DX:TwoSpeed | MAIN COOLING COIL 1 | Design Size Low Speed Gross Rated Total Cooling Capacity [W] | 19255.88829 |
| 52 | Coil:Cooling:DX:TwoSpeed | MAIN COOLING COIL 1 | Design Size Low Speed Gross Rated Sensible Heat Ratio | 0.78905 |
| 53 | Coil:Heating:Electric | MAIN HEATING COIL 1 | Design Size Nominal Capacity [W] | 9262.13463 |
| 54 | Fan:VariableVolume | SUPPLY FAN 1 | Design Size Maximum Flow Rate [m3/s] | 3.00973 |
| Environment Name | Environment Type | Start Date | End Date | Start DayOfWeek | Duration {#days} | Source:Start DayOfWeek | Use Daylight Saving | Use Holidays | Apply Weekend Holiday Rule | Use Rain Values | Use Snow Values | Sky Temperature Model | |
| 1 | RUNPERIOD 1 | WeatherFileRunPeriod | 01/01/2007 | 04/01/2007 | Monday | 91 | Use RunPeriod Specified Day | Yes | Yes | No | Yes | Yes | Clark and Allen |
| Daylight Saving Indicator | Source | Start Date | End Date | |
| 1 | No |
| NumberofWarmupDays | |
| 1 | 6 |
| Zone Name | Environment Type/Name | Average Warmup Temperature Difference {deltaC} | Std Dev Warmup Temperature Difference {deltaC} | Max Temperature Pass/Fail Convergence | Min Temperature Pass/Fail Convergence | Average Warmup Load Difference {W} | Std Dev Warmup Load Difference {W} | Heating Load Pass/Fail Convergence | Cooling Load Pass/Fail Convergence | |
| 1 | PLENUM-1 | RunPeriod: RUNPERIOD 1 | 0.1740541040 | 0.2238052475 | Pass | Pass | 0.3543808282 | 1.4580549523 | Pass | Pass |
| 2 | SPACE1-1 | RunPeriod: RUNPERIOD 1 | 0.1915210690 | 0.2627473802 | Pass | Pass | 0.2380112136 | 0.4049662656 | Pass | Pass |
| 3 | SPACE2-1 | RunPeriod: RUNPERIOD 1 | 0.1891480293 | 0.2599916407 | Pass | Pass | 0.2173171912 | 0.3598610092 | Pass | Pass |
| 4 | SPACE3-1 | RunPeriod: RUNPERIOD 1 | 0.1926194712 | 0.2643356321 | Pass | Pass | 0.2330451286 | 0.4248039888 | Pass | Pass |
| 5 | SPACE4-1 | RunPeriod: RUNPERIOD 1 | 0.1890662904 | 0.2600398845 | Pass | Pass | 0.2173135950 | 0.3598626997 | Pass | Pass |
| 6 | SPACE5-1 | RunPeriod: RUNPERIOD 1 | 0.2111842088 | 0.2920067409 | Pass | Pass | 0.1728488500 | 0.2624604689 | Pass | Pass |
Report: Annual Heat Emissions Summary
For: Entire Facility
Timestamp: 2020-09-18 19:55:49
Heat Emission by Components| Envelope Convection | Zone Exfiltration | Zone Exhaust Air | HVAC Relief Air | HVAC Reject Heat | Total | |
| Heat Emissions [GJ] | 404.47 | 2.88 | 0.00 | 58.08 | 4.30 | 469.72 |
Report: Climatic Data Summary
For: Entire Facility
Timestamp: 2020-09-18 19:55:49
SizingPeriod:DesignDay| Maximum Dry Bulb [C] | Daily Temperature Range [deltaC] | Humidity Value | Humidity Type | Wind Speed [m/s] | Wind Direction | |
| PITTSBURGH ALLEGHENY CO AP ANN HTG 99.6% CONDNS DB | -15.40 | 0.00 | -15.40 | Wetbulb [C] | 4.70 | 240.00 |
| PITTSBURGH ALLEGHENY CO AP ANN CLG .4% CONDNS DB=>MWB | 32.20 | 9.90 | 22.50 | Wetbulb [C] | 4.40 | 240.00 |
| Value | |
| None |
Report: Envelope Summary
For: Entire Facility
Timestamp: 2020-09-18 19:55:49
Opaque Exterior| Construction | Reflectance | U-Factor with Film [W/m2-K] | U-Factor no Film [W/m2-K] | Gross Area [m2] | Net Area [m2] | Azimuth [deg] | Tilt [deg] | Cardinal Direction | |
| WALL-1PF | WALL-1 | 0.22 | 0.384 | 0.408 | 18.30 | 18.30 | 210.00 | 90.00 | S |
| WALL-1PR | WALL-1 | 0.22 | 0.384 | 0.408 | 9.12 | 9.12 | 120.00 | 90.00 | E |
| WALL-1PB | WALL-1 | 0.22 | 0.384 | 0.408 | 18.30 | 18.30 | 30.00 | 90.00 | N |
| WALL-1PL | WALL-1 | 0.22 | 0.384 | 0.408 | 9.12 | 9.12 | 300.00 | 90.00 | W |
| TOP-1 | ROOF-1 | 0.35 | 0.271 | 0.282 | 463.60 | 463.60 | 210.00 | 0.00 | |
| FRONT-1 | WALL-1 | 0.22 | 0.384 | 0.408 | 73.20 | 51.39 | 210.00 | 90.00 | S |
| F1-1 | FLOOR-SLAB-1 | 0.35 | 1.649 | 2.249 | 99.16 | 99.16 | 30.00 | 180.00 | |
| RIGHT-1 | WALL-1 | 0.22 | 0.384 | 0.408 | 36.48 | 27.36 | 120.00 | 90.00 | E |
| F2-1 | FLOOR-SLAB-1 | 0.35 | 1.649 | 2.249 | 42.73 | 42.73 | 300.00 | 180.00 | |
| BACK-1 | WALL-1 | 0.22 | 0.384 | 0.408 | 73.20 | 52.35 | 30.00 | 90.00 | N |
| F3-1 | FLOOR-SLAB-1 | 0.35 | 1.649 | 2.249 | 96.48 | 96.48 | 74.22 | 180.00 | |
| LEFT-1 | WALL-1 | 0.22 | 0.384 | 0.408 | 36.48 | 27.36 | 300.00 | 90.00 | W |
| F4-1 | FLOOR-SLAB-1 | 0.35 | 1.649 | 2.249 | 42.73 | 42.73 | 120.00 | 180.00 | |
| F5-1 | FLOOR-SLAB-1 | 0.35 | 1.649 | 2.249 | 182.49 | 182.49 | 30.00 | 180.00 |
| Construction | Glass Area [m2] | Frame Area [m2] | Divider Area [m2] | Area of One Opening [m2] | Area of Multiplied Openings [m2] | Glass U-Factor [W/m2-K] | Glass SHGC | Glass Visible Transmittance | Frame Conductance [W/m2-K] | Divider Conductance [W/m2-K] | Shade Control | Parent Surface | Azimuth [deg] | Tilt [deg] | Cardinal Direction | |
| WF-1 | DBL CLR 3MM/13MM AIR | 16.56 | 0.00 | 0.00 | 16.56 | 16.56 | 2.720 | 0.764 | 0.812 | No | FRONT-1 | 210.00 | 90.00 | S | ||
| DF-1 | SGL GREY 3MM | 5.25 | 0.00 | 0.00 | 5.25 | 5.25 | 5.894 | 0.716 | 0.611 | No | FRONT-1 | 210.00 | 90.00 | S | ||
| WR-1 | DBL CLR 3MM/13MM AIR | 9.12 | 0.00 | 0.00 | 9.12 | 9.12 | 2.720 | 0.764 | 0.812 | No | RIGHT-1 | 120.00 | 90.00 | E | ||
| WB-1 | DBL CLR 3MM/13MM AIR | 16.44 | 0.00 | 0.00 | 16.44 | 16.44 | 2.720 | 0.764 | 0.812 | No | BACK-1 | 30.00 | 90.00 | N | ||
| DB-1 | SGL GREY 3MM | 4.41 | 0.00 | 0.00 | 4.41 | 4.41 | 5.894 | 0.716 | 0.611 | No | BACK-1 | 30.00 | 90.00 | N | ||
| WL-1 | DBL CLR 3MM/13MM AIR | 9.12 | 0.00 | 0.00 | 9.12 | 9.12 | 2.720 | 0.764 | 0.812 | No | LEFT-1 | 300.00 | 90.00 | W | ||
| Total or Average | 60.90 | 3.223 | 0.756 | 0.780 | ||||||||||||
| North Total or Average | 20.85 | 3.391 | 0.754 | 0.769 | ||||||||||||
| Non-North Total or Average | 40.05 | 3.136 | 0.757 | 0.785 |
| Construction | Area of One Opening [m2] | Area of Openings [m2] | Glass U-Factor [W/m2-K] | Glass SHGC | Glass Visible Transmittance | Parent Surface | |
| Total or Average | 0.00 | - | - | - |
| Construction | U-Factor with Film [W/m2-K] | U-Factor no Film [W/m2-K] | Gross Area [m2] | Parent Surface | |
| None |
Report: Shading Summary
For: Entire Facility
Timestamp: 2020-09-18 19:55:49
Sunlit Fraction| March 21 9am | March 21 noon | March 21 3pm | June 21 9am | June 21 noon | June 21 3pm | December 21 9am | December 21 noon | December 21 3pm | |
| WF-1 | 0.00 | 0.00 | 0.32 | ||||||
| DF-1 | 0.00 | 0.28 | 0.59 | ||||||
| WR-1 | 1.00 | 1.00 | 0.00 | ||||||
| WB-1 | 1.00 | 0.00 | 0.00 | ||||||
| DB-1 | 1.00 | 0.00 | 0.00 | ||||||
| WL-1 | 0.00 | 0.00 | 1.00 |
| Name | Type | Shaded Construction | Control | Glare Control | |
| None |
Report: Lighting Summary
For: Entire Facility
Timestamp: 2020-09-18 19:55:49
Interior Lighting| Zone | Lighting Power Density [W/m2] | Zone Area [m2] | Total Power [W] | End Use Subcategory | Schedule Name | Scheduled Hours/Week [hr] | Hours/Week > 1% [hr] | Full Load Hours/Week [hr] | Return Air Fraction | Conditioned (Y/N) | Consumption [GJ] | |
| SPACE1-1 LIGHTS 1 | SPACE1-1 | 15.9742 | 99.16 | 1584.00 | GeneralLights | LIGHTS-1 | 74.90 | 167.98 | 74.90 | 0.2000 | Y | 5.55 |
| SPACE2-1 LIGHTS 1 | SPACE2-1 | 16.0056 | 42.73 | 684.00 | GeneralLights | LIGHTS-1 | 74.90 | 167.98 | 74.90 | 0.2000 | Y | 2.40 |
| SPACE3-1 LIGHTS 1 | SPACE3-1 | 16.4179 | 96.48 | 1584.00 | GeneralLights | LIGHTS-1 | 74.90 | 167.98 | 74.90 | 0.2000 | Y | 5.55 |
