Program Version:EnergyPlus, Version 8.7.0-78a111df4a, YMD=2018.02.13 16:27
Tabular Output Report in Format: HTML
Building: Ref Bldg Medium Office New2004_v1.3_5.0
Environment: ANNUAL ** Chicago Ohare Intl Ap IL USA TMY3 WMO#=725300
Simulation Timestamp: 2018-02-13 16:27:46
Report: Annual Building Utility Performance Summary
For: Entire Facility
Timestamp: 2018-02-13 16:27:46
Values gathered over 8760.00 hours| Total Energy [GJ] | Energy Per Total Building Area [MJ/m2] | Energy Per Conditioned Building Area [MJ/m2] | |
| Total Site Energy | 2707.79 | 543.49 | 543.49 |
| Net Site Energy | 2707.79 | 543.49 | 543.49 |
| Total Source Energy | 9216.17 | 1849.82 | 1849.82 |
| Net Source Energy | 9216.17 | 1849.82 | 1849.82 |
| Site=>Source Conversion Factor | |
| Electricity | 3.546 |
| Natural Gas | 1.092 |
| District Cooling | 0.848 |
| District Heating | 1.647 |
| Steam | 0.585 |
| Gasoline | 1.050 |
| Diesel | 1.050 |
| Coal | 1.050 |
| Fuel Oil #1 | 1.050 |
| Fuel Oil #2 | 1.050 |
| Propane | 1.050 |
| Other Fuel 1 | 1.000 |
| Other Fuel 2 | 1.000 |
| Area [m2] | |
| Total Building Area | 4982.19 |
| Net Conditioned Building Area | 4982.19 |
| Unconditioned Building Area | 0.00 |
| Electricity [GJ] | Natural Gas [GJ] | Additional Fuel [GJ] | District Cooling [GJ] | District Heating [GJ] | Water [m3] | |
| Heating | 249.37 | 121.05 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | 317.08 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 606.24 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 232.57 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 1066.52 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 78.60 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 0.27 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 36.11 | 0.00 | 0.00 | 0.00 | 174.59 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total End Uses | 2550.63 | 157.16 | 0.00 | 0.00 | 0.00 | 174.59 |
| Subcategory | Electricity [GJ] | Natural Gas [GJ] | Additional Fuel [GJ] | District Cooling [GJ] | District Heating [GJ] | Water [m3] | |
| Heating | General | 249.37 | 121.05 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | General | 317.08 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | General | 606.24 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | Exterior Facade Lighting | 232.57 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | Elevators | 164.75 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| General | 901.77 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Exterior Equipment | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | Fan Energy | 78.60 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | General | 0.27 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | Water Heater | 0.00 | 36.11 | 0.00 | 0.00 | 0.00 | 0.00 |
| General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 174.59 | |
| Refrigeration | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Electricity Intensity [MJ/m2] | Natural Gas Intensity [MJ/m2] | Additional Fuel Intensity [MJ/m2] | District Cooling Intensity [MJ/m2] | District Heating Intensity [MJ/m2] | Water Intensity [m3/m2] | |
| Lighting | 168.36 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| HVAC | 129.52 | 31.54 | 0.00 | 0.00 | 0.00 | 0.04 |
| Other | 214.07 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total | 511.95 | 31.54 | 0.00 | 0.00 | 0.00 | 0.04 |
| Electricity Intensity [MJ/m2] | Natural Gas Intensity [MJ/m2] | Additional Fuel Intensity [MJ/m2] | District Cooling Intensity [MJ/m2] | District Heating Intensity [MJ/m2] | Water Intensity [m3/m2] | |
| Lighting | 168.36 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| HVAC | 129.52 | 31.54 | 0.00 | 0.00 | 0.00 | 0.04 |
| Other | 214.07 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total | 511.95 | 31.54 | 0.00 | 0.00 | 0.00 | 0.04 |
| Electricity [GJ] | Percent Electricity [%] | |
| Fuel-Fired Power Generation | 0.000 | 0.00 |
| High Temperature Geothermal* | 0.000 | 0.00 |
| Photovoltaic Power | 0.000 | 0.00 |
| Wind Power | 0.000 | 0.00 |
| Power Conversion | 0.000 | 0.00 |
| Net Decrease in On-Site Storage | 0.000 | 0.00 |
| Total On-Site Electric Sources | 0.000 | 0.00 |
| Electricity Coming From Utility | 2550.635 | 100.00 |
| Surplus Electricity Going To Utility | 0.000 | 0.00 |
| Net Electricity From Utility | 2550.635 | 100.00 |
| Total On-Site and Utility Electric Sources | 2550.635 | 100.00 |
| Total Electricity End Uses | 2550.635 | 100.00 |
| Heat [GJ] | Percent Heat [%] | |
| Water-Side Heat Recovery | 0.00 | |
| Air to Air Heat Recovery for Cooling | 0.00 | |
| Air to Air Heat Recovery for Heating | 0.00 | |
| High-Temperature Geothermal* | 0.00 | |
| Solar Water Thermal | 0.00 | |
| Solar Air Thermal | 0.00 | |
| Total On-Site Thermal Sources | 0.00 |
| Water [m3] | Percent Water [%] | |
| Rainwater Collection | 0.00 | 0.00 |
| Condensate Collection | 0.00 | 0.00 |
| Groundwater Well | 0.00 | 0.00 |
| Total On Site Water Sources | 0.00 | 0.00 |
| - | - | - |
| Initial Storage | 0.00 | 0.00 |
| Final Storage | 0.00 | 0.00 |
| Change in Storage | 0.00 | 0.00 |
| - | - | - |
| Water Supplied by Utility | 174.59 | 100.00 |
| - | - | - |
| Total On Site, Change in Storage, and Utility Water Sources | 174.59 | 100.00 |
| Total Water End Uses | 174.59 | 100.00 |
| Degrees [deltaC] | |
| Tolerance for Zone Heating Setpoint Not Met Time | 0.56 |
| Tolerance for Zone Cooling Setpoint Not Met Time | 0.56 |
| Facility [Hours] | |
| Time Setpoint Not Met During Occupied Heating | 9.67 |
| Time Setpoint Not Met During Occupied Cooling | 0.17 |
| Time Not Comfortable Based on Simple ASHRAE 55-2004 | 1493.33 |
Table of Contents
TopCOMPONENTS OF PEAK ELECTRICAL DEMAND
| Meter |COOLING PART LOAD PERFORMANCE
| VAV_1_COOLC DXCOIL | VAV_2_COOLC DXCOIL | VAV_3_COOLC DXCOIL |EMISSIONS DATA SUMMARY
| Meter |FAN PART LOAD PERFORMANCE
| VAV_1_FAN | VAV_2_FAN | VAV_3_FAN |HEATING PART LOAD PERFORMANCE
| VAV_1_HEATC | VAV_2_HEATC | VAV_3_HEATC |ZONE AIR RELATIVE HUMIDITY
| CORE_BOTTOM | CORE_MID | CORE_TOP | FIRSTFLOOR_PLENUM | MIDFLOOR_PLENUM | PERIMETER_BOT_ZN_1 | PERIMETER_BOT_ZN_2 | PERIMETER_BOT_ZN_3 | PERIMETER_BOT_ZN_4 | PERIMETER_MID_ZN_1 | PERIMETER_MID_ZN_2 | PERIMETER_MID_ZN_3 | PERIMETER_MID_ZN_4 | PERIMETER_TOP_ZN_1 | PERIMETER_TOP_ZN_2 | PERIMETER_TOP_ZN_3 | PERIMETER_TOP_ZN_4 | TOPFLOOR_PLENUM |AVAILABILITY MANAGER NIGHT CYCLE CONTROL STATUS
| VAV_1 AVAILABILITY MANAGER | VAV_2 AVAILABILITY MANAGER | VAV_3 AVAILABILITY MANAGER |AIR SYSTEM OUTDOOR AIR FLOW FRACTION
| VAV_1 | VAV_2 | VAV_3 |Zone Component Load Summary
| CORE_BOTTOM | CORE_MID | CORE_TOP | PERIMETER_BOT_ZN_1 | PERIMETER_BOT_ZN_2 | PERIMETER_BOT_ZN_3 | PERIMETER_BOT_ZN_4 | PERIMETER_MID_ZN_1 | PERIMETER_MID_ZN_2 | PERIMETER_MID_ZN_3 | PERIMETER_MID_ZN_4 | PERIMETER_TOP_ZN_1 | PERIMETER_TOP_ZN_2 | PERIMETER_TOP_ZN_3 | PERIMETER_TOP_ZN_4 |Report: Input Verification and Results Summary
For: Entire Facility
Timestamp: 2018-02-13 16:27:46
General| Value | |
| Program Version and Build | EnergyPlus, Version 8.7.0-78a111df4a, YMD=2018.02.13 16:27 |
| RunPeriod | ANNUAL |
| Weather File | Chicago Ohare Intl Ap IL USA TMY3 WMO#=725300 |
| Latitude [deg] | 41.98 |
| Longitude [deg] | -87.9 |
| Elevation [m] | 201.00 |
| Time Zone | -6.0 |
| North Axis Angle [deg] | 0.00 |
| Rotation for Appendix G [deg] | 0.00 |
| Hours Simulated [hrs] | 8760.00 |
| Total | North (315 to 45 deg) | East (45 to 135 deg) | South (135 to 225 deg) | West (225 to 315 deg) | |
| Gross Wall Area [m2] | 1977.67 | 593.30 | 395.53 | 593.30 | 395.53 |
| Above Ground Wall Area [m2] | 1977.67 | 593.30 | 395.53 | 593.30 | 395.53 |
| Window Opening Area [m2] | 652.83 | 195.85 | 130.57 | 195.85 | 130.57 |
| Gross Window-Wall Ratio [%] | 33.01 | 33.01 | 33.01 | 33.01 | 33.01 |
| Above Ground Window-Wall Ratio [%] | 33.01 | 33.01 | 33.01 | 33.01 | 33.01 |
| Total | North (315 to 45 deg) | East (45 to 135 deg) | South (135 to 225 deg) | West (225 to 315 deg) | |
| Gross Wall Area [m2] | 1977.67 | 593.30 | 395.53 | 593.30 | 395.53 |
| Above Ground Wall Area [m2] | 1977.67 | 593.30 | 395.53 | 593.30 | 395.53 |
| Window Opening Area [m2] | 652.83 | 195.85 | 130.57 | 195.85 | 130.57 |
| Gross Window-Wall Ratio [%] | 33.01 | 33.01 | 33.01 | 33.01 | 33.01 |
| Above Ground Window-Wall Ratio [%] | 33.01 | 33.01 | 33.01 | 33.01 | 33.01 |
| Total | |
| Gross Roof Area [m2] | 1660.73 |
| Skylight Area [m2] | 0.00 |
| Skylight-Roof Ratio [%] | 0.00 |
| Area [m2] | Conditioned (Y/N) | Part of Total Floor Area (Y/N) | Volume [m3] | Multipliers | Above Ground Gross Wall Area [m2] | Underground Gross Wall Area [m2] | Window Glass Area [m2] | Opening Area [m2] | Lighting [W/m2] | People [m2 per person] | Plug and Process [W/m2] | |
| CORE_BOTTOM | 983.54 | Yes | Yes | 2698.04 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 10.7600 | 18.58 | 43.4074 |
| CORE_MID | 983.54 | Yes | Yes | 2698.04 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 10.7600 | 18.58 | 10.7600 |
| CORE_TOP | 983.54 | Yes | Yes | 2698.04 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 10.7600 | 18.58 | 10.7600 |
| FIRSTFLOOR_PLENUM | 1660.73 | Yes | No | 2024.76 | 1.00 | 202.84 | 0.00 | 0.00 | 0.00 | |||
| MIDFLOOR_PLENUM | 1660.73 | Yes | No | 2024.76 | 1.00 | 202.84 | 0.00 | 0.00 | 0.00 | |||
| PERIMETER_BOT_ZN_1 | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 10.7600 | 18.58 | 10.7600 |
| PERIMETER_BOT_ZN_2 | 131.26 | Yes | Yes | 360.08 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 10.7600 | 18.58 | 10.7600 |
| PERIMETER_BOT_ZN_3 | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 10.7600 | 18.58 | 10.7600 |
| PERIMETER_BOT_ZN_4 | 131.25 | Yes | Yes | 360.05 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 10.7600 | 18.58 | 10.7600 |
| PERIMETER_MID_ZN_1 | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 10.7600 | 18.58 | 10.7600 |
| PERIMETER_MID_ZN_2 | 131.26 | Yes | Yes | 360.08 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 10.7600 | 18.58 | 10.7600 |
| PERIMETER_MID_ZN_3 | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 10.7600 | 18.58 | 10.7600 |
| PERIMETER_MID_ZN_4 | 131.25 | Yes | Yes | 360.05 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 10.7600 | 18.58 | 10.7600 |
| PERIMETER_TOP_ZN_1 | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 10.7600 | 18.58 | 10.7600 |
| PERIMETER_TOP_ZN_2 | 131.26 | Yes | Yes | 360.08 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 10.7600 | 18.58 | 10.7600 |
| PERIMETER_TOP_ZN_3 | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 10.7600 | 18.58 | 10.7600 |
| PERIMETER_TOP_ZN_4 | 131.25 | Yes | Yes | 360.05 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 10.7600 | 18.58 | 10.7600 |
| TOPFLOOR_PLENUM | 1660.73 | Yes | No | 2024.76 | 1.00 | 202.84 | 0.00 | 0.00 | 0.00 | |||
| Total | 4982.19 | 13667.13 | 1369.16 | 0.00 | 652.83 | 652.83 | 10.7600 | 18.58 | 17.2049 | |||
| Conditioned Total | 4982.19 | 13667.13 | 1369.16 | 0.00 | 652.83 | 652.83 | 10.7600 | 18.58 | 17.2049 | |||
| Unconditioned Total | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | ||||||
| Not Part of Total | 9964.37 | 12148.56 | 1217.03 | 0.00 | 0.00 | 0.00 | 0.0000 | 0.0000 |
Report: Demand End Use Components Summary
For: Entire Facility
Timestamp: 2018-02-13 16:27:46
End Uses| Electricity [W] | Natural Gas [W] | Propane [W] | District Cooling [W] | Steam [W] | Water [m3/s] | |
| Time of Peak | 02-JAN-06:19 | 07-JAN-07:19 | - | - | - | 05-JAN-12:39 |
| Heating | 264838.71 | 134026.18 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 5360.83 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 14804.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 21443.33 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 3839.19 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 8.44 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 6519.86 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total End Uses | 310294.50 | 140546.04 | 0.00 | 0.00 | 0.00 | 0.00 |
| Subcategory | Electricity [W] | Natural Gas [W] | Propane [W] | District Cooling [W] | Steam [W] | Water [m3/s] | |
| Heating | General | 264838.71 | 134026.18 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | General | 5360.83 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | Exterior Facade Lighting | 14804.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | Elevators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| General | 21443.33 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Exterior Equipment | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | Fan Energy | 3839.19 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | General | 8.44 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | Water Heater | 0.00 | 6519.86 | 0.00 | 0.00 | 0.00 | 0.00 |
| General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Refrigeration | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
Report: Source Energy End Use Components Summary
For: Entire Facility
Timestamp: 2018-02-13 16:27:46
Values gathered over 8760.00 hours| Source Electricity [GJ] | Source Natural Gas [GJ] | Source Additional Fuel [GJ] | Source District Cooling [GJ] | Source District Heating [GJ] | |
| Heating | 884.25 | 132.18 | 0.00 | 0.00 | 0.00 |
| Cooling | 1124.36 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 2149.72 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 824.69 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 3781.89 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 278.70 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 0.94 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 39.43 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total Source Energy End Use Components | 9044.55 | 171.62 | 0.00 | 0.00 | 0.00 |
| Source Electricity [MJ/m2] | Source Natural Gas [MJ/m2] | Source Additional Fuel [MJ/m2] | Source District Cooling [MJ/m2] | Source District Heating [MJ/m2] | |
| Heating | 177.48 | 26.53 | 0.00 | 0.00 | 0.00 |
| Cooling | 225.68 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 431.48 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 165.53 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 759.08 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 55.94 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 0.19 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 7.91 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total Source Energy End Use Components | 1815.38 | 34.45 | 0.00 | 0.00 | 0.00 |
| Source Electricity [MJ/m2] | Source Natural Gas [MJ/m2] | Source Additional Fuel [MJ/m2] | Source District Cooling [MJ/m2] | Source District Heating [MJ/m2] | |
| Heating | 177.48 | 26.53 | 0.00 | 0.00 | 0.00 |
| Cooling | 225.68 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 431.48 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 165.53 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 759.08 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 55.94 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 0.19 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 7.91 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total Source Energy End Use Components | 1815.38 | 34.45 | 0.00 | 0.00 | 0.00 |
Report: Climatic Data Summary
For: Entire Facility
Timestamp: 2018-02-13 16:27:46
SizingPeriod:DesignDay| Maximum Dry Bulb [C] | Daily Temperature Range [deltaC] | Humidity Value | Humidity Type | Wind Speed [m/s] | Wind Direction | |
| CHICAGO ANN CLG .4% CONDNS WB=>MDB | 31.20 | 10.70 | 25.50 | Wetbulb [C] | 5.30 | 230.00 |
| CHICAGO ANN HTG 99.6% CONDNS DB | -20.60 | 0.00 | -20.60 | Wetbulb [C] | 4.90 | 270.00 |
| Value | |
| None |
Report: Envelope Summary
For: Entire Facility
Timestamp: 2018-02-13 16:27:46
