| Time of Peak Load | 1/21 06:10:00 |
| Outside Dry Bulb Temperature [C] | -20.6 |
| Outside Wet Bulb Temperature [C] | -20.6 |
| Outside Humidity Ratio at Peak [kgWater/kgAir] | 0.00061 |
| Zone Dry Bulb Temperature [C] | 21.00 |
| Zone Relative Humdity [%] | 51.72 |
| Zone Humidity Ratio at Peak [kgWater/kgAir] | 0.00800 |
| Peak Design Sensible Load [W] | -20796.6 |
| Estimated Instant + Delayed Sensible Load [W] | -21216.1 |
| Difference [W] | 419.56 |
Report: Zone Component Load Summary
For: PERIMETER_BOT_ZN_1
Timestamp: 2018-02-13 16:27:46
Estimated Cooling Peak Load Components| Sensible - Instant [W] | Sensible - Delayed [W] | Sensible - Return Air [W] | Latent [W] | Total [W] | %Grand Total | |
| People | 543.26 | 681.02 | 563.02 | 1787.30 | 10.25 | |
| Lights | 0.00 | 3559.89 | 892.38 | 4452.27 | 25.54 | |
| Equipment | 1115.48 | 3737.00 | 0.00 | 4852.48 | 27.83 | |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Water Use Equipment | 0.00 | 0.00 | 0.00 | 0.00 | ||
| HVAC Equipment Losses | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Power Generation Equipment | 0.00 | 0.00 | 0.00 | 0.00 | ||
| DOAS Direct to Zone | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Infiltration | 76.45 | 291.91 | 368.36 | 2.11 | ||
| Zone Ventilation | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Interzone Mixing | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Roof | 0.00 | 0.00 | 0.00 | |||
| Interzone Ceiling | -1216.1 | -1216.1 | -7.0 | |||
| Other Roof | 0.00 | 0.00 | 0.00 | |||
| Exterior Wall | -1051.5 | -1051.5 | -6.0 | |||
| Interzone Wall | -3470.4 | -3470.4 | -19.9 | |||
| Ground Contact Wall | 0.00 | 0.00 | 0.00 | |||
| Other Wall | 0.00 | 0.00 | 0.00 | |||
| Exterior Floor | 0.00 | 0.00 | 0.00 | |||
| Interzone Floor | 0.00 | 0.00 | 0.00 | |||
| Ground Contact Floor | -2499.2 | -2499.2 | -14.3 | |||
| Other Floor | 0.00 | 0.00 | 0.00 | |||
| Fenestration Conduction | 872.48 | 872.48 | 5.00 | |||
| Fenestration Solar | 13338.37 | 13338.37 | 76.51 | |||
| Opaque Door | 0.00 | 0.00 | 0.00 | |||
| Grand Total | 2607.67 | 13079.08 | 892.38 | 854.93 | 17434.06 |
| Value | |
| Time of Peak Load | 7/21 13:10:00 |
| Outside Dry Bulb Temperature [C] | 30.75 |
| Outside Wet Bulb Temperature [C] | 25.68 |
| Outside Humidity Ratio at Peak [kgWater/kgAir] | 0.01878 |
| Zone Dry Bulb Temperature [C] | 24.00 |
| Zone Relative Humdity [%] | 47.24 |
| Zone Humidity Ratio at Peak [kgWater/kgAir] | 0.00878 |
| Peak Design Sensible Load [W] | 13787.83 |
| Estimated Instant + Delayed Sensible Load [W] | 15686.74 |
| Difference [W] | -1898.9 |
| Sensible - Instant [W] | Sensible - Delayed [W] | Sensible - Return Air [W] | Latent [W] | Total [W] | %Grand Total | |
| People | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Lights | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Equipment | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Water Use Equipment | 0.00 | 0.00 | 0.00 | -0.00 | ||
