Program Version:EnergyPlus, Version 9.1.0-08d2e308bb, YMD=2021.07.16 12:28
Tabular Output Report in Format: HTML
Building: Ref Bldg Medium Office New2004_v1.3_5.0
Environment: PHILADELPHIA 2014 ** PHILADELPHIA - USA Custom-720304 WMO#=720304
Simulation Timestamp: 2021-07-16 12:28:42
Report: Annual Building Utility Performance Summary
For: Entire Facility
Timestamp: 2021-07-16 12:28:42
Values gathered over 8760.00 hours| Total Energy [GJ] | Energy Per Total Building Area [MJ/m2] | Energy Per Conditioned Building Area [MJ/m2] | |
| Total Site Energy | 2433.99 | 488.54 | 488.54 |
| Net Site Energy | 2433.99 | 488.54 | 488.54 |
| Total Source Energy | 7895.84 | 1584.81 | 1584.81 |
| Net Source Energy | 7895.84 | 1584.81 | 1584.81 |
| Site=>Source Conversion Factor | |
| Electricity | 3.546 |
| Natural Gas | 1.092 |
| District Cooling | 0.848 |
| District Heating | 1.647 |
| Steam | 0.585 |
| Gasoline | 1.050 |
| Diesel | 1.050 |
| Coal | 1.050 |
| Fuel Oil #1 | 1.050 |
| Fuel Oil #2 | 1.050 |
| Propane | 1.050 |
| Other Fuel 1 | 1.000 |
| Other Fuel 2 | 1.000 |
| Area [m2] | |
| Total Building Area | 4982.19 |
| Net Conditioned Building Area | 4982.19 |
| Unconditioned Building Area | 0.00 |
| Electricity [GJ] | Natural Gas [GJ] | Additional Fuel [GJ] | District Cooling [GJ] | District Heating [GJ] | Water [m3] | |
| Heating | 80.41 | 263.43 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | 303.99 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 566.57 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 232.69 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 879.79 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 70.72 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 0.27 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 36.13 | 0.00 | 0.00 | 0.00 | 174.75 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total End Uses | 2134.44 | 299.55 | 0.00 | 0.00 | 0.00 | 174.75 |
| Subcategory | Electricity [GJ] | Natural Gas [GJ] | Additional Fuel [GJ] | District Cooling [GJ] | District Heating [GJ] | Water [m3] | |
| Heating | General | 80.41 | 263.43 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | General | 303.99 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | General | 566.57 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | Exterior Facade Lighting | 232.69 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | General | 714.87 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Elevators | 164.92 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Exterior Equipment | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | Fan Energy | 70.72 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | General | 0.27 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | Water Heater | 0.00 | 36.13 | 0.00 | 0.00 | 0.00 | 0.00 |
| General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 174.75 | |
| Refrigeration | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Electricity Intensity [MJ/m2] | Natural Gas Intensity [MJ/m2] | Additional Fuel Intensity [MJ/m2] | District Cooling Intensity [MJ/m2] | District Heating Intensity [MJ/m2] | Water Intensity [m3/m2] | |
| Lighting | 160.42 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| HVAC | 91.40 | 60.12 | 0.00 | 0.00 | 0.00 | 0.04 |
| Other | 176.59 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total | 428.41 | 60.12 | 0.00 | 0.00 | 0.00 | 0.04 |
| Electricity Intensity [MJ/m2] | Natural Gas Intensity [MJ/m2] | Additional Fuel Intensity [MJ/m2] | District Cooling Intensity [MJ/m2] | District Heating Intensity [MJ/m2] | Water Intensity [m3/m2] | |
| Lighting | 160.42 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| HVAC | 91.40 | 60.12 | 0.00 | 0.00 | 0.00 | 0.04 |
| Other | 176.59 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total | 428.41 | 60.12 | 0.00 | 0.00 | 0.00 | 0.04 |
| Electricity [GJ] | Percent Electricity [%] | |
| Fuel-Fired Power Generation | 0.000 | 0.00 |
| High Temperature Geothermal* | 0.000 | 0.00 |
| Photovoltaic Power | 0.000 | 0.00 |
| Wind Power | 0.000 | 0.00 |
| Power Conversion | 0.000 | 0.00 |
| Net Decrease in On-Site Storage | 0.000 | 0.00 |
| Total On-Site Electric Sources | 0.000 | 0.00 |
| Electricity Coming From Utility | 2134.440 | 100.00 |
| Surplus Electricity Going To Utility | 0.000 | 0.00 |
| Net Electricity From Utility | 2134.440 | 100.00 |
| Total On-Site and Utility Electric Sources | 2134.440 | 100.00 |
| Total Electricity End Uses | 2134.440 | 100.00 |
| Heat [GJ] | Percent Heat [%] | |
| Water-Side Heat Recovery | 0.00 | |
| Air to Air Heat Recovery for Cooling | 0.00 | |
| Air to Air Heat Recovery for Heating | 0.00 | |
| High-Temperature Geothermal* | 0.00 | |
| Solar Water Thermal | 0.00 | |
| Solar Air Thermal | 0.00 | |
| Total On-Site Thermal Sources | 0.00 |
| Water [m3] | Percent Water [%] | |
| Rainwater Collection | 0.00 | 0.00 |
| Condensate Collection | 0.00 | 0.00 |
| Groundwater Well | 0.00 | 0.00 |
| Total On Site Water Sources | 0.00 | 0.00 |
| - | - | - |
| Initial Storage | 0.00 | 0.00 |
| Final Storage | 0.00 | 0.00 |
| Change in Storage | 0.00 | 0.00 |
| - | - | - |
| Water Supplied by Utility | 174.75 | 100.00 |
| - | - | - |
| Total On Site, Change in Storage, and Utility Water Sources | 174.75 | 100.00 |
| Total Water End Uses | 174.75 | 100.00 |
| Degrees [deltaC] | |
| Tolerance for Zone Heating Setpoint Not Met Time | 0.56 |
| Tolerance for Zone Cooling Setpoint Not Met Time | 0.56 |
| Facility [Hours] | |
| Time Setpoint Not Met During Occupied Heating | 3.50 |
| Time Setpoint Not Met During Occupied Cooling | 0.50 |
| Time Not Comfortable Based on Simple ASHRAE 55-2004 | 2575.17 |
Table of Contents
TopEMISSIONS DATA SUMMARY
| Meter |COMPONENTS OF PEAK ELECTRICAL DEMAND
| Meter |HEATING PART LOAD PERFORMANCE
| VAV_1_HEATC | VAV_2_HEATC | VAV_3_HEATC |COOLING PART LOAD PERFORMANCE
| VAV_1_COOLC DXCOIL | VAV_2_COOLC DXCOIL | VAV_3_COOLC DXCOIL |FAN PART LOAD PERFORMANCE
| VAV_1_FAN | VAV_2_FAN | VAV_3_FAN |Report: Input Verification and Results Summary
For: Entire Facility
Timestamp: 2021-07-16 12:28:42
General| Value | |
| Program Version and Build | EnergyPlus, Version 9.1.0-08d2e308bb, YMD=2021.07.16 12:28 |
| RunPeriod | PHILADELPHIA 2014 |
| Weather File | PHILADELPHIA - USA Custom-720304 WMO#=720304 |
| Latitude [deg] | 40.14 |
| Longitude [deg] | -75.3 |
| Elevation [m] | 92.00 |
| Time Zone | -5.0 |
| North Axis Angle [deg] | 0.00 |
| Rotation for Appendix G [deg] | 0.00 |
| Hours Simulated [hrs] | 8760.00 |
| Total | North (315 to 45 deg) | East (45 to 135 deg) | South (135 to 225 deg) | West (225 to 315 deg) | |
| Gross Wall Area [m2] | 1977.67 | 593.30 | 395.53 | 593.30 | 395.53 |
| Above Ground Wall Area [m2] | 1977.67 | 593.30 | 395.53 | 593.30 | 395.53 |
| Window Opening Area [m2] | 652.83 | 195.85 | 130.57 | 195.85 | 130.57 |
| Gross Window-Wall Ratio [%] | 33.01 | 33.01 | 33.01 | 33.01 | 33.01 |
| Above Ground Window-Wall Ratio [%] | 33.01 | 33.01 | 33.01 | 33.01 | 33.01 |
| Total | North (315 to 45 deg) | East (45 to 135 deg) | South (135 to 225 deg) | West (225 to 315 deg) | |
| Gross Wall Area [m2] | 1977.67 | 593.30 | 395.53 | 593.30 | 395.53 |
| Above Ground Wall Area [m2] | 1977.67 | 593.30 | 395.53 | 593.30 | 395.53 |
| Window Opening Area [m2] | 652.83 | 195.85 | 130.57 | 195.85 | 130.57 |
| Gross Window-Wall Ratio [%] | 33.01 | 33.01 | 33.01 | 33.01 | 33.01 |
| Above Ground Window-Wall Ratio [%] | 33.01 | 33.01 | 33.01 | 33.01 | 33.01 |
| Total | |
| Gross Roof Area [m2] | 1660.73 |
| Skylight Area [m2] | 0.00 |
| Skylight-Roof Ratio [%] | 0.00 |
| Area [m2] | Conditioned (Y/N) | Part of Total Floor Area (Y/N) | Volume [m3] | Multipliers | Above Ground Gross Wall Area [m2] | Underground Gross Wall Area [m2] | Window Glass Area [m2] | Opening Area [m2] | Lighting [W/m2] | People [m2 per person] | Plug and Process [W/m2] | |
| CORE_BOTTOM | 983.54 | Yes | Yes | 2698.04 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 10.0460 | 14.09 | 41.1744 |
| CORE_MID | 983.54 | Yes | Yes | 2698.04 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 10.0460 | 14.09 | 8.5270 |
| CORE_TOP | 983.54 | Yes | Yes | 2698.04 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 10.0460 | 14.09 | 8.5270 |
| FIRSTFLOOR_PLENUM | 1660.73 | Yes | No | 2024.76 | 1.00 | 202.84 | 0.00 | 0.00 | 0.00 | 0.0000 | 0.0000 | |
| MIDFLOOR_PLENUM | 1660.73 | Yes | No | 2024.76 | 1.00 | 202.84 | 0.00 | 0.00 | 0.00 | 0.0000 | 0.0000 | |
| PERIMETER_BOT_ZN_1 | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 10.0460 | 14.09 | 8.5270 |
| PERIMETER_BOT_ZN_2 | 131.26 | Yes | Yes | 360.08 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 10.0460 | 14.09 | 8.5270 |
| PERIMETER_BOT_ZN_3 | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 10.0460 | 14.09 | 8.5270 |
| PERIMETER_BOT_ZN_4 | 131.25 | Yes | Yes | 360.05 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 10.0460 | 14.09 | 8.5270 |
| PERIMETER_MID_ZN_1 | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 10.0460 | 14.09 | 8.5270 |
| PERIMETER_MID_ZN_2 | 131.26 | Yes | Yes | 360.08 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 10.0460 | 14.09 | 8.5270 |
| PERIMETER_MID_ZN_3 | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 10.0460 | 14.09 | 8.5270 |
| PERIMETER_MID_ZN_4 | 131.25 | Yes | Yes | 360.05 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 10.0460 | 14.09 | 8.5270 |
| PERIMETER_TOP_ZN_1 | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 10.0460 | 14.09 | 8.5270 |
| PERIMETER_TOP_ZN_2 | 131.26 | Yes | Yes | 360.08 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 10.0460 | 14.09 | 8.5270 |
| PERIMETER_TOP_ZN_3 | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 10.0460 | 14.09 | 8.5270 |
| PERIMETER_TOP_ZN_4 | 131.25 | Yes | Yes | 360.05 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 10.0460 | 14.09 | 8.5270 |
| TOPFLOOR_PLENUM | 1660.73 | Yes | No | 2024.76 | 1.00 | 202.84 | 0.00 | 0.00 | 0.00 | 0.0000 | 0.0000 | |
| Total | 4982.19 | 13667.13 | 1369.16 | 0.00 | 652.83 | 652.83 | 10.0460 | 14.09 | 14.9719 | |||
| Conditioned Total | 4982.19 | 13667.13 | 1369.16 | 0.00 | 652.83 | 652.83 | 10.0460 | 14.09 | 14.9719 | |||
| Unconditioned Total | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | ||||||
| Not Part of Total | 4982.19 | 6074.28 | 608.51 | 0.00 | 0.00 | 0.00 | 0.0000 | 0.0000 |
Report: Component Sizing Summary
For: Entire Facility
Timestamp: 2021-07-16 12:28:42
AirTerminal:SingleDuct:VAV:Reheat| Design Size Maximum Air Flow Rate [m3/s] | Design Size Constant Minimum Air Flow Fraction | User-Specified Constant Minimum Air Flow Fraction | Design Size Minimum Air Flow Rate [m3/s] | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | Design Size Maximum Flow Fraction during Reheat [] | |
| CORE_BOTTOM VAV BOX COMPONENT | 3.99 | 0.200000 | 0.300000 | 1.20 | 0.001217 | 0.300000 |
| CORE_MID VAV BOX COMPONENT | 3.72 | 0.201694 | 0.300000 | 1.11 | 0.001133 | 0.300000 |
| CORE_TOP VAV BOX COMPONENT | 3.93 | 0.200000 | 0.300000 | 1.18 | 0.001198 | 0.300000 |
| PERIMETER_BOT_ZN_1 VAV BOX COMPONENT | 0.764719 | 0.206601 | 0.300000 | 0.229416 | 0.001106 | 0.300000 |
| PERIMETER_BOT_ZN_2 VAV BOX COMPONENT | 0.811345 | 0.200000 | 0.300000 | 0.243404 | 0.001854 | 0.300000 |
| PERIMETER_BOT_ZN_3 VAV BOX COMPONENT | 0.735377 | 0.214844 | 0.300000 | 0.220613 | 0.001064 | 0.300000 |
| PERIMETER_BOT_ZN_4 VAV BOX COMPONENT | 0.848647 | 0.200000 | 0.300000 | 0.254594 | 0.001940 | 0.300000 |
| PERIMETER_MID_ZN_1 VAV BOX COMPONENT | 0.921094 | 0.200000 | 0.300000 | 0.276328 | 0.001333 | 0.300000 |
| PERIMETER_MID_ZN_2 VAV BOX COMPONENT | 0.932022 | 0.200000 | 0.300000 | 0.279607 | 0.002130 | 0.300000 |
| PERIMETER_MID_ZN_3 VAV BOX COMPONENT | 0.884067 | 0.200000 | 0.300000 | 0.265220 | 0.001279 | 0.300000 |
| PERIMETER_MID_ZN_4 VAV BOX COMPONENT | 0.947421 | 0.200000 | 0.300000 | 0.284226 | 0.002165 | 0.300000 |
| PERIMETER_TOP_ZN_1 VAV BOX COMPONENT | 0.973078 | 0.200000 | 0.300000 | 0.291923 | 0.001408 | 0.300000 |
| PERIMETER_TOP_ZN_2 VAV BOX COMPONENT | 0.919386 | 0.200000 | 0.300000 | 0.275816 | 0.002101 | 0.300000 |