Opaque Exterior| Construction | Reflectance | U-Factor with Film [W/m2-K] | U-Factor no Film [W/m2-K] | Gross Area [m2] | Net Area [m2] | Azimuth [deg] | Tilt [deg] | Cardinal Direction | |
| CORE_BOT_ZN_5_FLOOR | PROJECT SLAB ON GRADE FLOOR | 0.30 | 0.503 | 0.548 | 983.54 | 983.54 | 0.00 | 180.00 | |
| PERIMETER_BOT_PLENUM_WALL_EAST | STEEL-FRAMED_R-13 + R-15.6 CI_EXT-WALL | 0.30 | 0.240 | 0.249 | 40.57 | 40.57 | 90.00 | 90.00 | E |
| PERIMETER_BOT_PLENUM_WALL_NORTH | STEEL-FRAMED_R-13 + R-15.6 CI_EXT-WALL | 0.30 | 0.240 | 0.249 | 60.85 | 60.85 | 0.00 | 90.00 | N |
| PERIMETER_BOT_PLENUM_WALL_SOUTH | STEEL-FRAMED_R-13 + R-15.6 CI_EXT-WALL | 0.30 | 0.240 | 0.249 | 60.85 | 60.85 | 180.00 | 90.00 | S |
| PERIMETER_BOT_PLENUM_WALL_WEST | STEEL-FRAMED_R-13 + R-15.6 CI_EXT-WALL | 0.30 | 0.240 | 0.249 | 40.57 | 40.57 | 270.00 | 90.00 | W |
| PERIMETER_MID_PLENUM_WALL_EAST | STEEL-FRAMED_R-13 + R-15.6 CI_EXT-WALL | 0.30 | 0.240 | 0.249 | 40.57 | 40.57 | 90.00 | 90.00 | E |
| PERIMETER_MID_PLENUM_WALL_NORTH | STEEL-FRAMED_R-13 + R-15.6 CI_EXT-WALL | 0.30 | 0.240 | 0.249 | 60.85 | 60.85 | 0.00 | 90.00 | N |
| PERIMETER_MID_PLENUM_WALL_SOUTH | STEEL-FRAMED_R-13 + R-15.6 CI_EXT-WALL | 0.30 | 0.240 | 0.249 | 60.85 | 60.85 | 180.00 | 90.00 | S |
| PERIMETER_MID_PLENUM_WALL_WEST | STEEL-FRAMED_R-13 + R-15.6 CI_EXT-WALL | 0.30 | 0.240 | 0.249 | 40.57 | 40.57 | 270.00 | 90.00 | W |
| PERIMETER_BOT_ZN_1_WALL_SOUTH | STEEL-FRAMED_R-13 + R-15.6 CI_EXT-WALL | 0.30 | 0.240 | 0.249 | 136.92 | 71.63 | 180.00 | 90.00 | S |
| PERIMETER_BOT_ZN_1_FLOOR | PROJECT SLAB ON GRADE FLOOR | 0.30 | 0.503 | 0.548 | 207.34 | 207.34 | 180.00 | 180.00 | |
| PERIMETER_BOT_ZN_2_WALL_EAST | STEEL-FRAMED_R-13 + R-15.6 CI_EXT-WALL | 0.30 | 0.240 | 0.249 | 91.28 | 47.75 | 90.00 | 90.00 | E |
| PERIMETER_BOT_ZN_2_FLOOR | PROJECT SLAB ON GRADE FLOOR | 0.30 | 0.503 | 0.548 | 131.26 | 131.26 | 90.00 | 180.00 | |
| PERIMETER_BOT_ZN_3_WALL_NORTH | STEEL-FRAMED_R-13 + R-15.6 CI_EXT-WALL | 0.30 | 0.240 | 0.249 | 136.92 | 71.63 | 0.00 | 90.00 | N |
| PERIMETER_BOT_ZN_3_FLOOR | PROJECT SLAB ON GRADE FLOOR | 0.30 | 0.503 | 0.548 | 207.34 | 207.34 | 0.00 | 180.00 | |
| PERIMETER_BOT_ZN_4_WALL_WEST | STEEL-FRAMED_R-13 + R-15.6 CI_EXT-WALL | 0.30 | 0.240 | 0.249 | 91.28 | 47.75 | 270.00 | 90.00 | W |
| PERIMETER_BOT_ZN_4_FLOOR | PROJECT SLAB ON GRADE FLOOR | 0.30 | 0.503 | 0.548 | 131.25 | 131.25 | 270.00 | 180.00 | |
| PERIMETER_MID_ZN_1_WALL_SOUTH | STEEL-FRAMED_R-13 + R-15.6 CI_EXT-WALL | 0.30 | 0.240 | 0.249 | 136.92 | 71.63 | 180.00 | 90.00 | S |
| PERIMETER_MID_ZN_2_WALL_EAST | STEEL-FRAMED_R-13 + R-15.6 CI_EXT-WALL | 0.30 | 0.240 | 0.249 | 91.28 | 47.75 | 90.00 | 90.00 | E |
| PERIMETER_MID_ZN_3_WALL_NORTH | STEEL-FRAMED_R-13 + R-15.6 CI_EXT-WALL | 0.30 | 0.240 | 0.249 | 136.92 | 71.63 | 0.00 | 90.00 | N |
| PERIMETER_MID_ZN_4_WALL_WEST | STEEL-FRAMED_R-13 + R-15.6 CI_EXT-WALL | 0.30 | 0.240 | 0.249 | 91.28 | 47.75 | 270.00 | 90.00 | W |
| PERIMETER_TOP_ZN_1_WALL_SOUTH | STEEL-FRAMED_R-13 + R-15.6 CI_EXT-WALL | 0.30 | 0.240 | 0.249 | 136.92 | 71.63 | 180.00 | 90.00 | S |
| PERIMETER_TOP_ZN_2_WALL_EAST | STEEL-FRAMED_R-13 + R-15.6 CI_EXT-WALL | 0.30 | 0.240 | 0.249 | 91.28 | 47.75 | 90.00 | 90.00 | E |
| PERIMETER_TOP_ZN_3_WALL_NORTH | STEEL-FRAMED_R-13 + R-15.6 CI_EXT-WALL | 0.30 | 0.240 | 0.249 | 136.92 | 71.63 | 0.00 | 90.00 | N |
| PERIMETER_TOP_ZN_4_WALL_WEST | STEEL-FRAMED_R-13 + R-15.6 CI_EXT-WALL | 0.30 | 0.240 | 0.249 | 91.28 | 47.75 | 270.00 | 90.00 | W |
| PERIMETER_TOP_PLENUM_WALL_EAST | STEEL-FRAMED_R-13 + R-15.6 CI_EXT-WALL | 0.30 | 0.240 | 0.249 | 40.57 | 40.57 | 90.00 | 90.00 | E |
| PERIMETER_TOP_PLENUM_WALL_NORTH | STEEL-FRAMED_R-13 + R-15.6 CI_EXT-WALL | 0.30 | 0.240 | 0.249 | 60.85 | 60.85 | 0.00 | 90.00 | N |
| PERIMETER_TOP_PLENUM_WALL_SOUTH | STEEL-FRAMED_R-13 + R-15.6 CI_EXT-WALL | 0.30 | 0.240 | 0.249 | 60.85 | 60.85 | 180.00 | 90.00 | S |
| PERIMETER_TOP_PLENUM_WALL_WEST | STEEL-FRAMED_R-13 + R-15.6 CI_EXT-WALL | 0.30 | 0.240 | 0.249 | 40.57 | 40.57 | 270.00 | 90.00 | W |
| BUILDING_ROOF | IEAD_R-30 CI_ROOF | 0.30 | 0.184 | 0.188 | 1660.73 | 1660.73 | 0.00 | 0.00 |
| Construction | Glass Area [m2] | Frame Area [m2] | Divider Area [m2] | Area of One Opening [m2] | Area of Multiplied Openings [m2] | Glass U-Factor [W/m2-K] | Glass SHGC | Glass Visible Transmittance | Frame Conductance [W/m2-K] | Divider Conductance [W/m2-K] | Shade Control | Parent Surface | Azimuth [deg] | Tilt [deg] | Cardinal Direction | |
| PERIMETER_BOT_ZN_1_WALL_SOUTH_WINDOW | STD_WINDOW_UVALUE_1.647_SHGC_0.34_VT_0.69 | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 1.641 | 0.340 | 0.690 | No | PERIMETER_BOT_ZN_1_WALL_SOUTH | 180.00 | 90.00 | S | ||
| PERIMETER_BOT_ZN_2_WALL_EAST_WINDOW | STD_WINDOW_UVALUE_1.647_SHGC_0.34_VT_0.69 | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 1.641 | 0.340 | 0.690 | No | PERIMETER_BOT_ZN_2_WALL_EAST | 90.00 | 90.00 | E | ||
| PERIMETER_BOT_ZN_3_WALL_NORTH_WINDOW | STD_WINDOW_UVALUE_1.647_SHGC_0.34_VT_0.69 | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 1.641 | 0.340 | 0.690 | No | PERIMETER_BOT_ZN_3_WALL_NORTH | 0.00 | 90.00 | N | ||
| PERIMETER_BOT_ZN_4_WALL_WEST_WINDOW | STD_WINDOW_UVALUE_1.647_SHGC_0.34_VT_0.69 | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 1.641 | 0.340 | 0.690 | No | PERIMETER_BOT_ZN_4_WALL_WEST | 270.00 | 90.00 | W | ||
| PERIMETER_MID_ZN_1_WALL_SOUTH_WINDOW | STD_WINDOW_UVALUE_1.647_SHGC_0.34_VT_0.69 | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 1.641 | 0.340 | 0.690 | No | PERIMETER_MID_ZN_1_WALL_SOUTH | 180.00 | 90.00 | S | ||
| PERIMETER_MID_ZN_2_WALL_EAST_WINDOW | STD_WINDOW_UVALUE_1.647_SHGC_0.34_VT_0.69 | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 1.641 | 0.340 | 0.690 | No | PERIMETER_MID_ZN_2_WALL_EAST | 90.00 | 90.00 | E | ||
| PERIMETER_MID_ZN_3_WALL_NORTH_WINDOW | STD_WINDOW_UVALUE_1.647_SHGC_0.34_VT_0.69 | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 1.641 | 0.340 | 0.690 | No | PERIMETER_MID_ZN_3_WALL_NORTH | 0.00 | 90.00 | N | ||
| PERIMETER_MID_ZN_4_WALL_WEST_WINDOW | STD_WINDOW_UVALUE_1.647_SHGC_0.34_VT_0.69 | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 1.641 | 0.340 | 0.690 | No | PERIMETER_MID_ZN_4_WALL_WEST | 270.00 | 90.00 | W | ||
| PERIMETER_TOP_ZN_1_WALL_SOUTH_WINDOW | STD_WINDOW_UVALUE_1.647_SHGC_0.34_VT_0.69 | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 1.641 | 0.340 | 0.690 | No | PERIMETER_TOP_ZN_1_WALL_SOUTH | 180.00 | 90.00 | S | ||
| PERIMETER_TOP_ZN_2_WALL_EAST_WINDOW | STD_WINDOW_UVALUE_1.647_SHGC_0.34_VT_0.69 | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 1.641 | 0.340 | 0.690 | No | PERIMETER_TOP_ZN_2_WALL_EAST | 90.00 | 90.00 | E | ||
| PERIMETER_TOP_ZN_3_WALL_NORTH_WINDOW | STD_WINDOW_UVALUE_1.647_SHGC_0.34_VT_0.69 | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 1.641 | 0.340 | 0.690 | No | PERIMETER_TOP_ZN_3_WALL_NORTH | 0.00 | 90.00 | N | ||
| PERIMETER_TOP_ZN_4_WALL_WEST_WINDOW | STD_WINDOW_UVALUE_1.647_SHGC_0.34_VT_0.69 | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 1.641 | 0.340 | 0.690 | No | PERIMETER_TOP_ZN_4_WALL_WEST | 270.00 | 90.00 | W | ||
| Total or Average | 652.83 | 1.641 | 0.340 | 0.690 | ||||||||||||
| North Total or Average | 195.85 | 1.641 | 0.340 | 0.690 | ||||||||||||
| Non-North Total or Average | 456.98 | 1.641 | 0.340 | 0.690 |
| Construction | Area of One Opening [m2] | Area of Openings [m2] | Glass U-Factor [W/m2-K] | Glass SHGC | Glass Visible Transmittance | Parent Surface | |
| Total or Average | 0.00 | - | - | - |
| Construction | U-Factor with Film [W/m2-K] | U-Factor no Film [W/m2-K] | Gross Area [m2] | Parent Surface | |
| None |
Report: Shading Summary
For: Entire Facility
Timestamp: 2018-02-13 16:27:46
Sunlit Fraction| March 21 9am | March 21 noon | March 21 3pm | June 21 9am | June 21 noon | June 21 3pm | December 21 9am | December 21 noon | December 21 3pm | |
| PERIMETER_BOT_ZN_1_WALL_SOUTH_WINDOW | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 |
| PERIMETER_BOT_ZN_2_WALL_EAST_WINDOW | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 0.00 |
| PERIMETER_BOT_ZN_3_WALL_NORTH_WINDOW | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_BOT_ZN_4_WALL_WEST_WINDOW | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 |
| PERIMETER_MID_ZN_1_WALL_SOUTH_WINDOW | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 |
| PERIMETER_MID_ZN_2_WALL_EAST_WINDOW | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 0.00 |
| PERIMETER_MID_ZN_3_WALL_NORTH_WINDOW | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_MID_ZN_4_WALL_WEST_WINDOW | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 |
| PERIMETER_TOP_ZN_1_WALL_SOUTH_WINDOW | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 |
| PERIMETER_TOP_ZN_2_WALL_EAST_WINDOW | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 0.00 |
| PERIMETER_TOP_ZN_3_WALL_NORTH_WINDOW | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_TOP_ZN_4_WALL_WEST_WINDOW | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 |
| Name | Type | Shaded Construction | Control | Glare Control | |
| None |
Report: Lighting Summary
For: Entire Facility
Timestamp: 2018-02-13 16:27:46
Interior Lighting| Zone | Lighting Power Density [W/m2] | Zone Area [m2] | Total Power [W] | End Use Subcategory | Schedule Name | Scheduled Hours/Week [hr] | Hours/Week > 1% [hr] | Full Load Hours/Week [hr] | Return Air Fraction | Conditioned (Y/N) | Consumption [GJ] | |
| CORE_BOTTOM_LIGHTS | CORE_BOTTOM | 10.7600 | 983.54 | 10582.85 | General | BLDG_LIGHT_SCH | 61.85 | 168.00 | 60.24 | 0.4000 | Y | 119.68 |
| CORE_MID_LIGHTS | CORE_MID | 10.7600 | 983.54 | 10582.85 | General | BLDG_LIGHT_SCH | 61.85 | 168.00 | 60.24 | 0.4000 | Y | 119.68 |
| CORE_TOP_LIGHTS | CORE_TOP | 10.7600 | 983.54 | 10582.85 | General | BLDG_LIGHT_SCH | 61.85 | 168.00 | 60.24 | 0.4000 | Y | 119.68 |
| PERIMETER_BOT_ZN_1_LIGHTS | PERIMETER_BOT_ZN_1 | 10.7600 | 207.34 | 2230.96 | General | BLDG_LIGHT_SCH | 61.85 | 168.00 | 60.24 | 0.4000 | Y | 25.23 |
| PERIMETER_BOT_ZN_2_LIGHTS | PERIMETER_BOT_ZN_2 | 10.7600 | 131.26 | 1412.38 | General | BLDG_LIGHT_SCH | 61.85 | 168.00 | 60.24 | 0.4000 | Y | 15.97 |
| PERIMETER_BOT_ZN_3_LIGHTS | PERIMETER_BOT_ZN_3 | 10.7600 | 207.34 | 2230.96 | General | BLDG_LIGHT_SCH | 61.85 | 168.00 | 60.24 | 0.4000 | Y | 25.23 |
| PERIMETER_BOT_ZN_4_LIGHTS | PERIMETER_BOT_ZN_4 | 10.7600 | 131.25 | 1412.29 | General | BLDG_LIGHT_SCH | 61.85 | 168.00 | 60.24 | 0.4000 | Y | 15.97 |
| PERIMETER_MID_ZN_1_LIGHTS | PERIMETER_MID_ZN_1 | 10.7600 | 207.34 | 2230.96 | General | BLDG_LIGHT_SCH | 61.85 | 168.00 | 60.24 | 0.4000 | Y | 25.23 |
| PERIMETER_MID_ZN_2_LIGHTS | PERIMETER_MID_ZN_2 | 10.7600 | 131.26 | 1412.38 | General | BLDG_LIGHT_SCH | 61.85 | 168.00 | 60.24 | 0.4000 | Y | 15.97 |
| PERIMETER_MID_ZN_3_LIGHTS | PERIMETER_MID_ZN_3 | 10.7600 | 207.34 | 2230.96 | General | BLDG_LIGHT_SCH | 61.85 | 168.00 | 60.24 | 0.4000 | Y | 25.23 |
| PERIMETER_MID_ZN_4_LIGHTS | PERIMETER_MID_ZN_4 | 10.7600 | 131.25 | 1412.29 | General | BLDG_LIGHT_SCH | 61.85 | 168.00 | 60.24 | 0.4000 | Y | 15.97 |
| PERIMETER_TOP_ZN_1_LIGHTS | PERIMETER_TOP_ZN_1 | 10.7600 | 207.34 | 2230.96 | General | BLDG_LIGHT_SCH | 61.85 | 168.00 | 60.24 | 0.4000 | Y | 25.23 |
| PERIMETER_TOP_ZN_2_LIGHTS | PERIMETER_TOP_ZN_2 | 10.7600 | 131.26 | 1412.38 | General | BLDG_LIGHT_SCH | 61.85 | 168.00 | 60.24 | 0.4000 | Y | 15.97 |
| PERIMETER_TOP_ZN_3_LIGHTS | PERIMETER_TOP_ZN_3 | 10.7600 | 207.34 | 2230.96 | General | BLDG_LIGHT_SCH | 61.85 | 168.00 | 60.24 | 0.4000 | Y | 25.23 |
| PERIMETER_TOP_ZN_4_LIGHTS | PERIMETER_TOP_ZN_4 | 10.7600 | 131.25 | 1412.29 | General | BLDG_LIGHT_SCH | 61.85 | 168.00 | 60.24 | 0.4000 | Y | 15.97 |
| Interior Lighting Total | 10.7600 | 4982.19 | 53608.32 | 606.24 |
| Zone | Control Name | Daylighting Method | Control Type | Fraction Controlled | Lighting Installed in Zone [W] | Lighting Controlled [W] | |
| None |
| Total Watts | Astronomical Clock/Schedule | Schedule Name | Scheduled Hours/Week [hr] | Hours/Week > 1% [hr] | Full Load Hours/Week [hr] | Consumption [GJ] | |
| EXTERIOR FACADE LIGHTING | 14804.00 | AstronomicalClock | - | 83.69 | 83.69 | 232.57 | |
| Exterior Lighting Total | 14804.00 | 232.57 |
Report: Equipment Summary
For: Entire Facility
Timestamp: 2018-02-13 16:27:46
Central Plant| Type | Nominal Capacity [W] | Nominal Efficiency [W/W] | IPLV in SI Units [W/W] | IPLV in IP Units [Btu/W-h] | |
| None |
| Type | Design Coil Load [W] | Nominal Total Capacity [W] | Nominal Sensible Capacity [W] | Nominal Latent Capacity [W] | Nominal Sensible Heat Ratio | Nominal Efficiency [W/W] | Nominal Coil UA Value [W/C] | Nominal Coil Surface Area [m2] | |
| VAV_1_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | 174257.32 | 127269.03 | 46988.29 | 0.73 | 3.23 | |||
| VAV_2_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | 152318.78 | 111687.57 | 40631.22 | 0.73 | 3.23 | |||
| VAV_3_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | 153412.45 | 112590.10 | 40822.35 | 0.73 | 3.23 |
| DX Cooling Coil Type | Standard Rated Net Cooling Capacity [W] | Standard Rated Net COP [W/W] | EER [Btu/W-h] | SEER [Btu/W-h] | IEER [Btu/W-h] | |
| VAV_1_COOLC DXCOIL | 173141.3 | 2.78 | 9.50 | N/A | 12.67 | |
| VAV_2_COOLC DXCOIL | 151235.5 | 2.78 | 9.48 | N/A | 12.66 | |
| VAV_3_COOLC DXCOIL | 152327.5 | 2.78 | 9.48 | N/A | 12.65 |
| DX Cooling Coil Type | Rated Net Cooling Capacity Test A [W] | Rated Electric Power Test A [W] | Rated Net Cooling Capacity Test B [W] | Rated Electric Power Test B [W] | Rated Net Cooling Capacity Test C [W] | Rated Electric Power Test C [W] | Rated Net Cooling Capacity Test D [W] | Rated Electric Power Test D [W] | |
| VAV_1_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | ||||||||
| VAV_2_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | ||||||||
| VAV_3_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed |
| DX Heating Coil Type | High Temperature Heating (net) Rating Capacity [W] | Low Temperature Heating (net) Rating Capacity [W] | HSPF [Btu/W-h] | Region Number | |
| None |
| Type | Design Coil Load [W] | Nominal Total Capacity [W] | Nominal Efficiency [W/W] | |
| CORE_BOTTOM VAV BOX REHEAT COIL | Coil:Heating:Electric | 48903.01 | 1.00 | |
| CORE_MID VAV BOX REHEAT COIL | Coil:Heating:Electric | 39519.54 | 1.00 | |
| CORE_TOP VAV BOX REHEAT COIL | Coil:Heating:Electric | 40048.69 | 1.00 | |
| PERIMETER_BOT_ZN_1 VAV BOX REHEAT COIL | Coil:Heating:Electric | 16345.58 | 1.00 | |
| PERIMETER_BOT_ZN_2 VAV BOX REHEAT COIL | Coil:Heating:Electric | 12859.58 | 1.00 | |
| PERIMETER_BOT_ZN_3 VAV BOX REHEAT COIL | Coil:Heating:Electric | 11306.10 | 1.00 | |
| PERIMETER_BOT_ZN_4 VAV BOX REHEAT COIL | Coil:Heating:Electric | 13256.66 | 1.00 | |
| PERIMETER_MID_ZN_1 VAV BOX REHEAT COIL | Coil:Heating:Electric | 15469.17 | 1.00 | |
| PERIMETER_MID_ZN_2 VAV BOX REHEAT COIL | Coil:Heating:Electric | 11870.28 | 1.00 | |
| PERIMETER_MID_ZN_3 VAV BOX REHEAT COIL | Coil:Heating:Electric | 11478.45 | 1.00 | |
| PERIMETER_MID_ZN_4 VAV BOX REHEAT COIL | Coil:Heating:Electric | 12276.23 | 1.00 | |
| PERIMETER_TOP_ZN_1 VAV BOX REHEAT COIL | Coil:Heating:Electric | 16050.11 | 1.00 | |
| PERIMETER_TOP_ZN_2 VAV BOX REHEAT COIL | Coil:Heating:Electric | 11927.78 | 1.00 | |
| PERIMETER_TOP_ZN_3 VAV BOX REHEAT COIL | Coil:Heating:Electric | 15991.50 | 1.00 | |
| PERIMETER_TOP_ZN_4 VAV BOX REHEAT COIL | Coil:Heating:Electric | 12364.71 | 1.00 | |
| VAV_1_HEATC | Coil:Heating:Fuel | 41862.67 | 0.80 | |
| VAV_2_HEATC | Coil:Heating:Fuel | 43395.37 | 0.80 | |
| VAV_3_HEATC | Coil:Heating:Fuel | 43287.82 | 0.80 |
| Type | Total Efficiency [W/W] | Delta Pressure [pa] | Max Air Flow Rate [m3/s] | Rated Electric Power [W] | Rated Power Per Max Air Flow Rate [W-s/m3] | Motor Heat In Air Fraction | End Use | |
| VAV_1_FAN | Fan:SystemModel | 0.59 | 1109.65 | 8.57 | 16079.42 | 1875.99 | 1.00 | Fan Energy |