| HVAC Equipment Losses | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Power Generation Equipment | 0.00 | 0.00 | 0.00 | -0.00 | ||
| DOAS | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Infiltration | -2362.1 | -825.4 | -3187.5 | 41.64 | ||
| Zone Ventilation | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Interzone Mixing | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Roof | 0.00 | 0.00 | -0.00 | |||
| Interzone Ceiling | -133.4 | -133.4 | 1.74 | |||
| Other Roof | 0.00 | 0.00 | -0.00 | |||
| Exterior Wall | -711.8 | -711.8 | 9.30 | |||
| Interzone Wall | 300.33 | 300.33 | -3.9 | |||
| Ground Contact Wall | 0.00 | 0.00 | -0.00 | |||
| Other Wall | 0.00 | 0.00 | -0.00 | |||
| Exterior Floor | 0.00 | 0.00 | -0.00 | |||
| Interzone Floor | 0.00 | 0.00 | -0.00 | |||
| Ground Contact Floor | 39.54 | 39.54 | -0.5 | |||
| Other Floor | 0.00 | 0.00 | -0.00 | |||
| Fenestration Conduction | -3962.3 | -3962.3 | 51.76 | |||
| Fenestration Solar | 0.00 | 0.00 | -0.00 | |||
| Opaque Door | 0.00 | 0.00 | -0.00 | |||
| Grand Total | -6324.4 | -505.3 | 0.00 | -825.4 | -7655.1 |
| Value | |
| Time of Peak Load | 1/21 06:00:00 |
| Outside Dry Bulb Temperature [C] | -20.6 |
| Outside Wet Bulb Temperature [C] | -20.6 |
| Outside Humidity Ratio at Peak [kgWater/kgAir] | 0.00061 |
| Zone Dry Bulb Temperature [C] | 20.99 |
| Zone Relative Humdity [%] | 42.46 |
| Zone Humidity Ratio at Peak [kgWater/kgAir] | 0.00655 |
| Peak Design Sensible Load [W] | -6835.4 |
| Estimated Instant + Delayed Sensible Load [W] | -6829.7 |
| Difference [W] | -5.6 |
Report: Zone Component Load Summary
For: PERIMETER_BOT_ZN_2
Timestamp: 2018-02-13 16:27:46
Estimated Cooling Peak Load Components| Sensible - Instant [W] | Sensible - Delayed [W] | Sensible - Return Air [W] | Latent [W] | Total [W] | %Grand Total | |
| People | 343.92 | 346.43 | 356.44 | 1046.80 | 7.99 | |
| Lights | 0.00 | 2060.19 | 564.95 | 2625.14 | 20.03 | |
| Equipment | 706.19 | 2154.96 | 0.00 | 2861.15 | 21.83 | |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Water Use Equipment | 0.00 | 0.00 | 0.00 | 0.00 | ||
| HVAC Equipment Losses | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Power Generation Equipment | 0.00 | 0.00 | 0.00 | 0.00 | ||
| DOAS Direct to Zone | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Infiltration | 1.06 | 197.82 | 198.88 | 1.52 | ||
| Zone Ventilation | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Interzone Mixing | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Roof | 0.00 | 0.00 | 0.00 | |||
| Interzone Ceiling | -883.9 | -883.9 | -6.7 | |||
| Other Roof | 0.00 | 0.00 | 0.00 | |||
| Exterior Wall | -653.0 | -653.0 | -5.0 | |||
| Interzone Wall | -3016.1 | -3016.1 | -23.0 | |||
| Ground Contact Wall | 0.00 | 0.00 | 0.00 | |||
| Other Wall | 0.00 | 0.00 | 0.00 | |||
| Exterior Floor | 0.00 | 0.00 | 0.00 | |||
| Interzone Floor | 0.00 | 0.00 | 0.00 | |||
| Ground Contact Floor | -1494.8 | -1494.8 | -11.4 | |||
| Other Floor | 0.00 | 0.00 | 0.00 | |||
| Fenestration Conduction | 463.82 | 463.82 | 3.54 | |||