| PERIMETER_TOP_ZN_3 VAV BOX COMPONENT | 0.926336 | 0.200000 | 0.300000 | 0.277901 | 0.001340 | 0.300000 |
| PERIMETER_TOP_ZN_4 VAV BOX COMPONENT | 1.03 | 0.200000 | 0.300000 | 0.307713 | 0.002344 | 0.300000 |
| Design Size Nominal Capacity [W] | |
| CORE_BOTTOM VAV BOX REHEAT COIL | 48417.80 |
| CORE_MID VAV BOX REHEAT COIL | 45091.20 |
| CORE_TOP VAV BOX REHEAT COIL | 47669.35 |
| PERIMETER_BOT_ZN_1 VAV BOX REHEAT COIL | 9279.84 |
| PERIMETER_BOT_ZN_2 VAV BOX REHEAT COIL | 9845.65 |
| PERIMETER_BOT_ZN_3 VAV BOX REHEAT COIL | 8923.78 |
| PERIMETER_BOT_ZN_4 VAV BOX REHEAT COIL | 10298.31 |
| PERIMETER_MID_ZN_1 VAV BOX REHEAT COIL | 11177.44 |
| PERIMETER_MID_ZN_2 VAV BOX REHEAT COIL | 11310.06 |
| PERIMETER_MID_ZN_3 VAV BOX REHEAT COIL | 10728.12 |
| PERIMETER_MID_ZN_4 VAV BOX REHEAT COIL | 11496.92 |
| PERIMETER_TOP_ZN_1 VAV BOX REHEAT COIL | 11808.26 |
| PERIMETER_TOP_ZN_2 VAV BOX REHEAT COIL | 11156.72 |
| PERIMETER_TOP_ZN_3 VAV BOX REHEAT COIL | 11241.06 |
| PERIMETER_TOP_ZN_4 VAV BOX REHEAT COIL | 12446.96 |
| Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | Sum of Air Terminal Maximum Flow Rates [m3/s] | Adjusted Heating Design Air Flow Rate [m3/s] | Adjusted Cooling Design Air Flow Rate [m3/s] | Adjusted Main Design Air Flow Rate [m3/s] | User Heating Air Flow Ratio [] | Calculated Heating Air Flow Ratio [] | Design Supply Air Flow Rate [m3/s] | |
| VAV_1 | 2.15 | 2.15 | 7.15 | 2.15 | 7.15 | 7.15 | 0.300000 | 0.300000 | 7.15 |
| VAV_2 | 2.22 | 2.22 | 7.40 | 2.22 | 7.40 | 7.40 | 0.300000 | 0.300000 | 7.40 |
| VAV_3 | 2.33 | 2.33 | 7.77 | 2.33 | 7.77 | 7.77 | 0.300000 | 0.300000 | 7.77 |
| Maximum Outdoor Air Flow Rate [m3/s] | Minimum Outdoor Air Flow Rate [m3/s] | |
| VAV_1_OA_CONTROLLER | 7.15 | 1.47 |
| VAV_2_OA_CONTROLLER | 7.40 | 1.47 |
| VAV_3_OA_CONTROLLER | 7.77 | 1.47 |
| Design Size High Speed Rated Air Flow Rate [m3/s] | Design Size High Speed Gross Rated Total Cooling Capacity [W] | Design Size High Speed Rated Sensible Heat Ratio | Design Size Low Speed Rated Air Flow Rate [m3/s] | Design Size Low Speed Gross Rated Total Cooling Capacity [W] | Design Size Low Speed Gross Rated Sensible Heat Ratio | |
| VAV_1_COOLC DXCOIL | 7.15 | 152559.17 | 0.748234 | 2.38 | 50847.97 | 0.748234 |
| VAV_2_COOLC DXCOIL | 7.40 | 148489.62 | 0.771313 | 2.47 | 49491.59 | 0.771313 |
| VAV_3_COOLC DXCOIL | 7.77 | 152464.16 | 0.780270 | 2.59 | 50816.30 | 0.780270 |
| Design Size Design Maximum Air Flow Rate [m3/s] | Design Electric Power Consumption [W] | |
| VAV_1_FAN | 7.15 | 13413.38 |
| Design Size Nominal Capacity [W] | |
| VAV_1_HEATC | 63931.00 |
| VAV_2_HEATC | 63721.69 |
| VAV_3_HEATC | 63410.53 |
| Design Size Maximum Flow Rate [m3/s] | |
| VAV_2_FAN | 7.40 |
| VAV_3_FAN | 7.77 |
| Maximum Loop Flow Rate [m3/s] | Plant Loop Volume [m3] | |
| SWHSYS1 | 0.000031 | 0.003744 |
| Design Flow Rate [m3/s] | Design Power Consumption [W] | |
| SWHSYS1 PUMP | 0.000031 | 8.44 |
| Use Side Design Flow Rate [m3/s] | |
| SWHSYS1 WATER HEATER | 0.000031 |
Report: Climatic Data Summary
For: Entire Facility
Timestamp: 2021-07-16 12:28:42
SizingPeriod:DesignDay| Maximum Dry Bulb [C] | Daily Temperature Range [deltaC] | Humidity Value | Humidity Type | Wind Speed [m/s] | Wind Direction | |
| CHICAGO ANN HTG 99.6% CONDNS DB | -20.60 | 0.00 | -20.60 | Wetbulb [C] | 4.90 | 270.00 |
| CHICAGO ANN CLG .4% CONDNS WB=>MDB | 31.20 | 10.70 | 25.50 | Wetbulb [C] | 5.30 | 230.00 |
| Value | |
| None |
Report: Envelope Summary
For: Entire Facility
Timestamp: 2021-07-16 12:28:42
Opaque Exterior| Construction | Reflectance | U-Factor with Film [W/m2-K] | U-Factor no Film [W/m2-K] | Gross Area [m2] | Net Area [m2] | Azimuth [deg] | Tilt [deg] | Cardinal Direction | |
| CORE_BOT_ZN_5_FLOOR | EXT-SLAB | 0.30 | 2.193 | 3.401 | 983.54 | 983.54 | 0.00 | 180.00 | |
| PERIMETER_BOT_PLENUM_WALL_EAST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.520 | 0.563 | 40.57 | 40.57 | 90.00 | 90.00 | E |
| PERIMETER_BOT_PLENUM_WALL_NORTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.520 | 0.563 | 60.85 | 60.85 | 0.00 | 90.00 | N |
| PERIMETER_BOT_PLENUM_WALL_SOUTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.520 | 0.563 | 60.85 | 60.85 | 180.00 | 90.00 | S |
| PERIMETER_BOT_PLENUM_WALL_WEST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.520 | 0.563 | 40.57 | 40.57 | 270.00 | 90.00 | W |
| PERIMETER_MID_PLENUM_WALL_EAST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.520 | 0.563 | 40.57 | 40.57 | 90.00 | 90.00 | E |
| PERIMETER_MID_PLENUM_WALL_NORTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.520 | 0.563 | 60.85 | 60.85 | 0.00 | 90.00 | N |
| PERIMETER_MID_PLENUM_WALL_SOUTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.520 | 0.563 | 60.85 | 60.85 | 180.00 | 90.00 | S |
| PERIMETER_MID_PLENUM_WALL_WEST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.520 | 0.563 | 40.57 | 40.57 | 270.00 | 90.00 | W |
| PERIMETER_BOT_ZN_1_WALL_SOUTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.520 | 0.563 | 136.92 | 71.63 | 180.00 | 90.00 | S |
| PERIMETER_BOT_ZN_1_FLOOR | EXT-SLAB | 0.30 | 2.193 | 3.401 | 207.34 | 207.34 | 180.00 | 180.00 | |
| PERIMETER_BOT_ZN_2_WALL_EAST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.520 | 0.563 | 91.28 | 47.75 | 90.00 | 90.00 | E |
| PERIMETER_BOT_ZN_2_FLOOR | EXT-SLAB | 0.30 | 2.193 | 3.401 | 131.26 | 131.26 | 90.00 | 180.00 | |
| PERIMETER_BOT_ZN_3_WALL_NORTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.520 | 0.563 | 136.92 | 71.63 | 0.00 | 90.00 | N |
| PERIMETER_BOT_ZN_3_FLOOR | EXT-SLAB | 0.30 | 2.193 | 3.401 | 207.34 | 207.34 | 0.00 | 180.00 | |
| PERIMETER_BOT_ZN_4_WALL_WEST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.520 | 0.563 | 91.28 | 47.75 | 270.00 | 90.00 | W |
| PERIMETER_BOT_ZN_4_FLOOR | EXT-SLAB | 0.30 | 2.193 | 3.401 | 131.25 | 131.25 | 270.00 | 180.00 | |
| PERIMETER_MID_ZN_1_WALL_SOUTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.520 | 0.563 | 136.92 | 71.63 | 180.00 | 90.00 | S |
| PERIMETER_MID_ZN_2_WALL_EAST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.520 | 0.563 | 91.28 | 47.75 | 90.00 | 90.00 | E |
| PERIMETER_MID_ZN_3_WALL_NORTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.520 | 0.563 | 136.92 | 71.63 | 0.00 | 90.00 | N |
| PERIMETER_MID_ZN_4_WALL_WEST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.520 | 0.563 | 91.28 | 47.75 | 270.00 | 90.00 | W |
| PERIMETER_TOP_ZN_1_WALL_SOUTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.520 | 0.563 | 136.92 | 71.63 | 180.00 | 90.00 | S |
| PERIMETER_TOP_ZN_2_WALL_EAST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.520 | 0.563 | 91.28 | 47.75 | 90.00 | 90.00 | E |
| PERIMETER_TOP_ZN_3_WALL_NORTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.520 | 0.563 | 136.92 | 71.63 | 0.00 | 90.00 | N |
| PERIMETER_TOP_ZN_4_WALL_WEST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.520 | 0.563 | 91.28 | 47.75 | 270.00 | 90.00 | W |
| PERIMETER_TOP_PLENUM_WALL_EAST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.520 | 0.563 | 40.57 | 40.57 | 90.00 | 90.00 | E |
| PERIMETER_TOP_PLENUM_WALL_NORTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.520 | 0.563 | 60.85 | 60.85 | 0.00 | 90.00 | N |
| PERIMETER_TOP_PLENUM_WALL_SOUTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.520 | 0.563 | 60.85 | 60.85 | 180.00 | 90.00 | S |
| PERIMETER_TOP_PLENUM_WALL_WEST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.520 | 0.563 | 40.57 | 40.57 | 270.00 | 90.00 | W |
| BUILDING_ROOF | IEAD NON-RES ROOF | 0.30 | 0.358 | 0.376 | 1660.73 | 1660.73 | 0.00 | 0.00 |
| Construction | Glass Area [m2] | Frame Area [m2] | Divider Area [m2] | Area of One Opening [m2] | Area of Multiplied Openings [m2] | Glass U-Factor [W/m2-K] | Glass SHGC | Glass Visible Transmittance | Frame Conductance [W/m2-K] | Divider Conductance [W/m2-K] | Shade Control | Parent Surface | Azimuth [deg] | Tilt [deg] | Cardinal Direction | |
| PERIMETER_BOT_ZN_1_WALL_SOUTH_WINDOW | WINDOW NON-RES FIXED | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 1.647 | 0.228 | 0.138 | No | PERIMETER_BOT_ZN_1_WALL_SOUTH | 180.00 | 90.00 | S | ||
| PERIMETER_BOT_ZN_2_WALL_EAST_WINDOW | WINDOW NON-RES FIXED | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 1.647 | 0.228 | 0.138 | No | PERIMETER_BOT_ZN_2_WALL_EAST | 90.00 | 90.00 | E | ||
| PERIMETER_BOT_ZN_3_WALL_NORTH_WINDOW | WINDOW NON-RES FIXED | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 1.647 | 0.228 | 0.138 | No | PERIMETER_BOT_ZN_3_WALL_NORTH | 0.00 | 90.00 | N | ||
| PERIMETER_BOT_ZN_4_WALL_WEST_WINDOW | WINDOW NON-RES FIXED | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 1.647 | 0.228 | 0.138 | No | PERIMETER_BOT_ZN_4_WALL_WEST | 270.00 | 90.00 | W | ||
| PERIMETER_MID_ZN_1_WALL_SOUTH_WINDOW | WINDOW NON-RES FIXED | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 1.647 | 0.228 | 0.138 | No | PERIMETER_MID_ZN_1_WALL_SOUTH | 180.00 | 90.00 | S | ||
| PERIMETER_MID_ZN_2_WALL_EAST_WINDOW | WINDOW NON-RES FIXED | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 1.647 | 0.228 | 0.138 | No | PERIMETER_MID_ZN_2_WALL_EAST | 90.00 | 90.00 | E | ||
| PERIMETER_MID_ZN_3_WALL_NORTH_WINDOW | WINDOW NON-RES FIXED | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 1.647 | 0.228 | 0.138 | No | PERIMETER_MID_ZN_3_WALL_NORTH | 0.00 | 90.00 | N | ||
| PERIMETER_MID_ZN_4_WALL_WEST_WINDOW | WINDOW NON-RES FIXED | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 1.647 | 0.228 | 0.138 | No | PERIMETER_MID_ZN_4_WALL_WEST | 270.00 | 90.00 | W | ||
| PERIMETER_TOP_ZN_1_WALL_SOUTH_WINDOW | WINDOW NON-RES FIXED | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 1.647 | 0.228 | 0.138 | No | PERIMETER_TOP_ZN_1_WALL_SOUTH | 180.00 | 90.00 | S | ||
| PERIMETER_TOP_ZN_2_WALL_EAST_WINDOW | WINDOW NON-RES FIXED | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 1.647 | 0.228 | 0.138 | No | PERIMETER_TOP_ZN_2_WALL_EAST | 90.00 | 90.00 | E | ||
| PERIMETER_TOP_ZN_3_WALL_NORTH_WINDOW | WINDOW NON-RES FIXED | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 1.647 | 0.228 | 0.138 | No | PERIMETER_TOP_ZN_3_WALL_NORTH | 0.00 | 90.00 | N | ||
| PERIMETER_TOP_ZN_4_WALL_WEST_WINDOW | WINDOW NON-RES FIXED | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 1.647 | 0.228 | 0.138 | No | PERIMETER_TOP_ZN_4_WALL_WEST | 270.00 | 90.00 | W | ||
| Total or Average | 652.83 | 1.647 | 0.228 | 0.138 | ||||||||||||
| North Total or Average | 195.85 | 1.647 | 0.228 | 0.138 | ||||||||||||
| Non-North Total or Average | 456.98 | 1.647 | 0.228 | 0.138 |
| Construction | Area of One Opening [m2] | Area of Openings [m2] | Glass U-Factor [W/m2-K] | Glass SHGC | Glass Visible Transmittance | Parent Surface | |
| Total or Average | 0.00 | - | - | - |
| Construction | U-Factor with Film [W/m2-K] | U-Factor no Film [W/m2-K] | Gross Area [m2] | Parent Surface | |
| None |
Report: Equipment Summary
For: Entire Facility
Timestamp: 2021-07-16 12:28:42
Central Plant| Type | Nominal Capacity [W] | Nominal Efficiency [W/W] | IPLV in SI Units [W/W] | IPLV in IP Units [Btu/W-h] | |
| None |
| Type | Design Coil Load [W] | Nominal Total Capacity [W] | Nominal Sensible Capacity [W] | Nominal Latent Capacity [W] | Nominal Sensible Heat Ratio | Nominal Efficiency [W/W] | Nominal Coil UA Value [W/C] | Nominal Coil Surface Area [m2] | |
| VAV_1_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | 152559.17 | 114149.97 | 38409.20 | 0.75 | 3.23 | |||
| VAV_2_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | 148489.62 | 114532.04 | 33957.58 | 0.77 | 3.23 | |||
| VAV_3_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | 152464.16 | 118963.25 | 33500.90 | 0.78 | 3.23 |
| DX Cooling Coil Type | Standard Rated Net Cooling Capacity [W] | Standard Rated Net COP [W/W] | EER [Btu/W-h] | SEER [Btu/W-h] | IEER [Btu/W-h] | |
| VAV_1_COOLC DXCOIL | 151486.5 | 2.80 | 9.55 | N/A | 12.69 | |
| VAV_2_COOLC DXCOIL | 147423.0 | 2.78 | 9.47 | N/A | 12.62 | |
| VAV_3_COOLC DXCOIL | 151391.6 | 2.77 | 9.45 | N/A | 12.59 |