| SPACE4-1 LIGHTS 1 | SPACE4-1 | 16.0056 | 42.73 | 684.00 | GeneralLights | LIGHTS-1 | 74.90 | 167.98 | 74.90 | 0.2000 | Y | 2.40 |
| SPACE5-1 LIGHTS 1 | SPACE5-1 | 16.2420 | 182.49 | 2964.00 | GeneralLights | LIGHTS-1 | 74.90 | 167.98 | 74.90 | 0.2000 | Y | 10.39 |
| Interior Lighting Total | 16.1777 | 463.60 | 7500.00 | 26.29 |
| Zone | Control Name | Daylighting Method | Control Type | Fraction Controlled | Lighting Installed in Zone [W] | Lighting Controlled [W] | |
| None |
| Total Watts | Astronomical Clock/Schedule | Schedule Name | Scheduled Hours/Week [hr] | Hours/Week > 1% [hr] | Full Load Hours/Week [hr] | Consumption [GJ] | |
| Exterior Lighting Total | 0.00 | 0.00 |
Report: Equipment Summary
For: Entire Facility
Timestamp: 2020-09-18 19:55:49
Central Plant| Type | Nominal Capacity [W] | Nominal Efficiency [W/W] | IPLV in SI Units [W/W] | IPLV in IP Units [Btu/W-h] | |
| None |
| Type | Design Coil Load [W] | Nominal Total Capacity [W] | Nominal Sensible Capacity [W] | Nominal Latent Capacity [W] | Nominal Sensible Heat Ratio | Nominal Efficiency [W/W] | Nominal Coil UA Value [W/C] | Nominal Coil Surface Area [m2] | |
| MAIN COOLING COIL 1 | Coil:Cooling:DX:TwoSpeed | 57773.44 | 45586.26 | 12187.18 | 0.79 | 3.00 |
| DX Cooling Coil Type | Standard Rated Net Cooling Capacity [W] | Standard Rated Net COP [W/W] | EER [Btu/W-h] | SEER [Btu/W-h] | IEER [Btu/W-h] | |
| None |
| DX Cooling Coil Type | Rated Net Cooling Capacity Test A [W] | Rated Electric Power Test A [W] | Rated Net Cooling Capacity Test B [W] | Rated Electric Power Test B [W] | Rated Net Cooling Capacity Test C [W] | Rated Electric Power Test C [W] | Rated Net Cooling Capacity Test D [W] | Rated Electric Power Test D [W] | |
| None |
| DX Heating Coil Type | High Temperature Heating (net) Rating Capacity [W] | Low Temperature Heating (net) Rating Capacity [W] | HSPF [Btu/W-h] | Region Number | |
| None |
| Type | Design Coil Load [W] | Nominal Total Capacity [W] | Nominal Efficiency [W/W] | |
| SPACE1-1 ZONE COIL | Coil:Heating:Electric | 5430.27 | 0.98 | |
| SPACE2-1 ZONE COIL | Coil:Heating:Electric | 2292.57 | 0.98 | |
| SPACE3-1 ZONE COIL | Coil:Heating:Electric | 5269.13 | 0.98 | |
| SPACE4-1 ZONE COIL | Coil:Heating:Electric | 2292.57 | 0.98 | |
| SPACE5-1 ZONE COIL | Coil:Heating:Electric | 4015.23 | 0.98 | |
| MAIN HEATING COIL 1 | Coil:Heating:Electric | 9262.13 | 0.98 |
| Type | Total Efficiency [W/W] | Delta Pressure [pa] | Max Air Flow Rate [m3/s] | Rated Electric Power [W] | Rated Power Per Max Air Flow Rate [W-s/m3] | Motor Heat In Air Fraction | Fan Energy Index | End Use Subcategory | Design Day Name for Fan Sizing Peak | Date/Time for Fan Sizing Peak | |
| SUPPLY FAN 1 | Fan:VariableVolume | 0.70 | 600.00 | 3.01 | 2579.77 | 857.14 | 1.00 | 1.52 | General | PITTSBURGH ALLEGHENY CO AP ANN CLG .4% CONDNS DB=>MWB | 7/21 16:45:00 |
| Type | Control | Head [pa] | Water Flow [m3/s] | Electric Power [W] | Power Per Water Flow Rate [W-s/m3] | Motor Efficiency [W/W] | End Use Subcategory | |
| None |
| Type | Storage Volume [m3] | Input [W] | Thermal Efficiency [W/W] | Recovery Efficiency [W/W] | Energy Factor | |
| None |
Report: HVAC Sizing Summary
For: Entire Facility
Timestamp: 2020-09-18 19:55:49
Zone Sensible Cooling| Calculated Design Load [W] | User Design Load [W] | User Design Load per Area [W/m2] | Calculated Design Air Flow [m3/s] | User Design Air Flow [m3/s] | Design Day Name | Date/Time Of Peak {TIMESTAMP} | Thermostat Setpoint Temperature at Peak Load [C] | Indoor Temperature at Peak Load [C] | Indoor Humidity Ratio at Peak Load [kgWater/kgDryAir] | Outdoor Temperature at Peak Load [C] | Outdoor Humidity Ratio at Peak Load [kgWater/kgDryAir] | Minimum Outdoor Air Flow Rate [m3/s] | Heat Gain Rate from DOAS [W] | |
| SPACE1-1 | 4390.53 | 5707.69 | 57.56 | 0.473 | 0.615 | PITTSBURGH ALLEGHENY CO AP ANN CLG .4% CONDNS DB=>MWB | 7/21 16:30:00 | 23.90 | 23.90 | 0.00938 | 31.21 | 0.01398 | 0.102 | 0.00 |
| SPACE2-1 | 3559.07 | 4626.79 | 108.27 | 0.383 | 0.498 | PITTSBURGH ALLEGHENY CO AP ANN CLG .4% CONDNS DB=>MWB | 7/21 09:45:00 | 23.90 | 23.90 | 0.00921 | 28.02 | 0.01397 | 0.045 | 0.00 |
| SPACE3-1 | 4713.21 | 6127.17 | 63.51 | 0.507 | 0.660 | PITTSBURGH ALLEGHENY CO AP ANN CLG .4% CONDNS DB=>MWB | 7/21 09:00:00 | 23.90 | 23.90 | 0.00937 | 26.76 | 0.01397 | 0.101 | 0.00 |
| SPACE4-1 | 3814.89 | 4959.36 | 116.05 | 0.411 | 0.534 | PITTSBURGH ALLEGHENY CO AP ANN CLG .4% CONDNS DB=>MWB | 7/21 17:30:00 | 23.90 | 23.90 | 0.00920 | 30.32 | 0.01398 | 0.045 | 0.00 |
| SPACE5-1 | 5023.93 | 6531.11 | 35.79 | 0.541 | 0.703 | PITTSBURGH ALLEGHENY CO AP ANN CLG .4% CONDNS DB=>MWB | 7/21 16:45:00 | 23.90 | 23.90 | 0.00960 | 31.01 | 0.01398 | 0.187 | 0.00 |
| Calculated Design Load [W] | User Design Load [W] | User Design Load per Area [W/m2] | Calculated Design Air Flow [m3/s] | User Design Air Flow [m3/s] | Design Day Name | Date/Time Of Peak {TIMESTAMP} | Thermostat Setpoint Temperature at Peak Load [C] | Indoor Temperature at Peak Load [C] | Indoor Humidity Ratio at Peak Load [kgWater/kgDryAir] | Outdoor Temperature at Peak Load [C] | Outdoor Humidity Ratio at Peak Load [kgWater/kgDryAir] | Minimum Outdoor Air Flow Rate [m3/s] | Heat Gain Rate from DOAS [W] | |
| SPACE1-1 | 3415.48 | 4440.12 | 44.78 | 0.211 | 0.274 | PITTSBURGH ALLEGHENY CO AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 21.10 | 21.10 | 0.00394 | -15.40 | 0.00102 | 0.102 | 0.00 |
| SPACE2-1 | 1441.96 | 1874.54 | 43.86 | 0.089 | 0.116 | PITTSBURGH ALLEGHENY CO AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 21.10 | 21.10 | 0.00394 | -15.40 | 0.00102 | 0.045 | 0.00 |
| SPACE3-1 | 3314.13 | 4308.37 | 44.66 | 0.205 | 0.266 | PITTSBURGH ALLEGHENY CO AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 21.10 | 21.10 | 0.00394 | -15.40 | 0.00102 | 0.101 | 0.00 |
| SPACE4-1 | 1441.96 | 1874.54 | 43.86 | 0.089 | 0.116 | PITTSBURGH ALLEGHENY CO AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 21.10 | 21.10 | 0.00394 | -15.40 | 0.00102 | 0.045 | 0.00 |
| SPACE5-1 | 2525.47 | 3283.11 | 17.99 | 0.156 | 0.203 | PITTSBURGH ALLEGHENY CO AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 21.10 | 21.10 | 0.00385 | -15.40 | 0.00102 | 0.187 | 0.00 |
| Calculated cooling [m3/s] | User cooling [m3/s] | Calculated heating [m3/s] | User heating [m3/s] | Adjusted cooling [m3/s] | Adjusted heating [m3/s] | Adjusted main [m3/s] | Calculated Heating Air Flow Ratio [] | User Heating Air Flow Ratio [] | |
| VAV SYS 1 | 3.01 | 3.01 | 0.97 | 0.97 | 3.0097 | 0.9744 | 3.0097 | 0.3237 | 1.0000 |
| Previous Design Volume Flow Rate [m3/s] | Algorithm Volume Flow Rate [m3/s] | Coincident Design Volume Flow Rate [m3/s] | Coincident Size Adjusted | Peak Sizing Period Name | Peak Day into Period {TIMESTAMP}[day] | Peak Hour Of Day {TIMESTAMP}[hr] | Peak Step Start Minute {TIMESTAMP}[min] | |
| None |