| Fenestration Solar | 11956.09 | 11956.09 | 91.24 | |||
| Opaque Door | 0.00 | 0.00 | 0.00 | |||
| Grand Total | 1515.00 | 10469.92 | 564.95 | 554.26 | 13104.13 |
| Value | |
| Time of Peak Load | 7/21 08:50:00 |
| Outside Dry Bulb Temperature [C] | 24.98 |
| Outside Wet Bulb Temperature [C] | 24.20 |
| Outside Humidity Ratio at Peak [kgWater/kgAir] | 0.01878 |
| Zone Dry Bulb Temperature [C] | 24.00 |
| Zone Relative Humdity [%] | 46.99 |
| Zone Humidity Ratio at Peak [kgWater/kgAir] | 0.00873 |
| Peak Design Sensible Load [W] | 10847.42 |
| Estimated Instant + Delayed Sensible Load [W] | 11984.91 |
| Difference [W] | -1137.5 |
| Sensible - Instant [W] | Sensible - Delayed [W] | Sensible - Return Air [W] | Latent [W] | Total [W] | %Grand Total | |
| People | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Lights | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Equipment | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Water Use Equipment | 0.00 | 0.00 | 0.00 | -0.00 | ||
| HVAC Equipment Losses | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Power Generation Equipment | 0.00 | 0.00 | 0.00 | -0.00 | ||
| DOAS | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Infiltration | -1574.7 | -550.0 | -2124.7 | 41.72 | ||
| Zone Ventilation | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Interzone Mixing | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Roof | 0.00 | 0.00 | -0.00 | |||
| Interzone Ceiling | -59.2 | -59.2 | 1.16 | |||
| Other Roof | 0.00 | 0.00 | -0.00 | |||
| Exterior Wall | -473.8 | -473.8 | 9.30 | |||
| Interzone Wall | 177.36 | 177.36 | -3.5 | |||
| Ground Contact Wall | 0.00 | 0.00 | -0.00 | |||
| Other Wall | 0.00 | 0.00 | -0.00 | |||
| Exterior Floor | 0.00 | 0.00 | -0.00 | |||
| Interzone Floor | 0.00 | 0.00 | -0.00 | |||
| Ground Contact Floor | 32.18 | 32.18 | -0.6 | |||
| Other Floor | 0.00 | 0.00 | -0.00 | |||
| Fenestration Conduction | -2644.3 | -2644.3 | 51.92 | |||
| Fenestration Solar | 0.00 | 0.00 | -0.00 | |||
| Opaque Door | 0.00 | 0.00 | -0.00 | |||
| Grand Total | -4219.1 | -323.5 | 0.00 | -550.0 | -5092.6 |
| Value | |
| Time of Peak Load | 1/21 06:00:00 |
| Outside Dry Bulb Temperature [C] | -20.6 |
| Outside Wet Bulb Temperature [C] | -20.6 |
| Outside Humidity Ratio at Peak [kgWater/kgAir] | 0.00061 |
| Zone Dry Bulb Temperature [C] | 20.99 |
| Zone Relative Humdity [%] | 42.45 |
| Zone Humidity Ratio at Peak [kgWater/kgAir] | 0.00655 |
| Peak Design Sensible Load [W] | -4546.9 |
| Estimated Instant + Delayed Sensible Load [W] | -4542.6 |
| Difference [W] | -4.3 |
Report: Zone Component Load Summary
For: PERIMETER_BOT_ZN_3
Timestamp: 2018-02-13 16:27:46
Estimated Cooling Peak Load Components| Sensible - Instant [W] | Sensible - Delayed [W] | Sensible - Return Air [W] | Latent [W] | Total [W] | %Grand Total | |
| People | 525.78 | 251.24 | 587.99 | 1365.01 | 13.17 | |
| Lights | 0.00 | 3014.62 | 892.38 | 3907.00 | 37.69 | |
| Equipment | 1115.48 | 3169.37 | 0.00 | 4284.85 | 41.34 | |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Water Use Equipment | 0.00 | 0.00 | 0.00 | 0.00 | ||