| VAV_2_FAN | Fan:VariableVolume | 0.59 | 1109.65 | 7.56 | 14191.12 | 1875.99 | 1.00 | Fan Energy |
| VAV_3_FAN | Fan:VariableVolume | 0.59 | 1109.65 | 7.64 | 14324.02 | 1875.99 | 1.00 | Fan Energy |
| Type | Control | Head [pa] | Water Flow [m3/s] | Electric Power [W] | Power Per Water Flow Rate [W-s/m3] | Motor Efficiency [W/W] | |
| SWHSYS1 PUMP | Pump:ConstantSpeed | Intermittent | 179352.00 | 0.000031 | 8.44 | 270515.84 | 0.85 |
| Type | Storage Volume [m3] | Input [W] | Thermal Efficiency [W/W] | Recovery Efficiency [W/W] | Energy Factor | |
| SWHSYS1 WATER HEATER | WaterHeater:Mixed | 0.38 | 845000.00 | 0.80 | 1.83 | 0.57 |
| DX Cooling Coil Type | Assocated Fan | Net Cooling Capacity [W] | COP [W/W] | EER [Btu/W-h] | IEER [Btu/W-h] | Supply Air Flow 100% [kg/s] | COP 75% Capacity [W/W] | EER 75% Capacity [Btu/W-h] | Supply Air Flow 75% [kg/s] | COP 50% Capacity [W/W] | EER 50% Capacity [Btu/W-h] | Supply Air Flow 50% [kg/s] | COP 25% Capacity [W/W] | EER 25% Capacity [Btu/W-h] | Supply Air Flow 25% [kg/s] | |
| VAV_1_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | VAV_1_FAN | 173141.33 | 2.78 | 9.50 | 12.67 | 9.6797 | 3.46 | 11.79 | 7.7053 | 4.17 | 14.22 | 5.1292 | 4.28 | 14.60 | 2.2627 |
| VAV_2_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | VAV_2_FAN | 151235.45 | 2.78 | 9.48 | 12.66 | 8.5429 | 3.45 | 11.77 | 6.7998 | 4.16 | 14.21 | 4.5250 | 4.27 | 14.58 | 1.9939 |
| VAV_3_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | VAV_3_FAN | 152327.49 | 2.78 | 9.48 | 12.65 | 8.6229 | 3.45 | 11.77 | 6.8634 | 4.16 | 14.20 | 4.5672 | 4.27 | 14.58 | 2.0122 |
Report: HVAC Sizing Summary
For: Entire Facility
Timestamp: 2018-02-13 16:27:46
Zone Sensible Cooling| Calculated Design Load [W] | User Design Load [W] | User Design Load per Area [W/m2] | Calculated Design Air Flow [m3/s] | User Design Air Flow [m3/s] | Design Day Name | Date/Time Of Peak {TIMESTAMP} | Thermostat Setpoint Temperature at Peak Load [C] | Indoor Temperature at Peak Load [C] | Indoor Humidity Ratio at Peak Load [kgWater/kgAir] | Outdoor Temperature at Peak Load [C] | Outdoor Humidity Ratio at Peak Load [kgWater/kgAir] | Minimum Outdoor Air Flow Rate [m3/s] | Heat Gain Rate from DOAS [W] | |
| CORE_BOTTOM | 41251.53 | 54864.54 | 55.78 | 3.070 | 4.083 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 09:00:00 | 24.00 | 24.00 | 0.00879 | 25.31 | 0.01878 | 0.662 | 0.00 |
| CORE_MID | 33973.46 | 45184.71 | 45.94 | 2.481 | 3.299 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 07:00:00 | 24.00 | 24.00 | 0.00886 | 21.46 | 0.01650 | 0.662 | 0.00 |
| CORE_TOP | 34422.85 | 45782.38 | 46.55 | 2.514 | 3.343 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 07:00:00 | 24.00 | 24.00 | 0.00885 | 21.46 | 0.01650 | 0.662 | 0.00 |
| PERIMETER_BOT_ZN_1 | 13787.83 | 18337.81 | 88.44 | 1.026 | 1.365 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 13:10:00 | 24.00 | 24.00 | 0.00878 | 30.75 | 0.01878 | 0.139 | 0.00 |
| PERIMETER_BOT_ZN_2 | 10847.42 | 14427.07 | 109.91 | 0.807 | 1.074 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 08:50:00 | 24.00 | 24.00 | 0.00873 | 24.98 | 0.01878 | 0.088 | 0.00 |
| PERIMETER_BOT_ZN_3 | 9690.01 | 12887.71 | 62.16 | 0.710 | 0.944 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 07:00:00 | 24.00 | 24.00 | 0.00891 | 21.46 | 0.01650 | 0.139 | 0.00 |
| PERIMETER_BOT_ZN_4 | 11182.35 | 14872.52 | 113.31 | 0.832 | 1.107 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 16:40:00 | 24.00 | 24.00 | 0.00872 | 29.99 | 0.01878 | 0.088 | 0.00 |
| PERIMETER_MID_ZN_1 | 13048.52 | 17354.54 | 83.70 | 0.971 | 1.291 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 13:10:00 | 24.00 | 24.00 | 0.00879 | 30.75 | 0.01878 | 0.139 | 0.00 |
| PERIMETER_MID_ZN_2 | 10012.89 | 13317.14 | 101.45 | 0.745 | 0.991 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 08:50:00 | 24.00 | 24.00 | 0.00875 | 24.98 | 0.01878 | 0.088 | 0.00 |
| PERIMETER_MID_ZN_3 | 9833.38 | 13078.40 | 63.08 | 0.720 | 0.958 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 07:00:00 | 24.00 | 24.00 | 0.00890 | 21.46 | 0.01650 | 0.139 | 0.00 |
| PERIMETER_MID_ZN_4 | 10355.29 | 13772.54 | 104.93 | 0.771 | 1.025 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 16:50:00 | 24.00 | 24.00 | 0.00874 | 29.84 | 0.01878 | 0.088 | 0.00 |
| PERIMETER_TOP_ZN_1 | 13106.86 | 17432.13 | 84.08 | 0.975 | 1.297 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 13:10:00 | 24.00 | 24.00 | 0.00879 | 30.75 | 0.01878 | 0.139 | 0.00 |
| PERIMETER_TOP_ZN_2 | 10061.40 | 13381.66 | 101.95 | 0.749 | 0.996 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 08:50:00 | 24.00 | 24.00 | 0.00875 | 24.98 | 0.01878 | 0.088 | 0.00 |
| PERIMETER_TOP_ZN_3 | 9922.02 | 13196.29 | 63.65 | 0.727 | 0.967 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 07:00:00 | 24.00 | 24.00 | 0.00890 | 21.46 | 0.01650 | 0.139 | 0.00 |
| PERIMETER_TOP_ZN_4 | 10429.93 | 13871.81 | 105.69 | 0.776 | 1.032 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 16:50:00 | 24.00 | 24.00 | 0.00874 | 29.84 | 0.01878 | 0.088 | 0.00 |
| Calculated Design Load [W] | User Design Load [W] | User Design Load per Area [W/m2] | Calculated Design Air Flow [m3/s] | User Design Air Flow [m3/s] | Design Day Name | Date/Time Of Peak {TIMESTAMP} | Thermostat Setpoint Temperature at Peak Load [C] | Indoor Temperature at Peak Load [C] | Indoor Humidity Ratio at Peak Load [kgWater/kgAir] | Outdoor Temperature at Peak Load [C] | Outdoor Humidity Ratio at Peak Load [kgWater/kgAir] | Minimum Outdoor Air Flow Rate [m3/s] | Heat Gain Rate from DOAS [W] | |
| CORE_BOTTOM | 3912.39 | 5203.48 | 5.29 | 0.113 | 0.662 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 06:10:00 | 21.00 | 21.00 | 0.00800 | -20.60 | 0.00061 | 0.662 | 0.00 |
| CORE_MID | 5763.75 | 7665.79 | 7.79 | 0.166 | 0.662 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 06:10:00 | 21.00 | 21.00 | 0.00800 | -20.60 | 0.00061 | 0.662 | 0.00 |
| CORE_TOP | 20796.56 | 27659.43 | 28.12 | 0.598 | 0.795 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 06:10:00 | 21.00 | 21.00 | 0.00800 | -20.60 | 0.00061 | 0.662 | 0.00 |
| PERIMETER_BOT_ZN_1 | 6835.38 | 9091.06 | 43.85 | 0.197 | 0.261 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 06:00:00 | 21.00 | 20.99 | 0.00655 | -20.60 | 0.00061 | 0.139 | 0.00 |
| PERIMETER_BOT_ZN_2 | 4546.92 | 6047.41 | 46.07 | 0.131 | 0.174 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 06:00:00 | 21.00 | 20.99 | 0.00655 | -20.60 | 0.00061 | 0.088 | 0.00 |
| PERIMETER_BOT_ZN_3 | 6781.43 | 9019.31 | 43.50 | 0.195 | 0.259 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 06:00:00 | 21.00 | 20.99 | 0.00654 | -20.60 | 0.00061 | 0.139 | 0.00 |
| PERIMETER_BOT_ZN_4 | 4543.89 | 6043.37 | 46.04 | 0.131 | 0.174 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 06:00:00 | 21.00 | 20.99 | 0.00655 | -20.60 | 0.00061 | 0.088 | 0.00 |
| PERIMETER_MID_ZN_1 | 7106.64 | 9451.83 | 45.59 | 0.204 | 0.272 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 06:00:00 | 21.00 | 20.99 | 0.00659 | -20.60 | 0.00061 | 0.139 | 0.00 |
| PERIMETER_MID_ZN_2 | 4697.63 | 6247.85 | 47.60 | 0.135 | 0.180 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 06:00:00 | 21.00 | 20.99 | 0.00658 | -20.60 | 0.00061 | 0.088 | 0.00 |
| PERIMETER_MID_ZN_3 | 7033.07 | 9353.98 | 45.11 | 0.202 | 0.269 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 06:00:00 | 21.00 | 20.99 | 0.00658 | -20.60 | 0.00061 | 0.139 | 0.00 |
| PERIMETER_MID_ZN_4 | 4706.36 | 6259.45 | 47.69 | 0.135 | 0.180 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 06:00:00 | 21.00 | 20.99 | 0.00659 | -20.60 | 0.00061 | 0.088 | 0.00 |
| PERIMETER_TOP_ZN_1 | 10512.26 | 13981.31 | 67.43 | 0.302 | 0.402 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 06:00:00 | 21.00 | 20.99 | 0.00699 | -20.60 | 0.00061 | 0.139 | 0.00 |
| PERIMETER_TOP_ZN_2 | 6852.46 | 9113.78 | 69.43 | 0.197 | 0.262 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 06:00:00 | 21.00 | 20.99 | 0.00697 | -20.60 | 0.00061 | 0.088 | 0.00 |
| PERIMETER_TOP_ZN_3 | 10473.88 | 13930.26 | 67.19 | 0.301 | 0.401 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 06:00:00 | 21.00 | 20.99 | 0.00698 | -20.60 | 0.00061 | 0.139 | 0.00 |
| PERIMETER_TOP_ZN_4 | 6867.03 | 9133.16 | 69.58 | 0.197 | 0.263 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 06:00:00 | 21.00 | 20.99 | 0.00697 | -20.60 | 0.00061 | 0.088 | 0.00 |
| Calculated cooling [m3/s] | User cooling [m3/s] | Calculated heating [m3/s] | User heating [m3/s] | |
| VAV_1 | 8.57 | 8.57 | 1.53 | 1.53 |
| VAV_2 | 7.56 | 7.56 | 1.56 | 1.56 |
| VAV_3 | 7.64 | 7.64 | 2.12 | 2.12 |
| Previous Design Volume Flow Rate [m3/s] | Algorithm Volume Flow Rate [m3/s] | Coincident Design Volume Flow Rate [m3/s] | Coincident Size Adjusted | Peak Sizing Period Name | Peak Day into Period {TIMESTAMP}[day] | Peak Hour Of Day {TIMESTAMP}[hr] | Peak Step Start Minute {TIMESTAMP}[min] | |
| None |
Report: System Summary
For: Entire Facility
Timestamp: 2018-02-13 16:27:46
Economizer| High Limit Shutoff Control | Minimum Outdoor Air [m3/s] | Maximum Outdoor Air [m3/s] | Return Air Temp Limit | Return Air Enthalpy Limit | Outdoor Air Temperature Limit [C] | Outdoor Air Enthalpy Limit [C] | |
| VAV_1_OA_CONTROLLER | DifferentialDryBulb | 1.12 | 8.57 | - | |||
| VAV_2_OA_CONTROLLER | DifferentialDryBulb | 1.12 | 7.56 | - | |||
| VAV_3_OA_CONTROLLER | DifferentialDryBulb | 1.12 | 7.64 | - |
| Controller:MechanicalVentilation Name | Outdoor Air Per Person [m3/s-person] | Outdoor Air Per Area [m3/s-m2] | Outdoor Air Per Zone [m3/s] | Outdoor Air ACH [ach] | Outdoor Air Method | Outdoor Air Schedule Name | Air Distribution Effectiveness in Cooling Mode | Air Distribution Effectiveness in Heating Mode | Air Distribution Effectiveness Schedule Name | |
| None |
| Winter Clothes [hr] | Summer Clothes [hr] | Summer or Winter Clothes [hr] | |
| CORE_BOTTOM | 1503.00 | 2678.00 | 50.67 |
| CORE_MID | 1708.00 | 2883.17 | 214.50 |
| CORE_TOP | 2197.17 | 3226.83 | 838.17 |
| PERIMETER_BOT_ZN_1 | 1952.33 | 3238.00 | 579.17 |
| PERIMETER_BOT_ZN_2 | 1839.50 | 3709.33 | 777.00 |
| PERIMETER_BOT_ZN_3 | 2119.33 | 3493.17 | 908.67 |
| PERIMETER_BOT_ZN_4 | 1650.17 | 3942.50 | 829.00 |
| PERIMETER_MID_ZN_1 | 2096.33 | 3092.50 | 624.83 |
| PERIMETER_MID_ZN_2 | 2123.50 | 3481.50 | 857.33 |
| PERIMETER_MID_ZN_3 | 2355.17 | 3296.67 | 980.17 |
| PERIMETER_MID_ZN_4 | 1938.83 | 3662.33 | 889.50 |
| PERIMETER_TOP_ZN_1 | 2425.67 | 3268.00 | 1049.50 |
| PERIMETER_TOP_ZN_2 | 2558.83 | 3582.67 | 1342.17 |
| PERIMETER_TOP_ZN_3 | 2779.67 | 3436.33 | 1465.83 |
| PERIMETER_TOP_ZN_4 | 2343.50 | 3746.00 | 1332.17 |
| FIRSTFLOOR_PLENUM | 0.00 | 0.00 | 0.00 |
| MIDFLOOR_PLENUM | 0.00 | 0.00 | 0.00 |
| TOPFLOOR_PLENUM | 0.00 | 0.00 | 0.00 |
| Facility | 3607.67 | 4260.67 | 1493.33 |
| During Heating [hr] | During Cooling [hr] | During Occupied Heating [hr] | During Occupied Cooling [hr] | |
| CORE_BOTTOM | 0.33 | 0.00 | 0.33 | 0.00 |
| CORE_MID | 0.50 | 0.00 | 0.50 | 0.00 |
| CORE_TOP | 6.17 | 0.00 | 6.17 | 0.00 |
| PERIMETER_BOT_ZN_1 | 5.33 | 14.33 | 1.83 | 0.00 |
| PERIMETER_BOT_ZN_2 | 10.67 | 9.83 | 1.83 | 0.00 |
| PERIMETER_BOT_ZN_3 | 14.67 | 0.00 | 4.83 | 0.00 |
| PERIMETER_BOT_ZN_4 | 10.67 | 7.50 | 1.67 | 0.00 |
| PERIMETER_MID_ZN_1 | 4.67 | 9.33 | 1.83 | 0.00 |
| PERIMETER_MID_ZN_2 | 9.33 | 6.00 | 1.50 | 0.00 |
| PERIMETER_MID_ZN_3 | 12.17 | 0.00 | 4.00 | 0.00 |
| PERIMETER_MID_ZN_4 | 9.83 | 6.00 | 1.33 | 0.00 |
| PERIMETER_TOP_ZN_1 | 40.33 | 8.00 | 7.83 | 0.00 |
| PERIMETER_TOP_ZN_2 | 57.00 | 5.33 | 6.50 | 0.00 |
| PERIMETER_TOP_ZN_3 | 64.67 | 0.00 | 7.67 | 0.00 |
| PERIMETER_TOP_ZN_4 | 58.17 | 5.50 | 6.00 | 0.17 |
| FIRSTFLOOR_PLENUM | 0.00 | 0.00 | 0.00 | 0.00 |
| MIDFLOOR_PLENUM | 0.00 | 0.00 | 0.00 | 0.00 |
| TOPFLOOR_PLENUM | 0.00 | 0.00 | 0.00 | 0.00 |
| Facility | 79.33 | 43.67 | 9.67 | 0.17 |
Report: Outdoor Air Summary
For: Entire Facility
Timestamp: 2018-02-13 16:27:46
Average Outdoor Air During Occupied Hours| Average Number of Occupants | Nominal Number of Occupants | Zone Volume [m3] | Mechanical Ventilation [ach] | Infiltration [ach] | AFN Infiltration [ach] | Simple Ventilation [ach] | |
| CORE_BOTTOM | 29.43 | 52.94 | 2698.04 | 1.278 | 0.000 | 0.000 | 0.000 |
| CORE_MID | 29.43 | 52.94 | 2698.04 | 0.928 | 0.000 | 0.000 | 0.000 |
| CORE_TOP | 29.43 | 52.94 | 2698.04 | 0.913 | 0.000 | 0.000 | 0.000 |
| PERIMETER_BOT_ZN_1 | 6.20 | 11.16 | 568.77 | 1.864 | 0.089 | 0.000 | 0.000 |
| PERIMETER_BOT_ZN_2 | 3.93 | 7.06 | 360.08 | 2.140 | 0.093 | 0.000 | 0.000 |
| PERIMETER_BOT_ZN_3 | 6.20 | 11.16 | 568.77 | 1.205 | 0.088 | 0.000 | 0.000 |
| PERIMETER_BOT_ZN_4 | 3.93 | 7.06 | 360.05 | 2.182 | 0.093 | 0.000 | 0.000 |
| PERIMETER_MID_ZN_1 | 6.20 | 11.16 | 568.77 | 1.788 | 0.089 | 0.000 | 0.000 |
| PERIMETER_MID_ZN_2 | 3.93 | 7.06 | 360.08 | 2.041 | 0.093 | 0.000 | 0.000 |
| PERIMETER_MID_ZN_3 | 6.20 | 11.16 | 568.77 | 1.272 | 0.089 | 0.000 | 0.000 |
| PERIMETER_MID_ZN_4 | 3.93 | 7.06 | 360.05 | 2.081 | 0.093 | 0.000 | 0.000 |
| PERIMETER_TOP_ZN_1 | 6.20 | 11.16 | 568.77 | 1.738 | 0.088 | 0.000 | 0.000 |
| PERIMETER_TOP_ZN_2 | 3.93 | 7.06 | 360.08 | 2.005 | 0.093 | 0.000 | 0.000 |
| PERIMETER_TOP_ZN_3 | 6.20 | 11.16 | 568.77 | 1.256 | 0.088 | 0.000 | 0.000 |
| PERIMETER_TOP_ZN_4 | 3.93 | 7.06 | 360.05 | 2.054 | 0.093 | 0.000 | 0.000 |
| Average Number of Occupants | Nominal Number of Occupants | Zone Volume [m3] | Mechanical Ventilation [ach] | Infiltration [ach] | AFN Infiltration [ach] | Simple Ventilation [ach] | |
| CORE_BOTTOM | 29.43 | 52.94 | 2698.04 | 0.000 | 0.000 | 0.000 | 0.000 |
| CORE_MID | 29.43 | 52.94 | 2698.04 | 0.000 | 0.000 | 0.000 | 0.000 |
| CORE_TOP | 29.43 | 52.94 | 2698.04 | 0.000 | 0.000 | 0.000 | 0.000 |
| PERIMETER_BOT_ZN_1 | 6.20 | 11.16 | 568.77 | 0.000 | 0.002 | 0.000 | 0.000 |
| PERIMETER_BOT_ZN_2 | 3.93 | 7.06 | 360.08 | 0.000 | 0.002 | 0.000 | 0.000 |
| PERIMETER_BOT_ZN_3 | 6.20 | 11.16 | 568.77 | 0.000 | 0.002 | 0.000 | 0.000 |
| PERIMETER_BOT_ZN_4 | 3.93 | 7.06 | 360.05 | 0.000 | 0.002 | 0.000 | 0.000 |
| PERIMETER_MID_ZN_1 | 6.20 | 11.16 | 568.77 | 0.000 | 0.002 | 0.000 | 0.000 |
| PERIMETER_MID_ZN_2 | 3.93 | 7.06 | 360.08 | 0.000 | 0.002 | 0.000 | 0.000 |
| PERIMETER_MID_ZN_3 | 6.20 | 11.16 | 568.77 | 0.000 | 0.002 | 0.000 | 0.000 |
| PERIMETER_MID_ZN_4 | 3.93 | 7.06 | 360.05 | 0.000 | 0.002 | 0.000 | 0.000 |
| PERIMETER_TOP_ZN_1 | 6.20 | 11.16 | 568.77 | 0.000 | 0.002 | 0.000 | 0.000 |
| PERIMETER_TOP_ZN_2 | 3.93 | 7.06 | 360.08 | 0.000 | 0.002 | 0.000 | 0.000 |
| PERIMETER_TOP_ZN_3 | 6.20 | 11.16 | 568.77 | 0.000 | 0.002 | 0.000 | 0.000 |
| PERIMETER_TOP_ZN_4 | 3.93 | 7.06 | 360.05 | 0.000 | 0.002 | 0.000 | 0.000 |
Report: Object Count Summary
For: Entire Facility
Timestamp: 2018-02-13 16:27:46
Surfaces by Class| Total | Outdoors | |
| Wall | 72 | 24 |
| Floor | 30 | 5 |
| Roof | 26 | 1 |
| Internal Mass | 15 | 0 |
| Building Detached Shading | 0 | 0 |
| Fixed Detached Shading | 0 | 0 |
| Window | 12 | 12 |
| Door | 0 | 0 |
| Glass Door | 0 | 0 |
| Shading | 0 | 0 |
| Overhang | 0 | 0 |
| Fin | 0 | 0 |
| Tubular Daylighting Device Dome | 0 | 0 |
| Tubular Daylighting Device Diffuser | 0 | 0 |
| Count | |
| HVAC Air Loops | 3 |
| Conditioned Zones | 18 |
| Unconditioned Zones | 0 |
| Supply Plenums | 0 |
| Return Plenums | 3 |
| Count | |
| IDF Objects | 683 |
| Defaulted Fields | 65 |
| Fields with Defaults | 1879 |
| Autosized Fields | 138 |
| Autosizable Fields | 155 |
| Autocalculated Fields | 210 |
| Autocalculatable Fields | 350 |
Report: Energy Meters
For: Entire Facility
Timestamp: 2018-02-13 16:27:46
Annual and Peak Values - Electricity| Electricity Annual Value [GJ] | Electricity Minimum Value [W] | Timestamp of Minimum {TIMESTAMP} | Electricity Maximum Value [W] | Timestamp of Maximum {TIMESTAMP} | |