| DX Cooling Coil Type | Rated Net Cooling Capacity Test A [W] | Rated Electric Power Test A [W] | Rated Net Cooling Capacity Test B [W] | Rated Electric Power Test B [W] | Rated Net Cooling Capacity Test C [W] | Rated Electric Power Test C [W] | Rated Net Cooling Capacity Test D [W] | Rated Electric Power Test D [W] | |
| VAV_1_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | ||||||||
| VAV_2_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | ||||||||
| VAV_3_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed |
| DX Heating Coil Type | High Temperature Heating (net) Rating Capacity [W] | Low Temperature Heating (net) Rating Capacity [W] | HSPF [Btu/W-h] | Region Number | |
| None |
| Type | Design Coil Load [W] | Nominal Total Capacity [W] | Nominal Efficiency [W/W] | |
| CORE_BOTTOM VAV BOX REHEAT COIL | Coil:Heating:Electric | 48417.80 | 1.00 | |
| CORE_MID VAV BOX REHEAT COIL | Coil:Heating:Electric | 45091.20 | 1.00 | |
| CORE_TOP VAV BOX REHEAT COIL | Coil:Heating:Electric | 47669.35 | 1.00 | |
| PERIMETER_BOT_ZN_1 VAV BOX REHEAT COIL | Coil:Heating:Electric | 9279.84 | 1.00 | |
| PERIMETER_BOT_ZN_2 VAV BOX REHEAT COIL | Coil:Heating:Electric | 9845.65 | 1.00 | |
| PERIMETER_BOT_ZN_3 VAV BOX REHEAT COIL | Coil:Heating:Electric | 8923.78 | 1.00 | |
| PERIMETER_BOT_ZN_4 VAV BOX REHEAT COIL | Coil:Heating:Electric | 10298.31 | 1.00 | |
| PERIMETER_MID_ZN_1 VAV BOX REHEAT COIL | Coil:Heating:Electric | 11177.44 | 1.00 | |
| PERIMETER_MID_ZN_2 VAV BOX REHEAT COIL | Coil:Heating:Electric | 11310.06 | 1.00 | |
| PERIMETER_MID_ZN_3 VAV BOX REHEAT COIL | Coil:Heating:Electric | 10728.12 | 1.00 | |
| PERIMETER_MID_ZN_4 VAV BOX REHEAT COIL | Coil:Heating:Electric | 11496.92 | 1.00 | |
| PERIMETER_TOP_ZN_1 VAV BOX REHEAT COIL | Coil:Heating:Electric | 11808.26 | 1.00 | |
| PERIMETER_TOP_ZN_2 VAV BOX REHEAT COIL | Coil:Heating:Electric | 11156.72 | 1.00 | |
| PERIMETER_TOP_ZN_3 VAV BOX REHEAT COIL | Coil:Heating:Electric | 11241.06 | 1.00 | |
| PERIMETER_TOP_ZN_4 VAV BOX REHEAT COIL | Coil:Heating:Electric | 12446.96 | 1.00 | |
| VAV_1_HEATC | Coil:Heating:Fuel | 63931.00 | 0.80 | |
| VAV_2_HEATC | Coil:Heating:Fuel | 63721.69 | 0.80 | |
| VAV_3_HEATC | Coil:Heating:Fuel | 63410.53 | 0.80 |
| Type | Total Efficiency [W/W] | Delta Pressure [pa] | Max Air Flow Rate [m3/s] | Rated Electric Power [W] | Rated Power Per Max Air Flow Rate [W-s/m3] | Motor Heat In Air Fraction | Fan Energy Index | End Use Subcategory | Design Day Name for Fan Sizing Peak | Date/Time for Fan Sizing Peak | |
| VAV_1_FAN | Fan:SystemModel | 0.59 | 1109.65 | 7.15 | 13413.38 | 1875.99 | 1.00 | 1.12 | Fan Energy | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 09:00:00 |
| VAV_2_FAN | Fan:VariableVolume | 0.59 | 1109.65 | 7.40 | 13883.10 | 1875.99 | 1.00 | 1.12 | Fan Energy | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 07:00:00 |
| VAV_3_FAN | Fan:VariableVolume | 0.59 | 1109.65 | 7.77 | 14581.64 | 1875.99 | 1.00 | 1.11 | Fan Energy | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 07:00:00 |
| Type | Control | Head [pa] | Water Flow [m3/s] | Electric Power [W] | Power Per Water Flow Rate [W-s/m3] | Motor Efficiency [W/W] | End Use Subcategory | |
| SWHSYS1 PUMP | Pump:ConstantSpeed | Intermittent | 179352.00 | 0.000031 | 8.44 | 270515.84 | 0.85 | General |
| Type | Storage Volume [m3] | Input [W] | Thermal Efficiency [W/W] | Recovery Efficiency [W/W] | Energy Factor | |
| SWHSYS1 WATER HEATER | WaterHeater:Mixed | 0.38 | 845000.00 | 0.80 | 1.83 | 0.57 |
| DX Cooling Coil Type | Assocated Fan | Net Cooling Capacity [W] | COP [W/W] | EER [Btu/W-h] | IEER [Btu/W-h] | Supply Air Flow 100% [kg/s] | COP 75% Capacity [W/W] | EER 75% Capacity [Btu/W-h] | Supply Air Flow 75% [kg/s] | COP 50% Capacity [W/W] | EER 50% Capacity [Btu/W-h] | Supply Air Flow 50% [kg/s] | COP 25% Capacity [W/W] | EER 25% Capacity [Btu/W-h] | Supply Air Flow 25% [kg/s] | |
| VAV_1_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | VAV_1_FAN | 151486.52 | 2.80 | 9.55 | 12.69 | 8.1801 | 3.46 | 11.81 | 6.5999 | 4.17 | 14.22 | 4.4272 | 4.29 | 14.64 | 1.8229 |
| VAV_2_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | VAV_2_FAN | 147423.02 | 2.78 | 9.47 | 12.62 | 8.4666 | 3.44 | 11.73 | 6.8443 | 4.15 | 14.15 | 4.5925 | 4.28 | 14.60 | 1.8539 |
| VAV_3_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | VAV_3_FAN | 151391.64 | 2.77 | 9.45 | 12.59 | 8.8926 | 3.43 | 11.70 | 7.1931 | 4.14 | 14.12 | 4.8280 | 4.28 | 14.59 | 1.9343 |
Report: HVAC Sizing Summary
For: Entire Facility
Timestamp: 2021-07-16 12:28:42
Zone Sensible Cooling| Calculated Design Load [W] | User Design Load [W] | User Design Load per Area [W/m2] | Calculated Design Air Flow [m3/s] | User Design Air Flow [m3/s] | Design Day Name | Date/Time Of Peak {TIMESTAMP} | Thermostat Setpoint Temperature at Peak Load [C] | Indoor Temperature at Peak Load [C] | Indoor Humidity Ratio at Peak Load [kgWater/kgAir] | Outdoor Temperature at Peak Load [C] | Outdoor Humidity Ratio at Peak Load [kgWater/kgAir] | Minimum Outdoor Air Flow Rate [m3/s] | Heat Gain Rate from DOAS [W] | |
| CORE_BOTTOM | 35862.99 | 47697.78 | 48.50 | 3.000 | 3.990 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 09:00:00 | 22.64 | 22.63 | 0.00884 | 25.31 | 0.01878 | 0.873 | 0.00 |
| CORE_MID | 34640.53 | 46071.90 | 46.84 | 2.794 | 3.716 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 07:00:00 | 22.64 | 22.63 | 0.00887 | 21.46 | 0.01650 | 0.873 | 0.00 |
| CORE_TOP | 36591.74 | 48667.01 | 49.48 | 2.954 | 3.928 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 07:00:00 | 22.64 | 22.63 | 0.00886 | 21.46 | 0.01650 | 0.873 | 0.00 |
| PERIMETER_BOT_ZN_1 | 6873.91 | 9142.30 | 44.09 | 0.575 | 0.765 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 13:20:00 | 22.64 | 22.63 | 0.00887 | 30.84 | 0.01878 | 0.184 | 0.00 |
| PERIMETER_BOT_ZN_2 | 7293.17 | 9699.92 | 73.90 | 0.610 | 0.811 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 08:40:00 | 22.64 | 22.63 | 0.00872 | 24.64 | 0.01878 | 0.116 | 0.00 |
| PERIMETER_BOT_ZN_3 | 6883.32 | 9154.82 | 44.15 | 0.553 | 0.735 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 07:00:00 | 22.64 | 22.63 | 0.00894 | 21.46 | 0.01650 | 0.184 | 0.00 |
| PERIMETER_BOT_ZN_4 | 7628.47 | 10145.87 | 77.30 | 0.638 | 0.849 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 17:10:00 | 22.64 | 22.63 | 0.00871 | 29.52 | 0.01878 | 0.116 | 0.00 |
| PERIMETER_MID_ZN_1 | 8279.60 | 11011.87 | 53.11 | 0.693 | 0.921 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 13:10:00 | 22.64 | 22.63 | 0.00881 | 30.75 | 0.01878 | 0.184 | 0.00 |
| PERIMETER_MID_ZN_2 | 8377.99 | 11142.73 | 84.89 | 0.701 | 0.932 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 08:30:00 | 22.64 | 22.63 | 0.00869 | 24.30 | 0.01878 | 0.116 | 0.00 |
| PERIMETER_MID_ZN_3 | 8211.01 | 10920.65 | 52.67 | 0.665 | 0.884 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 07:00:00 | 22.64 | 22.63 | 0.00883 | 21.46 | 0.01650 | 0.184 | 0.00 |
| PERIMETER_MID_ZN_4 | 8516.39 | 11326.80 | 86.30 | 0.712 | 0.947 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 17:10:00 | 22.64 | 22.63 | 0.00869 | 29.52 | 0.01878 | 0.116 | 0.00 |
| PERIMETER_TOP_ZN_1 | 8746.90 | 11633.38 | 56.11 | 0.732 | 0.973 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 13:40:00 | 22.64 | 22.63 | 0.00879 | 31.02 | 0.01878 | 0.184 | 0.00 |
| PERIMETER_TOP_ZN_2 | 8466.99 | 11261.10 | 85.79 | 0.691 | 0.919 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 07:00:00 | 22.64 | 22.63 | 0.00870 | 21.46 | 0.01650 | 0.116 | 0.00 |
| PERIMETER_TOP_ZN_3 | 8599.10 | 11436.80 | 55.16 | 0.696 | 0.926 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 07:00:00 | 22.64 | 22.63 | 0.00882 | 21.46 | 0.01650 | 0.184 | 0.00 |
| PERIMETER_TOP_ZN_4 | 9220.18 | 12262.84 | 93.43 | 0.771 | 1.026 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 17:20:00 | 22.64 | 22.63 | 0.00868 | 29.35 | 0.01878 | 0.116 | 0.00 |
| Calculated Design Load [W] | User Design Load [W] | User Design Load per Area [W/m2] | Calculated Design Air Flow [m3/s] | User Design Air Flow [m3/s] | Design Day Name | Date/Time Of Peak {TIMESTAMP} | Thermostat Setpoint Temperature at Peak Load [C] | Indoor Temperature at Peak Load [C] | Indoor Humidity Ratio at Peak Load [kgWater/kgAir] | Outdoor Temperature at Peak Load [C] | Outdoor Humidity Ratio at Peak Load [kgWater/kgAir] | Minimum Outdoor Air Flow Rate [m3/s] | Heat Gain Rate from DOAS [W] | |
| CORE_BOTTOM | 1765.41 | 2348.00 | 2.39 | 0.047 | 0.873 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | 19.03 | 19.03 | 0.00763 | -20.60 | 0.00061 | 0.873 | 0.00 |
| CORE_MID | 5313.44 | 7066.88 | 7.19 | 0.141 | 0.873 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:10:00 | 19.03 | 19.03 | 0.00800 | -20.60 | 0.00061 | 0.873 | 0.00 |
| CORE_TOP | 16346.66 | 21741.06 | 22.10 | 0.434 | 0.873 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 19.03 | 19.03 | 0.00800 | -20.60 | 0.00061 | 0.873 | 0.00 |
| PERIMETER_BOT_ZN_1 | 4016.81 | 5342.35 | 25.77 | 0.107 | 0.184 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | 19.03 | 19.03 | 0.00800 | -20.60 | 0.00061 | 0.184 | 0.00 |
| PERIMETER_BOT_ZN_2 | 2675.73 | 3558.72 | 27.11 | 0.071 | 0.116 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | 19.03 | 19.03 | 0.00800 | -20.60 | 0.00061 | 0.116 | 0.00 |
| PERIMETER_BOT_ZN_3 | 3911.53 | 5202.33 | 25.09 | 0.104 | 0.184 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | 19.03 | 19.03 | 0.00800 | -20.60 | 0.00061 | 0.184 | 0.00 |
| PERIMETER_BOT_ZN_4 | 2672.57 | 3554.52 | 27.08 | 0.071 | 0.116 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | 19.03 | 19.03 | 0.00800 | -20.60 | 0.00061 | 0.116 | 0.00 |
| PERIMETER_MID_ZN_1 | 5046.92 | 6712.40 | 32.37 | 0.134 | 0.184 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:20:00 | 19.03 | 19.03 | 0.00800 | -20.60 | 0.00061 | 0.184 | 0.00 |
| PERIMETER_MID_ZN_2 | 3328.00 | 4426.24 | 33.72 | 0.088 | 0.118 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:20:00 | 19.03 | 19.03 | 0.00800 | -20.60 | 0.00061 | 0.116 | 0.00 |
| PERIMETER_MID_ZN_3 | 4965.27 | 6603.81 | 31.85 | 0.132 | 0.184 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:20:00 | 19.03 | 19.03 | 0.00800 | -20.60 | 0.00061 | 0.184 | 0.00 |
| PERIMETER_MID_ZN_4 | 3337.31 | 4438.62 | 33.82 | 0.089 | 0.118 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:20:00 | 19.03 | 19.03 | 0.00800 | -20.60 | 0.00061 | 0.116 | 0.00 |
| PERIMETER_TOP_ZN_1 | 7571.80 | 10070.49 | 48.57 | 0.201 | 0.268 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 19.03 | 19.03 | 0.00800 | -20.60 | 0.00061 | 0.184 | 0.00 |
| PERIMETER_TOP_ZN_2 | 4923.39 | 6548.11 | 49.89 | 0.131 | 0.174 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 19.03 | 19.03 | 0.00800 | -20.60 | 0.00061 | 0.116 | 0.00 |
| PERIMETER_TOP_ZN_3 | 7516.38 | 9996.79 | 48.21 | 0.200 | 0.266 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 19.03 | 19.03 | 0.00800 | -20.60 | 0.00061 | 0.184 | 0.00 |
| PERIMETER_TOP_ZN_4 | 4938.85 | 6568.68 | 50.05 | 0.131 | 0.175 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 19.03 | 19.03 | 0.00800 | -20.60 | 0.00061 | 0.116 | 0.00 |
| Calculated cooling [m3/s] | User cooling [m3/s] | Calculated heating [m3/s] | User heating [m3/s] | Adjusted cooling [m3/s] | Adjusted heating [m3/s] | Adjusted main [m3/s] | Calculated Heating Air Flow Ratio [] | User Heating Air Flow Ratio [] | |
| VAV_1 | 7.15 | 7.15 | 1.47 | 1.47 | 7.1500 | 2.1450 | 7.1500 | 0.3000 | 0.3000 |
| VAV_2 | 7.40 | 7.40 | 1.48 | 1.48 | 7.4004 | 2.2201 | 7.4004 | 0.3000 | 0.3000 |
| VAV_3 | 7.77 | 7.77 | 1.75 | 1.75 | 7.7728 | 2.3318 | 7.7728 | 0.3000 | 0.3000 |
| Previous Design Volume Flow Rate [m3/s] | Algorithm Volume Flow Rate [m3/s] | Coincident Design Volume Flow Rate [m3/s] | Coincident Size Adjusted | Peak Sizing Period Name | Peak Day into Period {TIMESTAMP}[day] | Peak Hour Of Day {TIMESTAMP}[hr] | Peak Step Start Minute {TIMESTAMP}[min] | |
| None |