| Coil Type | HVAC Type | HVAC Name | Coil Final Gross Total Capacity [W] | Coil Final Gross Sensible Capacity [W] | Coil Final Reference Air Volume Flow Rate [m3/s] | Coil Final Reference Plant Fluid Volume Flow Rate [m3/s] | Coil U-value Times Area Value [W/K] | Design Day Name at Sensible Ideal Loads Peak | Date/Time at Sensible Ideal Loads Peak | Design Day Name at Air Flow Ideal Loads Peak | Date/Time at Air Flow Ideal Loads Peak | Coil Total Capacity at Ideal Loads Peak [W] | Coil Sensible Capacity at Ideal Loads Peak [W] | Coil Air Volume Flow Rate at Ideal Loads Peak [m3/s] | Coil Entering Air Drybulb at Ideal Loads Peak [C] | Coil Entering Air Wetbulb at Ideal Loads Peak [C] | Coil Entering Air Humidity Ratio at Ideal Loads Peak [kgWater/kgDryAir] | Coil Leaving Air Drybulb at Ideal Loads Peak [C] | Coil Leaving Air Wetbulb at Ideal Loads Peak [C] | Coil Leaving Air Humidity Ratio at Ideal Loads Peak [kgWater/kgDryAir] | Outdoor Air Drybulb at Ideal Loads Peak [C] | Outdoor Air Humidity Ratio at Ideal Loads Peak [kgWater/kgDryAir] | Outdoor Air Wetbulb at Ideal Loads Peak [C] | Outdoor Air Flow Percentage at Ideal Loads Peak [%] | Zone Air Drybulb at Ideal Loads Peak [C] | Zone Air Humidity Ratio at Ideal Loads Peak [kgWater/kgDryAir] | Zone Air Relative Humidity at Ideal Loads Peak [%] | Zone Sensible Heat Gain at Ideal Loads Peak [W] | Zone Latent Heat Gain at Ideal Loads Peak [W] | Coil Total Capacity at Rating Conditions [W] | Coil Sensible Capacity at Rating Conditions [W] | |
| SPACE1-1 ZONE COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | SPACE1-1 ATU | 5430.266 | 5430.266 | -999.0 | -999.0 | -999.000 | PITTSBURGH ALLEGHENY CO AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | PITTSBURGH ALLEGHENY CO AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 5430.27 | 5430.27 | 0.274149 | 18.00 | 14.20 | 0.00900000 | 35.00 | 15.93 | 0.00400000 | -15.40 | 0.00102482 | -15.40 | 0.0000 | 21.10 | 0.00393863 | 24.3467 | 4440.12 | 0.00 | -999.00 | -999.00 |
| SPACE2-1 ZONE COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | SPACE2-1 ATU | 2292.566 | 2292.566 | -999.0 | -999.0 | -999.000 | PITTSBURGH ALLEGHENY CO AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | PITTSBURGH ALLEGHENY CO AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 2292.57 | 2292.57 | 0.115741 | 18.00 | 14.20 | 0.00900000 | 35.00 | 15.93 | 0.00400000 | -15.40 | 0.00102482 | -15.40 | 0.0000 | 21.10 | 0.00393761 | 24.3404 | 1874.54 | 0.00 | -999.00 | -999.00 |
| SPACE3-1 ZONE COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | SPACE3-1 ATU | 5269.133 | 5269.133 | -999.0 | -999.0 | -999.000 | PITTSBURGH ALLEGHENY CO AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | PITTSBURGH ALLEGHENY CO AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 5269.13 | 5269.13 | 0.266014 | 18.00 | 14.20 | 0.00900000 | 35.00 | 15.93 | 0.00400000 | -15.40 | 0.00102482 | -15.40 | 0.0000 | 21.10 | 0.00393680 | 24.3354 | 4308.37 | 0.00 | -999.00 | -999.00 |
| SPACE4-1 ZONE COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | SPACE4-1 ATU | 2292.566 | 2292.566 | -999.0 | -999.0 | -999.000 | PITTSBURGH ALLEGHENY CO AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | PITTSBURGH ALLEGHENY CO AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 2292.57 | 2292.57 | 0.115741 | 18.00 | 14.20 | 0.00900000 | 35.00 | 15.93 | 0.00400000 | -15.40 | 0.00102482 | -15.40 | 0.0000 | 21.10 | 0.00393761 | 24.3404 | 1874.54 | 0.00 | -999.00 | -999.00 |
| SPACE5-1 ZONE COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | SPACE5-1 ATU | 4015.229 | 4015.229 | -999.0 | -999.0 | -999.000 | PITTSBURGH ALLEGHENY CO AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | PITTSBURGH ALLEGHENY CO AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 4015.23 | 4015.23 | 0.202710 | 18.00 | 14.20 | 0.00900000 | 35.00 | 15.93 | 0.00400000 | -15.40 | 0.00102482 | -15.40 | 0.0000 | 21.10 | 0.00385008 | 23.8027 | 3283.11 | 0.00 | -999.00 | -999.00 |
| MAIN COOLING COIL 1 | Coil:Cooling:DX:TwoSpeed | AirLoopHVAC | VAV SYS 1 | 57773.442 | 45586.264 | 3.009727 | -999.0 | -999.000 | PITTSBURGH ALLEGHENY CO AP ANN CLG .4% CONDNS DB=>MWB | 7/21 16:30:00 | PITTSBURGH ALLEGHENY CO AP ANN CLG .4% CONDNS DB=>MWB | 7/21 16:45:00 | 58205.63 | 48343.87 | 3.009727 | 25.26 | 17.67 | 0.01010317 | 11.27 | 11.27 | 0.00900000 | 29.50 | 0.01397505 | 21.78 | 15.9798 | 23.90 | 0.00941599 | 48.6778 | 18814.04 | 0.00 | 0.00 | 0.00 |
| MAIN HEATING COIL 1 | Coil:Heating:Electric | AirLoopHVAC | VAV SYS 1 | 9262.135 | 9262.135 | -999.0 | -999.0 | -999.000 | PITTSBURGH ALLEGHENY CO AP ANN HTG 99.6% CONDNS DB | 1/21 09:15:00 | PITTSBURGH ALLEGHENY CO AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 9262.13 | 9262.13 | 3.009727 | 15.34 | 7.41 | 0.00345691 | 18.00 | 14.20 | 0.00900000 | -15.40 | 0.00102482 | -15.40 | 15.9798 | 10.74 | 0.00244236 | 29.3618 | 6553.61 | 0.00 | -999.00 | -999.00 |
Report: Coil Sizing Details
For: Entire Facility
Timestamp: 2020-09-18 19:55:49
Coils| Coil Type | Coil Location | HVAC Type | HVAC Name | Zone Name(s) | System Sizing Method Concurrence | System Sizing Method Capacity | System Sizing Method Air Flow | Autosized Coil Capacity? | Autosized Coil Airflow? | Autosized Coil Water Flow? | OA Pretreated prior to coil inlet? | Coil Final Gross Total Capacity [W] | Coil Final Gross Sensible Capacity [W] | Coil Final Reference Air Volume Flow Rate [m3/s] | Coil Final Reference Plant Fluid Volume Flow Rate [m3/s] | Coil U-value Times Area Value [W/K] | Terminal Unit Reheat Coil Multiplier | DX Coil Capacity Increase Ratio from Too Low Flow/Capacity Ratio | DX Coil Capacity Decrease Ratio from Too High Flow/Capacity Ratio | Moist Air Heat Capacity [J/kg-K] | Dry Air Heat Capacity [J/kg-K] | Standard Air Density Adjusted for Elevation [kg/m3] | Supply Fan Name for Coil | Supply Fan Type for Coil | Supply Fan Maximum Air Volume Flow Rate [m3/s] | Supply Fan Maximum Air Mass Flow Rate [kg/s] | Plant Name for Coil | Plant Fluid Specific Heat Capacity [J/kg-K] | Plant Fluid Density [kg/m3] | Plant Maximum Fluid Mass Flow Rate [kg/s] | Plant Design Fluid Return Temperature [C] | Plant Design Fluid Supply Temperature [C] | Plant Design Fluid Temperature Difference [deltaC] | Plant Design Capacity [W] | Coil Capacity Percentage of Plant Design Capacity [%] | Coil Fluid Flow Rate Percentage of Plant Design Flow Rate [%] | Design Day Name at Sensible Ideal Loads Peak | Date/Time at Sensible Ideal Loads Peak | Design Day Name at Total Ideal Loads Peak | Date/Time at Total Ideal Loads Peak | Design Day Name at Air Flow Ideal Loads Peak | Date/Time at Air Flow Ideal Loads Peak | Peak Load Type to Size On | Coil Total Capacity at Ideal Loads Peak [W] | Coil Sensible Capacity at Ideal Loads Peak [W] | Coil Off-Rating Capacity Modifier at Ideal Loads Peak [ ] | Coil Air Mass Flow Rate at Ideal Loads Peak [kg/s] | Coil Air Volume Flow Rate at Ideal Loads Peak [m3/s] | Coil Entering Air Drybulb at Ideal Loads Peak [C] | Coil Entering Air Wetbulb at Ideal Loads Peak [C] | Coil Entering Air Humidity Ratio at Ideal Loads Peak [kgWater/kgDryAir] | Coil Entering Air Enthalpy at Ideal Loads Peak [J/KG-K] | Coil Leaving Air Drybulb at Ideal Loads Peak [C] | Coil Leaving Air Wetbulb at Ideal Loads Peak [C] | Coil Leaving Air Humidity Ratio at Ideal Loads Peak [kgWater/kgDryAir] | Coil Leaving Air Enthalpy at Ideal Loads Peak [J/KG-K] | Coil Plant Fluid Mass Flow Rate at Ideal Loads Peak [kg/s] | Coil Entering Plant Fluid Temperature at Ideal Loads Peak [C] | Coil Leaving Plant Fluid Temperature at Ideal Loads Peak [C] | Coil Plant Fluid Temperature Difference at Ideal Loads Peak [deltaC] | Supply Fan Air Heat Gain at Ideal Loads Peak [W] | Coil and Fan Net Total Capacity at Ideal Loads Peak [W] | Outdoor Air Drybulb at Ideal Loads Peak [C] | Outdoor Air Humidity Ratio at Ideal Loads Peak [kgWater/kgDryAir] | Outdoor Air Wetbulb at Ideal Loads Peak [C] | Outdoor Air Volume Flow Rate at Ideal Loads Peak [m3/s] | Outdoor Air Flow Percentage at Ideal Loads Peak [%] | System Return Air Drybulb at Ideal Loads Peak [C] | System Return Air Humidity Ratio at Ideal Loads Peak [kgWater/kgDryAir] | Zone Air Drybulb at Ideal Loads Peak [C] | Zone Air Humidity Ratio at Ideal Loads Peak [kgWater/kgDryAir] | Zone Air Relative Humidity at Ideal Loads Peak [%] | Zone Sensible Heat Gain at Ideal Loads Peak [W] | Zone Latent Heat Gain at Ideal Loads Peak [W] | Coil Total Capacity at Rating Conditions [W] | Coil Sensible Capacity at Rating Conditions [W] | Coil Air Mass Flow Rate at Rating Conditions [kg/s] | Coil Entering Air Drybulb at Rating Conditions [C] | Coil Entering Air Wetbulb at Rating Conditions [C] | Coil Entering Air Humidity Ratio at Rating Conditions [kgWater/kgDryAir] | Coil Entering Air Enthalpy at Rating Conditions [J/KG-K] | Coil Leaving Air Drybulb at Rating Conditions [C] | Coil Leaving Air Wetbulb at Rating Conditions [C] | Coil Leaving Air Humidity Ratio at Rating Conditions [kgWater/kgDryAir] | Coil Leaving Air Enthalpy at Rating Conditions [J/KG-K] | |
| SPACE1-1 ZONE COIL | Coil:Heating:Electric | Zone Equipment | ZONEHVAC:AIRDISTRIBUTIONUNIT | SPACE1-1 ATU | SPACE1-1 | N/A | N/A | N/A | Yes | No | unknown | No | 5430.266 | 5430.266 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1012.2758 | 1004.8586 | 1.1510 | unknown | unknown | -999.0 | -999.0 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | PITTSBURGH ALLEGHENY CO AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | unknown | unknown | PITTSBURGH ALLEGHENY CO AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | Sensible | 5430.27 | 5430.27 | 1.0000 | 0.31555372 | 0.274149 | 18.00 | 14.20 | 0.00900000 | 40896.7 | 35.00 | 15.93 | 0.00400000 | 45433.4 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 5430.27 | -15.40 | 0.00102482 | -15.40 | 0.00000000 | 0.0000 | 21.16 | 0.00393863 | 21.10 | 0.00393863 | 24.3467 | 4440.12 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | |
| SPACE2-1 ZONE COIL | Coil:Heating:Electric | Zone Equipment | ZONEHVAC:AIRDISTRIBUTIONUNIT | SPACE2-1 ATU | SPACE2-1 | N/A | N/A | N/A | Yes | No | unknown | No | 2292.566 | 2292.566 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1012.2758 | 1004.8586 | 1.1510 | unknown | unknown | -999.0 | -999.0 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | PITTSBURGH ALLEGHENY CO AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | unknown | unknown | PITTSBURGH ALLEGHENY CO AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | Sensible | 2292.57 | 2292.57 | 1.0000 | 0.13322143 | 0.115741 | 18.00 | 14.20 | 0.00900000 | 40896.7 | 35.00 | 15.93 | 0.00400000 | 45433.4 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 2292.57 | -15.40 | 0.00102482 | -15.40 | 0.00000000 | 0.0000 | 21.17 | 0.00393761 | 21.10 | 0.00393761 | 24.3404 | 1874.54 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | |
| SPACE3-1 ZONE COIL | Coil:Heating:Electric | Zone Equipment | ZONEHVAC:AIRDISTRIBUTIONUNIT | SPACE3-1 ATU | SPACE3-1 | N/A | N/A | N/A | Yes | No | unknown | No | 5269.133 | 5269.133 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1012.2758 | 1004.8586 | 1.1510 | unknown | unknown | -999.0 | -999.0 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | PITTSBURGH ALLEGHENY CO AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | unknown | unknown | PITTSBURGH ALLEGHENY CO AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | Sensible | 5269.13 | 5269.13 | 1.0000 | 0.30619029 | 0.266014 | 18.00 | 14.20 | 0.00900000 | 40896.7 | 35.00 | 15.93 | 0.00400000 | 45433.4 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 5269.13 | -15.40 | 0.00102482 | -15.40 | 0.00000000 | 0.0000 | 21.17 | 0.00393680 | 21.10 | 0.00393680 | 24.3354 | 4308.37 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | |
| SPACE4-1 ZONE COIL | Coil:Heating:Electric | Zone Equipment | ZONEHVAC:AIRDISTRIBUTIONUNIT | SPACE4-1 ATU | SPACE4-1 | N/A | N/A | N/A | Yes | No | unknown | No | 2292.566 | 2292.566 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1012.2758 | 1004.8586 | 1.1510 | unknown | unknown | -999.0 | -999.0 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | PITTSBURGH ALLEGHENY CO AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | unknown | unknown | PITTSBURGH ALLEGHENY CO AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | Sensible | 2292.57 | 2292.57 | 1.0000 | 0.13322143 | 0.115741 | 18.00 | 14.20 | 0.00900000 | 40896.7 | 35.00 | 15.93 | 0.00400000 | 45433.4 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 2292.57 | -15.40 | 0.00102482 | -15.40 | 0.00000000 | 0.0000 | 21.17 | 0.00393761 | 21.10 | 0.00393761 | 24.3404 | 1874.54 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | |
| SPACE5-1 ZONE COIL | Coil:Heating:Electric | Zone Equipment | ZONEHVAC:AIRDISTRIBUTIONUNIT | SPACE5-1 ATU | SPACE5-1 | N/A | N/A | N/A | Yes | No | unknown | No | 4015.229 | 4015.229 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1012.2758 | 1004.8586 | 1.1510 | unknown | unknown | -999.0 | -999.0 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | PITTSBURGH ALLEGHENY CO AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | unknown | unknown | PITTSBURGH ALLEGHENY CO AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | Sensible | 4015.23 | 4015.23 | 1.0000 | 0.23332569 | 0.202710 | 18.00 | 14.20 | 0.00900000 | 40896.7 | 35.00 | 15.93 | 0.00400000 | 45433.4 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 4015.23 | -15.40 | 0.00102482 | -15.40 | 0.00000000 | 0.0000 | 21.26 | 0.00385008 | 21.10 | 0.00385008 | 23.8027 | 3283.11 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | |
| MAIN COOLING COIL 1 | Coil:Cooling:DX:TwoSpeed | AirLoop | AirLoopHVAC | VAV SYS 1 | SPACE1-1; SPACE2-1; SPACE3-1; SPACE4-1; SPACE5-1; | Non-Coincident | CoolingDesignCapacity | N/A | Yes | Yes | unknown | No | 57773.442 | 45586.264 | 3.009727 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1023.6213 | 1004.8586 | 1.1510 | SUPPLY FAN 1 | Fan:VariableVolume | 3.009727 | 3.46429023 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | PITTSBURGH ALLEGHENY CO AP ANN CLG .4% CONDNS DB=>MWB | 7/21 16:30:00 | PITTSBURGH ALLEGHENY CO AP ANN CLG .4% CONDNS DB=>MWB | 7/21 16:30:00 | PITTSBURGH ALLEGHENY CO AP ANN CLG .4% CONDNS DB=>MWB | 7/21 16:45:00 | Sensible | 58205.63 | 48343.87 | 0.9926 | 3.46429023 | 3.009727 | 25.26 | 17.67 | 0.01010317 | 51120.2 | 11.27 | 11.27 | 0.00900000 | 34024.1 | -999.0 | -999.00 | -999.00 | -999.00 | 2579.766 | 55625.86 | 29.50 | 0.01397505 | 21.78 | 0.48094880 | 15.9798 | 24.45 | 0.00936677 | 23.90 | 0.00941599 | 48.6778 | 18814.04 | 0.00 | 0.00 | 0.00 | 3.32713382 | 26.67 | 19.44 | 0.01117891 | 55307.7 | 26.67 | 19.45 | 0.01117891 | 55307.7 | |