| HVAC Equipment Losses | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Power Generation Equipment | 0.00 | 0.00 | 0.00 | 0.00 | ||
| DOAS Direct to Zone | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Infiltration | -34.8 | 214.96 | 180.17 | 1.74 | ||
| Zone Ventilation | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Interzone Mixing | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Roof | 0.00 | 0.00 | 0.00 | |||
| Interzone Ceiling | -275.3 | -275.3 | -2.7 | |||
| Other Roof | 0.00 | 0.00 | 0.00 | |||
| Exterior Wall | -662.3 | -662.3 | -6.4 | |||
| Interzone Wall | -1682.7 | -1682.7 | -16.2 | |||
| Ground Contact Wall | 0.00 | 0.00 | 0.00 | |||
| Other Wall | 0.00 | 0.00 | 0.00 | |||
| Exterior Floor | 0.00 | 0.00 | 0.00 | |||
| Interzone Floor | 0.00 | 0.00 | 0.00 | |||
| Ground Contact Floor | -462.3 | -462.3 | -4.5 | |||
| Other Floor | 0.00 | 0.00 | 0.00 | |||
| Fenestration Conduction | -352.5 | -352.5 | -3.4 | |||
| Fenestration Solar | 4062.92 | 4062.92 | 39.20 | |||
| Opaque Door | 0.00 | 0.00 | 0.00 | |||
| Grand Total | 1253.98 | 7415.45 | 892.38 | 802.96 | 10364.77 |
| Value | |
| Time of Peak Load | 7/21 07:00:00 |
| Outside Dry Bulb Temperature [C] | 21.46 |
| Outside Wet Bulb Temperature [C] | 21.46 |
| Outside Humidity Ratio at Peak [kgWater/kgAir] | 0.01650 |
| Zone Dry Bulb Temperature [C] | 24.00 |
| Zone Relative Humdity [%] | 47.96 |
| Zone Humidity Ratio at Peak [kgWater/kgAir] | 0.00891 |
| Peak Design Sensible Load [W] | 9690.01 |
| Estimated Instant + Delayed Sensible Load [W] | 8669.44 |
| Difference [W] | 1020.57 |
| Sensible - Instant [W] | Sensible - Delayed [W] | Sensible - Return Air [W] | Latent [W] | Total [W] | %Grand Total | |
| People | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Lights | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Equipment | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Water Use Equipment | 0.00 | 0.00 | 0.00 | -0.00 | ||
| HVAC Equipment Losses | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Power Generation Equipment | 0.00 | 0.00 | 0.00 | -0.00 | ||
| DOAS | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Infiltration | -2362.1 | -824.1 | -3186.2 | 41.92 | ||
| Zone Ventilation | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Interzone Mixing | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Roof | 0.00 | 0.00 | -0.00 | |||
| Interzone Ceiling | -85.0 | -85.0 | 1.12 | |||
| Other Roof | 0.00 | 0.00 | -0.00 | |||
| Exterior Wall | -712.3 | -712.3 | 9.37 | |||
| Interzone Wall | 298.11 | 298.11 | -3.9 | |||
| Ground Contact Wall | 0.00 | 0.00 | -0.00 | |||
| Other Wall | 0.00 | 0.00 | -0.00 | |||
| Exterior Floor | 0.00 | 0.00 | -0.00 | |||
| Interzone Floor | 0.00 | 0.00 | -0.00 | |||
| Ground Contact Floor | 53.58 | 53.58 | -0.7 | |||
| Other Floor | 0.00 | 0.00 | -0.00 | |||
| Fenestration Conduction | -3968.6 | -3968.6 | 52.22 | |||
| Fenestration Solar | 0.00 | 0.00 | -0.00 | |||