| Electricity:Facility | 2550.63 | 18771.35 | 01-JAN-08:00 | 310294.50 | 02-JAN-06:20 |
| Electricity:Building | 1672.76 | 18762.91 | 01-JAN-00:10 | 118650.80 | 02-JAN-08:10 |
| Electricity:Zone:CORE_BOTTOM | 462.45 | 3704.00 | 01-JAN-00:10 | 41204.96 | 02-JAN-08:10 |
| InteriorLights:Electricity | 606.24 | 2680.42 | 01-JAN-00:10 | 48247.49 | 02-JAN-08:10 |
| InteriorLights:Electricity:Zone:CORE_BOTTOM | 119.68 | 529.14 | 01-JAN-00:10 | 9524.57 | 02-JAN-08:10 |
| General:InteriorLights:Electricity | 606.24 | 2680.42 | 01-JAN-00:10 | 48247.49 | 02-JAN-08:10 |
| Electricity:Zone:CORE_MID | 297.70 | 3704.00 | 01-JAN-00:10 | 19049.14 | 02-JAN-08:10 |
| InteriorLights:Electricity:Zone:CORE_MID | 119.68 | 529.14 | 01-JAN-00:10 | 9524.57 | 02-JAN-08:10 |
| Electricity:Zone:CORE_TOP | 297.70 | 3704.00 | 01-JAN-00:10 | 19049.14 | 02-JAN-08:10 |
| InteriorLights:Electricity:Zone:CORE_TOP | 119.68 | 529.14 | 01-JAN-00:10 | 9524.57 | 02-JAN-08:10 |
| Electricity:Zone:PERIMETER_BOT_ZN_1 | 62.76 | 780.84 | 01-JAN-00:10 | 4015.73 | 02-JAN-08:10 |
| InteriorLights:Electricity:Zone:PERIMETER_BOT_ZN_1 | 25.23 | 111.55 | 01-JAN-00:10 | 2007.86 | 02-JAN-08:10 |
| Electricity:Zone:PERIMETER_BOT_ZN_2 | 39.73 | 494.33 | 01-JAN-00:10 | 2542.29 | 02-JAN-08:10 |
| InteriorLights:Electricity:Zone:PERIMETER_BOT_ZN_2 | 15.97 | 70.62 | 01-JAN-00:10 | 1271.14 | 02-JAN-08:10 |
| Electricity:Zone:PERIMETER_BOT_ZN_3 | 62.76 | 780.84 | 01-JAN-00:10 | 4015.73 | 02-JAN-08:10 |
| InteriorLights:Electricity:Zone:PERIMETER_BOT_ZN_3 | 25.23 | 111.55 | 01-JAN-00:10 | 2007.86 | 02-JAN-08:10 |
| Electricity:Zone:PERIMETER_BOT_ZN_4 | 39.73 | 494.30 | 01-JAN-00:10 | 2542.12 | 02-JAN-08:10 |
| InteriorLights:Electricity:Zone:PERIMETER_BOT_ZN_4 | 15.97 | 70.61 | 01-JAN-00:10 | 1271.06 | 02-JAN-08:10 |
| Electricity:Zone:PERIMETER_MID_ZN_1 | 62.76 | 780.84 | 01-JAN-00:10 | 4015.73 | 02-JAN-08:10 |
| InteriorLights:Electricity:Zone:PERIMETER_MID_ZN_1 | 25.23 | 111.55 | 01-JAN-00:10 | 2007.86 | 02-JAN-08:10 |
| Electricity:Zone:PERIMETER_MID_ZN_2 | 39.73 | 494.33 | 01-JAN-00:10 | 2542.29 | 02-JAN-08:10 |
| InteriorLights:Electricity:Zone:PERIMETER_MID_ZN_2 | 15.97 | 70.62 | 01-JAN-00:10 | 1271.14 | 02-JAN-08:10 |
| Electricity:Zone:PERIMETER_MID_ZN_3 | 62.76 | 780.84 | 01-JAN-00:10 | 4015.73 | 02-JAN-08:10 |
| InteriorLights:Electricity:Zone:PERIMETER_MID_ZN_3 | 25.23 | 111.55 | 01-JAN-00:10 | 2007.86 | 02-JAN-08:10 |
| Electricity:Zone:PERIMETER_MID_ZN_4 | 39.73 | 494.30 | 01-JAN-00:10 | 2542.12 | 02-JAN-08:10 |
| InteriorLights:Electricity:Zone:PERIMETER_MID_ZN_4 | 15.97 | 70.61 | 01-JAN-00:10 | 1271.06 | 02-JAN-08:10 |
| Electricity:Zone:PERIMETER_TOP_ZN_1 | 62.76 | 780.84 | 01-JAN-00:10 | 4015.73 | 02-JAN-08:10 |
| InteriorLights:Electricity:Zone:PERIMETER_TOP_ZN_1 | 25.23 | 111.55 | 01-JAN-00:10 | 2007.86 | 02-JAN-08:10 |
| Electricity:Zone:PERIMETER_TOP_ZN_2 | 39.73 | 494.33 | 01-JAN-00:10 | 2542.29 | 02-JAN-08:10 |
| InteriorLights:Electricity:Zone:PERIMETER_TOP_ZN_2 | 15.97 | 70.62 | 01-JAN-00:10 | 1271.14 | 02-JAN-08:10 |
| Electricity:Zone:PERIMETER_TOP_ZN_3 | 62.76 | 780.84 | 01-JAN-00:10 | 4015.73 | 02-JAN-08:10 |
| InteriorLights:Electricity:Zone:PERIMETER_TOP_ZN_3 | 25.23 | 111.55 | 01-JAN-00:10 | 2007.86 | 02-JAN-08:10 |
| Electricity:Zone:PERIMETER_TOP_ZN_4 | 39.73 | 494.30 | 01-JAN-00:10 | 2542.12 | 02-JAN-08:10 |
| InteriorLights:Electricity:Zone:PERIMETER_TOP_ZN_4 | 15.97 | 70.61 | 01-JAN-00:10 | 1271.06 | 02-JAN-08:10 |
| InteriorEquipment:Electricity | 1066.52 | 16082.50 | 01-JAN-00:10 | 70403.31 | 02-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:CORE_BOTTOM | 342.77 | 3174.86 | 01-JAN-00:10 | 31680.39 | 02-JAN-08:10 |
| Elevators:InteriorEquipment:Electricity | 164.75 | 0.00 | 01-JAN-00:10 | 22155.82 | 02-JAN-08:10 |
| General:InteriorEquipment:Electricity | 901.77 | 16082.50 | 01-JAN-00:10 | 48247.49 | 02-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:CORE_MID | 178.02 | 3174.86 | 01-JAN-00:10 | 9524.57 | 02-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:CORE_TOP | 178.02 | 3174.86 | 01-JAN-00:10 | 9524.57 | 02-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:PERIMETER_BOT_ZN_1 | 37.53 | 669.29 | 01-JAN-00:10 | 2007.86 | 02-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:PERIMETER_BOT_ZN_2 | 23.76 | 423.71 | 01-JAN-00:10 | 1271.14 | 02-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:PERIMETER_BOT_ZN_3 | 37.53 | 669.29 | 01-JAN-00:10 | 2007.86 | 02-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:PERIMETER_BOT_ZN_4 | 23.76 | 423.69 | 01-JAN-00:10 | 1271.06 | 02-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:PERIMETER_MID_ZN_1 | 37.53 | 669.29 | 01-JAN-00:10 | 2007.86 | 02-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:PERIMETER_MID_ZN_2 | 23.76 | 423.71 | 01-JAN-00:10 | 1271.14 | 02-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:PERIMETER_MID_ZN_3 | 37.53 | 669.29 | 01-JAN-00:10 | 2007.86 | 02-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:PERIMETER_MID_ZN_4 | 23.76 | 423.69 | 01-JAN-00:10 | 1271.06 | 02-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:PERIMETER_TOP_ZN_1 | 37.53 | 669.29 | 01-JAN-00:10 | 2007.86 | 02-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:PERIMETER_TOP_ZN_2 | 23.76 | 423.71 | 01-JAN-00:10 | 1271.14 | 02-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:PERIMETER_TOP_ZN_3 | 37.53 | 669.29 | 01-JAN-00:10 | 2007.86 | 02-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:PERIMETER_TOP_ZN_4 | 23.76 | 423.69 | 01-JAN-00:10 | 1271.06 | 02-JAN-08:10 |
| ElectricityPurchased:Facility | 2550.63 | 18771.35 | 15-JAN-10:00 | 310294.50 | 02-JAN-06:20 |
| ElectricityPurchased:Plant | 2550.63 | 18771.35 | 15-JAN-10:00 | 310294.50 | 02-JAN-06:20 |
| Cogeneration:ElectricityPurchased | 2550.63 | 18771.35 | 15-JAN-10:00 | 310294.50 | 02-JAN-06:20 |
| ElectricitySurplusSold:Facility | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| ElectricitySurplusSold:Plant | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| Cogeneration:ElectricitySurplusSold | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| ElectricityNet:Facility | 2550.63 | 18771.35 | 15-JAN-10:00 | 310294.50 | 02-JAN-06:20 |
| ElectricityNet:Plant | 2550.63 | 18771.35 | 15-JAN-10:00 | 310294.50 | 02-JAN-06:20 |
| Cogeneration:ElectricityNet | 2550.63 | 18771.35 | 15-JAN-10:00 | 310294.50 | 02-JAN-06:20 |
| Electricity:HVAC | 645.04 | 0.00 | 01-JAN-00:40 | 268677.90 | 02-JAN-06:20 |
| Heating:Electricity | 249.37 | 0.00 | 01-JAN-00:40 | 264838.71 | 02-JAN-06:20 |
| Fans:Electricity | 78.60 | 0.00 | 01-JAN-00:40 | 12742.36 | 05-JUL-05:10 |
| Fan Energy:Fans:Electricity | 78.60 | 0.00 | 01-JAN-00:40 | 12742.36 | 05-JUL-05:10 |
| ExteriorLights:Electricity | 232.57 | 0.00 | 01-JAN-07:30 | 14804.00 | 01-JAN-00:10 |
| Exterior Facade Lighting:ExteriorLights:Electricity | 232.57 | 0.00 | 01-JAN-07:30 | 14804.00 | 01-JAN-00:10 |
| Cooling:Electricity | 317.08 | 0.00 | 01-JAN-00:10 | 101234.58 | 19-JUL-15:10 |
| Electricity:Plant | 0.27 | 8.44 | 01-JAN-00:20 | 8.44 | 01-JAN-00:10 |
| Pumps:Electricity | 0.27 | 8.44 | 01-JAN-00:20 | 8.44 | 01-JAN-00:10 |
| Gas Annual Value [GJ] | Gas Minimum Value [W] | Timestamp of Minimum {TIMESTAMP} | Gas Maximum Value [W] | Timestamp of Maximum {TIMESTAMP} | |
| Gas:Facility | 157.16 | 20.00 | 01-JAN-00:40 | 140546.04 | 07-JAN-07:20 |
| Gas:Plant | 36.11 | 20.00 | 01-JAN-00:10 | 6536.86 | 15-FEB-12:20 |
| WaterSystems:Gas | 36.11 | 20.00 | 01-JAN-00:10 | 6536.86 | 15-FEB-12:20 |
| Water Heater:WaterSystems:Gas | 36.11 | 20.00 | 01-JAN-00:10 | 6536.86 | 15-FEB-12:20 |
| Gas:HVAC | 121.05 | 0.00 | 01-JAN-00:40 | 135275.66 | 07-JAN-07:10 |
| Heating:Gas | 121.05 | 0.00 | 01-JAN-00:40 | 135275.66 | 07-JAN-07:10 |
| Cooling Annual Value [GJ] | Cooling Minimum Value [W] | Timestamp of Minimum {TIMESTAMP} | Cooling Maximum Value [W] | Timestamp of Maximum {TIMESTAMP} | |
| None |
| Annual Value [m3] | Minimum Value [m3/s] | Timestamp of Minimum {TIMESTAMP} | Maximum Value [m3/s] | Timestamp of Maximum {TIMESTAMP} | |
| Water:Facility | 174.59 | 0.00 | 01-JAN-00:10 | 0.00 | 05-JAN-12:40 |
| Water:Plant | 174.59 | 0.00 | 01-JAN-00:10 | 0.00 | 05-JAN-12:40 |
| WaterSystems:Water | 174.59 | 0.00 | 01-JAN-00:10 | 0.00 | 05-JAN-12:40 |
| Water Heater:WaterSystems:Water | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| MainsWater:Facility | 174.59 | 0.00 | 01-JAN-00:10 | 0.00 | 05-JAN-12:40 |
| MainsWater:Plant | 174.59 | 0.00 | 01-JAN-00:10 | 0.00 | 05-JAN-12:40 |
| WaterSystems:MainsWater | 174.59 | 0.00 | 01-JAN-00:10 | 0.00 | 05-JAN-12:40 |
| Water Heater:WaterSystems:MainsWater | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| General:WaterSystems:Water | 174.59 | 0.00 | 01-JAN-00:10 | 0.00 | 05-JAN-12:40 |
| General:WaterSystems:MainsWater | 174.59 | 0.00 | 01-JAN-00:10 | 0.00 | 05-JAN-12:40 |
| Annual Value [kg] | Minimum Value [kg/s] | Timestamp of Minimum {TIMESTAMP} | Maximum Value [kg/s] | Timestamp of Maximum {TIMESTAMP} | |
| CO2:Facility | 879739.77 | 0.006 | 01-JAN-08:00 | 0.106 | 02-JAN-06:20 |
| NaturalGasEmissions:CO2 | 8187.90 | 0.000 | 01-JAN-00:40 | 0.007 | 07-JAN-07:20 |
| CO:Facility | 308.78 | 0.000 | 01-JAN-08:00 | 0.000 | 02-JAN-06:20 |
| NaturalGasEmissions:CO | 6.27 | 0.000 | 01-JAN-00:40 | 0.000 | 07-JAN-07:20 |
| CH4:Facility | 1906.00 | 0.000 | 16-JAN-12:10 | 0.000 | 02-JAN-06:20 |
| NaturalGasEmissions:CH4 | 0.17 | 0.000 | 01-JAN-00:40 | 0.000 | 07-JAN-07:20 |
| NOx:Facility | 1594.44 | 0.000 | 01-JAN-08:00 | 0.000 | 02-JAN-06:20 |
| NaturalGasEmissions:NOx | 7.43 | 0.000 | 01-JAN-00:40 | 0.000 | 07-JAN-07:20 |
| N2O:Facility | 20.64 | 0.000 | 01-JAN-08:00 | 0.000 | 02-JAN-06:20 |
| NaturalGasEmissions:N2O | 0.17 | 0.000 | 01-JAN-00:40 | 0.000 | 07-JAN-07:20 |
| SO2:Facility | 4774.83 | 0.000 | 01-JAN-08:00 | 0.001 | 02-JAN-06:20 |
| NaturalGasEmissions:SO2 | 0.04 | 0.000 | 01-JAN-00:40 | 0.000 | 07-JAN-07:20 |
| PM:Facility | 0.00 | 0.000 | 01-JAN-00:10 | 0.000 | 01-JAN-00:10 |
| NaturalGasEmissions:PM | 0.00 | 0.000 | 01-JAN-00:10 | 0.000 | 01-JAN-00:10 |
| PM10:Facility | 44.92 | 0.000 | 16-JAN-12:10 | 0.000 | 02-JAN-06:20 |
| NaturalGasEmissions:PM10 | 0.56 | 0.000 | 01-JAN-00:40 | 0.000 | 07-JAN-07:20 |
| PM2.5:Facility | 0.00 | 0.000 | 01-JAN-00:10 | 0.000 | 01-JAN-00:10 |
| NaturalGasEmissions:PM2.5 | 0.00 | 0.000 | 01-JAN-00:10 | 0.000 | 01-JAN-00:10 |
| NH3:Facility | 0.00 | 0.000 | 01-JAN-00:10 | 0.000 | 01-JAN-00:10 |
| NaturalGasEmissions:NH3 | 0.00 | 0.000 | 01-JAN-00:10 | 0.000 | 01-JAN-00:10 |
| NMVOC:Facility | 26.40 | 0.000 | 01-JAN-08:00 | 0.000 | 02-JAN-06:20 |
| NaturalGasEmissions:NMVOC | 0.41 | 0.000 | 01-JAN-00:40 | 0.000 | 07-JAN-07:20 |
| Hg:Facility | 0.01 | 0.000 | 01-JAN-08:00 | 0.000 | 02-JAN-06:20 |
| NaturalGasEmissions:Hg | 0.00 | 0.000 | 01-JAN-00:40 | 0.000 | 07-JAN-07:20 |
| Pb:Facility | 0.07 | 0.000 | 01-JAN-08:00 | 0.000 | 02-JAN-06:20 |
| NaturalGasEmissions:Pb | 0.00 | 0.000 | 01-JAN-00:40 | 0.000 | 07-JAN-07:20 |
| Nuclear High:Facility | 0.00 | 0.000 | 01-JAN-00:10 | 0.000 | 01-JAN-00:10 |
| NaturalGasEmissions:Nuclear High | 0.00 | 0.000 | 01-JAN-00:10 | 0.000 | 01-JAN-00:10 |
| ElectricEmissions:CO2 | 871551.87 | 0.006 | 01-JAN-08:00 | 0.106 | 02-JAN-06:20 |
| ElectricEmissions:CO | 302.51 | 0.000 | 01-JAN-08:00 | 0.000 | 02-JAN-06:20 |
| ElectricEmissions:CH4 | 1905.83 | 0.000 | 16-JAN-12:10 | 0.000 | 02-JAN-06:20 |
| ElectricEmissions:NOx | 1587.00 | 0.000 | 01-JAN-08:00 | 0.000 | 02-JAN-06:20 |
| ElectricEmissions:N2O | 20.48 | 0.000 | 01-JAN-08:00 | 0.000 | 02-JAN-06:20 |
| ElectricEmissions:SO2 | 4774.79 | 0.000 | 01-JAN-08:00 | 0.001 | 02-JAN-06:20 |
| ElectricEmissions:PM | 0.00 | 0.000 | 01-JAN-00:10 | 0.000 | 01-JAN-00:10 |
| ElectricEmissions:PM10 | 44.36 | 0.000 | 16-JAN-12:10 | 0.000 | 02-JAN-06:20 |
| ElectricEmissions:PM2.5 | 0.00 | 0.000 | 01-JAN-00:10 | 0.000 | 01-JAN-00:10 |
| ElectricEmissions:NH3 | 0.00 | 0.000 | 01-JAN-00:10 | 0.000 | 01-JAN-00:10 |
| ElectricEmissions:NMVOC | 25.99 | 0.000 | 01-JAN-08:00 | 0.000 | 02-JAN-06:20 |
| ElectricEmissions:Hg | 0.01 | 0.000 | 01-JAN-08:00 | 0.000 | 02-JAN-06:20 |
| ElectricEmissions:Pb | 0.07 | 0.000 | 01-JAN-08:00 | 0.000 | 02-JAN-06:20 |
| ElectricEmissions:Nuclear High | 0.00 | 0.000 | 01-JAN-00:10 | 0.000 | 01-JAN-00:10 |
| Carbon Equivalent:Facility | 253527.27 | 0.002 | 16-JAN-12:10 | 0.031 | 02-JAN-06:20 |
| CarbonEquivalentEmissions:Carbon Equivalent | 253527.27 | 0.002 | 16-JAN-12:10 | 0.031 | 02-JAN-06:20 |
| Annual Value [m3] | Minimum Value [m3/s] | Timestamp of Minimum {TIMESTAMP} | Maximum Value [m3/s] | Timestamp of Maximum {TIMESTAMP} | |
| Nuclear Low:Facility | 0.000 | 0.000 | 01-JAN-00:10 | 0.000 | 01-JAN-00:10 |
| NaturalGasEmissions:Nuclear Low | 0.000 | 0.000 | 01-JAN-00:10 | 0.000 | 01-JAN-00:10 |
| ElectricEmissions:Nuclear Low | 0.000 | 0.000 | 01-JAN-00:10 | 0.000 | 01-JAN-00:10 |
| Annual Value [L] | Minimum Value [L] | Timestamp of Minimum {TIMESTAMP} | Maximum Value [L] | Timestamp of Maximum {TIMESTAMP} | |
| WaterEnvironmentalFactors:Facility | 1099210.302 | 0.008 | 01-JAN-08:00 | 0.134 | 02-JAN-06:20 |
| NaturalGasEmissions:WaterEnvironmentalFactors | 0.000 | 0.000 | 01-JAN-00:10 | 0.000 | 01-JAN-00:10 |
| ElectricEmissions:WaterEnvironmentalFactors | 1099210.302 | 0.008 | 01-JAN-08:00 | 0.134 | 02-JAN-06:20 |
| Annual Value [GJ] | Minimum Value [W] | Timestamp of Minimum {TIMESTAMP} | Maximum Value [W] | Timestamp of Maximum {TIMESTAMP} | |
| PlantLoopHeatingDemand:Facility | 22.09 | 124.66 | 13-AUG-00:20 | 2725.28 | 14-FEB-12:10 |
| PlantLoopHeatingDemand:Plant | 22.09 | 124.66 | 13-AUG-00:20 | 2725.28 | 14-FEB-12:10 |
| WaterSystems:PlantLoopHeatingDemand | 22.09 | 124.66 | 13-AUG-00:20 | 2725.28 | 14-FEB-12:10 |
| Water Heater:WaterSystems:PlantLoopHeatingDemand | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| EnergyTransfer:Facility | 3297.76 | 124.66 | 13-AUG-08:30 | 529106.40 | 18-JUL-14:00 |
| EnergyTransfer:Building | 1649.86 | 0.00 | 01-JAN-00:40 | 237514.92 | 02-JAN-06:10 |
| EnergyTransfer:Zone:CORE_BOTTOM | 330.08 | 0.00 | 01-JAN-00:40 | 34259.31 | 19-JUL-08:00 |
| Heating:EnergyTransfer | 179.60 | 0.00 | 01-JAN-00:40 | 237514.92 | 02-JAN-06:10 |
| Heating:EnergyTransfer:Zone:CORE_BOTTOM | 3.44 | 0.00 | 01-JAN-00:10 | 33083.97 | 02-JAN-06:10 |
| Cooling:EnergyTransfer | 1470.26 | 0.00 | 01-JAN-00:40 | 177883.41 | 18-JUL-15:10 |
| Cooling:EnergyTransfer:Zone:CORE_BOTTOM | 326.64 | 0.00 | 01-JAN-00:40 | 34259.31 | 19-JUL-08:00 |
| EnergyTransfer:Zone:CORE_MID | 225.79 | 0.00 | 01-JAN-00:40 | 32367.91 | 02-JAN-06:10 |
| Heating:EnergyTransfer:Zone:CORE_MID | 3.89 | 0.00 | 01-JAN-00:10 | 32367.91 | 02-JAN-06:10 |
| Cooling:EnergyTransfer:Zone:CORE_MID | 221.91 | 0.00 | 01-JAN-00:40 | 26759.67 | 16-JUN-05:10 |
| EnergyTransfer:Zone:CORE_TOP | 208.67 | 0.00 | 01-JAN-00:40 | 33850.03 | 06-FEB-06:10 |
| Heating:EnergyTransfer:Zone:CORE_TOP | 8.75 | 0.00 | 01-JAN-00:40 | 33850.03 | 06-FEB-06:10 |
| Cooling:EnergyTransfer:Zone:CORE_TOP | 199.92 | 0.00 | 01-JAN-00:10 | 26658.58 | 21-JUL-05:10 |
| EnergyTransfer:Zone:FIRSTFLOOR_PLENUM | 38.28 | 0.00 | 01-JAN-00:40 | 12369.93 | 02-JAN-08:10 |
| Heating:EnergyTransfer:Zone:FIRSTFLOOR_PLENUM | 18.70 | 0.00 | 01-JAN-00:40 | 12369.93 | 02-JAN-08:10 |
| Cooling:EnergyTransfer:Zone:FIRSTFLOOR_PLENUM | 19.58 | 0.00 | 01-JAN-00:10 | 5062.36 | 16-JUL-21:10 |
| EnergyTransfer:Zone:MIDFLOOR_PLENUM | 37.21 | 0.00 | 01-JAN-00:40 | 13066.63 | 02-JAN-08:10 |
| Heating:EnergyTransfer:Zone:MIDFLOOR_PLENUM | 25.59 | 0.00 | 01-JAN-00:40 | 13066.63 | 02-JAN-08:10 |
| Cooling:EnergyTransfer:Zone:MIDFLOOR_PLENUM | 11.62 | 0.00 | 01-JAN-00:10 | 4384.87 | 28-JUL-05:20 |
| EnergyTransfer:Zone:PERIMETER_BOT_ZN_1 | 87.22 | 0.00 | 01-JAN-00:40 | 14143.53 | 28-SEP-12:30 |
| Heating:EnergyTransfer:Zone:PERIMETER_BOT_ZN_1 | 2.43 | 0.00 | 01-JAN-00:40 | 11055.79 | 07-JAN-06:10 |