| Coil Type | HVAC Type | HVAC Name | Coil Final Gross Total Capacity [W] | Coil Final Gross Sensible Capacity [W] | Coil Final Reference Air Volume Flow Rate [m3/s] | Coil Final Reference Plant Fluid Volume Flow Rate [m3/s] | Coil U-value Times Area Value [W/K] | Design Day Name at Sensible Ideal Loads Peak | Date/Time at Sensible Ideal Loads Peak | Design Day Name at Air Flow Ideal Loads Peak | Date/Time at Air Flow Ideal Loads Peak | Coil Total Capacity at Ideal Loads Peak [W] | Coil Sensible Capacity at Ideal Loads Peak [W] | Coil Air Volume Flow Rate at Ideal Loads Peak [m3/s] | Coil Entering Air Drybulb at Ideal Loads Peak [C] | Coil Entering Air Wetbulb at Ideal Loads Peak [C] | Coil Entering Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Coil Leaving Air Drybulb at Ideal Loads Peak [C] | Coil Leaving Air Wetbulb at Ideal Loads Peak [C] | Coil Leaving Air Humidity Ratio at Ideal Loads Peak [C] | Outdoor Air Drybulb at Ideal Loads Peak [C] | Outdoor Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Outdoor Air Wetbulb at Ideal Loads Peak [C] | Outdoor Air Flow Percentage at Ideal Loads Peak [%] | Zone Air Drybulb at Ideal Loads Peak [C] | Zone Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Zone Air Relative Humidity at Ideal Loads Peak [%] | Zone Sensible Heat Gain at Ideal Loads Peak [W] | Zone Latent Heat Gain at Ideal Loads Peak [W] | Coil Total Capacity at Rating Conditions [W] | Coil Sensible Capacity at Rating Conditions [W] | |
| CORE_BOTTOM VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | CORE_BOTTOM VAV BOX | 48417.796 | 48417.796 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | 48417.80 | 35304.51 | 0.872796 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.03 | 0.00762551 | 55.1391 | 2348.00 | 0.00 | -999.00 | -999.00 |
| CORE_MID VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | CORE_MID VAV BOX | 45091.201 | 45091.201 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:10:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:10:00 | 45091.20 | 35304.51 | 0.872796 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.03 | 0.00800000 | 57.8121 | 7066.88 | 0.00 | -999.00 | -999.00 |
| CORE_TOP VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | CORE_TOP VAV BOX | 47669.349 | 47669.349 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 47669.35 | 35304.51 | 0.872796 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.03 | 0.00800000 | 57.8121 | 21741.06 | 0.00 | -999.00 | -999.00 |
| PERIMETER_BOT_ZN_1 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_BOT_ZN_1 VAV BOX | 9279.842 | 9279.842 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | 9279.84 | 7442.50 | 0.183993 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.03 | 0.00800000 | 57.8121 | 5342.35 | 0.00 | -999.00 | -999.00 |
| PERIMETER_BOT_ZN_2 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_BOT_ZN_2 VAV BOX | 9845.648 | 9845.648 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | 9845.65 | 4711.72 | 0.116483 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.03 | 0.00800000 | 57.8121 | 3558.72 | 0.00 | -999.00 | -999.00 |
| PERIMETER_BOT_ZN_3 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_BOT_ZN_3 VAV BOX | 8923.780 | 8923.780 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | 8923.78 | 7442.50 | 0.183993 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.03 | 0.00800000 | 57.8121 | 5202.33 | 0.00 | -999.00 | -999.00 |
| PERIMETER_BOT_ZN_4 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_BOT_ZN_4 VAV BOX | 10298.309 | 10298.309 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | 10298.31 | 4711.41 | 0.116475 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.03 | 0.00800000 | 57.8121 | 3554.52 | 0.00 | -999.00 | -999.00 |
| PERIMETER_MID_ZN_1 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_MID_ZN_1 VAV BOX | 11177.441 | 11177.441 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:20:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:20:00 | 11177.44 | 7442.50 | 0.183993 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.03 | 0.00800000 | 57.8121 | 6712.40 | 0.00 | -999.00 | -999.00 |
| PERIMETER_MID_ZN_2 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_MID_ZN_2 VAV BOX | 11310.063 | 11310.063 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:20:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:20:00 | 11310.06 | 4758.79 | 0.117646 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.03 | 0.00800000 | 57.8121 | 4426.24 | 0.00 | -999.00 | -999.00 |
| PERIMETER_MID_ZN_3 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_MID_ZN_3 VAV BOX | 10728.124 | 10728.124 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:20:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:20:00 | 10728.12 | 7442.50 | 0.183993 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.03 | 0.00800000 | 57.8121 | 6603.81 | 0.00 | -999.00 | -999.00 |
| PERIMETER_MID_ZN_4 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_MID_ZN_4 VAV BOX | 11496.920 | 11496.920 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:20:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:20:00 | 11496.92 | 4772.10 | 0.117975 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.03 | 0.00800000 | 57.8121 | 4438.62 | 0.00 | -999.00 | -999.00 |
| PERIMETER_TOP_ZN_1 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_TOP_ZN_1 VAV BOX | 11808.265 | 11808.265 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 11808.26 | 10827.09 | 0.267667 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.03 | 0.00800000 | 57.8121 | 10070.49 | 0.00 | -999.00 | -999.00 |
| PERIMETER_TOP_ZN_2 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_TOP_ZN_2 VAV BOX | 11156.725 | 11156.725 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 11156.72 | 7040.07 | 0.174044 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.03 | 0.00800000 | 57.8121 | 6548.11 | 0.00 | -999.00 | -999.00 |
| PERIMETER_TOP_ZN_3 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_TOP_ZN_3 VAV BOX | 11241.060 | 11241.060 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 11241.06 | 10747.85 | 0.265708 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.03 | 0.00800000 | 57.8121 | 9996.79 | 0.00 | -999.00 | -999.00 |
| PERIMETER_TOP_ZN_4 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_TOP_ZN_4 VAV BOX | 12446.965 | 12446.965 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 12446.96 | 7062.18 | 0.174591 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.03 | 0.00800000 | 57.8121 | 6568.68 | 0.00 | -999.00 | -999.00 |
| VAV_1_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | AirLoopHVAC | VAV_1 | 152559.171 | 114149.972 | 7.150029 | -999.0 | -999.000 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 13:00:00 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 09:00:00 | 147360.28 | 101106.76 | 7.150029 | 24.14 | 18.24 | 0.01083031 | 11.26 | 11.26 | 0.00850000 | 25.93 | 0.01854760 | 24.17 | 20.6117 | 22.63 | 0.00882666 | 51.0230 | 85840.68 | 0.00 | 152544.29 | 114073.24 |
| VAV_1_HEATC | Coil:Heating:Fuel | AirLoopHVAC | VAV_1 | 63930.999 | 63930.999 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 00:10:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 00:10:00 | 63931.00 | 63931.00 | 2.145009 | -20.60 | -20.60 | 0.00061258 | 16.70 | 13.08 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 68.7056 | 19.03 | 0.00777821 | 56.2294 | 20005.93 | 0.00 | -999.00 | -999.00 |
| VAV_2_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | AirLoopHVAC | VAV_2 | 148489.616 | 114532.040 | 7.400411 | -999.0 | -999.000 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 15:00:00 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 07:00:00 | 143216.32 | 101837.68 | 7.400411 | 23.81 | 17.88 | 0.01051613 | 11.26 | 11.26 | 0.00850000 | 24.01 | 0.01736105 | 22.90 | 19.9143 | 22.63 | 0.00881405 | 50.9504 | 90473.95 | 0.00 | 148475.13 | 114431.56 |
| VAV_2_HEATC | Coil:Heating:Fuel | AirLoopHVAC | VAV_2 | 63721.690 | 63721.690 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 17:40:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:20:00 | 63721.69 | 63721.69 | 2.220123 | -20.53 | -20.53 | 0.00062590 | 16.70 | 13.08 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 66.3810 | 19.03 | 0.00800000 | 57.8121 | 29247.95 | 0.00 | -999.00 | -999.00 |
| VAV_3_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | AirLoopHVAC | VAV_3 | 152464.157 | 118963.255 | 7.772774 | -999.0 | -999.000 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 16:20:00 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 07:00:00 | 147467.89 | 106857.18 | 7.772774 | 23.72 | 17.73 | 0.01037182 | 11.26 | 11.26 | 0.00850000 | 23.70 | 0.01708363 | 22.63 | 18.9603 | 22.63 | 0.00880151 | 50.8788 | 95261.13 | 0.00 | 152449.29 | 118850.75 |
| VAV_3_HEATC | Coil:Heating:Fuel | AirLoopHVAC | VAV_3 | 63410.529 | 63410.529 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 01:00:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 63410.53 | 63410.53 | 2.331832 | -14.25 | -14.25 | 0.00179581 | 16.70 | 13.08 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 63.2010 | 19.03 | 0.00800000 | 57.8121 | 54925.12 | 0.00 | -999.00 | -999.00 |
Report: System Summary
For: Entire Facility
Timestamp: 2021-07-16 12:28:42
Economizer| High Limit Shutoff Control | Minimum Outdoor Air [m3/s] | Maximum Outdoor Air [m3/s] | Return Air Temp Limit | Return Air Enthalpy Limit | Outdoor Air Temperature Limit [C] | Outdoor Air Enthalpy Limit [C] | |
| VAV_1_OA_CONTROLLER | DifferentialDryBulb | 1.47 | 7.15 | - | |||
| VAV_2_OA_CONTROLLER | DifferentialDryBulb | 1.47 | 7.40 | - | |||
| VAV_3_OA_CONTROLLER | DifferentialDryBulb | 1.47 | 7.77 | - |
| Controller:MechanicalVentilation Name | Outdoor Air Per Person [m3/s-person] | Outdoor Air Per Area [m3/s-m2] | Outdoor Air Per Zone [m3/s] | Outdoor Air ACH [ach] | Outdoor Air Method | Outdoor Air Schedule Name | Air Distribution Effectiveness in Cooling Mode | Air Distribution Effectiveness in Heating Mode | Air Distribution Effectiveness Schedule Name | |
| None |
| Winter Clothes [hr] | Summer Clothes [hr] | Summer or Winter Clothes [hr] | |
| CORE_BOTTOM | 787.67 | 5087.17 | 787.67 |
| CORE_MID | 1249.17 | 4958.33 | 1180.67 |
| CORE_TOP | 2014.83 | 4925.83 | 1883.00 |
| PERIMETER_BOT_ZN_1 | 1167.33 | 5043.33 | 1167.33 |
| PERIMETER_BOT_ZN_2 | 2129.83 | 4970.83 | 2129.33 |
| PERIMETER_BOT_ZN_3 | 2138.67 | 5096.83 | 2138.67 |
| PERIMETER_BOT_ZN_4 | 2230.17 | 4848.00 | 2223.83 |
| PERIMETER_MID_ZN_1 | 1103.67 | 4754.33 | 1058.33 |
| PERIMETER_MID_ZN_2 | 2028.17 | 4669.50 | 1974.33 |
| PERIMETER_MID_ZN_3 | 2001.83 | 5005.33 | 1966.00 |
| PERIMETER_MID_ZN_4 | 2121.83 | 4595.33 | 2017.33 |
| PERIMETER_TOP_ZN_1 | 1607.17 | 4557.00 | 1509.83 |
| PERIMETER_TOP_ZN_2 | 2286.33 | 4466.17 | 2179.00 |
| PERIMETER_TOP_ZN_3 | 2321.17 | 4857.83 | 2236.00 |
| PERIMETER_TOP_ZN_4 | 2530.17 | 4467.17 | 2303.67 |
| FIRSTFLOOR_PLENUM | 0.00 | 0.00 | 0.00 |
| MIDFLOOR_PLENUM | 0.00 | 0.00 | 0.00 |
| TOPFLOOR_PLENUM | 0.00 | 0.00 | 0.00 |
| Facility | 2886.67 | 5104.33 | 2575.17 |
| During Heating [hr] | During Cooling [hr] | During Occupied Heating [hr] | During Occupied Cooling [hr] | |
| CORE_BOTTOM | 0.00 | 0.00 | 0.00 | 0.00 |
| CORE_MID | 0.00 | 0.00 | 0.00 | 0.00 |
| CORE_TOP | 0.00 | 0.50 | 0.00 | 0.50 |
| PERIMETER_BOT_ZN_1 | 0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_BOT_ZN_2 | 0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_BOT_ZN_3 | 0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_BOT_ZN_4 | 0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_MID_ZN_1 | 0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_MID_ZN_2 | 0.00 | 0.83 | 0.00 | 0.00 |
| PERIMETER_MID_ZN_3 | 0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_MID_ZN_4 | 0.00 | 1.00 | 0.00 | 0.00 |
| PERIMETER_TOP_ZN_1 | 1.17 | 0.67 | 0.33 | 0.17 |
| PERIMETER_TOP_ZN_2 | 4.67 | 1.83 | 0.00 | 0.00 |
| PERIMETER_TOP_ZN_3 | 9.67 | 0.17 | 3.50 | 0.17 |
| PERIMETER_TOP_ZN_4 | 3.33 | 2.50 | 0.00 | 0.00 |
| FIRSTFLOOR_PLENUM | 0.00 | 0.00 | 0.00 | 0.00 |
| MIDFLOOR_PLENUM | 0.00 | 0.00 | 0.00 | 0.00 |
| TOPFLOOR_PLENUM | 0.00 | 0.00 | 0.00 | 0.00 |
| Facility | 10.50 | 7.00 | 3.50 | 0.50 |
Report: EMISSIONS DATA SUMMARY
For: Meter
Timestamp: 2021-07-16 12:28:42