| MAIN HEATING COIL 1 | Coil:Heating:Electric | AirLoop | AirLoopHVAC | VAV SYS 1 | SPACE1-1; SPACE2-1; SPACE3-1; SPACE4-1; SPACE5-1; | Non-Coincident | HeatingDesignCapacity | N/A | Yes | No | unknown | No | 9262.135 | 9262.135 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1021.5706 | 1004.8586 | 1.1510 | SUPPLY FAN 1 | Fan:VariableVolume | 3.009727 | 3.46429023 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | PITTSBURGH ALLEGHENY CO AP ANN HTG 99.6% CONDNS DB | 1/21 09:15:00 | unknown | unknown | PITTSBURGH ALLEGHENY CO AP ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | Sensible | 9262.13 | 9262.13 | 1.0000 | 3.46429023 | 3.009727 | 15.34 | 7.41 | 0.00345691 | 24157.7 | 18.00 | 14.20 | 0.00900000 | 40896.7 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 9262.13 | -15.40 | 0.00102482 | -15.40 | 0.48094880 | 15.9798 | 21.19 | 0.00391947 | 10.74 | 0.00244236 | 29.3618 | 6553.61 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 |
Report: System Summary
For: Entire Facility
Timestamp: 2020-09-18 19:55:49
Economizer| High Limit Shutoff Control | Minimum Outdoor Air [m3/s] | Maximum Outdoor Air [m3/s] | Return Air Temp Limit | Return Air Enthalpy Limit | Outdoor Air Temperature Limit [C] | Outdoor Air Enthalpy Limit [C] | |
| OA CONTROLLER 1 | FixedDryBulb | 0.48 | 3.01 | - |
| Controller:MechanicalVentilation Name | Outdoor Air Per Person [m3/s-person] | Outdoor Air Per Area [m3/s-m2] | Outdoor Air Per Zone [m3/s] | Outdoor Air ACH [ach] | Outdoor Air Method | Outdoor Air Schedule Name | Air Distribution Effectiveness in Cooling Mode | Air Distribution Effectiveness in Heating Mode | Air Distribution Effectiveness Schedule Name | |
| None |
| Winter Clothes [hr] | Summer Clothes [hr] | Summer or Winter Clothes [hr] | |
| SPACE1-1 | 365.25 | 673.00 | 244.00 |
| SPACE2-1 | 293.25 | 658.25 | 164.50 |
| SPACE3-1 | 289.00 | 799.25 | 250.25 |
| SPACE4-1 | 304.75 | 747.25 | 241.00 |
| SPACE5-1 | 194.00 | 733.50 | 151.00 |
| PLENUM-1 | 0.00 | 0.00 | 0.00 |
| Facility | 492.50 | 825.25 | 289.25 |
| During Heating [hr] | During Cooling [hr] | During Occupied Heating [hr] | During Occupied Cooling [hr] | |
| SPACE1-1 | 588.25 | 97.75 | 182.75 | 97.75 |
| SPACE2-1 | 505.75 | 48.00 | 118.25 | 48.00 |
| SPACE3-1 | 595.50 | 28.25 | 192.25 | 28.25 |
| SPACE4-1 | 581.00 | 30.00 | 188.00 | 30.00 |
| SPACE5-1 | 384.00 | 70.50 | 111.25 | 70.50 |
| PLENUM-1 | 0.00 | 0.00 | 0.00 | 0.00 |
| Facility | 613.00 | 126.75 | 207.00 | 126.75 |
Report: Outdoor Air Summary
For: Entire Facility
Timestamp: 2020-09-18 19:55:49
Average Outdoor Air During Occupied Hours| Average Number of Occupants | Nominal Number of Occupants | Zone Volume [m3] | Mechanical Ventilation [ach] | Infiltration [ach] | AFN Infiltration [ach] | Simple Ventilation [ach] | |
| SPACE1-1 | 11.00 | 11.00 | 239.25 | 2.181 | 0.063 | 0.000 | 0.000 |
| SPACE2-1 | 5.00 | 5.00 | 103.31 | 2.775 | 0.063 | 0.000 | 0.000 |
| SPACE3-1 | 11.00 | 11.00 | 239.25 | 1.989 | 0.063 | 0.000 | 0.000 |
| SPACE4-1 | 5.00 | 5.00 | 103.31 | 2.588 | 0.063 | 0.000 | 0.000 |
| SPACE5-1 | 20.00 | 20.00 | 447.68 | 1.436 | 0.063 | 0.000 | 0.000 |
| Average Number of Occupants | Nominal Number of Occupants | Zone Volume [m3] | Mechanical Ventilation [ach] | Infiltration [ach] | AFN Infiltration [ach] | Simple Ventilation [ach] | |
| SPACE1-1 | 11.00 | 11.00 | 239.25 | 1.404 | 0.000 | 0.000 | 0.000 |
| SPACE2-1 | 5.00 | 5.00 | 103.31 | 1.510 | 0.000 | 0.000 | 0.000 |
| SPACE3-1 | 11.00 | 11.00 | 239.25 | 1.444 | 0.000 | 0.000 | 0.000 |
| SPACE4-1 | 5.00 | 5.00 | 103.31 | 1.501 | 0.000 | 0.000 | 0.000 |
| SPACE5-1 | 20.00 | 20.00 | 447.68 | 0.863 | 0.000 | 0.000 | 0.000 |
Report: Object Count Summary
For: Entire Facility
Timestamp: 2020-09-18 19:55:49
Surfaces by Class| Total | Outdoors | |
| Wall | 24 | 8 |
| Floor | 10 | 5 |
| Roof | 6 | 1 |
| Internal Mass | 0 | 0 |
| Building Detached Shading | 0 | 0 |
| Fixed Detached Shading | 0 | 0 |
| Window | 6 | 6 |
| Door | 0 | 0 |
| Glass Door | 2 | 2 |
| Shading | 4 | 4 |
| Overhang | 0 | 0 |
| Fin | 0 | 0 |
| Tubular Daylighting Device Dome | 0 | 0 |
| Tubular Daylighting Device Diffuser | 0 | 0 |
| Count | |
| HVAC Air Loops | 1 |
| Conditioned Zones | 6 |
| Unconditioned Zones | 0 |
| Supply Plenums | 0 |
| Return Plenums | 1 |
| Count | |
| IDF Objects | 0 |
| Defaulted Fields | 0 |
| Fields with Defaults | 0 |
| Autosized Fields | 0 |
| Autosizable Fields | 0 |
| Autocalculated Fields | 0 |
| Autocalculatable Fields | 0 |
Report: Energy Meters
For: Entire Facility
Timestamp: 2020-09-18 19:55:49
Annual and Peak Values - Electricity| Electricity Annual Value [GJ] | Electricity Minimum Value [W] | Timestamp of Minimum {TIMESTAMP} | Electricity Maximum Value [W] | Timestamp of Maximum {TIMESTAMP} | |
| Electricity:Facility | 61.95 | 656.37 | 01-JAN-01:30 | 24920.41 | 05-JAN-08:30 |
| Electricity:Building | 34.94 | 475.00 | 01-JAN-00:15 | 10000.00 | 01-JAN-08:15 |
| Electricity:Zone:SPACE1-1 | 7.38 | 100.32 | 01-JAN-00:15 | 2112.00 | 01-JAN-08:15 |
| InteriorLights:Electricity | 26.29 | 375.00 | 01-JAN-00:15 | 7500.00 | 01-JAN-08:15 |
| InteriorLights:Electricity:Zone:SPACE1-1 | 5.55 | 79.20 | 01-JAN-00:15 | 1584.00 | 01-JAN-08:15 |
| GeneralLights:InteriorLights:Electricity | 26.29 | 375.00 | 01-JAN-00:15 | 7500.00 | 01-JAN-08:15 |
| Electricity:Zone:SPACE2-1 | 3.19 | 43.32 | 01-JAN-00:15 | 912.00 | 01-JAN-08:15 |
| InteriorLights:Electricity:Zone:SPACE2-1 | 2.40 | 34.20 | 01-JAN-00:15 | 684.00 | 01-JAN-08:15 |
| Electricity:Zone:SPACE3-1 | 7.38 | 100.32 | 01-JAN-00:15 | 2112.00 | 01-JAN-08:15 |
| InteriorLights:Electricity:Zone:SPACE3-1 | 5.55 | 79.20 | 01-JAN-00:15 | 1584.00 | 01-JAN-08:15 |
| Electricity:Zone:SPACE4-1 | 3.19 | 43.32 | 01-JAN-00:15 | 912.00 | 01-JAN-08:15 |
| InteriorLights:Electricity:Zone:SPACE4-1 | 2.40 | 34.20 | 01-JAN-00:15 | 684.00 | 01-JAN-08:15 |
| Electricity:Zone:SPACE5-1 | 13.81 | 187.72 | 01-JAN-00:15 | 3952.00 | 01-JAN-08:15 |
| InteriorLights:Electricity:Zone:SPACE5-1 | 10.39 | 148.20 | 01-JAN-00:15 | 2964.00 | 01-JAN-08:15 |
| InteriorEquipment:Electricity | 8.65 | 100.00 | 01-JAN-00:15 | 2500.00 | 01-JAN-08:15 |
| InteriorEquipment:Electricity:Zone:SPACE1-1 | 1.83 | 21.12 | 01-JAN-00:15 | 528.00 | 01-JAN-08:15 |
| General:InteriorEquipment:Electricity | 8.65 | 100.00 | 01-JAN-00:15 | 2500.00 | 01-JAN-08:15 |
| InteriorEquipment:Electricity:Zone:SPACE2-1 | 0.79 | 9.12 | 01-JAN-00:15 | 228.00 | 01-JAN-08:15 |
| InteriorEquipment:Electricity:Zone:SPACE3-1 | 1.83 | 21.12 | 01-JAN-00:15 | 528.00 | 01-JAN-08:15 |
| InteriorEquipment:Electricity:Zone:SPACE4-1 | 0.79 | 9.12 | 01-JAN-00:15 | 228.00 | 01-JAN-08:15 |
| InteriorEquipment:Electricity:Zone:SPACE5-1 | 3.42 | 39.52 | 01-JAN-00:15 | 988.00 | 01-JAN-08:15 |
| ElectricityPurchased:Facility | 61.95 | 656.37 | 06-FEB-18:15 | 24920.41 | 05-JAN-08:30 |
| ElectricityPurchased:Plant | 61.95 | 656.37 | 06-FEB-18:15 | 24920.41 | 05-JAN-08:30 |
| Cogeneration:ElectricityPurchased | 61.95 | 656.37 | 06-FEB-18:15 | 24920.41 | 05-JAN-08:30 |
| General:Cogeneration:ElectricityPurchased | 61.95 | 656.37 | 06-FEB-18:15 | 24920.41 | 05-JAN-08:30 |
| ElectricitySurplusSold:Facility | 0.00 | 0.00 | 01-JAN-00:15 | 0.00 | 01-JAN-00:15 |
| ElectricitySurplusSold:Plant | 0.00 | 0.00 | 01-JAN-00:15 | 0.00 | 01-JAN-00:15 |
| Cogeneration:ElectricitySurplusSold | 0.00 | 0.00 | 01-JAN-00:15 | 0.00 | 01-JAN-00:15 |