| Cooling:EnergyTransfer:Zone:PERIMETER_BOT_ZN_1 | 84.79 | 0.00 | 01-JAN-00:10 | 14143.53 | 28-SEP-12:30 |
| EnergyTransfer:Zone:PERIMETER_BOT_ZN_2 | 53.89 | 0.00 | 01-JAN-00:40 | 9840.50 | 06-JUL-08:40 |
| Heating:EnergyTransfer:Zone:PERIMETER_BOT_ZN_2 | 2.01 | 0.00 | 01-JAN-00:40 | 7674.91 | 27-JAN-06:10 |
| Cooling:EnergyTransfer:Zone:PERIMETER_BOT_ZN_2 | 51.88 | 0.00 | 01-JAN-00:10 | 9840.50 | 06-JUL-08:40 |
| EnergyTransfer:Zone:PERIMETER_BOT_ZN_3 | 55.44 | 0.00 | 01-JAN-00:40 | 9295.69 | 21-FEB-06:10 |
| Heating:EnergyTransfer:Zone:PERIMETER_BOT_ZN_3 | 3.35 | 0.00 | 01-JAN-00:40 | 9295.69 | 21-FEB-06:10 |
| Cooling:EnergyTransfer:Zone:PERIMETER_BOT_ZN_3 | 52.09 | 0.00 | 01-JAN-00:10 | 7539.17 | 19-JUL-12:30 |
| EnergyTransfer:Zone:PERIMETER_BOT_ZN_4 | 53.56 | 0.00 | 01-JAN-00:40 | 9879.19 | 02-AUG-16:00 |
| Heating:EnergyTransfer:Zone:PERIMETER_BOT_ZN_4 | 2.14 | 0.00 | 01-JAN-00:40 | 7698.96 | 21-FEB-06:10 |
| Cooling:EnergyTransfer:Zone:PERIMETER_BOT_ZN_4 | 51.42 | 0.00 | 01-JAN-00:10 | 9879.19 | 02-AUG-16:00 |
| EnergyTransfer:Zone:PERIMETER_MID_ZN_1 | 81.82 | 0.00 | 01-JAN-00:40 | 12676.02 | 28-SEP-12:30 |
| Heating:EnergyTransfer:Zone:PERIMETER_MID_ZN_1 | 2.47 | 0.00 | 01-JAN-00:40 | 12337.44 | 06-FEB-06:10 |
| Cooling:EnergyTransfer:Zone:PERIMETER_MID_ZN_1 | 79.35 | 0.00 | 01-JAN-00:10 | 12676.02 | 28-SEP-12:30 |
| EnergyTransfer:Zone:PERIMETER_MID_ZN_2 | 51.76 | 0.00 | 01-JAN-00:40 | 9022.39 | 06-FEB-06:10 |
| Heating:EnergyTransfer:Zone:PERIMETER_MID_ZN_2 | 2.00 | 0.00 | 01-JAN-00:40 | 9022.39 | 06-FEB-06:10 |
| Cooling:EnergyTransfer:Zone:PERIMETER_MID_ZN_2 | 49.76 | 0.00 | 01-JAN-00:10 | 8821.96 | 06-JUL-08:50 |
| EnergyTransfer:Zone:PERIMETER_MID_ZN_3 | 56.65 | 0.00 | 01-JAN-00:40 | 9796.07 | 06-FEB-06:10 |
| Heating:EnergyTransfer:Zone:PERIMETER_MID_ZN_3 | 3.39 | 0.00 | 01-JAN-00:40 | 9796.07 | 06-FEB-06:10 |
| Cooling:EnergyTransfer:Zone:PERIMETER_MID_ZN_3 | 53.26 | 0.00 | 01-JAN-00:10 | 7605.11 | 19-JUL-14:30 |
| EnergyTransfer:Zone:PERIMETER_MID_ZN_4 | 51.78 | 0.00 | 01-JAN-00:40 | 8989.78 | 06-FEB-06:10 |
| Heating:EnergyTransfer:Zone:PERIMETER_MID_ZN_4 | 2.16 | 0.00 | 01-JAN-00:40 | 8989.78 | 06-FEB-06:10 |
| Cooling:EnergyTransfer:Zone:PERIMETER_MID_ZN_4 | 49.62 | 0.00 | 01-JAN-00:10 | 8932.65 | 02-AUG-16:00 |
| EnergyTransfer:Zone:PERIMETER_TOP_ZN_1 | 78.85 | 0.00 | 01-JAN-00:40 | 13644.20 | 06-FEB-06:10 |
| Heating:EnergyTransfer:Zone:PERIMETER_TOP_ZN_1 | 6.78 | 0.00 | 01-JAN-00:40 | 13644.20 | 06-FEB-06:10 |
| Cooling:EnergyTransfer:Zone:PERIMETER_TOP_ZN_1 | 72.07 | 0.00 | 01-JAN-00:10 | 12735.81 | 18-APR-13:30 |
| EnergyTransfer:Zone:PERIMETER_TOP_ZN_2 | 50.36 | 0.00 | 01-JAN-00:40 | 9905.79 | 06-FEB-06:10 |
| Heating:EnergyTransfer:Zone:PERIMETER_TOP_ZN_2 | 5.42 | 0.00 | 01-JAN-00:40 | 9905.79 | 06-FEB-06:10 |
| Cooling:EnergyTransfer:Zone:PERIMETER_TOP_ZN_2 | 44.94 | 0.00 | 01-JAN-00:10 | 8830.63 | 06-JUL-08:50 |
| EnergyTransfer:Zone:PERIMETER_TOP_ZN_3 | 57.47 | 0.00 | 01-JAN-00:40 | 14218.37 | 06-FEB-06:10 |
| Heating:EnergyTransfer:Zone:PERIMETER_TOP_ZN_3 | 9.77 | 0.00 | 01-JAN-00:40 | 14218.37 | 06-FEB-06:10 |
| Cooling:EnergyTransfer:Zone:PERIMETER_TOP_ZN_3 | 47.70 | 0.00 | 01-JAN-00:10 | 7809.92 | 17-JUL-14:30 |
| EnergyTransfer:Zone:PERIMETER_TOP_ZN_4 | 50.93 | 0.00 | 01-JAN-00:40 | 10193.11 | 06-FEB-06:10 |
| Heating:EnergyTransfer:Zone:PERIMETER_TOP_ZN_4 | 5.92 | 0.00 | 01-JAN-00:40 | 10193.11 | 06-FEB-06:10 |
| Cooling:EnergyTransfer:Zone:PERIMETER_TOP_ZN_4 | 45.01 | 0.00 | 01-JAN-00:10 | 8996.47 | 15-JUN-15:40 |
| EnergyTransfer:Zone:TOPFLOOR_PLENUM | 80.12 | 0.00 | 01-JAN-00:40 | 20478.95 | 06-FEB-06:20 |
| Heating:EnergyTransfer:Zone:TOPFLOOR_PLENUM | 71.40 | 0.00 | 01-JAN-00:40 | 20478.95 | 06-FEB-06:20 |
| Cooling:EnergyTransfer:Zone:TOPFLOOR_PLENUM | 8.72 | 0.00 | 01-JAN-00:10 | 5682.79 | 16-JUL-19:30 |
| EnergyTransfer:Plant | 22.09 | 124.66 | 13-AUG-00:20 | 2725.28 | 14-FEB-12:10 |
| WaterSystems:EnergyTransfer | 22.09 | 124.66 | 13-AUG-00:20 | 2725.28 | 14-FEB-12:10 |
| General:WaterSystems:EnergyTransfer | 22.09 | 124.66 | 13-AUG-00:20 | 2725.28 | 14-FEB-12:10 |
| EnergyTransfer:HVAC | 1625.81 | 0.00 | 01-JAN-00:40 | 350418.26 | 18-JUL-14:00 |
| HeatingCoils:EnergyTransfer | 346.20 | 0.00 | 01-JAN-00:40 | 284968.37 | 06-FEB-07:10 |
| CoolingCoils:EnergyTransfer | 1279.61 | 0.00 | 01-JAN-00:10 | 350418.26 | 18-JUL-14:00 |
| Source:Facility | 18260.72 | 133148.27 | 15-JAN-10:00 | 2200630.42 | 02-JAN-06:20 |
| NaturalGasEmissions:Source | 171.62 | 21.84 | 01-JAN-00:40 | 153476.27 | 07-JAN-07:20 |
| ElectricEmissions:Source | 9044.55 | 66563.21 | 01-JAN-08:00 | 1100304.29 | 02-JAN-06:20 |
| PurchasedElectricEmissions:Source | 9044.55 | 66563.21 | 15-JAN-10:00 | 1100304.29 | 02-JAN-06:20 |
| SoldElectricEmissions:Source | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
Report: Sensible Heat Gain Summary
For: Entire Facility
Timestamp: 2018-02-13 16:27:46
Annual Building Sensible Heat Gain Components| HVAC Zone Eq & Other Sensible Air Heating [GJ] | HVAC Zone Eq & Other Sensible Air Cooling [GJ] | HVAC Terminal Unit Sensible Air Heating [GJ] | HVAC Terminal Unit Sensible Air Cooling [GJ] | HVAC Input Heated Surface Heating [GJ] | HVAC Input Cooled Surface Cooling [GJ] | People Sensible Heat Addition [GJ] | Lights Sensible Heat Addition [GJ] | Equipment Sensible Heat Addition [GJ] | Window Heat Addition [GJ] | Interzone Air Transfer Heat Addition [GJ] | Infiltration Heat Addition [GJ] | Opaque Surface Conduction and Other Heat Addition [GJ] | Equipment Sensible Heat Removal [GJ] | Window Heat Removal [GJ] | Interzone Air Transfer Heat Removal [GJ] | Infiltration Heat Removal [GJ] | Opaque Surface Conduction and Other Heat Removal [GJ] | |
| CORE_BOTTOM | 0.000 | 0.000 | 0.271 | -326.770 | 0.000 | 0.000 | 37.142 | 119.678 | 342.768 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | -173.089 |
| CORE_MID | 0.000 | 0.000 | 0.689 | -222.029 | 0.000 | 0.000 | 38.606 | 119.678 | 178.020 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | -114.964 |
| CORE_TOP | 0.000 | 0.000 | 5.747 | -200.075 | 0.000 | 0.000 | 39.589 | 119.678 | 178.020 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | -142.959 |
| PERIMETER_BOT_ZN_1 | 0.000 | 0.000 | 1.759 | -84.805 | 0.000 | 0.000 | 8.304 | 25.229 | 37.528 | 80.098 | 0.000 | 0.201 | 0.000 | 0.000 | -26.974 | 0.000 | -13.457 | -27.884 |
| PERIMETER_BOT_ZN_2 | 0.000 | 0.000 | 1.587 | -51.889 | 0.000 | 0.000 | 5.402 | 15.972 | 23.758 | 39.831 | 0.000 | 0.161 | 0.000 | 0.000 | -17.959 | 0.000 | -8.662 | -8.202 |
| PERIMETER_BOT_ZN_3 | 0.000 | 0.000 | 2.675 | -52.110 | 0.000 | 0.000 | 8.403 | 25.229 | 37.528 | 25.225 | 0.000 | 0.221 | 0.001 | 0.000 | -28.667 | 0.000 | -13.005 | -5.499 |
| PERIMETER_BOT_ZN_4 | 0.000 | 0.000 | 1.713 | -51.430 | 0.000 | 0.000 | 5.474 | 15.971 | 23.757 | 39.132 | 0.000 | 0.164 | 0.000 | 0.000 | -18.482 | 0.000 | -8.706 | -7.592 |
| PERIMETER_MID_ZN_1 | 0.000 | 0.000 | 1.791 | -79.369 | 0.000 | 0.000 | 8.296 | 25.229 | 37.528 | 80.006 | 0.000 | 0.191 | 0.001 | 0.000 | -27.805 | 0.000 | -13.739 | -32.128 |
| PERIMETER_MID_ZN_2 | 0.000 | 0.000 | 1.565 | -49.773 | 0.000 | 0.000 | 5.367 | 15.972 | 23.758 | 39.651 | 0.000 | 0.145 | 0.000 | 0.000 | -18.571 | 0.000 | -8.907 | -9.207 |
| PERIMETER_MID_ZN_3 | 0.000 | 0.000 | 2.711 | -53.279 | 0.000 | 0.000 | 8.393 | 25.229 | 37.528 | 25.038 | 0.000 | 0.208 | 0.000 | 0.000 | -29.614 | 0.000 | -13.362 | -2.852 |
| PERIMETER_MID_ZN_4 | 0.000 | 0.000 | 1.725 | -49.632 | 0.000 | 0.000 | 5.428 | 15.971 | 23.757 | 38.942 | 0.000 | 0.148 | 0.000 | 0.000 | -19.112 | 0.000 | -8.938 | -8.288 |
| PERIMETER_TOP_ZN_1 | 0.000 | 0.000 | 6.135 | -72.086 | 0.000 | 0.000 | 8.387 | 25.229 | 37.528 | 80.537 | 0.000 | 0.193 | 0.000 | 0.000 | -26.457 | 0.000 | -13.018 | -46.450 |
| PERIMETER_TOP_ZN_2 | 0.000 | 0.000 | 5.012 | -44.947 | 0.000 | 0.000 | 5.404 | 15.972 | 23.758 | 39.950 | 0.000 | 0.148 | 0.000 | 0.000 | -17.678 | 0.000 | -8.472 | -19.147 |
| PERIMETER_TOP_ZN_3 | 0.000 | 0.000 | 9.118 | -47.721 | 0.000 | 0.000 | 8.478 | 25.229 | 37.528 | 25.451 | 0.000 | 0.210 | 0.000 | 0.000 | -28.102 | 0.000 | -12.688 | -17.504 |
| PERIMETER_TOP_ZN_4 | 0.000 | 0.000 | 5.512 | -45.021 | 0.000 | 0.000 | 5.460 | 15.971 | 23.757 | 39.215 | 0.000 | 0.151 | 0.000 | 0.000 | -18.213 | 0.000 | -8.505 | -18.327 |
| FIRSTFLOOR_PLENUM | 18.702 | -19.574 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.248 | 21.812 | 0.000 | 0.000 | 0.000 | -21.187 | -0.000 |
| MIDFLOOR_PLENUM | 25.587 | -11.619 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.218 | 6.633 | 0.000 | 0.000 | 0.000 | -20.818 | -0.000 |
| TOPFLOOR_PLENUM | 71.403 | -8.715 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.860 | 85.732 | 0.000 | 0.000 | 0.000 | -150.281 | 0.000 |
| Total Facility | 115.692 | -39.908 | 48.009 | -1430.934 | 0.000 | 0.000 | 198.131 | 606.239 | 1066.523 | 553.077 | 0.000 | 4.468 | 114.180 | 0.000 | -277.635 | 0.000 | -323.745 | -634.093 |
| Time of Peak {TIMESTAMP} | HVAC Zone Eq & Other Sensible Air Heating [W] | HVAC Zone Eq & Other Sensible Air Cooling [W] | HVAC Terminal Unit Sensible Air Heating [W] | HVAC Terminal Unit Sensible Air Cooling [W] | HVAC Input Heated Surface Heating [W] | HVAC Input Cooled Surface Cooling [W] | People Sensible Heat Addition [W] | Lights Sensible Heat Addition [W] | Equipment Sensible Heat Addition [W] | Window Heat Addition [W] | Interzone Air Transfer Heat Addition [W] | Infiltration Heat Addition [W] | Opaque Surface Conduction and Other Heat Addition [W] | Equipment Sensible Heat Removal [W] | Window Heat Removal [W] | Interzone Air Transfer Heat Removal [W] | Infiltration Heat Removal [W] | Opaque Surface Conduction and Other Heat Removal [W] | |
| CORE_BOTTOM | 28-JUL-05:02 | 0.00 | 0.00 | 0.00 | -55650.85 | 0.00 | 0.00 | 293.46 | 1058.29 | 4233.14 | 0.00 | 0.00 | 0.00 | 50065.96 | 0.00 | -0.00 | 0.00 | 0.00 | 0.00 |
| CORE_MID | 04-AUG-05:04 | 0.00 | 0.00 | 0.00 | -47640.80 | 0.00 | 0.00 | 283.68 | 1058.29 | 4233.14 | 0.00 | 0.00 | 0.00 | 42065.70 | 0.00 | -0.00 | 0.00 | 0.00 | 0.00 |
| CORE_TOP | 18-JUL-05:04 | 0.00 | 0.00 | 0.00 | -49347.38 | 0.00 | 0.00 | 282.87 | 1058.29 | 4233.14 | 0.00 | 0.00 | 0.00 | 43773.08 | 0.00 | -0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_BOT_ZN_1 | 16-APR-13:12 | 0.00 | 0.00 | 0.00 | -19097.61 | 0.00 | 0.00 | 0.00 | 111.55 | 669.29 | 15174.69 | 0.00 | 156.30 | 2985.78 | 0.00 | -0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_BOT_ZN_2 | 16-JUL-08:32 | 0.00 | 0.00 | 0.00 | -13913.13 | 0.00 | 0.00 | 0.00 | 70.62 | 423.71 | 11237.27 | 0.00 | 78.74 | 2102.78 | 0.00 | -0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_BOT_ZN_3 | 06-JUL-05:02 | 0.00 | 0.00 | 0.00 | -12683.92 | 0.00 | 0.00 | 61.57 | 223.10 | 892.38 | 3576.52 | 0.00 | 0.00 | 7963.32 | 0.00 | -0.00 | 0.00 | -32.97 | 0.00 |
| PERIMETER_BOT_ZN_4 | 16-JUL-16:32 | 0.00 | 0.00 | 0.00 | -13876.72 | 0.00 | 0.00 | 0.00 | 70.61 | 423.69 | 10578.37 | 0.00 | 183.66 | 2620.40 | 0.00 | -0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_MID_ZN_1 | 16-APR-13:02 | 0.00 | 0.00 | 0.00 | -16322.26 | 0.00 | 0.00 | 0.00 | 111.55 | 669.29 | 15468.86 | 0.00 | 152.89 | 0.00 | 0.00 | -0.00 | 0.00 | 0.00 | -80.32 |
| PERIMETER_MID_ZN_2 | 16-JUL-09:02 | 0.00 | 0.00 | 0.00 | -11507.92 | 0.00 | 0.00 | 0.00 | 70.62 | 423.71 | 10824.89 | 0.00 | 104.03 | 84.67 | 0.00 | -0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_MID_ZN_3 | 15-JUN-05:02 | 0.00 | 0.00 | 0.00 | -12665.76 | 0.00 | 0.00 | 62.02 | 223.10 | 892.38 | 2640.04 | 0.00 | 0.00 | 8876.02 | 0.00 | -0.00 | 0.00 | -27.81 | 0.00 |
| PERIMETER_MID_ZN_4 | 16-JUL-16:22 | 0.00 | 0.00 | 0.00 | -11791.23 | 0.00 | 0.00 | 0.00 | 70.61 | 423.69 | 10918.90 | 0.00 | 185.26 | 192.77 | 0.00 | -0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_TOP_ZN_1 | 16-APR-13:02 | 0.00 | 0.00 | 0.00 | -16780.03 | 0.00 | 0.00 | 0.00 | 111.55 | 669.29 | 15457.56 | 0.00 | 151.26 | 390.38 | 0.00 | -0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_TOP_ZN_2 | 16-JUL-09:02 | 0.00 | 0.00 | 0.00 | -11902.21 | 0.00 | 0.00 | 0.00 | 70.62 | 423.71 | 10814.84 | 0.00 | 102.67 | 490.37 | 0.00 | -0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_TOP_ZN_3 | 15-JUN-05:02 | 0.00 | 0.00 | 0.00 | -12867.79 | 0.00 | 0.00 | 61.20 | 223.10 | 892.38 | 2628.74 | 0.00 | 0.00 | 9091.70 | 0.00 | -0.00 | 0.00 | -29.32 | 0.00 |
| PERIMETER_TOP_ZN_4 | 16-JUL-16:22 | 0.00 | 0.00 | 0.00 | -12443.26 | 0.00 | 0.00 | 0.00 | 70.61 | 423.69 | 10902.41 | 0.00 | 183.50 | 863.05 | 0.00 | -0.00 | 0.00 | 0.00 | 0.00 |
| FIRSTFLOOR_PLENUM | 05-AUG-05:10 | 0.00 | -5989.64 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 6068.35 | 0.00 | -0.00 | 0.00 | -78.71 | 0.00 |
| MIDFLOOR_PLENUM | 06-JUL-05:04 | 0.00 | -6001.79 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 6077.19 | 0.00 | -0.00 | 0.00 | -75.39 | 0.00 |
| TOPFLOOR_PLENUM | 16-JUL-17:10 | 0.00 | -6432.31 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 3571.47 | 2860.84 | 0.00 | -0.00 | 0.00 | 0.00 | 0.00 |
| Total Facility | 15-JUN-05:02 | 0.00 | 16298.44 | 0.00 | -274082.49 | 0.00 | 0.00 | 1488.06 | 5360.83 | 21443.33 | 18467.72 | 0.00 | 0.00 | 212085.50 | 0.00 | 0.00 | 0.00 | -1061.40 | 0.00 |
| Time of Peak {TIMESTAMP} | HVAC Zone Eq & Other Sensible Air Heating [W] | HVAC Zone Eq & Other Sensible Air Cooling [W] | HVAC Terminal Unit Sensible Air Heating [W] | HVAC Terminal Unit Sensible Air Cooling [W] | HVAC Input Heated Surface Heating [W] | HVAC Input Cooled Surface Cooling [W] | People Sensible Heat Addition [W] | Lights Sensible Heat Addition [W] | Equipment Sensible Heat Addition [W] | Window Heat Addition [W] | Interzone Air Transfer Heat Addition [W] | Infiltration Heat Addition [W] | Opaque Surface Conduction and Other Heat Addition [W] | Equipment Sensible Heat Removal [W] | Window Heat Removal [W] | Interzone Air Transfer Heat Removal [W] | Infiltration Heat Removal [W] | Opaque Surface Conduction and Other Heat Removal [W] | |
| CORE_BOTTOM | 02-JAN-06:02 | 0.00 | 0.00 | 41601.81 | -0.00 | 0.00 | 0.00 | 527.77 | 1058.29 | 4233.14 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | 0.00 | 0.00 | -47421.01 |
| CORE_MID | 02-JAN-06:02 | 0.00 | 0.00 | 34208.17 | -0.00 | 0.00 | 0.00 | 530.67 | 1058.29 | 4233.14 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | 0.00 | 0.00 | -40030.27 |
| CORE_TOP | 02-JAN-06:02 | 0.00 | 0.00 | 35441.73 | -0.00 | 0.00 | 0.00 | 539.79 | 1058.29 | 4233.14 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | 0.00 | 0.00 | -41272.95 |
| PERIMETER_BOT_ZN_1 | 06-FEB-06:02 | 0.00 | 0.00 | 13914.83 | -0.00 | 0.00 | 0.00 | 113.17 | 223.10 | 892.38 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -3548.43 | 0.00 | -560.11 | -11034.95 |
| PERIMETER_BOT_ZN_2 | 06-FEB-06:02 | 0.00 | 0.00 | 10786.40 | -0.00 | 0.00 | 0.00 | 71.65 | 141.24 | 564.95 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -2353.84 | 0.00 | -377.46 | -8832.95 |
| PERIMETER_BOT_ZN_3 | 06-FEB-05:12 | 0.00 | 0.00 | 10421.49 | -0.00 | 0.00 | 0.00 | 0.00 | 223.10 | 892.38 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -3509.32 | 0.00 | -2128.08 | -5899.57 |
| PERIMETER_BOT_ZN_4 | 21-FEB-06:02 | 0.00 | 0.00 | 11135.43 | -0.00 | 0.00 | 0.00 | 72.60 | 141.23 | 564.92 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -1715.53 | 0.00 | -263.08 | -9935.57 |
| PERIMETER_MID_ZN_1 | 06-FEB-06:02 | 0.00 | 0.00 | 13489.31 | -0.00 | 0.00 | 0.00 | 115.77 | 223.10 | 892.38 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -3595.17 | 0.00 | -550.44 | -10574.95 |
| PERIMETER_MID_ZN_2 | 06-FEB-06:02 | 0.00 | 0.00 | 10381.53 | -0.00 | 0.00 | 0.00 | 74.33 | 141.24 | 564.95 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -2369.46 | 0.00 | -366.12 | -8426.48 |
| PERIMETER_MID_ZN_3 | 06-FEB-06:02 | 0.00 | 0.00 | 10351.61 | -0.00 | 0.00 | 0.00 | 117.21 | 223.10 | 892.38 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -3551.37 | 0.00 | -535.95 | -7496.98 |