Custom Monthly Report| CO2:FACILITY [kg] | NOX:FACILITY [kg] | SO2:FACILITY [kg] | PM:FACILITY [kg] | HG:FACILITY [kg] | WATERENVIRONMENTALFACTORS:FACILITY [L] | CARBON EQUIVALENT:FACILITY [kg] | |
| January | 66552.5321 | 116.8531 | 338.6375 | 0.0000 | 0.0010 | 77952.5678 | 19122.2923 |
| February | 54908.4677 | 96.9735 | 282.7770 | 0.0000 | 0.0009 | 65094.5644 | 15785.2146 |
| March | 56282.3409 | 100.3962 | 295.8248 | 0.0000 | 0.0009 | 68099.5080 | 16195.2842 |
| April | 53932.3209 | 97.9233 | 293.7784 | 0.0000 | 0.0009 | 67630.7468 | 15545.1289 |
| May | 61473.2747 | 111.7911 | 335.9096 | 0.0000 | 0.0010 | 77330.0143 | 17721.3550 |
| June | 69848.0211 | 127.0554 | 381.8791 | 0.0000 | 0.0012 | 87912.7255 | 20136.1290 |
| July | 73865.2812 | 134.3786 | 403.9367 | 0.0000 | 0.0012 | 92990.6357 | 21294.4823 |
| August | 73195.0907 | 133.1556 | 400.2490 | 0.0000 | 0.0012 | 92141.6866 | 21101.2169 |
| September | 61454.0627 | 111.7720 | 335.8998 | 0.0000 | 0.0010 | 77327.7776 | 17716.0574 |
| October | 60320.8114 | 109.5513 | 328.7491 | 0.0000 | 0.0010 | 75681.3917 | 17386.9429 |
| November | 53237.3658 | 95.6599 | 283.9885 | 0.0000 | 0.0009 | 65375.7030 | 15329.6330 |
| December | 59875.3174 | 106.7074 | 314.1227 | 0.0000 | 0.0010 | 72311.5842 | 17227.6808 |
| Annual Sum or Average |<PHONE_NUMBER> | 1342.2175 | 3995.7521 | 0.0000 | 0.0121 |<PHONE_NUMBER> |<PHONE_NUMBER> |
| Minimum of Months | 53237.3658 | 95.6599 | 282.7770 | 0.0000 | 0.0009 | 65094.5644 | 15329.6330 |
| Maximum of Months | 73865.2812 | 134.3786 | 403.9367 | 0.0000 | 0.0012 | 92990.6357 | 21294.4823 |
Report: COMPONENTS OF PEAK ELECTRICAL DEMAND
For: Meter
Timestamp: 2021-07-16 12:28:42
Custom Monthly Report| ELECTRICITY:FACILITY [J] | ELECTRICITY:FACILITY {Maximum}[W] | ELECTRICITY:FACILITY {TIMESTAMP} | INTERIORLIGHTS:ELECTRICITY {AT MAX/MIN} [W] | INTERIOREQUIPMENT:ELECTRICITY {AT MAX/MIN} [W] | FANS:ELECTRICITY {AT MAX/MIN} [W] | HEATING:ELECTRICITY {AT MAX/MIN} [W] | COOLING:ELECTRICITY {AT MAX/MIN} [W] | EXTERIORLIGHTS:ELECTRICITY {AT MAX/MIN} [W] | PUMPS:ELECTRICITY {AT MAX/MIN} [W] | HEATREJECTION:ELECTRICITY [] | EXTERIOREQUIPMENT:ELECTRICITY [] | HUMIDIFICATION:ELECTRICITY [] | HEATRECOVERY:ELECTRICITY [] | WATERSYSTEMS:ELECTRICITY [] | REFRIGERATION:ELECTRICITY [] | GENERATORS:ELECTRICITY [] | ELECTRICITYPRODUCED:FACILITY [] | |
| January | 0.180883E+12 | 168313.414 | 02-JAN-06:10 | 5005.104 | 16993.240 | 3605.330 | 127897.300 | 0.000 | 14804.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| February | 0.151047E+12 | 151833.392 | 18-FEB-06:10 | 5005.104 | 16993.240 | 3605.330 | 111417.279 | 0.000 | 14804.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| March | 0.158020E+12 | 132879.205 | 04-MAR-08:09 | 45045.936 | 60390.613 | 3605.330 | 23828.886 | 0.000 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| April | 0.156932E+12 | 141587.510 | 15-APR-12:00 | 45045.936 | 53647.536 | 4499.977 | 0.000 | 38385.621 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| May | 0.179438E+12 | 167652.427 | 02-MAY-13:00 | 45045.936 | 50115.449 | 6095.302 | 0.000 | 66387.300 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| June | 0.203995E+12 | 188397.263 | 17-JUN-15:00 | 45045.936 | 53005.339 | 8261.422 | 0.000 | 82076.127 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| July | 0.215778E+12 | 214527.730 | 02-JUL-15:09 | 45045.936 | 53005.339 | 8520.800 | 0.000 | 107947.216 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| August | 0.213808E+12 | 180237.977 | 12-AUG-07:00 | 45045.936 | 60390.613 | 6158.060 | 0.000 | 68634.928 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| September | 0.179433E+12 | 197697.349 | 11-SEP-12:00 | 45045.936 | 53647.536 | 7195.084 | 0.000 | 91800.353 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| October | 0.175613E+12 | 163638.942 | 07-OCT-10:00 | 45045.936 | 52042.042 | 4978.836 | 0.000 | 61563.689 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| November | 0.151699E+12 | 137362.438 | 01-NOV-07:10 | 45045.936 | 60390.613 | 3605.330 | 0.000 | 28312.119 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| December | 0.167794E+12 | 137650.345 | 16-DEC-08:09 | 45045.936 | 60390.613 | 3605.330 | 28600.026 | 0.000 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| Annual Sum or Average | 0.213444E+13 | |||||||||||||||||
| Minimum of Months | 0.151047E+12 | 132879.205 | 5005.104 | 16993.240 | 3605.330 | 0.000 | 0.000 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | |
| Maximum of Months | 0.215778E+12 | 214527.730 | 45045.936 | 60390.613 | 8520.800 | 127897.300 | 107947.216 | 14804.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
Report: HEATING PART LOAD PERFORMANCE
For: VAV_1_HEATC
Timestamp: 2021-07-16 12:28:42
Custom Monthly Report| HEATING COIL GAS RATE [W] | HEATING COIL GAS RATE {Maximum}[W] | HEATING COIL GAS RATE {TIMESTAMP} | |
| January | 10309. | 57821. | 04-JAN-07:10 |
| February | 8064. | 52078. | 12-FEB-07:05 |
| March | 4917. | 43190. | 01-MAR-07:10 |
| April | 355. | 18645. | 16-APR-06:03 |
| May | 0. | 0. | 01-MAY-00:10 |
| June | 0. | 0. | 01-JUN-00:10 |
| July | 0. | 0. | 01-JUL-00:10 |
| August | 0. | 0. | 01-AUG-00:10 |
| September | 21. | 9457. | 18-SEP-06:03 |
| October | 381. | 21339. | 26-OCT-06:10 |
| November | 2960. | 30515. | 25-NOV-07:05 |
| December | 5438. | 37668. | 11-DEC-07:03 |
| Annual Sum or Average | 2709. | ||
| Minimum of Months | 0. | 0. | |
| Maximum of Months | 10309. | 57821. |
Report: HEATING PART LOAD PERFORMANCE
For: VAV_2_HEATC
Timestamp: 2021-07-16 12:28:42
Custom Monthly Report| HEATING COIL GAS RATE [W] | HEATING COIL GAS RATE {Maximum}[W] | HEATING COIL GAS RATE {TIMESTAMP} | |
| January | 10471. | 57649. | 04-JAN-07:10 |
| February | 8214. | 51792. | 12-FEB-07:05 |
| March | 4974. | 42781. | 01-MAR-07:10 |
| April | 292. | 16873. | 16-APR-06:03 |
| May | 0. | 0. | 01-MAY-00:10 |
| June | 0. | 0. | 01-JUN-00:10 |
| July | 0. | 0. | 01-JUL-00:10 |
| August | 0. | 0. | 01-AUG-00:10 |
| September | 13. | 8064. | 18-SEP-06:03 |
| October | 354. | 20477. | 26-OCT-06:10 |
| November | 3034. | 30287. | 25-NOV-07:05 |
| December | 5596. | 37325. | 11-DEC-07:03 |
| Annual Sum or Average | 2750. | ||
| Minimum of Months | 0. | 0. | |
| Maximum of Months | 10471. | 57649. |
Report: HEATING PART LOAD PERFORMANCE
For: VAV_3_HEATC
Timestamp: 2021-07-16 12:28:42
Custom Monthly Report| HEATING COIL GAS RATE [W] | HEATING COIL GAS RATE {Maximum}[W] | HEATING COIL GAS RATE {TIMESTAMP} | |
| January | 10893. | 62111. | 04-JAN-07:10 |
| February | 8552. | 55856. | 12-FEB-07:05 |
| March | 5200. | 47053. | 01-MAR-07:10 |
| April | 362. | 18945. | 16-APR-06:03 |
| May | 0. | 0. | 01-MAY-00:10 |
| June | 0. | 0. | 01-JUN-00:10 |
| July | 0. | 0. | 01-JUL-00:10 |
| August | 0. | 0. | 01-AUG-00:10 |
| September | 22. | 9886. | 18-SEP-06:03 |
| October | 419. | 23343. | 26-OCT-06:10 |
| November | 3280. | 33752. | 25-NOV-07:05 |
| December | 5946. | 40638. | 11-DEC-07:03 |
| Annual Sum or Average | 2894. | ||
| Minimum of Months | 0. | 0. | |
| Maximum of Months | 10893. | 62111. |
Report: COOLING PART LOAD PERFORMANCE
For: VAV_1_COOLC DXCOIL
Timestamp: 2021-07-16 12:28:42
Custom Monthly Report| COOLING COIL ELECTRIC POWER [W] | COOLING COIL ELECTRIC POWER {Maximum}[W] | COOLING COIL ELECTRIC POWER {TIMESTAMP} | |
| January | 53. | 6417. | 11-JAN-15:00 |
| February | 0. | 0. | 01-FEB-00:10 |
| March | 174. | 4946. | 12-MAR-14:00 |
| April | 1243. | 12555. | 15-APR-13:00 |
| May | 4069. | 20031. | 02-MAY-14:00 |
| June | 7707. | 34398. | 19-JUN-05:02 |
| July | 9144. | 37273. | 08-JUL-05:02 |
| August | 8054. | 36910. | 22-AUG-05:02 |
| September | 4459. | 32793. | 02-SEP-05:02 |
| October | 2275. | 19996. | 07-OCT-11:20 |
| November | 373. | 9691. | 01-NOV-07:20 |
| December | 105. | 5434. | 21-DEC-15:30 |
| Annual Sum or Average | 3135. | ||
| Minimum of Months | 0. | 0. | |
| Maximum of Months | 9144. | 37273. |
Report: COOLING PART LOAD PERFORMANCE
For: VAV_2_COOLC DXCOIL
Timestamp: 2021-07-16 12:28:42
Custom Monthly Report| COOLING COIL ELECTRIC POWER [W] | COOLING COIL ELECTRIC POWER {Maximum}[W] | COOLING COIL ELECTRIC POWER {TIMESTAMP} | |
| January | 54. | 6660. | 11-JAN-15:00 |
| February | 0. | 0. | 01-FEB-00:10 |
| March | 172. | 5112. | 22-MAR-15:00 |
| April | 1265. | 19138. | 15-APR-05:02 |
| May | 4290. | 32187. | 16-MAY-05:02 |
| June | 7763. | 35926. | 26-JUN-05:02 |
| July | 9090. | 36278. | 08-JUL-05:02 |
| August | 7664. | 35926. | 22-AUG-05:02 |
| September | 4395. | 36036. | 02-SEP-05:02 |
| October | 2302. | 29595. | 07-OCT-05:02 |
| November | 368. | 11821. | 01-NOV-05:02 |
| December | 106. | 5528. | 21-DEC-15:50 |
| Annual Sum or Average | 3120. | ||
| Minimum of Months | 0. | 0. | |
| Maximum of Months | 9090. | 36278. |
Report: COOLING PART LOAD PERFORMANCE
For: VAV_3_COOLC DXCOIL
Timestamp: 2021-07-16 12:28:42
Custom Monthly Report| COOLING COIL ELECTRIC POWER [W] | COOLING COIL ELECTRIC POWER {Maximum}[W] | COOLING COIL ELECTRIC POWER {TIMESTAMP} | |
| January | 57. | 7000. | 11-JAN-15:00 |
| February | 0. | 0. | 01-FEB-00:10 |
| March | 178. | 5369. | 22-MAR-15:00 |
| April | 1348. | 20253. | 15-APR-05:02 |
| May | 4764. | 34609. | 16-MAY-05:02 |
| June | 8666. | 36887. | 26-JUN-05:02 |
| July | 10036. | 38920. | 02-JUL-15:00 |
| August | 8105. | 36887. | 22-AUG-05:02 |
| September | 4614. | 37000. | 02-SEP-05:04 |
| October | 2397. | 31702. | 07-OCT-05:02 |
| November | 378. | 10150. | 01-NOV-05:10 |
| December | 110. | 5767. | 21-DEC-15:40 |
| Annual Sum or Average | 3384. | ||
| Minimum of Months | 0. | 0. | |
| Maximum of Months | 10036. | 38920. |
Report: FAN PART LOAD PERFORMANCE
For: VAV_1_FAN
Timestamp: 2021-07-16 12:28:42
Custom Monthly Report| FAN ELECTRIC POWER [W] | FAN ELECTRIC POWER {Maximum}[W] | FAN ELECTRIC POWER {TIMESTAMP} | |
| January | 585. | 1342. | 13-JAN-13:50 |
| February | 615. | 1360. | 20-FEB-14:00 |
| March | 634. | 1481. | 12-MAR-13:00 |
| April | 686. | 1696. | 14-APR-16:10 |
| May | 705. | 1907. | 12-MAY-16:10 |
| June | 878. | 8413. | 18-JUN-05:02 |
| July | 988. | 12650. | 14-JUL-05:02 |
| August | 960. | 10427. | 22-AUG-05:02 |
| September | 823. | 4594. | 02-SEP-05:02 |
| October | 739. | 1933. | 04-OCT-15:10 |
| November | 618. | 1602. | 01-NOV-13:00 |
| December | 612. | 1421. | 20-DEC-13:50 |
| Annual Sum or Average | 737. | ||
| Minimum of Months | 585. | 1342. | |
| Maximum of Months | 988. | 12650. |
Report: FAN PART LOAD PERFORMANCE
For: VAV_2_FAN
Timestamp: 2021-07-16 12:28:42
Custom Monthly Report| FAN ELECTRIC POWER [W] | FAN ELECTRIC POWER {Maximum}[W] | FAN ELECTRIC POWER {TIMESTAMP} | |
| January | 599. | 1313. | 13-JAN-13:30 |
| February | 628. | 1293. | 20-FEB-13:40 |
| March | 641. | 1365. | 11-MAR-13:30 |
| April | 687. | 7331. | 15-APR-05:02 |
| May | 747. | 10859. | 27-MAY-05:02 |
| June | 860. | 13793. | 19-JUN-05:02 |
| July | 920. | 13878. | 14-JUL-05:02 |
| August | 841. | 12822. | 22-AUG-05:02 |
| September | 766. | 13878. | 02-SEP-05:02 |
| October | 727. | 9822. | 07-OCT-05:02 |
| November | 617. | 1579. | 01-NOV-05:02 |
| December | 620. | 1332. | 20-DEC-13:30 |
| Annual Sum or Average | 721. | ||
| Minimum of Months | 599. | 1293. | |
| Maximum of Months | 920. | 13878. |
Report: FAN PART LOAD PERFORMANCE
For: VAV_3_FAN
Timestamp: 2021-07-16 12:28:42
Custom Monthly Report| FAN ELECTRIC POWER [W] | FAN ELECTRIC POWER {Maximum}[W] | FAN ELECTRIC POWER {TIMESTAMP} | |
| January | 713. | 1283. | 13-JAN-13:40 |
| February | 688. | 1283. | 20-FEB-14:10 |
| March | 669. | 1373. | 12-MAR-13:50 |
| April | 722. | 8736. | 14-APR-05:02 |
| May | 838. | 12434. | 27-MAY-05:02 |
| June | 991. | 14576. | 19-JUN-05:02 |
| July | 1061. | 14576. | 08-JUL-05:02 |
| August | 895. | 14307. | 22-AUG-05:02 |
| September | 802. | 14576. | 02-SEP-05:02 |
| October | 751. | 10986. | 07-OCT-05:02 |
| November | 640. | 1443. | 18-NOV-13:05 |
| December | 653. | 1299. | 20-DEC-13:30 |
| Annual Sum or Average | 785. | ||
| Minimum of Months | 640. | 1283. | |
| Maximum of Months | 1061. | 14576. |