| General:Cogeneration:ElectricitySurplusSold | 0.00 | 0.00 | 01-JAN-00:15 | 0.00 | 01-JAN-00:15 |
| ElectricityNet:Facility | 61.95 | 656.37 | 06-FEB-18:15 | 24920.41 | 05-JAN-08:30 |
| ElectricityNet:Plant | 61.95 | 656.37 | 06-FEB-18:15 | 24920.41 | 05-JAN-08:30 |
| Cogeneration:ElectricityNet | 61.95 | 656.37 | 06-FEB-18:15 | 24920.41 | 05-JAN-08:30 |
| General:Cogeneration:ElectricityNet | 61.95 | 656.37 | 06-FEB-18:15 | 24920.41 | 05-JAN-08:30 |
| Electricity:HVAC | 27.01 | 181.37 | 06-FEB-18:15 | 14920.41 | 05-JAN-08:30 |
| Heating:Electricity | 15.84 | 0.00 | 01-JAN-00:15 | 9451.16 | 01-JAN-08:15 |
| General:Heating:Electricity | 15.84 | 0.00 | 01-JAN-00:15 | 9451.16 | 01-JAN-08:15 |
| Fans:Electricity | 6.87 | 181.37 | 06-FEB-18:15 | 2577.20 | 08-MAR-17:00 |
| General:Fans:Electricity | 6.87 | 181.37 | 06-FEB-18:15 | 2577.20 | 08-MAR-17:00 |
| Cooling:Electricity | 4.30 | 0.00 | 01-JAN-00:30 | 3740.00 | 05-JAN-08:00 |
| General:Cooling:Electricity | 4.30 | 0.00 | 01-JAN-00:30 | 3740.00 | 05-JAN-08:00 |
| Gas Annual Value [GJ] | Gas Minimum Value [W] | Timestamp of Minimum {TIMESTAMP} | Gas Maximum Value [W] | Timestamp of Maximum {TIMESTAMP} | |
| None |
| Cooling Annual Value [GJ] | Cooling Minimum Value [W] | Timestamp of Minimum {TIMESTAMP} | Cooling Maximum Value [W] | Timestamp of Maximum {TIMESTAMP} | |
| None |
| Annual Value [m3] | Minimum Value [m3/s] | Timestamp of Minimum {TIMESTAMP} | Maximum Value [m3/s] | Timestamp of Maximum {TIMESTAMP} | |
| Water:Facility | 0.00 | 0.00 | 01-JAN-00:15 | 0.00 | 01-JAN-00:15 |
| Water:HVAC | 0.00 | 0.00 | 01-JAN-00:15 | 0.00 | 01-JAN-00:15 |
| Cooling:Water | 0.00 | 0.00 | 01-JAN-00:15 | 0.00 | 01-JAN-00:15 |
| General:Cooling:Water | 0.00 | 0.00 | 01-JAN-00:15 | 0.00 | 01-JAN-00:15 |
| MainsWater:Facility | 0.00 | 0.00 | 01-JAN-00:15 | 0.00 | 01-JAN-00:15 |
| MainsWater:HVAC | 0.00 | 0.00 | 01-JAN-00:15 | 0.00 | 01-JAN-00:15 |
| Cooling:MainsWater | 0.00 | 0.00 | 01-JAN-00:15 | 0.00 | 01-JAN-00:15 |
| General:Cooling:MainsWater | 0.00 | 0.00 | 01-JAN-00:15 | 0.00 | 01-JAN-00:15 |
| Annual Value [kg] | Minimum Value [kg/s] | Timestamp of Minimum {TIMESTAMP} | Maximum Value [kg/s] | Timestamp of Maximum {TIMESTAMP} | |
| Carbon Equivalent:Facility | 0.00 | 0.000 | 01-JAN-00:15 | 0.000 | 01-JAN-00:15 |
| CarbonEquivalentEmissions:Carbon Equivalent | 0.00 | 0.000 | 01-JAN-00:15 | 0.000 | 01-JAN-00:15 |
| Annual Value [m3] | Minimum Value [m3/s] | Timestamp of Minimum {TIMESTAMP} | Maximum Value [m3/s] | Timestamp of Maximum {TIMESTAMP} | |
| None |
| Annual Value [L] | Minimum Value [L] | Timestamp of Minimum {TIMESTAMP} | Maximum Value [L] | Timestamp of Maximum {TIMESTAMP} | |
| None |
| Annual Value [GJ] | Minimum Value [W] | Timestamp of Minimum {TIMESTAMP} | Maximum Value [W] | Timestamp of Maximum {TIMESTAMP} | |
| EnergyTransfer:Facility | 63.83 | 363.03 | 15-JAN-00:30 | 25342.68 | 05-JAN-10:00 |
| EnergyTransfer:Building | 48.31 | 350.40 | 09-MAR-06:45 | 20156.65 | 08-MAR-17:00 |
| EnergyTransfer:Zone:PLENUM-1 | 12.72 | 0.09 | 23-MAR-04:45 | 8036.13 | 31-MAR-08:30 |
| Heating:EnergyTransfer | 11.74 | 0.00 | 01-JAN-00:15 | 8522.01 | 08-MAR-08:30 |
| Heating:EnergyTransfer:Zone:PLENUM-1 | 10.73 | 0.00 | 01-JAN-00:15 | 8036.13 | 31-MAR-08:30 |
| General:Heating:EnergyTransfer | 11.74 | 0.00 | 01-JAN-00:15 | 8522.01 | 08-MAR-08:30 |
| Cooling:EnergyTransfer | 36.57 | 0.00 | 01-JAN-07:00 | 20008.10 | 08-MAR-17:00 |
| Cooling:EnergyTransfer:Zone:PLENUM-1 | 1.99 | 0.00 | 01-JAN-00:30 | 4263.20 | 08-MAR-18:00 |
| General:Cooling:EnergyTransfer | 36.57 | 0.00 | 01-JAN-07:00 | 20008.10 | 08-MAR-17:00 |
| EnergyTransfer:Zone:SPACE1-1 | 7.90 | 3.20 | 27-JAN-07:30 | 6844.92 | 17-FEB-15:00 |
| Heating:EnergyTransfer:Zone:SPACE1-1 | 0.31 | 0.00 | 01-JAN-00:15 | 1325.04 | 13-JAN-07:15 |
| Cooling:EnergyTransfer:Zone:SPACE1-1 | 7.60 | 0.00 | 01-JAN-07:00 | 6844.92 | 17-FEB-15:00 |
| EnergyTransfer:Zone:SPACE2-1 | 4.46 | 0.49 | 03-JAN-20:00 | 3837.84 | 08-MAR-08:45 |
| Heating:EnergyTransfer:Zone:SPACE2-1 | 0.10 | 0.00 | 01-JAN-00:15 | 582.77 | 13-JAN-07:15 |
| Cooling:EnergyTransfer:Zone:SPACE2-1 | 4.36 | 0.00 | 01-JAN-07:00 | 3837.84 | 08-MAR-08:45 |
| EnergyTransfer:Zone:SPACE3-1 | 6.33 | 1.71 | 27-JAN-07:30 | 3047.99 | 25-MAR-13:00 |
| Heating:EnergyTransfer:Zone:SPACE3-1 | 0.27 | 0.00 | 01-JAN-00:15 | 1299.59 | 13-JAN-07:15 |
| Cooling:EnergyTransfer:Zone:SPACE3-1 | 6.06 | 0.00 | 01-JAN-07:00 | 3047.99 | 25-MAR-13:00 |
| EnergyTransfer:Zone:SPACE4-1 | 3.55 | 0.52 | 03-JAN-20:00 | 3013.46 | 08-MAR-17:00 |
| Heating:EnergyTransfer:Zone:SPACE4-1 | 0.13 | 0.00 | 01-JAN-00:15 | 582.84 | 13-JAN-07:15 |
| Cooling:EnergyTransfer:Zone:SPACE4-1 | 3.42 | 0.00 | 01-JAN-07:00 | 3013.46 | 08-MAR-17:00 |
| EnergyTransfer:Zone:SPACE5-1 | 13.35 | 1.90 | 30-JAN-07:45 | 5220.21 | 17-FEB-15:00 |
| Heating:EnergyTransfer:Zone:SPACE5-1 | 0.20 | 0.00 | 01-JAN-00:15 | 2026.95 | 13-JAN-07:15 |
| Cooling:EnergyTransfer:Zone:SPACE5-1 | 13.15 | 0.00 | 01-JAN-07:00 | 5220.21 | 17-FEB-15:00 |
| EnergyTransfer:HVAC | 15.52 | 0.00 | 01-JAN-00:15 | 9262.13 | 03-JAN-08:30 |
| HeatingCoils:EnergyTransfer | 15.52 | 0.00 | 01-JAN-00:15 | 9262.13 | 03-JAN-08:30 |
| CoolingCoils:EnergyTransfer | 0.00 | 0.00 | 01-JAN-00:15 | 0.00 | 01-JAN-00:15 |
Report: Sensible Heat Gain Summary
For: Entire Facility
Timestamp: 2020-09-18 19:55:49
Annual Building Sensible Heat Gain Components| HVAC Zone Eq & Other Sensible Air Heating [GJ] | HVAC Zone Eq & Other Sensible Air Cooling [GJ] | HVAC Terminal Unit Sensible Air Heating [GJ] | HVAC Terminal Unit Sensible Air Cooling [GJ] | HVAC Input Heated Surface Heating [GJ] | HVAC Input Cooled Surface Cooling [GJ] | People Sensible Heat Addition [GJ] | Lights Sensible Heat Addition [GJ] | Equipment Sensible Heat Addition [GJ] | Window Heat Addition [GJ] | Interzone Air Transfer Heat Addition [GJ] | Infiltration Heat Addition [GJ] | Opaque Surface Conduction and Other Heat Addition [GJ] | Equipment Sensible Heat Removal [GJ] | Window Heat Removal [GJ] | Interzone Air Transfer Heat Removal [GJ] | Infiltration Heat Removal [GJ] | Opaque Surface Conduction and Other Heat Removal [GJ] | |
| SPACE1-1 | 0.000 | 0.000 | 0.307 | -7.595 | 0.000 | 0.000 | 2.802 | 5.552 | 1.827 | 4.089 | 0.000 | 0.000 | 0.000 | 0.000 | -5.747 | 0.000 | -0.544 | -0.691 |
| SPACE2-1 | 0.000 | 0.000 | 0.103 | -4.356 | 0.000 | 0.000 | 1.254 | 2.398 | 0.789 | 3.500 | 0.000 | 0.000 | 0.000 | 0.000 | -1.851 | 0.000 | -0.235 | -1.601 |
| SPACE3-1 | 0.000 | 0.000 | 0.266 | -6.063 | 0.000 | 0.000 | 2.867 | 5.552 | 1.827 | 0.815 | 0.000 | 0.000 | 0.807 | 0.000 | -5.534 | 0.000 | -0.537 | -0.001 |
| SPACE4-1 | 0.000 | 0.000 | 0.128 | -3.418 | 0.000 | 0.000 | 1.298 | 2.398 | 0.789 | 1.082 | 0.000 | 0.000 | 0.000 | 0.000 | -1.846 | 0.000 | -0.231 | -0.199 |
| SPACE5-1 | 0.000 | 0.000 | 0.201 | -13.147 | 0.000 | 0.000 | 4.991 | 10.390 | 3.418 | 0.000 | 0.000 | 0.000 | 0.001 | 0.000 | 0.000 | 0.000 | -1.053 | -4.801 |
| PLENUM-1 | 10.732 | -1.993 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | -8.739 |
| Total Facility | 10.732 | -1.993 | 1.006 | -34.580 | 0.000 | 0.000 | 13.212 | 26.290 | 8.649 | 9.486 | 0.000 | 0.000 | 0.809 | 0.000 | -14.978 | 0.000 | -2.600 | -16.031 |