| PERIMETER_MID_ZN_4 | 06-FEB-06:02 | 0.00 | 0.00 | 10672.92 | -0.00 | 0.00 | 0.00 | 74.14 | 141.23 | 564.92 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -2370.47 | 0.00 | -367.80 | -8714.93 |
| PERIMETER_TOP_ZN_1 | 06-FEB-05:22 | 0.00 | 0.00 | 14856.14 | -0.00 | 0.00 | 0.00 | 0.00 | 223.10 | 892.38 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -3476.48 | 0.00 | -2122.58 | -10372.56 |
| PERIMETER_TOP_ZN_2 | 06-FEB-05:22 | 0.00 | 0.00 | 10962.53 | -0.00 | 0.00 | 0.00 | 0.00 | 141.24 | 564.95 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -2299.76 | 0.00 | -1420.34 | -7948.62 |
| PERIMETER_TOP_ZN_3 | 06-FEB-05:22 | 0.00 | 0.00 | 15147.74 | -0.00 | 0.00 | 0.00 | 0.00 | 223.10 | 892.38 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -3451.72 | 0.00 | -2114.81 | -10696.69 |
| PERIMETER_TOP_ZN_4 | 06-FEB-06:02 | 0.00 | 0.00 | 11214.62 | -0.00 | 0.00 | 0.00 | 76.36 | 141.23 | 564.92 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -2282.78 | 0.00 | -355.94 | -9358.41 |
| FIRSTFLOOR_PLENUM | 02-JAN-08:65 | 12586.67 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | 0.00 | -379.51 | -12207.16 |
| MIDFLOOR_PLENUM | 02-JAN-08:65 | 13266.08 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | 0.00 | -369.92 | -12896.16 |
| TOPFLOOR_PLENUM | 06-FEB-06:10 | 22540.93 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | 0.00 | -6396.25 | -16144.68 |
| Total Facility | 06-FEB-06:02 | 17453.05 | 0.00 | 248579.40 | 0.00 | 0.00 | 0.00 | 2670.50 | 5360.83 | 21443.33 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -35074.16 | 0.00 | -12858.09 | -247574.85 |
Report: Standard 62.1 Summary
For: Entire Facility
Timestamp: 2018-02-13 16:27:46
System Ventilation Requirements for Cooling| Sum of Zone Primary Air Flow - Vpz-sum [m3/s] | System Population - Ps | Sum of Zone Population - Pz-sum | Occupant Diversity - D | Uncorrected Outdoor Air Intake Airflow - Vou [m3/s] | System Primary Airflow - Vps [m3/s] | Average Outdoor Air Fraction - Xs | System Ventilation Efficiency - Ev | Outdoor Air Intake Flow - Vot [m3/s] | Percent Outdoor Air - %OA | |
| VAV_1 | 8.571 | 89.38 | 89.38 | 1.00 | 1.1173 | 8.571 | 1.000 | 1.000 | 1.1173 | 0.13 |
| VAV_2 | 7.565 | 89.38 | 89.38 | 1.00 | 1.1173 | 7.565 | 1.000 | 1.000 | 1.1173 | 0.15 |
| VAV_3 | 7.635 | 89.38 | 89.38 | 1.00 | 1.1173 | 7.635 | 1.000 | 1.000 | 1.1173 | 0.15 |
| Sum of Zone Primary Air Flow - Vpz-sum [m3/s] | System Population - Ps | Sum of Zone Population - Pz-sum | Occupant Diversity - D | Uncorrected Outdoor Air Intake Airflow - Vou [m3/s] | System Primary Airflow - Vps [m3/s] | Average Outdoor Air Fraction - Xs | System Ventilation Efficiency - Ev | Outdoor Air Intake Flow Vot [m3/s] | Percent Outdoor Air - %OA | |
| VAV_1 | 1.530 | 89.38 | 89.38 | 1.00 | 1.1173 | 1.530 | 0.730 | 1.000 | 1.1173 | 0.73 |
| VAV_2 | 1.562 | 89.38 | 89.38 | 1.00 | 1.1173 | 1.562 | 0.715 | 1.000 | 1.1173 | 0.72 |
| VAV_3 | 2.123 | 89.38 | 89.38 | 1.00 | 1.1173 | 2.123 | 0.526 | 1.000 | 1.1173 | 0.53 |
| AirLoop Name | People Outdoor Air Rate - Rp [m3/s-person] | Zone Population - Pz | Area Outdoor Air Rate - Ra [m3/s-m2] | Zone Floor Area - Az [m2] | Breathing Zone Outdoor Airflow - Vbz [m3/s] | Cooling Zone Air Distribution Effectiveness - Ez-clg | Cooling Zone Outdoor Airflow - Voz-clg [m3/s] | Heating Zone Air Distribution Effectiveness - Ez-htg | Heating Zone Outdoor Airflow - Voz-htg [m3/s] | |
| CORE_BOTTOM | VAV_1 | 0.012500 | 52.94 | 0.000000 | 983.54 | 0.6617 | 1.000 | 0.6617 | 1.000 | 0.6617 |
| CORE_MID | VAV_2 | 0.012500 | 52.94 | 0.000000 | 983.54 | 0.6617 | 1.000 | 0.6617 | 1.000 | 0.6617 |
| CORE_TOP | VAV_3 | 0.012500 | 52.94 | 0.000000 | 983.54 | 0.6617 | 1.000 | 0.6617 | 1.000 | 0.6617 |
| PERIMETER_BOT_ZN_1 | VAV_1 | 0.012500 | 11.16 | 0.000000 | 207.34 | 0.1395 | 1.000 | 0.1395 | 1.000 | 0.1395 |
| PERIMETER_BOT_ZN_2 | VAV_1 | 0.012500 | 7.06 | 0.000000 | 131.26 | 0.0883 | 1.000 | 0.0883 | 1.000 | 0.0883 |
| PERIMETER_BOT_ZN_3 | VAV_1 | 0.012500 | 11.16 | 0.000000 | 207.34 | 0.1395 | 1.000 | 0.1395 | 1.000 | 0.1395 |
| PERIMETER_BOT_ZN_4 | VAV_1 | 0.012500 | 7.06 | 0.000000 | 131.25 | 0.0883 | 1.000 | 0.0883 | 1.000 | 0.0883 |
| PERIMETER_MID_ZN_1 | VAV_2 | 0.012500 | 11.16 | 0.000000 | 207.34 | 0.1395 | 1.000 | 0.1395 | 1.000 | 0.1395 |
| PERIMETER_MID_ZN_2 | VAV_2 | 0.012500 | 7.06 | 0.000000 | 131.26 | 0.0883 | 1.000 | 0.0883 | 1.000 | 0.0883 |
| PERIMETER_MID_ZN_3 | VAV_2 | 0.012500 | 11.16 | 0.000000 | 207.34 | 0.1395 | 1.000 | 0.1395 | 1.000 | 0.1395 |
| PERIMETER_MID_ZN_4 | VAV_2 | 0.012500 | 7.06 | 0.000000 | 131.25 | 0.0883 | 1.000 | 0.0883 | 1.000 | 0.0883 |
| PERIMETER_TOP_ZN_1 | VAV_3 | 0.012500 | 11.16 | 0.000000 | 207.34 | 0.1395 | 1.000 | 0.1395 | 1.000 | 0.1395 |
| PERIMETER_TOP_ZN_2 | VAV_3 | 0.012500 | 7.06 | 0.000000 | 131.26 | 0.0883 | 1.000 | 0.0883 | 1.000 | 0.0883 |
| PERIMETER_TOP_ZN_3 | VAV_3 | 0.012500 | 11.16 | 0.000000 | 207.34 | 0.1395 | 1.000 | 0.1395 | 1.000 | 0.1395 |
| PERIMETER_TOP_ZN_4 | VAV_3 | 0.012500 | 7.06 | 0.000000 | 131.25 | 0.0883 | 1.000 | 0.0883 | 1.000 | 0.0883 |
| People Outdoor Air Rate - Rp [m3/s-person] | Sum of Zone Population - Pz-sum | Area Outdoor Air Rate - Ra [m3/s-m2] | Sum of Zone Floor Area - Az-sum [m2] | Breathing Zone Outdoor Airflow - Vbz [m3/s] | Cooling Zone Outdoor Airflow - Voz-clg [m3/s] | Heating Zone Outdoor Airflow - Voz-htg [m3/s] | |
| VAV_1 | 0.012500 | 89.38 | 0.000000 | 1660.73 | 1.1173 | 1.1173 | 1.1173 |
| VAV_2 | 0.012500 | 89.38 | 0.000000 | 1660.73 | 1.1173 | 1.1173 | 1.1173 |
| VAV_3 | 0.012500 | 89.38 | 0.000000 | 1660.73 | 1.1173 | 1.1173 | 1.1173 |
| AirLoop Name | Box Type | Zone Primary Airflow - Vpz [m3/s] | Zone Discharge Airflow - Vdz [m3/s] | Minimum Zone Primary Airflow - Vpz-min [m3/s] | Zone Outdoor Airflow Cooling - Voz-clg [m3/s] | Primary Outdoor Air Fraction - Zpz | Primary Air Fraction - Ep | Secondary Recirculation Fraction- Er | Supply Air Fraction- Fa | Mixed Air Fraction - Fb | Outdoor Air Fraction - Fc | Zone Ventilation Efficiency - Evz | |
| CORE_BOTTOM | VAV_1 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 4.083 | 4.0825 | 0.8165 | 0.6617 | 0.000 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| CORE_MID | VAV_2 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 3.299 | 3.2992 | 0.7495 | 0.6617 | 0.000 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| CORE_TOP | VAV_3 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 3.343 | 3.3433 | 0.7495 | 0.6617 | 0.000 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| PERIMETER_BOT_ZN_1 | VAV_1 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 1.365 | 1.3646 | 0.2729 | 0.1395 | 0.000 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| PERIMETER_BOT_ZN_2 | VAV_1 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 1.074 | 1.0735 | 0.2147 | 0.0883 | 0.000 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| PERIMETER_BOT_ZN_3 | VAV_1 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.944 | 0.9439 | 0.1888 | 0.1395 | 0.000 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| PERIMETER_BOT_ZN_4 | VAV_1 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 1.107 | 1.1067 | 0.2213 | 0.0883 | 0.000 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| PERIMETER_MID_ZN_1 | VAV_2 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 1.291 | 1.2914 | 0.2583 | 0.1395 | 0.000 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| PERIMETER_MID_ZN_2 | VAV_2 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.991 | 0.9910 | 0.1982 | 0.0883 | 0.000 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| PERIMETER_MID_ZN_3 | VAV_2 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.958 | 0.9582 | 0.1916 | 0.1395 | 0.000 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| PERIMETER_MID_ZN_4 | VAV_2 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 1.025 | 1.0248 | 0.2050 | 0.0883 | 0.000 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| PERIMETER_TOP_ZN_1 | VAV_3 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 1.297 | 1.2972 | 0.2594 | 0.1395 | 0.000 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| PERIMETER_TOP_ZN_2 | VAV_3 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.996 | 0.9958 | 0.1992 | 0.0883 | 0.000 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| PERIMETER_TOP_ZN_3 | VAV_3 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.967 | 0.9670 | 0.1934 | 0.1395 | 0.000 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| PERIMETER_TOP_ZN_4 | VAV_3 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 1.032 | 1.0322 | 0.2064 | 0.0883 | 0.000 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| Sum of Zone Primary Airflow - Vpz-sum [m3/s] | System Primary Airflow - Vps [m3/s] | Sum of Zone Discharge Airflow - Vdz-sum [m3/s] | Sum of Min Zone Primary Airflow - Vpz-min [m3/s] | Zone Outdoor Airflow Cooling - Voz-clg [m3/s] | Zone Ventilation Efficiency - Evz-min | |
| VAV_1 | 8.57 | 8.571 | 8.57 | 1.7142 | 1.1173 | 1.000 |
| VAV_2 | 7.56 | 7.565 | 7.56 | 1.6025 | 1.1173 | 1.000 |
| VAV_3 | 7.64 | 7.635 | 7.64 | 1.6079 | 1.1173 | 1.000 |
| AirLoop Name | Box Type | Zone Primary Airflow - Vpz [m3/s] | Zone Discharge Airflow - Vdz [m3/s] | Minimum Zone Primary Airflow - Vpz-min [m3/s] | Zone Outdoor Airflow Heating - Voz-htg [m3/s] | Primary Outdoor Air Fraction - Zpz | Primary Air Fraction - Ep | Secondary Recirculation Fraction- Er | Supply Air Fraction- Fa | Mixed Air Fraction - Fb | Outdoor Air Fraction - Fc | Zone Ventilation Efficiency - Evz | |
| CORE_BOTTOM | VAV_1 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.662 | 0.662 | 0.662 | 0.6617 | 1.000 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| CORE_MID | VAV_2 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.662 | 0.662 | 0.662 | 0.6617 | 1.000 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| CORE_TOP | VAV_3 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.795 | 0.795 | 0.795 | 0.6617 | 0.832 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| PERIMETER_BOT_ZN_1 | VAV_1 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.261 | 0.261 | 0.261 | 0.1395 | 0.534 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| PERIMETER_BOT_ZN_2 | VAV_1 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.174 | 0.174 | 0.174 | 0.0883 | 0.508 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| PERIMETER_BOT_ZN_3 | VAV_1 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.259 | 0.259 | 0.259 | 0.1395 | 0.538 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| PERIMETER_BOT_ZN_4 | VAV_1 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.174 | 0.174 | 0.174 | 0.0883 | 0.508 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| PERIMETER_MID_ZN_1 | VAV_2 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.272 | 0.272 | 0.272 | 0.1395 | 0.513 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| PERIMETER_MID_ZN_2 | VAV_2 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.180 | 0.180 | 0.180 | 0.0883 | 0.492 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| PERIMETER_MID_ZN_3 | VAV_2 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.269 | 0.269 | 0.269 | 0.1395 | 0.519 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| PERIMETER_MID_ZN_4 | VAV_2 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.180 | 0.180 | 0.180 | 0.0883 | 0.491 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| PERIMETER_TOP_ZN_1 | VAV_3 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.402 | 0.402 | 0.402 | 0.1395 | 0.347 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| PERIMETER_TOP_ZN_2 | VAV_3 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.262 | 0.262 | 0.262 | 0.0883 | 0.337 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| PERIMETER_TOP_ZN_3 | VAV_3 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.401 | 0.401 | 0.401 | 0.1395 | 0.348 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| PERIMETER_TOP_ZN_4 | VAV_3 | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.263 | 0.263 | 0.263 | 0.0883 | 0.336 | 1.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 |
| Sum of Zone Primary Airflow - Vpz-sum [m3/s] | System Primary Airflow - Vps [m3/s] | Sum of Zone Discharge Airflow - Vdz-sum [m3/s] | Sum of Min Zone Primary Airflow - Vpz-min [m3/s] | Zone Outdoor Airflow Heating - Voz-htg [m3/s] | Zone Ventilation Efficiency - Evz-min | |
| VAV_1 | 1.53 | 1.530 | 1.53 | 1.53 | 1.1173 | 1.000 |
| VAV_2 | 1.56 | 1.562 | 1.56 | 1.56 | 1.1173 | 1.000 |
| VAV_3 | 2.12 | 2.123 | 2.12 | 2.12 | 1.1173 | 1.000 |
Report: LEED Summary
For: Entire Facility
Timestamp: 2018-02-13 16:27:46
Sec1.1A-General Information| Data | |
| Weather File | ANNUAL ** Chicago Ohare Intl Ap IL USA TMY3 WMO#=725300 |
| Total gross floor area [m2] | 4982.19 |
| Principal Heating Source | Electricity |
| Space Area [m2] | Regularly Occupied Area [m2] | Unconditioned Area [m2] | Typical Hours/Week in Operation [hr/wk] | |
| CORE_BOTTOM | 983.54 | 983.54 | 0.00 | 97.75 |
| CORE_MID | 983.54 | 983.54 | 0.00 | 97.75 |
| CORE_TOP | 983.54 | 983.54 | 0.00 | 97.75 |
| PERIMETER_BOT_ZN_1 | 207.34 | 207.34 | 0.00 | 97.75 |
| PERIMETER_BOT_ZN_2 | 131.26 | 131.26 | 0.00 | 97.75 |
| PERIMETER_BOT_ZN_3 | 207.34 | 207.34 | 0.00 | 97.75 |
| PERIMETER_BOT_ZN_4 | 131.25 | 131.25 | 0.00 | 97.75 |
| PERIMETER_MID_ZN_1 | 207.34 | 207.34 | 0.00 | 97.75 |
| PERIMETER_MID_ZN_2 | 131.26 | 131.26 | 0.00 | 97.75 |
| PERIMETER_MID_ZN_3 | 207.34 | 207.34 | 0.00 | 97.75 |
| PERIMETER_MID_ZN_4 | 131.25 | 131.25 | 0.00 | 97.75 |
| PERIMETER_TOP_ZN_1 | 207.34 | 207.34 | 0.00 | 97.75 |
| PERIMETER_TOP_ZN_2 | 131.26 | 131.26 | 0.00 | 97.75 |
| PERIMETER_TOP_ZN_3 | 207.34 | 207.34 | 0.00 | 97.75 |
| PERIMETER_TOP_ZN_4 | 131.25 | 131.25 | 0.00 | 97.75 |
| FIRSTFLOOR_PLENUM | 1660.73 | 1660.73 | 0.00 | 0.00 |
| MIDFLOOR_PLENUM | 1660.73 | 1660.73 | 0.00 | 0.00 |
| TOPFLOOR_PLENUM | 1660.73 | 1660.73 | 0.00 | 0.00 |
| Totals | 4982.19 | 4982.19 | 0.00 |
| Data | |
| Number of hours heating loads not met | 9.67 |
| Number of hours cooling loads not met | 0.17 |
| Number of hours not met | 9.83 |
| Utility Rate | Virtual Rate [$/unit energy] | Units of Energy | Units of Demand | |
| None |
| Electric Energy Use [GJ] | Electric Demand [W] | Natural Gas Energy Use [GJ] | Natural Gas Demand [W] | Additional Energy Use [GJ] | Additional Demand [W] | |
| Interior Lighting | 606.24 | 5360.83 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 232.57 | 14804.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Space Heating | 249.37 | 264838.71 | 121.05 | 134026.18 | 0.00 | 0.00 |
| Space Cooling | 317.08 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 0.27 | 8.44 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans-Interior | 78.60 | 3839.19 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans-Parking Garage | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Service Water Heating | 0.00 | 0.00 | 36.11 | 6519.86 | 0.00 | 0.00 |
| Receptacle Equipment | 1066.52 | 21443.33 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting-Process | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooking | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Industrial Process | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Elevators and Escalators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total Line | 2550.63 | 157.16 | 0.00 |
| Process Subtotal [GJ] | Total Energy Use [GJ] | |
| Electricity | 1066.52 | 2550.63 |
| Natural Gas | 0.00 | 157.16 |
| Additional | 0.00 | 0.00 |
| Total | 1066.52 | 2707.79 |
| Process Subtotal [$] | Total Energy Cost [$] | |
| Electricity | 0.00 | |
| Natural Gas | 0.00 | |
| Additional | 0.00 | |
| Total | 0.00 |
| Rated Capacity [kW] | Annual Energy Generated [GJ] | |