This is a sample NODE JS application , using Express framework and REST API (Salesforce). Use the Password with your security token to avoide failures. Added only Account object for reference. You can create record using just Account Name and Phone number. There is no validations and no error handling as of now. If there are any errors you will not be able to see it on the UI.


Pages, Numbers, and Keynote for iOS updated with performance and bug fixes
by Michael PotuckApple’s iWork suite for iOS and iPadOS has been updated today with “stability and performance improvements.”
Version 5.2.1 for Pages, Numbers, and Keynote is now available for iPhone and iPad.
It comes after a major update back in September that brought support for iOS 13 and iPadOS 13. That included Dark Mode support, multiwindow support for iPad, the ability to use external drives, and more.
The generic release notes for today’s updates mention minor changes:
This update contains stability and performance improvements.
Pages, Numbers, and Keynote are free downloads from the App Store.
FTC: We use income earning auto affiliate links. More.


|
JavaTM 2 Platform Standard Ed. 5.0 |
|||||||||
| PREV CLASS NEXT CLASS | FRAMES NO FRAMES | |||||||||
| SUMMARY: NESTED | FIELD | CONSTR | METHOD | DETAIL: FIELD | CONSTR | METHOD |
java.lang.Object java.net.ServerSocket
public class ServerSocket
This class implements server sockets. A server socket waits for requests to come in over the network. It performs some operation based on that request, and then possibly returns a result to the requester.
The actual work of the server socket is performed by an instance
of the SocketImpl
class. An application can
change the socket factory that creates the socket
implementation to configure itself to create sockets
appropriate to the local firewall.
SocketImpl
,
setSocketFactory(java.net.SocketImplFactory)
,
ServerSocketChannel
| Constructor Summary | |
|---|---|
ServerSocket()
Creates an unbound server socket. |
|
ServerSocket(int port)
Creates a server socket, bound to the specified port. |
|
ServerSocket(int port,
int backlog)
Creates a server socket and binds it to the specified local port number, with the specified backlog. |
|
ServerSocket(int port,
int backlog,
InetAddress bindAddr)
Create a server with the specified port, listen backlog, and local IP address to bind to. |
| Method Summary | |
|---|---|
Socket |
accept()
Listens for a connection to be made to this socket and accepts it. |
void |
bind(SocketAddress endpoint)
Binds the ServerSocket to a specific address
(IP address and port number). |
void |
bind(SocketAddress endpoint,
int backlog)
Binds the ServerSocket to a specific address
(IP address and port number). |
void |
close()
Closes this socket. |
ServerSocketChannel |
getChannel()
Returns the unique ServerSocketChannel object
associated with this socket, if any. |
InetAddress |
getInetAddress()
Returns the local address of this server socket. |
int |
getLocalPort()
Returns the port on which this socket is listening. |
SocketAddress |
getLocalSocketAddress()
Returns the address of the endpoint this socket is bound to, or null if it is not bound yet. |
int |
getReceiveBufferSize()
Gets the value of the SO_RCVBUF option for this ServerSocket, that is the proposed buffer size that will be used for Sockets accepted from this ServerSocket. |
boolean |
getReuseAddress()
Tests if SO_REUSEADDR is enabled. |
int |
getSoTimeout()
Retrive setting for SO_TIMEOUT. |
protected void |
implAccept(Socket s)
Subclasses of ServerSocket use this method to override accept() to return their own subclass of socket. |
boolean |
isBound()
Returns the binding state of the ServerSocket. |
boolean |
isClosed()
Returns the closed state of the ServerSocket. |
void |
setPerformancePreferences(int connectionTime,
int latency,
int bandwidth)
Sets performance preferences for this ServerSocket. |
void |
setReceiveBufferSize(int size)
Sets a default proposed value for the SO_RCVBUF option for sockets accepted from this ServerSocket. |
void |
setReuseAddress(boolean on)
Enable/disable the SO_REUSEADDR socket option. |
static void |
setSocketFactory(SocketImplFactory fac)
Sets the server socket implementation factory for the application. |
void |
setSoTimeout(int timeout)
Enable/disable SO_TIMEOUT with the specified timeout, in milliseconds. |
String |
toString()
Returns the implementation address and implementation port of this socket as a String . |
| Methods inherited from class java.lang.Object |
|---|
clone, equals, finalize, getClass, hashCode, notify, notifyAll, wait, wait, wait |
| Constructor Detail |
|---|
public ServerSocket() throws IOException
IOException
- IO error when opening the socket.public ServerSocket(int port) throws IOException
0
creates a socket on any free port.
The maximum queue length for incoming connection indications (a
request to connect) is set to 50
. If a connection
indication arrives when the queue is full, the connection is refused.
If the application has specified a server socket factory, that
factory's createSocketImpl
method is called to create
the actual socket implementation. Otherwise a "plain" socket is created.
If there is a security manager,
its checkListen
method is called
with the port
argument
as its argument to ensure the operation is allowed.
This could result in a SecurityException.
port
- the port number, or 0
to use any
free port.
IOException
- if an I/O error occurs when opening the socket.
SecurityException
- if a security manager exists and its checkListen
method doesn't allow the operation.SocketImpl
,
SocketImplFactory.createSocketImpl()
,
setSocketFactory(java.net.SocketImplFactory)
,
SecurityManager.checkListen(int)
public ServerSocket(int port, int backlog) throws IOException
0
creates a socket on any
free port.
The maximum queue length for incoming connection indications (a
request to connect) is set to the backlog
parameter. If
a connection indication arrives when the queue is full, the
connection is refused.
If the application has specified a server socket factory, that
factory's createSocketImpl
method is called to create
the actual socket implementation. Otherwise a "plain" socket is created.
If there is a security manager,
its checkListen
method is called
with the port
argument
as its argument to ensure the operation is allowed.
This could result in a SecurityException.
The backlog
argument must be a positive
value greater than 0. If the value passed if equal or less
than 0, then the default value will be assumed.
port
- the specified port, or 0
to use
any free port.backlog
- the maximum length of the queue.
IOException
- if an I/O error occurs when opening the socket.
SecurityException
- if a security manager exists and its checkListen
method doesn't allow the operation.SocketImpl
,
SocketImplFactory.createSocketImpl()
,
setSocketFactory(java.net.SocketImplFactory)
,
SecurityManager.checkListen(int)
public ServerSocket(int port, int backlog, InetAddress bindAddr) throws IOException
If there is a security manager, this method
calls its checkListen
method
with the port
argument
as its argument to ensure the operation is allowed.
This could result in a SecurityException.
The backlog
argument must be a positive
value greater than 0. If the value passed if equal or less
than 0, then the default value will be assumed.
port
- the local TCP portbacklog
- the listen backlogbindAddr
- the local InetAddress the server will bind to
SecurityException
- if a security manager exists and
its checkListen
method doesn't allow the operation.
IOException
- if an I/O error occurs when opening the socket.SocketOptions
,
SocketImpl
,
SecurityManager.checkListen(int)
| Method Detail |
|---|
public void bind(SocketAddress endpoint) throws IOException
ServerSocket
to a specific address
(IP address and port number).
If the address is null
, then the system will pick up
an ephemeral port and a valid local address to bind the socket.
endpoint
- The IP address & port number to bind to.
IOException
- if the bind operation fails, or if the socket
is already bound.
SecurityException
- if a SecurityManager
is present and
its checkListen
method doesn't allow the operation.
IllegalArgumentException
- if endpoint is a
SocketAddress subclass not supported by this socketpublic void bind(SocketAddress endpoint, int backlog) throws IOException
ServerSocket
to a specific address
(IP address and port number).
If the address is null
, then the system will pick up
an ephemeral port and a valid local address to bind the socket.
The backlog
argument must be a positive
value greater than 0. If the value passed if equal or less
than 0, then the default value will be assumed.
endpoint
- The IP address & port number to bind to.backlog
- The listen backlog length.
IOException
- if the bind operation fails, or if the socket
is already bound.
SecurityException
- if a SecurityManager
is present and
its checkListen
method doesn't allow the operation.
IllegalArgumentException
- if endpoint is a
SocketAddress subclass not supported by this socketpublic InetAddress getInetAddress()
null
if the socket is unbound.public int getLocalPort()
public SocketAddress getLocalSocketAddress()
null
if it is not bound yet.
SocketAddress
representing the local endpoint of this
socket, or null
if it is not bound yet.getInetAddress()
,
getLocalPort()
,
bind(SocketAddress)
public Socket accept() throws IOException
A new Socket s
is created and, if there
is a security manager,
the security manager's checkAccept
method is called
with s.getInetAddress().getHostAddress()
and
s.getPort()
as its arguments to ensure the operation is allowed.
This could result in a SecurityException.
IOException
- if an I/O error occurs when waiting for a
connection.
SecurityException
- if a security manager exists and its
checkListen
method doesn't allow the operation.
SocketTimeoutException
- if a timeout was previously set with setSoTimeout and
the timeout has been reached.
IllegalBlockingModeException
- if this socket has an associated channel, the channel is in
non-blocking mode, and there is no connection ready to be
acceptedSecurityManager.checkAccept(java.lang.String, int)
protected final void implAccept(Socket s) throws IOException
s
- the Socket
IllegalBlockingModeException
- if this socket has an associated channel,
and the channel is in non-blocking mode
IOException
- if an I/O error occurs when waiting
for a connection.public void close() throws IOException
accept()
will throw
a SocketException
.
If this socket has an associated channel then the channel is closed as well.
IOException
- if an I/O error occurs when closing the socket.public ServerSocketChannel getChannel()
ServerSocketChannel
object
associated with this socket, if any.
A server socket will have a channel if, and only if, the channel
itself was created via the ServerSocketChannel.open
method.
public boolean isBound()
public boolean isClosed()
public void setSoTimeout(int timeout) throws SocketException
timeout
- the specified timeout, in milliseconds
SocketException
- if there is an error in
the underlying protocol, such as a TCP error.getSoTimeout()
public int getSoTimeout() throws IOException
IOException
- if an I/O error occurssetSoTimeout(int)
public void setReuseAddress(boolean on) throws SocketException
When a TCP connection is closed the connection may remain in a timeout state for a period of time after the connection is closed (typically known as the TIME_WAIT state or 2MSL wait state). For applications using a well known socket address or port it may not be possible to bind a socket to the required SocketAddress if there is a connection in the timeout state involving the socket address or port.
Enabling SO_REUSEADDR prior to binding the socket
using bind(SocketAddress)
allows the socket to be
bound even though a previous connection is in a timeout
state.
When a ServerSocket is created the initial setting
of SO_REUSEADDR is not defined. Applications can
use getReuseAddress()
to determine the initial
setting of SO_REUSEADDR.
The behaviour when SO_REUSEADDR is enabled or
disabled after a socket is bound (See isBound()
)
is not defined.
on
- whether to enable or disable the socket option
SocketException
- if an error occurs enabling or
disabling the SO_RESUEADDR socket option,
or the socket is closed.getReuseAddress()
,
bind(SocketAddress)
,
isBound()
,
isClosed()
public boolean getReuseAddress() throws SocketException
boolean
indicating whether or not SO_REUSEADDR is enabled.
SocketException
- if there is an error
in the underlying protocol, such as a TCP error.setReuseAddress(boolean)
public String toString()
String
.
toString
in class Object
public static void setSocketFactory(SocketImplFactory fac) throws IOException
When an application creates a new server socket, the socket
implementation factory's createSocketImpl
method is
called to create the actual socket implementation.
Passing null
to the method is a no-op unless the factory
was already set.
If there is a security manager, this method first calls
the security manager's checkSetFactory
method
to ensure the operation is allowed.
This could result in a SecurityException.
fac
- the desired factory.
IOException
- if an I/O error occurs when setting the
socket factory.
SocketException
- if the factory has already been defined.
SecurityException
- if a security manager exists and its
checkSetFactory
method doesn't allow the operation.SocketImplFactory.createSocketImpl()
,
SecurityManager.checkSetFactory()
public void setReceiveBufferSize(int size) throws SocketException
Socket.getReceiveBufferSize()
after the socket
is returned by accept()
.
The value of SO_RCVBUF is used both to set the size of the internal socket receive buffer, and to set the size of the TCP receive window that is advertized to the remote peer.
It is possible to change the value subsequently, by calling
Socket.setReceiveBufferSize(int)
. However, if the application
wishes to allow a receive window larger than 64K bytes, as defined by RFC1323
then the proposed value must be set in the ServerSocket before
it is bound to a local address. This implies, that the ServerSocket must be
created with the no-argument constructor, then setReceiveBufferSize() must
be called and lastly the ServerSocket is bound to an address by calling bind().
Failure to do this will not cause an error, and the buffer size may be set to the requested value but the TCP receive window in sockets accepted from this ServerSocket will be no larger than 64K bytes.
size
- the size to which to set the receive buffer
size. This value must be greater than 0.
SocketException
- if there is an error
in the underlying protocol, such as a TCP error.
IllegalArgumentException
- if the
value is 0 or is negative.getReceiveBufferSize()
public int getReceiveBufferSize() throws SocketException
Note, the value actually set in the accepted socket is determined by
calling Socket.getReceiveBufferSize()
.
SocketException
- if there is an error
in the underlying protocol, such as a TCP error.setReceiveBufferSize(int)
public void setPerformancePreferences(int connectionTime, int latency, int bandwidth)
Sockets use the TCP/IP protocol by default. Some implementations may offer alternative protocols which have different performance characteristics than TCP/IP. This method allows the application to express its own preferences as to how these tradeoffs should be made when the implementation chooses from the available protocols.
Performance preferences are described by three integers whose values indicate the relative importance of short connection time, low latency, and high bandwidth. The absolute values of the integers are irrelevant; in order to choose a protocol the values are simply compared, with larger values indicating stronger preferences. If the application prefers short connection time over both low latency and high bandwidth, for example, then it could invoke this method with the values (1, 0, 0). If the application prefers high bandwidth above low latency, and low latency above short connection time, then it could invoke this method with the values (0, 1, 2).
Invoking this method after this socket has been bound will have no effect. This implies that in order to use this capability requires the socket to be created with the no-argument constructor.
connectionTime
- An int expressing the relative importance of a short
connection timelatency
- An int expressing the relative importance of low
latencybandwidth
- An int expressing the relative importance of high
bandwidth
|
JavaTM 2 Platform Standard Ed. 5.0 |
|||||||||
| PREV CLASS NEXT CLASS | FRAMES NO FRAMES | |||||||||
| SUMMARY: NESTED | FIELD | CONSTR | METHOD | DETAIL: FIELD | CONSTR | METHOD |
Copyright © 2004, 2010 Oracle and/or its affiliates. All rights reserved. Use is subject to license terms. Also see the documentation redistribution policy.