| Time of Peak {TIMESTAMP} | HVAC Zone Eq & Other Sensible Air Heating [W] | HVAC Zone Eq & Other Sensible Air Cooling [W] | HVAC Terminal Unit Sensible Air Heating [W] | HVAC Terminal Unit Sensible Air Cooling [W] | HVAC Input Heated Surface Heating [W] | HVAC Input Cooled Surface Cooling [W] | People Sensible Heat Addition [W] | Lights Sensible Heat Addition [W] | Equipment Sensible Heat Addition [W] | Window Heat Addition [W] | Interzone Air Transfer Heat Addition [W] | Infiltration Heat Addition [W] | Opaque Surface Conduction and Other Heat Addition [W] | Equipment Sensible Heat Removal [W] | Window Heat Removal [W] | Interzone Air Transfer Heat Removal [W] | Infiltration Heat Removal [W] | Opaque Surface Conduction and Other Heat Removal [W] | |
| SPACE1-1 | 17-FEB-14:47 | 0.00 | 0.00 | 0.00 | -14222.69 | 0.00 | 0.00 | 625.59 | 1584.00 | 528.00 | 5811.87 | 0.00 | 0.00 | 5717.10 | 0.00 | -0.00 | 0.00 | -43.87 | 0.00 |
| SPACE2-1 | 31-MAR-09:03 | 0.00 | 0.00 | 0.00 | -5319.29 | 0.00 | 0.00 | 294.47 | 684.00 | 228.00 | 5057.18 | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | 0.00 | -9.02 | -935.33 |
| SPACE3-1 | 08-MAR-16:46 | 0.00 | 0.00 | 0.00 | -4705.23 | 0.00 | 0.00 | 241.81 | 1584.00 | 528.00 | 164.53 | 0.00 | 0.00 | 2223.62 | 0.00 | -0.00 | 0.00 | -36.73 | 0.00 |
| SPACE4-1 | 08-MAR-16:46 | 0.00 | 0.00 | 0.00 | -4420.32 | 0.00 | 0.00 | 63.31 | 684.00 | 228.00 | 2442.57 | 0.00 | 0.00 | 1020.47 | 0.00 | -0.00 | 0.00 | -18.04 | 0.00 |
| SPACE5-1 | 17-FEB-14:47 | 0.00 | 0.00 | 0.00 | -11296.38 | 0.00 | 0.00 | 1289.01 | 2964.00 | 988.00 | 0.00 | 0.00 | 0.00 | 6135.88 | 0.00 | -0.00 | 0.00 | -80.51 | 0.00 |
| PLENUM-1 | 18-MAR-19:02 | 0.00 | -4732.29 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 4732.29 | 0.00 | -0.00 | 0.00 | 0.00 | 0.00 |
| Total Facility | 17-FEB-14:47 | 0.00 | 2126.09 | 0.00 | -30103.44 | 0.00 | 0.00 | 3385.63 | 7500.00 | 2500.00 | 6336.04 | 0.00 | 0.00 | 8542.13 | 0.00 | -82.95 | 0.00 | -203.50 | 0.00 |
| Time of Peak {TIMESTAMP} | HVAC Zone Eq & Other Sensible Air Heating [W] | HVAC Zone Eq & Other Sensible Air Cooling [W] | HVAC Terminal Unit Sensible Air Heating [W] | HVAC Terminal Unit Sensible Air Cooling [W] | HVAC Input Heated Surface Heating [W] | HVAC Input Cooled Surface Cooling [W] | People Sensible Heat Addition [W] | Lights Sensible Heat Addition [W] | Equipment Sensible Heat Addition [W] | Window Heat Addition [W] | Interzone Air Transfer Heat Addition [W] | Infiltration Heat Addition [W] | Opaque Surface Conduction and Other Heat Addition [W] | Equipment Sensible Heat Removal [W] | Window Heat Removal [W] | Interzone Air Transfer Heat Removal [W] | Infiltration Heat Removal [W] | Opaque Surface Conduction and Other Heat Removal [W] | |
| SPACE1-1 | 09-MAR-08:02 | 0.00 | 0.00 | 1605.24 | -0.00 | 0.00 | 0.00 | 913.09 | 1584.00 | 528.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -27.12 | 0.00 | -24.07 | -4579.15 |
| SPACE2-1 | 13-JAN-07:05 | 0.00 | 0.00 | 598.93 | -0.00 | 0.00 | 0.00 | 0.00 | 34.20 | 9.12 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -165.27 | 0.00 | -9.90 | -467.08 |
| SPACE3-1 | 09-MAR-08:02 | 0.00 | 0.00 | 1452.63 | -0.00 | 0.00 | 0.00 | 901.31 | 1584.00 | 528.00 | 150.72 | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | 0.00 | -25.47 | -4591.20 |
| SPACE4-1 | 08-MAR-08:02 | 0.00 | 0.00 | 740.26 | -0.00 | 0.00 | 0.00 | 430.20 | 684.00 | 228.00 | 327.42 | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | 0.00 | -9.94 | -2399.93 |
| SPACE5-1 | 15-JAN-07:34 | 0.00 | 0.00 | 2233.37 | -0.00 | 0.00 | 0.00 | 0.00 | 148.20 | 39.52 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | 0.00 | -39.00 | -2382.09 |
| PLENUM-1 | 24-MAR-08:15 | 9299.43 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | 0.00 | 0.00 | -9299.43 |
| Total Facility | 15-MAR-08:15 | 7041.25 | 2049.37 | 341.57 | -2049.37 | 0.00 | 0.00 | 4583.04 | 7500.00 | 2500.00 | 5445.62 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -328.64 | -27082.85 |
Report: Standard 62.1 Summary
For: Entire Facility
Timestamp: 2020-09-18 19:55:49
System Ventilation Requirements for Cooling| Sum of Zone Primary Air Flow - Vpz-sum [m3/s] | System Population - Ps | Sum of Zone Population - Pz-sum | Occupant Diversity - D | Uncorrected Outdoor Air Intake Airflow - Vou [m3/s] | System Primary Airflow - Vps [m3/s] | Average Outdoor Air Fraction - Xs | System Ventilation Efficiency - Ev | Outdoor Air Intake Flow - Vot [m3/s] | Percent Outdoor Air - %OA | Environment Name of Peak System Population - Ps | Date and Time of Last Peak System Population - Ps | |
| VAV SYS 1 | 3.0097 | 0.0000 | 52.0000 | 1.0000 | 0.4809 | 3.0097 | 0.1598 | 1.0000 | 0.4809 | 0.1598 |
| Sum of Zone Primary Air Flow - Vpz-sum [m3/s] | System Population - Ps | Sum of Zone Population - Pz-sum | Occupant Diversity - D | Uncorrected Outdoor Air Intake Airflow - Vou [m3/s] | System Primary Airflow - Vps [m3/s] | Average Outdoor Air Fraction - Xs | System Ventilation Efficiency - Ev | Outdoor Air Intake Flow Vot [m3/s] | Percent Outdoor Air - %OA | Environment Name of Peak System Population - Ps | Date and Time of Last Peak System Population - Ps | |
| VAV SYS 1 | 0.3010 | 0.0000 | 52.0000 | 1.0000 | 0.4809 | 0.3010 | 1.0000 | 1.0000 | 0.4809 | 1.5980 |
| AirLoop Name | People Outdoor Air Rate - Rp [m3/s-person] | Zone Population - Pz | Area Outdoor Air Rate - Ra [m3/s-m2] | Zone Floor Area - Az [m2] | Breathing Zone Outdoor Airflow - Vbz [m3/s] | Cooling Zone Air Distribution Effectiveness - Ez-clg | Cooling Zone Outdoor Airflow - Voz-clg [m3/s] | Heating Zone Air Distribution Effectiveness - Ez-htg | Heating Zone Outdoor Airflow - Voz-htg [m3/s] | |
| SPACE1-1 | VAV SYS 1 | 0.004720 | 11.0000 | 0.000508 | 99.16 | 0.1023 | 1.0000 | 0.1023 | 1.000 | 0.1023 |
| SPACE2-1 | VAV SYS 1 | 0.004720 | 5.0000 | 0.000508 | 42.73 | 0.0453 | 1.0000 | 0.0453 | 1.000 | 0.0453 |
| SPACE3-1 | VAV SYS 1 | 0.004720 | 11.0000 | 0.000508 | 96.48 | 0.1009 | 1.0000 | 0.1009 | 1.000 | 0.1009 |
| SPACE4-1 | VAV SYS 1 | 0.004720 | 5.0000 | 0.000508 | 42.73 | 0.0453 | 1.0000 | 0.0453 | 1.000 | 0.0453 |
| SPACE5-1 | VAV SYS 1 | 0.004720 | 20.0000 | 0.000508 | 182.49 | 0.1871 | 1.0000 | 0.1871 | 1.000 | 0.1871 |
| People Outdoor Air Rate - Rp [m3/s-person] | Sum of Zone Population - Pz-sum | Area Outdoor Air Rate - Ra [m3/s-m2] | Sum of Zone Floor Area - Az-sum [m2] | Breathing Zone Outdoor Airflow - Vbz [m3/s] | Cooling Zone Outdoor Airflow - Voz-clg [m3/s] | Heating Zone Outdoor Airflow - Voz-htg [m3/s] | |
| VAV SYS 1 | 0.004720 | 52.00 | 0.000508 | 463.6000 | 0.4809 | 0.4809 | 0.4809 |
| AirLoop Name | Box Type | Zone Primary Airflow - Vpz [m3/s] | Zone Discharge Airflow - Vdz [m3/s] | Minimum Zone Primary Airflow - Vpz-min [m3/s] | Zone Outdoor Airflow Cooling - Voz-clg [m3/s] | Primary Outdoor Air Fraction - Zpz | Primary Air Fraction - Ep | Secondary Recirculation Fraction- Er | Supply Air Fraction- Fa | Mixed Air Fraction - Fb | Outdoor Air Fraction - Fc | Zone Ventilation Efficiency - Evz | |