| Photovoltaic | 0.00 | 0.00 |
| Wind | 0.00 | 0.00 |
| Electricty [MJ/m2] | |
| Interior Lighting | 121.68 |
| Space Heating | 50.05 |
| Space Cooling | 63.64 |
| Fans-Interior | 15.78 |
| Service Water Heating | 0.00 |
| Receptacle Equipment | 214.07 |
| Miscellaneous | 46.73 |
| Subtotal | 511.95 |
| Natural Gas [MJ/m2] | |
| Space Heating | 24.30 |
| Service Water Heating | 7.25 |
| Miscellaneous | -0.00 |
| Subtotal | 31.54 |
| Additional [MJ/m2] | |
| Miscellaneous | 0.00 |
| Subtotal | 0.00 |
| Percent [%] | |
| Interior Lighting | 22.39 |
| Space Heating | 13.68 |
| Space Cooling | 11.71 |
| Fans-Interior | 2.90 |
| Service Water Heating | 1.33 |
| Receptacle Equipment | 39.39 |
| Miscellaneous | 8.60 |
Report: Component Sizing Summary
For: Entire Facility
Timestamp: 2018-02-13 16:27:46
AirTerminal:SingleDuct:VAV:Reheat| Design Size Maximum Air Flow Rate [m3/s] | Design Size Constant Minimum Air Flow Fraction | User-Specified Constant Minimum Air Flow Fraction | Design Size Minimum Air Flow Rate [m3/s] | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | Design Size Maximum Flow Fraction during Reheat [] | |
| CORE_BOTTOM VAV BOX COMPONENT | 4.08 | 0.200000 | 0.300000 | 1.22 | 0.001245 | 0.300000 |
| CORE_MID VAV BOX COMPONENT | 3.30 | 0.200000 | 0.300000 | 0.989750 | 0.001006 | 0.300000 |
| CORE_TOP VAV BOX COMPONENT | 3.34 | 0.200000 | 0.300000 | 1.00 | 0.001020 | 0.300000 |
| PERIMETER_BOT_ZN_1 VAV BOX COMPONENT | 1.36 | 0.200000 | 0.300000 | 0.409368 | 0.001974 | 0.300000 |
| PERIMETER_BOT_ZN_2 VAV BOX COMPONENT | 1.07 | 0.200000 | 0.300000 | 0.322063 | 0.002454 | 0.300000 |
| PERIMETER_BOT_ZN_3 VAV BOX COMPONENT | 0.943855 | 0.200000 | 0.300000 | 0.283157 | 0.001366 | 0.300000 |
| PERIMETER_BOT_ZN_4 VAV BOX COMPONENT | 1.11 | 0.200000 | 0.300000 | 0.332008 | 0.002530 | 0.300000 |
| PERIMETER_MID_ZN_1 VAV BOX COMPONENT | 1.29 | 0.200000 | 0.300000 | 0.387419 | 0.001869 | 0.300000 |
| PERIMETER_MID_ZN_2 VAV BOX COMPONENT | 0.990953 | 0.200000 | 0.300000 | 0.297286 | 0.002265 | 0.300000 |
| PERIMETER_MID_ZN_3 VAV BOX COMPONENT | 0.958243 | 0.200000 | 0.300000 | 0.287473 | 0.001386 | 0.300000 |
| PERIMETER_MID_ZN_4 VAV BOX COMPONENT | 1.02 | 0.200000 | 0.300000 | 0.307453 | 0.002342 | 0.300000 |
| PERIMETER_TOP_ZN_1 VAV BOX COMPONENT | 1.30 | 0.200000 | 0.300000 | 0.389151 | 0.001877 | 0.300000 |
| PERIMETER_TOP_ZN_2 VAV BOX COMPONENT | 0.995754 | 0.200000 | 0.300000 | 0.298726 | 0.002276 | 0.300000 |
| PERIMETER_TOP_ZN_3 VAV BOX COMPONENT | 0.966953 | 0.200000 | 0.300000 | 0.290086 | 0.001399 | 0.300000 |
| PERIMETER_TOP_ZN_4 VAV BOX COMPONENT | 1.03 | 0.200000 | 0.300000 | 0.309669 | 0.002359 | 0.300000 |
| Design Size Nominal Capacity [W] | |
| CORE_BOTTOM VAV BOX REHEAT COIL | 48903.01 |
| CORE_MID VAV BOX REHEAT COIL | 39519.54 |
| CORE_TOP VAV BOX REHEAT COIL | 40048.69 |
| PERIMETER_BOT_ZN_1 VAV BOX REHEAT COIL | 16345.58 |
| PERIMETER_BOT_ZN_2 VAV BOX REHEAT COIL | 12859.58 |
| PERIMETER_BOT_ZN_3 VAV BOX REHEAT COIL | 11306.10 |
| PERIMETER_BOT_ZN_4 VAV BOX REHEAT COIL | 13256.66 |
| PERIMETER_MID_ZN_1 VAV BOX REHEAT COIL | 15469.17 |
| PERIMETER_MID_ZN_2 VAV BOX REHEAT COIL | 11870.28 |
| PERIMETER_MID_ZN_3 VAV BOX REHEAT COIL | 11478.45 |
| PERIMETER_MID_ZN_4 VAV BOX REHEAT COIL | 12276.23 |
| PERIMETER_TOP_ZN_1 VAV BOX REHEAT COIL | 16050.11 |
| PERIMETER_TOP_ZN_2 VAV BOX REHEAT COIL | 11927.78 |
| PERIMETER_TOP_ZN_3 VAV BOX REHEAT COIL | 15991.50 |
| PERIMETER_TOP_ZN_4 VAV BOX REHEAT COIL | 12364.71 |
| Design Supply Air Flow Rate [m3/s] | |
| VAV_1 | 8.57 |
| VAV_2 | 7.56 |
| VAV_3 | 7.64 |
| Maximum Outdoor Air Flow Rate [m3/s] | Minimum Outdoor Air Flow Rate [m3/s] | |
| VAV_1_OA_CONTROLLER | 8.57 | 1.12 |
| VAV_2_OA_CONTROLLER | 7.56 | 1.12 |
| VAV_3_OA_CONTROLLER | 7.64 | 1.12 |
| Design Size High Speed Rated Air Flow Rate [m3/s] | Design Size High Speed Gross Rated Total Cooling Capacity [W] | Design Size High Speed Rated Sensible Heat Ratio | Design Size Low Speed Rated Air Flow Rate [m3/s] | Design Size Low Speed Gross Rated Total Cooling Capacity [W] | Design Size Low Speed Gross Rated Sensible Heat Ratio | |
| VAV_1_COOLC DXCOIL | 8.57 | 174257.32 | 0.730351 | 2.86 | 58079.96 | 0.730351 |
| VAV_2_COOLC DXCOIL | 7.56 | 152318.78 | 0.733249 | 2.52 | 50767.85 | 0.733249 |
| VAV_3_COOLC DXCOIL | 7.64 | 153412.45 | 0.733905 | 2.54 | 51132.37 | 0.733905 |
| Design Size Design Maximum Air Flow Rate [m3/s] | Design Electric Power Consumption [W] | |
| VAV_1_FAN | 8.57 | 16079.42 |
| Design Size Nominal Capacity [W] | |
| VAV_1_HEATC | 41862.67 |
| VAV_2_HEATC | 43395.37 |
| VAV_3_HEATC | 43287.82 |
| Design Size Maximum Flow Rate [m3/s] | |
| VAV_2_FAN | 7.56 |
| VAV_3_FAN | 7.64 |
| Maximum Loop Flow Rate [m3/s] | Plant Loop Volume [m3] | |
| SWHSYS1 | 0.000031 | 0.003744 |
| Design Flow Rate [m3/s] | Design Power Consumption [W] | |
| SWHSYS1 PUMP | 0.000031 | 8.44 |
| Use Side Design Flow Rate [m3/s] | |
| SWHSYS1 WATER HEATER | 0.000031 |
Report: Surface Shadowing Summary
For: Entire Facility
Timestamp: 2018-02-13 16:27:46
Surfaces (Walls, Roofs, etc) that may be Shadowed by Other Surfaces| None |
| Possible Shadow Receivers | |
| PERIMETER_BOT_ZN_1_WALL_SOUTH | PERIMETER_BOT_ZN_1_WALL_SOUTH_WINDOW | |
| PERIMETER_BOT_ZN_2_WALL_EAST | PERIMETER_BOT_ZN_2_WALL_EAST_WINDOW | |
| PERIMETER_BOT_ZN_3_WALL_NORTH | PERIMETER_BOT_ZN_3_WALL_NORTH_WINDOW | |
| PERIMETER_BOT_ZN_4_WALL_WEST | PERIMETER_BOT_ZN_4_WALL_WEST_WINDOW | |
| PERIMETER_MID_ZN_1_WALL_SOUTH | PERIMETER_MID_ZN_1_WALL_SOUTH_WINDOW | |
| PERIMETER_MID_ZN_2_WALL_EAST | PERIMETER_MID_ZN_2_WALL_EAST_WINDOW | |
| PERIMETER_MID_ZN_3_WALL_NORTH | PERIMETER_MID_ZN_3_WALL_NORTH_WINDOW | |
| PERIMETER_MID_ZN_4_WALL_WEST | PERIMETER_MID_ZN_4_WALL_WEST_WINDOW | |
| PERIMETER_TOP_ZN_1_WALL_SOUTH | PERIMETER_TOP_ZN_1_WALL_SOUTH_WINDOW | |
| PERIMETER_TOP_ZN_2_WALL_EAST | PERIMETER_TOP_ZN_2_WALL_EAST_WINDOW | |
| PERIMETER_TOP_ZN_3_WALL_NORTH | PERIMETER_TOP_ZN_3_WALL_NORTH_WINDOW | |
| PERIMETER_TOP_ZN_4_WALL_WEST | PERIMETER_TOP_ZN_4_WALL_WEST_WINDOW | |
Report: Component Cost Economics Summary
For: Entire Facility
Timestamp: 2018-02-13 16:27:46
Construction Cost Estimate Summary| Reference Bldg. | Current Bldg. Model | Difference | |
| Line Item SubTotal ($) | 0.00 | 581146.14 | 581146.14 |
| Misc. Costs ($) | 0.00 | 0.00 | 0.00 |
| Regional Adjustment ($) | 0.00 | 0.00 | 0.00 |
| Design Fee ($) | 0.00 | 0.00 | 0.00 |
| Contractor Fee ($) | 0.00 | 0.00 | 0.00 |
| Contingency ($) | 0.00 | 0.00 | 0.00 |
| Permits, Bonds, Insurance ($) | 0.00 | 0.00 | 0.00 |
| Commissioning ($) | 0.00 | 0.00 | 0.00 |
| Cost Estimate Total ($) | 0.00 | 581146.14 | 581146.14 |
| Cost Per Conditioned Building Area ($/m2) | 0.00 | 116.64 | 116.64 |
| Line No. | Item Name | Quantity. | Units | $ per Qty. | SubTotal $ | |
| -- | 1 | ROOFS:IEAD_R-30 CI_ROOF | 1660.73 | m2 | 79.00 | 131197.56 |
| -- | 2 | ROOF COST | 0.00 | m2 | 68.00 | 0.00 |
| -- | 3 | WINDOW COST | 0.00 | m2 | 232.00 | 0.00 |
| -- | 4 | WALL COST | 0.00 | m2 | 185.00 | 0.00 |
| -- | 5 | SOUTH:STD_WINDOW_UVALUE_1.647_SHGC_0.34_VT_0.69 | 652.83 | m2 | 259.00 | 169081.85 |
| -- | 6 | EXT-WALLS:STEEL-FRAMED_R-13 + R-15.6 CI_EXT-WALL | 1324.84 | m2 | 212.00 | 280866.72 |
| Line Item SubTotal | -- | -- | -- | -- | -- | 581146.14 |
Report: Adaptive Comfort Summary
For: Entire Facility
Timestamp: 2018-02-13 16:27:46
Time Not Meeting the Adaptive Comfort Models during Occupied Hours| ASHRAE55 90% Acceptability Limits [Hours] | ASHRAE55 80% Acceptability Limits [Hours] | CEN15251 Category I Acceptability Limits [Hours] | CEN15251 Category II Acceptability Limits [Hours] | CEN15251 Category III Acceptability Limits [Hours] |
Report: Initialization Summary
For: Entire Facility
Timestamp: 2018-02-13 16:27:46
Version| Version ID | |
| 1 | 8.7 |
| #TimeSteps | Minutes per TimeStep {minutes} | |
| 1 | 6 | 10 |
| Minimum System TimeStep {minutes} | Max HVAC Iterations | Minimum Plant Iterations | Maximum Plant Iterations | |
| 1 | 2 | 25 | 2 | 8 |
| Do Zone Sizing | Do System Sizing | Do Plant Sizing | Do Design Days | Do Weather Simulation | Do HVAC Sizing Simulation | |
| 1 | Yes | Yes | Yes | No | Yes | No |
| Tolerance for Time Heating Setpoint Not Met | Tolerance for Zone Cooling Setpoint Not Met Time | |
| 1 | 0.556 | 0.556 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | 19.53 | 19.50 | 19.54 | 19.60 | 20.00 | 21.64 | 22.23 | 22.38 | 21.45 | 20.12 | 19.80 | 19.63 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | -1.89 | -3.06 | -0.99 | 2.23 | 10.68 | 17.20 | 21.60 | 22.94 | 20.66 | 15.60 | 8.83 | 2.56 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 |
| Jan{dimensionless} | Feb{dimensionless} | Mar{dimensionless} | Apr{dimensionless} | May{dimensionless} | Jun{dimensionless} | Jul{dimensionless} | Aug{dimensionless} | Sep{dimensionless} | Oct{dimensionless} | Nov{dimensionless} | Dec{dimensionless} | |
| 1 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 |
| Normal | Daylighting {dimensionless} | |
| 1 | 1.000 | 1.000 |
| Jan{dimensionless} | Feb{dimensionless} | Mar{dimensionless} | Apr{dimensionless} | May{dimensionless} | Jun{dimensionless} | Jul{dimensionless} | Aug{dimensionless} | Sep{dimensionless} | Oct{dimensionless} | Nov{dimensionless} | Dec{dimensionless} | |
| 1 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 |
| Jan{dimensionless} | Feb{dimensionless} | Mar{dimensionless} | Apr{dimensionless} | May{dimensionless} | Jun{dimensionless} | Jul{dimensionless} | Aug{dimensionless} | Sep{dimensionless} | Oct{dimensionless} | Nov{dimensionless} | Dec{dimensionless} | |
| 1 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 |
| Wind Sensor Height Above Ground {m} | Wind Speed Profile Exponent {} | Wind Speed Profile Boundary Layer Thickness {m} | Air Temperature Sensor Height Above Ground {m} | Wind Speed Modifier Coefficient-Internal | Temperature Modifier Coefficient-Internal | |
| 1 | 10.000 | 0.140 | 270.000 | 1.500 | 1.586 | 9.750E-003 |
| Location Name | Latitude {N+/S- Deg} | Longitude {E+/W- Deg} | Time Zone Number {GMT+/-} | Elevation {m} | Standard Pressure at Elevation {Pa} | Standard RhoAir at Elevation | |
| 1 | Chicago Ohare Intl Ap IL USA TMY3 WMO#=725300 | 41.98 | -87.92 | -6.00 | 201.00 | 98934 | 1.1759 |
| Building Name | North Axis {deg} | Terrain | Loads Convergence Tolerance Value | Temperature Convergence Tolerance Value | Solar Distribution | Maximum Number of Warmup Days | Minimum Number of Warmup Days | |
| 1 | Ref Bldg Medium Office New2004_v1.3_5.0 | 0.000 | City | 4.00000E-002 | 0.20000 | FullInteriorAndExterior | 25 | 6 |
| Algorithm {Simple TARP CeilingDiffuser AdaptiveConvectionAlgorithm} |
|
| 1 | TARP |
| Algorithm {SimpleCombined TARP MoWitt DOE-2 AdaptiveConvectionAlgorithm} |
|
| 1 | DOE-2 |
| Value {Anisotropic} | |
| 1 | Anisotropic |
| Value {ThirdOrderBackwardDifference AnalyticalSolution EulerMethod} |
|
| 1 | AnalyticalSolution |
| Simulation {Yes/No} | Carbon Dioxide Concentration | |
| 1 | No | N/A |
| Simulation {Yes/No} | Generic Contaminant Concentration | |
| 1 | No | N/A |
| Enforce Mass Balance |
Adjust Zone Mixing |
Adjust Zone Infiltration {AddInfiltration AdjustInfiltration None} |
Infiltration Zones {MixingSourceZonesOnly AllZones} |
|
| 1 | No | N/A | N/A | N/A |
| Wind Speed Profile Exponent {} | Wind Speed Profile Boundary Layer Thickness {m} | Air Temperature Gradient Coefficient {K/m} | |
| 1 | 0.330 | 460.000 | 6.500000E-003 |
| Starting Corner | Vertex Input Direction | Coordinate System | Daylight Reference Point Coordinate System | Rectangular (Simple) Surface Coordinate System | |
| 1 | UpperLeftCorner | Counterclockwise | RelativeCoordinateSystem | RelativeCoordinateSystem | RelativeToZoneOrigin |
| Value {CTF - ConductionTransferFunction EMPD - MoisturePenetrationDepthConductionTransferFunction CondFD - ConductionFiniteDifference HAMT - CombinedHeatAndMoistureFiniteElement} - Description |
Inside Surface Max Temperature Limit{C} |
Surface Convection Coefficient Lower Limit {W/m2-K} |
Surface Convection Coefficient Upper Limit {W/m2-K} |
|
| 1 | CTF - ConductionTransferFunction | 200 | 0.10 | 1000.0 |
| Number of Fixed Detached Shades | Number of Building Detached Shades | Number of Attached Shades | |
| 1 | 0 | 0 | 0 |
| Number of Zones | Number of Zone Surfaces | Number of SubSurfaces | |
| 1 | 18 | 155 | 12 |
| Zone Name | North Axis {deg} | Origin X-Coordinate {m} | Origin Y-Coordinate {m} | Origin Z-Coordinate {m} | Centroid X-Coordinate {m} | Centroid Y-Coordinate {m} | Centroid Z-Coordinate {m} | Type | Zone Multiplier | Zone List Multiplier | Minimum X {m} | Maximum X {m} | Minimum Y {m} | Maximum Y {m} | Minimum Z {m} | Maximum Z {m} | Ceiling Height {m} | Volume {m3} | Zone Inside Convection Algorithm {Simple-Detailed-CeilingDiffuser-TrombeWall} | Zone Outside Convection Algorithm {Simple-Detailed-Tarp-MoWitt-DOE-2-BLAST} | Floor Area {m2} | Exterior Gross Wall Area {m2} | Exterior Net Wall Area {m2} | Exterior Window Area {m2} | Number of Surfaces | Number of SubSurfaces | Number of Shading SubSurfaces | Part of Total Building Area | |
| 1 | CORE_BOTTOM | 0.0 | 0.00 | 0.00 | 0.00 | 24.96 | 16.64 | 1.37 | 1 | 1 | 1 | 4.57 | 45.34 | 4.57 | 28.70 | 0.00 | 2.74 | 2.74 | 2698.04 | TARP | DOE-2 | 983.54 | 0.00 | 0.00 | 0.00 | 6 | 0 | 0 | Yes |
| 2 | CORE_MID | 0.0 | 0.00 | 0.00 | 0.00 | 24.96 | 16.64 | 5.33 | 1 | 1 | 1 | 4.57 | 45.34 | 4.57 | 28.70 | 3.96 | 6.71 | 2.74 | 2698.04 | TARP | DOE-2 | 983.54 | 0.00 | 0.00 | 0.00 | 6 | 0 | 0 | Yes |
| 3 | CORE_TOP | 0.0 | 0.00 | 0.00 | 0.00 | 24.96 | 16.64 | 9.30 | 1 | 1 | 1 | 4.57 | 45.34 | 4.57 | 28.70 | 7.92 | 10.67 | 2.74 | 2698.04 | TARP | DOE-2 | 983.54 | 0.00 | 0.00 | 0.00 | 6 | 0 | 0 | Yes |
| 4 | FIRSTFLOOR_PLENUM | 0.0 | 0.00 | 0.00 | 0.00 | 24.96 | 16.64 | 3.35 | 1 | 1 | 1 | 0.00 | 49.91 | 0.00 | 33.27 | 2.74 | 3.96 | 1.22 | 2024.76 | TARP | DOE-2 | 1660.73 | 202.84 | 202.84 | 0.00 | 14 | 0 | 0 | No |
| 5 | MIDFLOOR_PLENUM | 0.0 | 0.00 | 0.00 | 0.00 | 24.96 | 16.64 | 7.32 | 1 | 1 | 1 | 0.00 | 49.91 | 0.00 | 33.27 | 6.71 | 7.92 | 1.22 | 2024.76 | TARP | DOE-2 | 1660.73 | 202.84 | 202.84 | 0.00 | 14 | 0 | 0 | No |
| 6 | PERIMETER_BOT_ZN_1 | 0.0 | 0.00 | 0.00 | 0.00 | 24.96 | 2.16 | 1.37 | 1 | 1 | 1 | 0.00 | 49.91 | 0.00 | 4.57 | 0.00 | 2.74 | 2.74 | 568.77 | TARP | DOE-2 | 207.34 | 136.92 | 71.63 | 65.28 | 6 | 1 | 0 | Yes |
| 7 | PERIMETER_BOT_ZN_2 | 0.0 | 0.00 | 0.00 | 0.00 | 47.82 | 16.64 | 1.37 | 1 | 1 | 1 | 45.34 | 49.91 | 0.00 | 33.27 | 0.00 | 2.74 | 2.74 | 360.08 | TARP | DOE-2 | 131.26 | 91.28 | 47.75 | 43.52 | 6 | 1 | 0 | Yes |
| 8 | PERIMETER_BOT_ZN_3 | 0.0 | 0.00 | 0.00 | 0.00 | 24.96 | 31.11 | 1.37 | 1 | 1 | 1 | 0.00 | 49.91 | 28.70 | 33.27 | 0.00 | 2.74 | 2.74 | 568.77 | TARP | DOE-2 | 207.34 | 136.92 | 71.63 | 65.28 | 6 | 1 | 0 | Yes |
| 9 | PERIMETER_BOT_ZN_4 | 0.0 | 0.00 | 0.00 | 0.00 | 2.09 | 16.64 | 1.37 | 1 | 1 | 1 | 0.00 | 4.57 | 0.00 | 33.27 | 0.00 | 2.74 | 2.74 | 360.05 | TARP | DOE-2 | 131.25 | 91.28 | 47.75 | 43.52 | 6 | 1 | 0 | Yes |
| 10 | PERIMETER_MID_ZN_1 | 0.0 | 0.00 | 0.00 | 0.00 | 24.96 | 2.16 | 5.33 | 1 | 1 | 1 | 0.00 | 49.91 | 0.00 | 4.57 | 3.96 | 6.71 | 2.74 | 568.77 | TARP | DOE-2 | 207.34 | 136.92 | 71.63 | 65.28 | 6 | 1 | 0 | Yes |
| 11 | PERIMETER_MID_ZN_2 | 0.0 | 0.00 | 0.00 | 0.00 | 47.82 | 16.64 | 5.33 | 1 | 1 | 1 | 45.34 | 49.91 | 0.00 | 33.27 | 3.96 | 6.71 | 2.74 | 360.08 | TARP | DOE-2 | 131.26 | 91.28 | 47.75 | 43.52 | 6 | 1 | 0 | Yes |
| 12 | PERIMETER_MID_ZN_3 | 0.0 | 0.00 | 0.00 | 0.00 | 24.96 | 31.11 | 5.33 | 1 | 1 | 1 | 0.00 | 49.91 | 28.70 | 33.27 | 3.96 | 6.71 | 2.74 | 568.77 | TARP | DOE-2 | 207.34 | 136.92 | 71.63 | 65.28 | 6 | 1 | 0 | Yes |
| 13 | PERIMETER_MID_ZN_4 | 0.0 | 0.00 | 0.00 | 0.00 | 2.09 | 16.64 | 5.33 | 1 | 1 | 1 | 0.00 | 4.57 | 0.00 | 33.27 | 3.96 | 6.71 | 2.74 | 360.05 | TARP | DOE-2 | 131.25 | 91.28 | 47.75 | 43.52 | 6 | 1 | 0 | Yes |