| Opaque Door | 0.00 | 0.00 | -0.00 | |||
| Grand Total | -6330.7 | -445.6 | 0.00 | -824.1 | -7600.4 |
| Value | |
| Time of Peak Load | 1/21 06:00:00 |
| Outside Dry Bulb Temperature [C] | -20.6 |
| Outside Wet Bulb Temperature [C] | -20.6 |
| Outside Humidity Ratio at Peak [kgWater/kgAir] | 0.00061 |
| Zone Dry Bulb Temperature [C] | 20.99 |
| Zone Relative Humdity [%] | 42.40 |
| Zone Humidity Ratio at Peak [kgWater/kgAir] | 0.00654 |
| Peak Design Sensible Load [W] | -6781.4 |
| Estimated Instant + Delayed Sensible Load [W] | -6776.3 |
| Difference [W] | -5.1 |
Report: Zone Component Load Summary
For: PERIMETER_BOT_ZN_4
Timestamp: 2018-02-13 16:27:46
Estimated Cooling Peak Load Components| Sensible - Instant [W] | Sensible - Delayed [W] | Sensible - Return Air [W] | Latent [W] | Total [W] | %Grand Total | |
| People | 343.90 | 464.98 | 356.42 | 1165.30 | 8.29 | |
| Lights | 0.00 | 2282.26 | 564.92 | 2847.18 | 20.26 | |
| Equipment | 706.14 | 2393.86 | 0.00 | 3100.01 | 22.06 | |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Water Use Equipment | 0.00 | 0.00 | 0.00 | 0.00 | ||
| HVAC Equipment Losses | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Power Generation Equipment | 0.00 | 0.00 | 0.00 | 0.00 | ||
| DOAS Direct to Zone | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Infiltration | 50.16 | 195.76 | 245.92 | 1.75 | ||
| Zone Ventilation | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Interzone Mixing | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Roof | 0.00 | 0.00 | 0.00 | |||
| Interzone Ceiling | -1089.2 | -1089.2 | -7.8 | |||
| Other Roof | 0.00 | 0.00 | 0.00 | |||
| Exterior Wall | -672.6 | -672.6 | -4.8 | |||
| Interzone Wall | -2596.4 | -2596.4 | -18.5 | |||
| Ground Contact Wall | 0.00 | 0.00 | 0.00 | |||
| Other Wall | 0.00 | 0.00 | 0.00 | |||
| Exterior Floor | 0.00 | 0.00 | 0.00 | |||
| Interzone Floor | 0.00 | 0.00 | 0.00 | |||
| Ground Contact Floor | -1205.9 | -1205.9 | -8.6 | |||
| Other Floor | 0.00 | 0.00 | 0.00 | |||
| Fenestration Conduction | 891.86 | 891.86 | 6.35 | |||
| Fenestration Solar | 11364.36 | 11364.36 | 80.88 | |||
| Opaque Door | 0.00 | 0.00 | 0.00 | |||
| Grand Total | 1992.07 | 10941.44 | 564.92 | 552.18 | 14050.60 |
| Value | |
| Time of Peak Load | 7/21 16:40:00 |
| Outside Dry Bulb Temperature [C] | 29.99 |
| Outside Wet Bulb Temperature [C] | 25.49 |
| Outside Humidity Ratio at Peak [kgWater/kgAir] | 0.01878 |
| Zone Dry Bulb Temperature [C] | 24.00 |
| Zone Relative Humdity [%] | 46.94 |
| Zone Humidity Ratio at Peak [kgWater/kgAir] | 0.00872 |
| Peak Design Sensible Load [W] | 11182.35 |
| Estimated Instant + Delayed Sensible Load [W] | 12933.51 |
| Difference [W] | -1751.2 |
| Sensible - Instant [W] | Sensible - Delayed [W] | Sensible - Return Air [W] | Latent [W] | Total [W] | %Grand Total | |
| People | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Lights | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Equipment | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Water Use Equipment | 0.00 | 0.00 | 0.00 | -0.00 | ||