Add Product
SKU
Name
Price
Category
Edit Product
SKU
Name
Price
Category
Delete Product
Are you sure you want to delete:
NAME
Home
(current)
Dashboard
Products
Orders
Sign Out
Products
Add Product
SKU
Category
Product Name
Price
Action
ABC
Shoes
Air Jordan
100.00
Edit
Del


NAME
zip_file_extra_field_delete,
zip_file_extra_field_delete_by_id —
delete extra field for file in zip
LIBRARY
libzip (-lzip)
SYNOPSIS
#include <zip.h>
int
zip_file_extra_field_delete(
zip_t
*archive,
zip_uint64_t
index,
zip_uint16_t
extra_field_index,
zip_flags_t flags);
int
zip_file_extra_field_delete_by_id(
zip_t
*archive,
zip_uint64_t
index,
zip_uint16_t
extra_field_id,
zip_uint16_t
extra_field_index,
zip_flags_t flags);
DESCRIPTION
The
zip_file_extra_field_delete() function deletes the extra
field with index
extra_field_index for the file at
position
index in the zip archive.
If
extra_field_index is
ZIP_EXTRA_FIELD_ALL
, then all extra fields will be
deleted.
The following
flags are supported:
-
-
ZIP_FL_CENTRAL
- Delete extra fields from the archive's central
directory.
-
-
ZIP_FL_LOCAL
- Delete extra fields from the local file headers.
The
zip_file_extra_field_delete_by_id() function deletes the
extra field with ID (two-byte signature)
extra_field_id
and index
extra_field_index (in other words, the
extra_field_index'th extra field
with ID
extra_field_id) The other arguments are the same
as for
zip_file_extra_field_delete()
(
ZIP_EXTRA_FIELD_ALL
will delete all extra fields of
the specified ID).
Please note that due to the library design, the index of an extra field may be
different between central directory and local file headers. For this reason,
it is not allowed to specify both
ZIP_FL_CENTRAL
and
ZIP_FL_LOCAL
in
flags, except
when deleting all extra fields (i.e.,
extra_field_index
being
ZIP_EXTRA_FIELD_ALL
).
RETURN VALUES
Upon successful completion 0 is returned. Otherwise, -1 is returned and the
error code in
archive is set to indicate the error.
ERRORS
zip_file_extra_field_delete() and
zip_file_extra_field_delete_by_id() fail if:
-
-
- [
ZIP_ER_NOENT
]
- index is not a valid file index in
archive.
SEE ALSO
libzip(3),
zip_file_extra_field_get(3),
zip_file_extra_field_set(3),
zip_file_extra_fields_count(3)
HISTORY
zip_file_extra_field_delete() and
zip_file_extra_field_delete_by_id() were added in libzip
0.11.
AUTHORS
Dieter Baron
<
<EMAIL_ADDRESS>and
Thomas Klausner
<
tk@giga.or.at>