| 14 | PERIMETER_TOP_ZN_1 | 0.0 | 0.00 | 0.00 | 0.00 | 24.96 | 2.16 | 9.30 | 1 | 1 | 1 | 0.00 | 49.91 | 0.00 | 4.57 | 7.92 | 10.67 | 2.74 | 568.77 | TARP | DOE-2 | 207.34 | 136.92 | 71.63 | 65.28 | 6 | 1 | 0 | Yes |
| 15 | PERIMETER_TOP_ZN_2 | 0.0 | 0.00 | 0.00 | 0.00 | 47.82 | 16.64 | 9.30 | 1 | 1 | 1 | 45.34 | 49.91 | 0.00 | 33.27 | 7.92 | 10.67 | 2.74 | 360.08 | TARP | DOE-2 | 131.26 | 91.28 | 47.75 | 43.52 | 6 | 1 | 0 | Yes |
| 16 | PERIMETER_TOP_ZN_3 | 0.0 | 0.00 | 0.00 | 0.00 | 24.96 | 31.11 | 9.30 | 1 | 1 | 1 | 0.00 | 49.91 | 28.70 | 33.27 | 7.92 | 10.67 | 2.74 | 568.77 | TARP | DOE-2 | 207.34 | 136.92 | 71.63 | 65.28 | 6 | 1 | 0 | Yes |
| 17 | PERIMETER_TOP_ZN_4 | 0.0 | 0.00 | 0.00 | 0.00 | 2.09 | 16.64 | 9.30 | 1 | 1 | 1 | 0.00 | 4.57 | 0.00 | 33.27 | 7.92 | 10.67 | 2.74 | 360.05 | TARP | DOE-2 | 131.25 | 91.28 | 47.75 | 43.52 | 6 | 1 | 0 | Yes |
| 18 | TOPFLOOR_PLENUM | 0.0 | 0.00 | 0.00 | 0.00 | 24.96 | 16.64 | 11.28 | 1 | 1 | 1 | 0.00 | 49.91 | 0.00 | 33.27 | 10.67 | 11.89 | 1.22 | 2024.76 | TARP | DOE-2 | 1660.73 | 202.84 | 202.84 | 0.00 | 10 | 0 | 0 | No |
| Zone Name | Floor Area {m2} | # Occupants | Area per Occupant {m2/person} | Occupant per Area {person/m2} | Interior Lighting {W/m2} | Electric Load {W/m2} | Gas Load {W/m2} | Other Load {W/m2} | Hot Water Eq {W/m2} | Steam Equipment {W/m2} | Sum Loads per Area {W/m2} | Outdoor Controlled Baseboard Heat | |
| 1 | CORE_BOTTOM | 983.54 | 52.9 | 18.580 | 5.382E-002 | 10.760 | 43.407 | 0.000 | 0.000 | 0.000 | 0.000 | 54.167 | No |
| 2 | CORE_MID | 983.54 | 52.9 | 18.580 | 5.382E-002 | 10.760 | 10.760 | 0.000 | 0.000 | 0.000 | 0.000 | 21.520 | No |
| 3 | CORE_TOP | 983.54 | 52.9 | 18.580 | 5.382E-002 | 10.760 | 10.760 | 0.000 | 0.000 | 0.000 | 0.000 | 21.520 | No |
| 4 | FIRSTFLOOR_PLENUM | 1660.73 | 0.0 | N/A | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | No |
| 5 | MIDFLOOR_PLENUM | 1660.73 | 0.0 | N/A | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | No |
| 6 | PERIMETER_BOT_ZN_1 | 207.34 | 11.2 | 18.580 | 5.382E-002 | 10.760 | 10.760 | 0.000 | 0.000 | 0.000 | 0.000 | 21.520 | No |
| 7 | PERIMETER_BOT_ZN_2 | 131.26 | 7.1 | 18.580 | 5.382E-002 | 10.760 | 10.760 | 0.000 | 0.000 | 0.000 | 0.000 | 21.520 | No |
| 8 | PERIMETER_BOT_ZN_3 | 207.34 | 11.2 | 18.580 | 5.382E-002 | 10.760 | 10.760 | 0.000 | 0.000 | 0.000 | 0.000 | 21.520 | No |
| 9 | PERIMETER_BOT_ZN_4 | 131.25 | 7.1 | 18.580 | 5.382E-002 | 10.760 | 10.760 | 0.000 | 0.000 | 0.000 | 0.000 | 21.520 | No |
| 10 | PERIMETER_MID_ZN_1 | 207.34 | 11.2 | 18.580 | 5.382E-002 | 10.760 | 10.760 | 0.000 | 0.000 | 0.000 | 0.000 | 21.520 | No |
| 11 | PERIMETER_MID_ZN_2 | 131.26 | 7.1 | 18.580 | 5.382E-002 | 10.760 | 10.760 | 0.000 | 0.000 | 0.000 | 0.000 | 21.520 | No |
| 12 | PERIMETER_MID_ZN_3 | 207.34 | 11.2 | 18.580 | 5.382E-002 | 10.760 | 10.760 | 0.000 | 0.000 | 0.000 | 0.000 | 21.520 | No |
| 13 | PERIMETER_MID_ZN_4 | 131.25 | 7.1 | 18.580 | 5.382E-002 | 10.760 | 10.760 | 0.000 | 0.000 | 0.000 | 0.000 | 21.520 | No |
| 14 | PERIMETER_TOP_ZN_1 | 207.34 | 11.2 | 18.580 | 5.382E-002 | 10.760 | 10.760 | 0.000 | 0.000 | 0.000 | 0.000 | 21.520 | No |
| 15 | PERIMETER_TOP_ZN_2 | 131.26 | 7.1 | 18.580 | 5.382E-002 | 10.760 | 10.760 | 0.000 | 0.000 | 0.000 | 0.000 | 21.520 | No |
| 16 | PERIMETER_TOP_ZN_3 | 207.34 | 11.2 | 18.580 | 5.382E-002 | 10.760 | 10.760 | 0.000 | 0.000 | 0.000 | 0.000 | 21.520 | No |
| 17 | PERIMETER_TOP_ZN_4 | 131.25 | 7.1 | 18.580 | 5.382E-002 | 10.760 | 10.760 | 0.000 | 0.000 | 0.000 | 0.000 | 21.520 | No |
| 18 | TOPFLOOR_PLENUM | 1660.73 | 0.0 | N/A | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | No |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Number of People {} | People/Floor Area {person/m2} | Floor Area per person {m2/person} | Fraction Radiant | Fraction Convected | Sensible Fraction Calculation | Activity level | ASHRAE 55 Warnings | Carbon Dioxide Generation Rate | Nominal Minimum Number of People | Nominal Maximum Number of People | MRT Calculation Type | Work Efficiency | Clothing Insulation Calculation Method | Clothing Insulation Calculation Method Schedule | Clothing | Air Velocity | Fanger Calculation | Pierce Calculation | KSU Calculation | |
| 1 | CORE_BOTTOM PEOPLE | BLDG_OCC_SCH | CORE_BOTTOM | 983.54 | 52.9 | 52.9 | 5.382E-002 | 18.580 | 0.300 | 0.700 | AutoCalculate | ACTIVITY_SCH | No | 3.8200E-008 | 0 | 53 | Zone Averaged | WORK_EFF_SCH | Clothing Insulation Schedule | N/A | CLOTHING_SCH | AIR_VELO_SCH | Yes | No | No |
| 2 | CORE_MID PEOPLE | BLDG_OCC_SCH | CORE_MID | 983.54 | 52.9 | 52.9 | 5.382E-002 | 18.580 | 0.300 | 0.700 | AutoCalculate | ACTIVITY_SCH | No | 3.8200E-008 | 0 | 53 | Zone Averaged | WORK_EFF_SCH | Clothing Insulation Schedule | N/A | CLOTHING_SCH | AIR_VELO_SCH | Yes | No | No |
| 3 | CORE_TOP PEOPLE | BLDG_OCC_SCH | CORE_TOP | 983.54 | 52.9 | 52.9 | 5.382E-002 | 18.580 | 0.300 | 0.700 | AutoCalculate | ACTIVITY_SCH | No | 3.8200E-008 | 0 | 53 | Zone Averaged | WORK_EFF_SCH | Clothing Insulation Schedule | N/A | CLOTHING_SCH | AIR_VELO_SCH | Yes | No | No |
| 4 | PERIMETER_BOT_ZN_1 PEOPLE | BLDG_OCC_SCH | PERIMETER_BOT_ZN_1 | 207.34 | 11.2 | 11.2 | 5.382E-002 | 18.580 | 0.300 | 0.700 | AutoCalculate | ACTIVITY_SCH | No | 3.8200E-008 | 0 | 11 | Zone Averaged | WORK_EFF_SCH | Clothing Insulation Schedule | N/A | CLOTHING_SCH | AIR_VELO_SCH | Yes | No | No |
| 5 | PERIMETER_BOT_ZN_2 PEOPLE | BLDG_OCC_SCH | PERIMETER_BOT_ZN_2 | 131.26 | 7.1 | 7.1 | 5.382E-002 | 18.580 | 0.300 | 0.700 | AutoCalculate | ACTIVITY_SCH | No | 3.8200E-008 | 0 | 7 | Zone Averaged | WORK_EFF_SCH | Clothing Insulation Schedule | N/A | CLOTHING_SCH | AIR_VELO_SCH | Yes | No | No |
| 6 | PERIMETER_BOT_ZN_3 PEOPLE | BLDG_OCC_SCH | PERIMETER_BOT_ZN_3 | 207.34 | 11.2 | 11.2 | 5.382E-002 | 18.580 | 0.300 | 0.700 | AutoCalculate | ACTIVITY_SCH | No | 3.8200E-008 | 0 | 11 | Zone Averaged | WORK_EFF_SCH | Clothing Insulation Schedule | N/A | CLOTHING_SCH | AIR_VELO_SCH | Yes | No | No |
| 7 | PERIMETER_BOT_ZN_4 PEOPLE | BLDG_OCC_SCH | PERIMETER_BOT_ZN_4 | 131.25 | 7.1 | 7.1 | 5.382E-002 | 18.580 | 0.300 | 0.700 | AutoCalculate | ACTIVITY_SCH | No | 3.8200E-008 | 0 | 7 | Zone Averaged | WORK_EFF_SCH | Clothing Insulation Schedule | N/A | CLOTHING_SCH | AIR_VELO_SCH | Yes | No | No |
| 8 | PERIMETER_MID_ZN_1 PEOPLE | BLDG_OCC_SCH | PERIMETER_MID_ZN_1 | 207.34 | 11.2 | 11.2 | 5.382E-002 | 18.580 | 0.300 | 0.700 | AutoCalculate | ACTIVITY_SCH | No | 3.8200E-008 | 0 | 11 | Zone Averaged | WORK_EFF_SCH | Clothing Insulation Schedule | N/A | CLOTHING_SCH | AIR_VELO_SCH | Yes | No | No |
| 9 | PERIMETER_MID_ZN_2 PEOPLE | BLDG_OCC_SCH | PERIMETER_MID_ZN_2 | 131.26 | 7.1 | 7.1 | 5.382E-002 | 18.580 | 0.300 | 0.700 | AutoCalculate | ACTIVITY_SCH | No | 3.8200E-008 | 0 | 7 | Zone Averaged | WORK_EFF_SCH | Clothing Insulation Schedule | N/A | CLOTHING_SCH | AIR_VELO_SCH | Yes | No | No |
| 10 | PERIMETER_MID_ZN_3 PEOPLE | BLDG_OCC_SCH | PERIMETER_MID_ZN_3 | 207.34 | 11.2 | 11.2 | 5.382E-002 | 18.580 | 0.300 | 0.700 | AutoCalculate | ACTIVITY_SCH | No | 3.8200E-008 | 0 | 11 | Zone Averaged | WORK_EFF_SCH | Clothing Insulation Schedule | N/A | CLOTHING_SCH | AIR_VELO_SCH | Yes | No | No |
| 11 | PERIMETER_MID_ZN_4 PEOPLE | BLDG_OCC_SCH | PERIMETER_MID_ZN_4 | 131.25 | 7.1 | 7.1 | 5.382E-002 | 18.580 | 0.300 | 0.700 | AutoCalculate | ACTIVITY_SCH | No | 3.8200E-008 | 0 | 7 | Zone Averaged | WORK_EFF_SCH | Clothing Insulation Schedule | N/A | CLOTHING_SCH | AIR_VELO_SCH | Yes | No | No |
| 12 | PERIMETER_TOP_ZN_1 PEOPLE | BLDG_OCC_SCH | PERIMETER_TOP_ZN_1 | 207.34 | 11.2 | 11.2 | 5.382E-002 | 18.580 | 0.300 | 0.700 | AutoCalculate | ACTIVITY_SCH | No | 3.8200E-008 | 0 | 11 | Zone Averaged | WORK_EFF_SCH | Clothing Insulation Schedule | N/A | CLOTHING_SCH | AIR_VELO_SCH | Yes | No | No |
| 13 | PERIMETER_TOP_ZN_2 PEOPLE | BLDG_OCC_SCH | PERIMETER_TOP_ZN_2 | 131.26 | 7.1 | 7.1 | 5.382E-002 | 18.580 | 0.300 | 0.700 | AutoCalculate | ACTIVITY_SCH | No | 3.8200E-008 | 0 | 7 | Zone Averaged | WORK_EFF_SCH | Clothing Insulation Schedule | N/A | CLOTHING_SCH | AIR_VELO_SCH | Yes | No | No |
| 14 | PERIMETER_TOP_ZN_3 PEOPLE | BLDG_OCC_SCH | PERIMETER_TOP_ZN_3 | 207.34 | 11.2 | 11.2 | 5.382E-002 | 18.580 | 0.300 | 0.700 | AutoCalculate | ACTIVITY_SCH | No | 3.8200E-008 | 0 | 11 | Zone Averaged | WORK_EFF_SCH | Clothing Insulation Schedule | N/A | CLOTHING_SCH | AIR_VELO_SCH | Yes | No | No |
| 15 | PERIMETER_TOP_ZN_4 PEOPLE | BLDG_OCC_SCH | PERIMETER_TOP_ZN_4 | 131.25 | 7.1 | 7.1 | 5.382E-002 | 18.580 | 0.300 | 0.700 | AutoCalculate | ACTIVITY_SCH | No | 3.8200E-008 | 0 | 7 | Zone Averaged | WORK_EFF_SCH | Clothing Insulation Schedule | N/A | CLOTHING_SCH | AIR_VELO_SCH | Yes | No | No |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Lighting Level {W} | Lights/Floor Area {W/m2} | Lights per person {W/person} | Fraction Return Air | Fraction Radiant | Fraction Short Wave | Fraction Convected | Fraction Replaceable | End-Use Category | Nominal Minimum Lighting Level {W} | Nominal Maximum Lighting Level {W} | |
| 1 | CORE_BOTTOM_LIGHTS | BLDG_LIGHT_SCH | CORE_BOTTOM | 983.54 | 52.9 | 10582.854 | 10.760 | 199.921 | 0.400 | 0.400 | 0.200 | 0.000 | 1.000 | General | 0.000 | 10582.854 |
| 2 | CORE_MID_LIGHTS | BLDG_LIGHT_SCH | CORE_MID | 983.54 | 52.9 | 10582.854 | 10.760 | 199.921 | 0.400 | 0.400 | 0.200 | 0.000 | 1.000 | General | 0.000 | 10582.854 |
| 3 | CORE_TOP_LIGHTS | BLDG_LIGHT_SCH | CORE_TOP | 983.54 | 52.9 | 10582.854 | 10.760 | 199.921 | 0.400 | 0.400 | 0.200 | 0.000 | 1.000 | General | 0.000 | 10582.854 |
| 4 | PERIMETER_BOT_ZN_1_LIGHTS | BLDG_LIGHT_SCH | PERIMETER_BOT_ZN_1 | 207.34 | 11.2 | 2230.958 | 10.760 | 199.921 | 0.400 | 0.400 | 0.200 | 0.000 | 1.000 | General | 0.000 | 2230.958 |
| 5 | PERIMETER_BOT_ZN_2_LIGHTS | BLDG_LIGHT_SCH | PERIMETER_BOT_ZN_2 | 131.26 | 7.1 | 1412.381 | 10.760 | 199.921 | 0.400 | 0.400 | 0.200 | 0.000 | 1.000 | General | 0.000 | 1412.381 |
| 6 | PERIMETER_BOT_ZN_3_LIGHTS | BLDG_LIGHT_SCH | PERIMETER_BOT_ZN_3 | 207.34 | 11.2 | 2230.958 | 10.760 | 199.921 | 0.400 | 0.400 | 0.200 | 0.000 | 1.000 | General | 0.000 | 2230.958 |
| 7 | PERIMETER_BOT_ZN_4_LIGHTS | BLDG_LIGHT_SCH | PERIMETER_BOT_ZN_4 | 131.25 | 7.1 | 1412.289 | 10.760 | 199.921 | 0.400 | 0.400 | 0.200 | 0.000 | 1.000 | General | 0.000 | 1412.289 |
| 8 | PERIMETER_MID_ZN_1_LIGHTS | BLDG_LIGHT_SCH | PERIMETER_MID_ZN_1 | 207.34 | 11.2 | 2230.958 | 10.760 | 199.921 | 0.400 | 0.400 | 0.200 | 0.000 | 1.000 | General | 0.000 | 2230.958 |
| 9 | PERIMETER_MID_ZN_2_LIGHTS | BLDG_LIGHT_SCH | PERIMETER_MID_ZN_2 | 131.26 | 7.1 | 1412.381 | 10.760 | 199.921 | 0.400 | 0.400 | 0.200 | 0.000 | 1.000 | General | 0.000 | 1412.381 |
| 10 | PERIMETER_MID_ZN_3_LIGHTS | BLDG_LIGHT_SCH | PERIMETER_MID_ZN_3 | 207.34 | 11.2 | 2230.958 | 10.760 | 199.921 | 0.400 | 0.400 | 0.200 | 0.000 | 1.000 | General | 0.000 | 2230.958 |
| 11 | PERIMETER_MID_ZN_4_LIGHTS | BLDG_LIGHT_SCH | PERIMETER_MID_ZN_4 | 131.25 | 7.1 | 1412.289 | 10.760 | 199.921 | 0.400 | 0.400 | 0.200 | 0.000 | 1.000 | General | 0.000 | 1412.289 |
| 12 | PERIMETER_TOP_ZN_1_LIGHTS | BLDG_LIGHT_SCH | PERIMETER_TOP_ZN_1 | 207.34 | 11.2 | 2230.958 | 10.760 | 199.921 | 0.400 | 0.400 | 0.200 | 0.000 | 1.000 | General | 0.000 | 2230.958 |
| 13 | PERIMETER_TOP_ZN_2_LIGHTS | BLDG_LIGHT_SCH | PERIMETER_TOP_ZN_2 | 131.26 | 7.1 | 1412.381 | 10.760 | 199.921 | 0.400 | 0.400 | 0.200 | 0.000 | 1.000 | General | 0.000 | 1412.381 |
| 14 | PERIMETER_TOP_ZN_3_LIGHTS | BLDG_LIGHT_SCH | PERIMETER_TOP_ZN_3 | 207.34 | 11.2 | 2230.958 | 10.760 | 199.921 | 0.400 | 0.400 | 0.200 | 0.000 | 1.000 | General | 0.000 | 2230.958 |
| 15 | PERIMETER_TOP_ZN_4_LIGHTS | BLDG_LIGHT_SCH | PERIMETER_TOP_ZN_4 | 131.25 | 7.1 | 1412.289 | 10.760 | 199.921 | 0.400 | 0.400 | 0.200 | 0.000 | 1.000 | General | 0.000 | 1412.289 |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Equipment Level {W} | Equipment/Floor Area {W/m2} | Equipment per person {W/person} | Fraction Latent | Fraction Radiant | Fraction Lost | Fraction Convected | End-Use SubCategory | Nominal Minimum Equipment Level {W} | Nominal Maximum Equipment Level {W} | |
| 1 | CORE_BOTTOM_ELEVATORS_EQUIP | BLDG_ELEVATORS | CORE_BOTTOM | 983.54 | 52.9 | 32109.890 | 32.647 | 606.588 | 0.000 | 0.500 | 0.000 | 0.500 | Elevators | 0.000 | 22155.824 |
| 2 | CORE_BOTTOM_PLUGMISC_EQUIP | BLDG_EQUIP_SCH | CORE_BOTTOM | 983.54 | 52.9 | 10582.854 | 10.760 | 199.921 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 10582.854 |
| 3 | CORE_MID_PLUGMISC_EQUIP | BLDG_EQUIP_SCH | CORE_MID | 983.54 | 52.9 | 10582.854 | 10.760 | 199.921 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 10582.854 |
| 4 | CORE_TOP_PLUGMISC_EQUIP | BLDG_EQUIP_SCH | CORE_TOP | 983.54 | 52.9 | 10582.854 | 10.760 | 199.921 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 10582.854 |
| 5 | PERIMETER_BOT_ZN_1_PLUGMISC_EQUIP | BLDG_EQUIP_SCH | PERIMETER_BOT_ZN_1 | 207.34 | 11.2 | 2230.958 | 10.760 | 199.921 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 2230.958 |
| 6 | PERIMETER_BOT_ZN_2_PLUGMISC_EQUIP | BLDG_EQUIP_SCH | PERIMETER_BOT_ZN_2 | 131.26 | 7.1 | 1412.381 | 10.760 | 199.921 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 1412.381 |
| 7 | PERIMETER_BOT_ZN_3_PLUGMISC_EQUIP | BLDG_EQUIP_SCH | PERIMETER_BOT_ZN_3 | 207.34 | 11.2 | 2230.958 | 10.760 | 199.921 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 2230.958 |
| 8 | PERIMETER_BOT_ZN_4_PLUGMISC_EQUIP | BLDG_EQUIP_SCH | PERIMETER_BOT_ZN_4 | 131.25 | 7.1 | 1412.289 | 10.760 | 199.921 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 1412.289 |
| 9 | PERIMETER_MID_ZN_1_PLUGMISC_EQUIP | BLDG_EQUIP_SCH | PERIMETER_MID_ZN_1 | 207.34 | 11.2 | 2230.958 | 10.760 | 199.921 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 2230.958 |
| 10 | PERIMETER_MID_ZN_2_PLUGMISC_EQUIP | BLDG_EQUIP_SCH | PERIMETER_MID_ZN_2 | 131.26 | 7.1 | 1412.381 | 10.760 | 199.921 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 1412.381 |
| 11 | PERIMETER_MID_ZN_3_PLUGMISC_EQUIP | BLDG_EQUIP_SCH | PERIMETER_MID_ZN_3 | 207.34 | 11.2 | 2230.958 | 10.760 | 199.921 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 2230.958 |
| 12 | PERIMETER_MID_ZN_4_PLUGMISC_EQUIP | BLDG_EQUIP_SCH | PERIMETER_MID_ZN_4 | 131.25 | 7.1 | 1412.289 | 10.760 | 199.921 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 1412.289 |
| 13 | PERIMETER_TOP_ZN_1_PLUGMISC_EQUIP | BLDG_EQUIP_SCH | PERIMETER_TOP_ZN_1 | 207.34 | 11.2 | 2230.958 | 10.760 | 199.921 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 2230.958 |
| 14 | PERIMETER_TOP_ZN_2_PLUGMISC_EQUIP | BLDG_EQUIP_SCH | PERIMETER_TOP_ZN_2 | 131.26 | 7.1 | 1412.381 | 10.760 | 199.921 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 1412.381 |
| 15 | PERIMETER_TOP_ZN_3_PLUGMISC_EQUIP | BLDG_EQUIP_SCH | PERIMETER_TOP_ZN_3 | 207.34 | 11.2 | 2230.958 | 10.760 | 199.921 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 2230.958 |
| 16 | PERIMETER_TOP_ZN_4_PLUGMISC_EQUIP | BLDG_EQUIP_SCH | PERIMETER_TOP_ZN_4 | 131.25 | 7.1 | 1412.289 | 10.760 | 199.921 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 1412.289 |
| Construction Name | Index | #Layers | #CTFs | Time Step {hours} | ThermalConductance {w/m2-K} | OuterThermalAbsorptance | InnerThermalAbsorptance | OuterSolarAbsorptance | InnerSolarAbsorptance | Roughness | |
| 1 | AIR-WALL | 1 | 1 | 1 | 0.167 | 4.809 | 0.900 | 0.900 | 0.700 | 0.700 | Rough |
| 2 | DROPCEILING | 2 | 1 | 3 | 0.167 | 4.488 | 0.900 | 0.900 | 0.700 | 0.700 | MediumSmooth |
| 3 | EXT-SLAB | 3 | 2 | 7 | 0.167 | 3.401 | 0.900 | 0.900 | 0.700 | 0.700 | Rough |
| 4 | IEAD NON-RES ROOF | 4 | 3 | 9 | 0.167 | 0.3762 | 0.900 | 0.900 | 0.700 | 0.700 | VeryRough |
| 5 | IEAD_R-30 CI_ROOF | 5 | 3 | 17 | 0.167 | 0.1885 | 0.900 | 0.900 | 0.700 | 0.700 | VeryRough |