| SPACE1-1 | VAV SYS 1 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.6146 | 0.6146 | 0.0615 | 0.1023 | 0.0000 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| SPACE2-1 | VAV SYS 1 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.4982 | 0.4982 | 0.0498 | 0.0453 | 0.0000 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| SPACE3-1 | VAV SYS 1 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.6596 | 0.6596 | 0.0660 | 0.1009 | 0.0000 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| SPACE4-1 | VAV SYS 1 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.5340 | 0.5340 | 0.0534 | 0.0453 | 0.0000 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| SPACE5-1 | VAV SYS 1 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.7033 | 0.7033 | 0.0703 | 0.1871 | 0.0000 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| Sum of Zone Primary Airflow - Vpz-sum [m3/s] | System Primary Airflow - Vps [m3/s] | Sum of Zone Discharge Airflow - Vdz-sum [m3/s] | Sum of Min Zone Primary Airflow - Vpz-min [m3/s] | Zone Outdoor Airflow Cooling - Voz-clg [m3/s] | Zone Ventilation Efficiency - Evz-min | |
| VAV SYS 1 | 3.0097 | 3.0097 | 3.0097 | 0.3010 | 0.4809 | 1.0000 |
| AirLoop Name | Box Type | Zone Primary Airflow - Vpz [m3/s] | Zone Discharge Airflow - Vdz [m3/s] | Minimum Zone Primary Airflow - Vpz-min [m3/s] | Zone Outdoor Airflow Heating - Voz-htg [m3/s] | Primary Outdoor Air Fraction - Zpz | Primary Air Fraction - Ep | Secondary Recirculation Fraction- Er | Supply Air Fraction- Fa | Mixed Air Fraction - Fb | Outdoor Air Fraction - Fc | Zone Ventilation Efficiency - Evz | |
| SPACE1-1 | VAV SYS 1 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.0615 | 0.0615 | 0.0615 | 0.1023 | 0.3731 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| SPACE2-1 | VAV SYS 1 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.0498 | 0.0498 | 0.0498 | 0.0453 | 0.3915 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| SPACE3-1 | VAV SYS 1 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.0660 | 0.0660 | 0.0660 | 0.1009 | 0.3794 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| SPACE4-1 | VAV SYS 1 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.0534 | 0.0534 | 0.0534 | 0.0453 | 0.3915 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| SPACE5-1 | VAV SYS 1 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.0703 | 0.0703 | 0.0703 | 0.1871 | 0.9230 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| Sum of Zone Primary Airflow - Vpz-sum [m3/s] | System Primary Airflow - Vps [m3/s] | Sum of Zone Discharge Airflow - Vdz-sum [m3/s] | Sum of Min Zone Primary Airflow - Vpz-min [m3/s] | Zone Outdoor Airflow Heating - Voz-htg [m3/s] | Zone Ventilation Efficiency - Evz-min | |
| VAV SYS 1 | 0.3010 | 0.3010 | 0.3010 | 0.3010 | 0.4809 | 1.0000 |
Report: LEED Summary
For: Entire Facility
Timestamp: 2020-09-18 19:55:49
Sec1.1A-General Information| Data | |
| Weather File | RUNPERIOD 1 ** Pittsburgh Allegheny Co Ap PA USA TMY3 WMO#=725205 |
| Total gross floor area [m2] | 927.20 |
| Principal Heating Source | Electricity |
| Space Area [m2] | Regularly Occupied Area [m2] | Unconditioned Area [m2] | Typical Hours/Week in Operation [hr/wk] | |
| SPACE1-1 | 99.16 | 99.16 | 0.00 | 70.00 |
| SPACE2-1 | 42.73 | 42.73 | 0.00 | 70.00 |
| SPACE3-1 | 96.48 | 96.48 | 0.00 | 70.00 |
| SPACE4-1 | 42.73 | 42.73 | 0.00 | 70.00 |
| SPACE5-1 | 182.49 | 182.49 | 0.00 | 70.00 |
| PLENUM-1 | 463.60 | 463.60 | 0.00 | 0.00 |
| Totals | 927.20 | 927.20 | 0.00 |
| Data | |
| Number of hours heating loads not met | 207.00 |
| Number of hours cooling loads not met | 126.75 |
| Number of hours not met | 333.50 |
| Utility Rate | Virtual Rate [$/unit energy] | Units of Energy | Units of Demand | |
| None |
| Electric Energy Use [GJ] | Electric Demand [W] | Natural Gas Energy Use [GJ] | Natural Gas Demand [W] | Gasoline Use [GJ] | Gasoline Demand [W] | Diesel Use [GJ] | Diesel Demand [W] | Coal Use [GJ] | Coal Demand [W] | Fuel Oil No 1 Use [GJ] | Fuel Oil No 1 Demand [W] | Fuel Oil No 2 Use [GJ] | Fuel Oil No 2 Demand [W] | Propane Use [GJ] | Propane Demand [W] | Other Fuel 1 Use [GJ] | Other Fuel 1 Demand [W] | Other Fuel 2 Use [GJ] | Other Fuel 2 Demand [W] | District Cooling Use [GJ] | District Cooling Demand [W] | District Heating Use [GJ] | District Heating Demand [W] | |
| Heating -- General | 15.84 | 9451.16 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling -- General | 4.30 | 3740.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting -- GeneralLights | 26.29 | 7500.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting -- Not Subdivided | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment -- General | 8.65 | 2500.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment -- Not Subdivided | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans -- General | 6.87 | 2577.20 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps -- Not Subdivided | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection -- Not Subdivided | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification -- Not Subdivided | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery -- Not Subdivided | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems -- Not Subdivided | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration -- Not Subdivided | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators -- General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Process Subtotal [GJ] | Total Energy Use [GJ] | |
| Electricity | 8.65 | 61.95 |
| Natural Gas | 0.00 | 0.00 |
| Additional | 0.00 | 0.00 |
| Total | 8.65 | 61.95 |
| Process Subtotal [$] | Total Energy Cost [$] | |
| Electricity | 0.00 | |
| Natural Gas | 0.00 | |
| Additional | 0.00 | |
| Total | 0.00 |
| Rated Capacity [kW] | Annual Energy Generated [GJ] | |
| Photovoltaic | 0.00 | 0.00 |
| Wind | 0.00 | 0.00 |
| Electricty [MJ/m2] | |
| Interior Lighting (All) | 28.35 |
| Space Heating | 17.09 |
| Space Cooling | 4.63 |
| Fans (All) | 7.41 |
| Service Water Heating | 0.00 |
| Receptacle Equipment | 9.33 |
| Miscellaneous (All) | 66.82 |
| Subtotal | 66.82 |
| Natural Gas [MJ/m2] | |
| Space Heating | 0.00 |
| Service Water Heating | 0.00 |
| Miscellaneous (All) | 0.00 |
| Subtotal | 0.00 |
| Additional [MJ/m2] | |
| Subtotal | 0.00 |
| Miscellaneous | 0.00 |
| Percent [%] | |
| Interior Lighting (All) | 42.44 |
| Space Heating | 25.57 |
| Space Cooling | 6.94 |
| Fans (All) | 11.10 |
| Service Water Heating | 0.00 |
| Receptacle Equipment | 13.96 |
| Miscellaneous | -0.00 |
| Equivalent Full Load Hours of Operation Per Year [hr] | Hours > 1% [hr] | |
| OCCUPY-1 | 3650. | 3650. |
| LIGHTS-1 | 3905. | 8760. |
| EQUIP-1 | 1927. | 8760. |
| INFIL-SCH | 3624. | 3624. |
| SHADETRANSSCH | 0. | 0. |
| WORKEFFSCH | 0. | 0. |
| MIN OA SCHED | 8760. | 8760. |
| FANAVAILSCHED | 8760. | 8760. |
| COOLINGCOILAVAILSCHED | 0. | 0. |
| HEATINGCOILAVAILSCHED | 8760. | 8760. |
| REHEATCOILAVAILSCHED | 0. | 0. |
| TERMINALUNITAVAILSCHED | 8760. | 8760. |
| First Object Used | Month Assumed | 11am First Wednesday [C] | Days with Same 11am Value | 11pm First Wednesday [C] | Days with Same 11pm Value | |
| HTG-SETP-SCH | HEATINGSETPOINT | January | 21.10 | 365 | 12.80 | 365 |
| PLENUMHTG-SETP-SCH | PLENUMHEATINGSETPOINT | January | 12.80 | 365 | 12.80 | 365 |
| CLG-SETP-SCH | COOLINGSETPOINT | July | 23.90 | 365 | 40.00 | 365 |
| PLENUMCLG-SETP-SCH | PLENUMCOOLINGSETPOINT | July | 40.00 | 365 | 40.00 | 365 |