Joe M. wrote:sounds good. I wonder if you could get better-sounding horns, though...the "Nintendo" sound is a little worn with use.
silvert0384 wrote:It is a trick of the ear, because in those two spots, it is changing from a slow three pattern to a quicker four.  Ill still take a look.
Users browsing this forum: No registered users and 1 guest


Switch between devices, and pick up wherever you left off.


Home
Departments
Create
Read
Update
Delete
Hardware
Create
Read
Update
Delete
Types
Create
Read
Update
Delete
Users
Create
Read
Update
Delete
Vendors
Create
Read
Update
Delete
Reports
All Departments
All Hardware
All Types
All Users
All Vendors
Search
{% if loggedin == 'true' %}
Logout
{% else %}
Login
{% endif %}
{% block content %}{% endblock %}


You are about to embark on a quest that may or may not save the world from a monster that will set the world on fire. Each choice you make will ultimately determine the ending scene. Choose wisely!
Your story will save along the way. Feel free to take a break and come back to finish reading. Once you begin you must fully complete the story before you can begin again. Enjoy!
Copyright © 2021
All rights reserved. No part of this publication may be reproduced, distributed, or transmitted in any form or by any means without written permission of the publisher, except in the case of brief quotations embodied in critical reviews and certain other noncommercial uses permitted by copyright law.


Airline Booking
Mobile Version
view on a desktop for the full experience
From
Destination
NUMBER OF GUESTS
-
+
ARRIVAL
DEPARTURE
BOOK NOW


RESTful-Typescript-Koa
👷🏿 by Emmanuel N K
Introduction
This project is a simple RESTful API Template built using NodeJS, KOA, Typescript and TypeORM as an ORM for MongoDB. Middleware uses JWT, CORS, Winston Logger. Swagger API docs are used to produce an api front-end.
Check out the project homepage here: restful-typescript-koa
Or get straight to the action in an online API GUI here (courtesy of Swagger UI): restful-typescript-koa/swagger-html
Or view the project github here: restful-typescript-koa
What it has
- Node.js (v14.x.x)
- NPM (v6.x.x)
- Typescript
- KOA Framework v2
- MongoDB 4 with TypeORM
- Redis (Invalidating Authentication Tokens | Optional)
- Winston (logging)
- Swagger-UI (documenting the API)
- Mocha, Chai, Supertest (unit and integration tests)
- AJV for Schema validation
Available endpoints in this template
- This is just a template to be used as a starter to develop more robust APIs
- Keeps things simple by only handling authentication and CRUD operations for a user in the most RESTful way possible
- Versioning is not opinionated in this project. Apply it as you see fit.
- Available routes in this template are:
GET /
- index route
POST /login
- login (returns the access token to access protected routes)
GET /refresh
- a route to get a new jwt access token when the old one expires
GET /logout
- revoke access token (and optionally add it to redis blacklist)
GET /users
- get all users
POST /users
- create a new user
GET /users/:id
- fetch a user
PUT /users/:id
- update a user
DELETE /users/:id
- delete a user
- From these you can use the structure to build out other routes, controllers, services and entities.
Setup
Requirements
- Node.js version >= 12
- npm version >= 6
- docker and docker-compose (to run the mongodb db in localhost)
Setup
install dependencies:
npm install
OPTIONAL: setup the .env
file. Edit the environment variables inside accordingly:
cp .env.example .env
OPTIONAL: start the mongodb container in docker:
sudo docker-compose -f mongo.docker-compose up -d
OPTIONAL: start the redis container in docker:
sudo docker-compose -f redis.docker-compose up -d
Start
for development:
npm run watch-server
for deployment on local host:
npm run build
npm start
Test
to run all tests:
npm test
to run one test:
npm run test-one path/to/file.spec.ts
Coverage
to run code coverage:
npm run coverage
Build and Deployment
- Project is built into a docker container and dpeloyed on Heroku
- Project is deployed via Github Actions to Heroku Free Tier using a
ci.yml
file in the project
- The example site uses Mongo Atlas Free Tier and Heroku Redis Free Tier add-on
Design
Project File Structure
- The project is written in Typescript. After Typescript compiles, all subsequently built javascript files are in
/dist
- The entry point for the server is
src/server.ts
- Program flow:
server
--> routes
--> Services -->
controllers
--> Entities
Entities
are defined with and validated by TypeORM
- Custom Middlewares are in the
src/middleware
folder
- Database connection functions are in
src/providers/connections
- Schemas for modelling and validation are in
src/schemas
- Functions used in other parts of the program are in
src/libraries
- Custom Interfaces for Typescript Types are in
src/interfaces
- Tests are in the
test
folder
API Design
This project follows scalable project structure and RESTful best practices.
- The
routes
call controllers
- The
controllers
choose what services
to execute. No business logic goes in the controllers
- The
services
handle the business logic as well as database layer access.
entites
contain the entity models for database access
Rate Limiting
- Rate limiting is implemented using koa middleware that keeps track of access in either an in-memory cache or redis datastore.
- Redis would be the preferred albeit expensive option for this scenario.
Testing
- This project concentrates on API integration tests and those are acheived using Mocha as a test runner, Chai for assertions and Supertest for accessing the server and making requests.
- Tests are run against test databases on local and a test database docker container when in CI (Github Actions)
Authentication/Authorization
- Authentication is implemented using a jwt access and refresh token system. When a user logs in they are given a short term access token with which to perform authenticated requests. When this token expires they can access the
/refresh
endpoint to get another one. The refresh token is stored in the database.
- The refresh token should expire after a very long time and thus allow the user to maintain a sliding session until the refresh token expires or the refresh token is invalidated.
- This method can allow for multiple device login for an api.
- A drawback of this method is with explicit log out. When a user logs outs, the client deletes the old token but the token is still valid on the server side.
- The solution to this is to enable the redis based token blacklist.  You will need to set up the redis cluster before running any commands or revoking tokens.
Versioning
- If you want to version this API, then I would advise placing
controllers
, services
and routes
into a folder named v1
. Those are the most likely to change between versions.
- You then change the related files accordingly.
Contributing
- All contributions are welcomes
- Open up an issue if you encounter any problems. Thanks


We have come a long way from flying in Googlers
outside Africa to facilitate our events, to speaker sessions, and today we are
using local speakers for even a more technical events across Africa.
The Nigerian technology community is waxing stronger
through collaboration and community-powered initiatives. I base my
submissions on DevFest 2016 Season experiences across Nigerian Google Developer
Groups (GDGs).
Women Techmakers
GDG DevFests are large, community-run events that can
offer speaker sessions across multiple product areas, all-day hackathons, code
labs, and more. The official DevFest Season runs from September 1 through
November 30.
As a Country Mentor to Google Developer Groups in
Nigeria, I worked with my co-Mentor Femi Taiwo, GDG Leads and the Developer
Relations Team at Google Aniedi Udo-Obong and Charles Odili to plan and ensured
a successful clustered #DevFest16 in Nigeria.
Participants
We came up with strategies to ensure a more technical
event by raising the bar a notch higher in terms of technical contents, quality
of speakers and presentations, code-labs, Branding and packaging. This landed
us with 7 DevFests across Nigeria.
Host
Chapters
DevFest16 was held in clusters across geo-political
regions in Nigeria.
DevFest South West - Lagos
DevFest South West – EKSU, Ado-Ekiti
DevFest South South and South East – Port Harcourt
DevFest North East – Bauchi
DevFest North West – Kano
DevFest North Central – Abuja
DevFest Taraba - Jalingo
We had Delta State DevFest Roadshow, Asaba which was used to create awareness in the
newly opened Delta State Innovation Hub.
Aniedi Udo-Obong (Googler), Prosper (GDE) and Hanson (Country
Mentor)
Just like last year, we adopted the clustered approach
where GDGs within a region came together to organize their own DevFest instead
of everyone going to Lagos or having their own individual event in their single
chapter. In a situation where a chapter will travel more than 4-5 hours to the
hosting chapter, such chapter was encouraged to host their own event.
Participation
This year’s DevFest had 10% increase in women
participation. Port Harcourt recorded 1000+ participants, Ekiti State
University 600+, Lagos 350 and so on.
Speakers
We had Googlers within Nigeria, Google Developer Experts
in Nigeria, Entrepreneurs, Software Engineers and Software Developers who
handled various topics and code-labs on Firebase, Android, Progressive Web
Apps, Android Studio, AppEngine, Machine Learning, Robotics and Becoming a
World Class Developer. Developers and entrepreneurs also demoed their
products and startups.
Hanson Johnson - GDG Nigeria Country Mentor
Prof. Nimi Briggs, Former VC UniPort
with Aniedi Udo-Obong, Programme Manager at Google
Segun Famisa, Android Developer at Konga
Jude Ben, Founder ShareCube facilitating Firebase Session on
Android
Emem Akpanekpo, Founder/CEO Scholar demoing to Prof. Nimi
Briggs
Alexander of SDN
Breakout Session
Benefits
People often ask me, how do you benefit from all this events you organize? My answer
is always; I am a social entrepreneur, I pursue innovative ideas
with the potential to solve a community problem. As long as the positive impact we are creating is felt, I am good.
We also benefited from DevFest as follows:
We had new GDG members.
Newbies learned how to get started programming.
People got associated with mentors
Entrepreneurs met partners and co-founders
The quality of our events and delivery got improved from feedback.
Developers learned how to make their apps smarter with Machine Learning.
Firebase and Progressive Web Apps were made simple.
Fans of Android Development smiled home with tools to help them facilitate their learning process even when there
is no internet.
People had a platform to demo their products.
We made new friends
What Next?
Many people indicated interest to get started
programming while some wanted to join the community to have access to tools,
right information and people to collaborate with. I will recommend the
following in strengthening our local ecosystem:


General election 2019: Boris Johnson unveils Tory battle bus and it looks very, very familiar
Don't panic! After boarding 'Con Air' last week Boris Johnson finally has a battle bus - and the six-wheeled 2019 general election monstrosity reminds us of something
by Dan Bloom, https://www.facebook.com/mirrordanbloomWhen he unveiled his lie-strewn referendum bus in 2016, we cried: Who do you think you are kidding Mr Johnson?
And this time, Boris Johnson really has gone full Dad's Army with his six-wheeled Tory battlebus.
The red, white and blue Mercedes-Benz Tourismo is plastered with the phrase "GET unleash BREXIT britain's potential DONE".
But it's the little arrow at the end that couldn't help reminding us of something.
 Of course, it's the title sequence of Dad's Army.
Except this time the arrow is pointing not to the opposing WW2 Army but up into the blue sky, where most of Johnson's Brexit hopes reside.
Of course, Boris Johnson will no doubt insist it's nothing to do with the 1970s TV hit. After all, they don't like it up 'em.
And if he does, we have an alternative suggestion.
Doesn't it also look like the £100m, taxpayer-funded 'Get Ready for Brexit' campaign that wrongly prepared the nation for October 31?
The colours, the arrows... it's almost like they've taken inspiration from something paid for by HM Government. Which in an election campaign, would be extremely naughty. So we're sure they haven't.
The Prime Minister unveiled the bus today in Greater Manchester, in a half-empty warehouse - scuppering the risk of pesky protesters.
He emerged via the emergency exit and described it as a "wonderful" bus, news agency PA Media honourably reported.
He added in a speech to Tory activists there will be "buses that are a lot greener than this" once his party has implemented its "fantastic" policies.
Mr Johnson also said: "Some of you may be asking why do we even need a bus, why do we even need an election?
"The answer is because Parliament is unfortunately paralysed."
Mr Johnson later branded Labour's plan to nationalise broadband a "crazed Communist scheme", and largely got away with it, because he didn't take press questions at the launch.
Of course, we were kidding about the slogan earlier - though the read-across is rather unfortunate.
What it really says is: "Back Boris and vote Conservative to... Get Brexit Done."
It has a tagline stating: "A stronger economy to invest in our NHS, schools, police, infrastructure."
A small piece of text reading "emergency exit break glass" can also be seen.
But reliable sources inform PA Media this is a safety measure connected to the bus rather than a Conservative slogan.
Either way it certainly beats 'Con Air' - the nickname Boris Johnson gave to the plane he took last week when he was touring the nations of the UK.
In a hapless piece of PR, he boarded the jet at the same time as Labour was unveiling its own battle bus - which says it's "time for real change".


Series of books planned, based on NYT’s “1619 Project”
NEW YORK - The New York Times’ acclaimed “1619 Project” will be the basis for a series of books, for readers of all ages.
Random House Group imprints have acquired rights to the books, the publisher announced Wednesday. The books will build upon the Times’ magazine special issue from last summer that centred on the 400th anniversary of the first enslaved Africans to be brought to the U.S. and slavery’s enduring legacy. Releases will include an expanded version of the magazine issue, including essays, fiction and poetry. Random House also plans a graphic novel and four “1619 Project” publications for young people.
The books will be overseen in part by Times journalist Nikole Hannah-Jones, the initiator of the “1619 Project,” and by Jake Silverstein, editor in chief of The New York Times Magazine.


You can easy check it out from the GitHub repo.
There are plenty versions of the game. I personally prefer the classic one.