| HVAC Equipment Losses | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Power Generation Equipment | 0.00 | 0.00 | 0.00 | -0.00 | ||
| DOAS | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Infiltration | -1574.7 | -549.9 | -2124.7 | 41.75 | ||
| Zone Ventilation | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Interzone Mixing | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Roof | 0.00 | 0.00 | -0.00 | |||
| Interzone Ceiling | -59.5 | -59.5 | 1.17 | |||
| Other Roof | 0.00 | 0.00 | -0.00 | |||
| Exterior Wall | -474.3 | -474.3 | 9.32 | |||
| Interzone Wall | 177.11 | 177.11 | -3.5 | |||
| Ground Contact Wall | 0.00 | 0.00 | -0.00 | |||
| Other Wall | 0.00 | 0.00 | -0.00 | |||
| Exterior Floor | 0.00 | 0.00 | -0.00 | |||
| Interzone Floor | 0.00 | 0.00 | -0.00 | |||
| Ground Contact Floor | 32.09 | 32.09 | -0.6 | |||
| Other Floor | 0.00 | 0.00 | -0.00 | |||
| Fenestration Conduction | -2640.3 | -2640.3 | 51.88 | |||
| Fenestration Solar | 0.00 | 0.00 | -0.00 | |||
| Opaque Door | 0.00 | 0.00 | -0.00 | |||
| Grand Total | -4215.0 | -324.6 | 0.00 | -549.9 | -5089.5 |
| Value | |
| Time of Peak Load | 1/21 06:00:00 |
| Outside Dry Bulb Temperature [C] | -20.6 |
| Outside Wet Bulb Temperature [C] | -20.6 |
| Outside Humidity Ratio at Peak [kgWater/kgAir] | 0.00061 |
| Zone Dry Bulb Temperature [C] | 20.99 |
| Zone Relative Humdity [%] | 42.44 |
| Zone Humidity Ratio at Peak [kgWater/kgAir] | 0.00655 |
| Peak Design Sensible Load [W] | -4543.9 |
| Estimated Instant + Delayed Sensible Load [W] | -4539.6 |
| Difference [W] | -4.3 |
Report: Zone Component Load Summary
For: PERIMETER_MID_ZN_1
Timestamp: 2018-02-13 16:27:46
Estimated Cooling Peak Load Components| Sensible - Instant [W] | Sensible - Delayed [W] | Sensible - Return Air [W] | Latent [W] | Total [W] | %Grand Total | |
| People | 543.26 | 726.68 | 563.02 | 1832.96 | 10.96 | |
| Lights | 0.00 | 4125.97 | 892.38 | 5018.35 | 29.99 | |
| Equipment | 1115.48 | 4336.62 | 0.00 | 5452.10 | 32.59 | |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Water Use Equipment | 0.00 | 0.00 | 0.00 | 0.00 | ||
| HVAC Equipment Losses | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Power Generation Equipment | 0.00 | 0.00 | 0.00 | 0.00 | ||
| DOAS Direct to Zone | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Infiltration | 76.15 | 291.47 | 367.63 | 2.20 | ||
| Zone Ventilation | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Interzone Mixing | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Roof | 0.00 | 0.00 | 0.00 | |||
| Interzone Ceiling | -1247.5 | -1247.5 | -7.5 | |||
| Other Roof | 0.00 | 0.00 | 0.00 | |||
| Exterior Wall | -1132.2 | -1132.2 | -6.8 | |||
| Interzone Wall | -3823.7 | -3823.7 | -22.9 | |||
| Ground Contact Wall | 0.00 | 0.00 | 0.00 | |||
| Other Wall | 0.00 | 0.00 | 0.00 | |||
| Exterior Floor | 0.00 | 0.00 | 0.00 | |||
| Interzone Floor | -3943.8 | -3943.8 | -23.6 | |||
| Ground Contact Floor | 0.00 | 0.00 | 0.00 | |||
| Other Floor | 0.00 | 0.00 | 0.00 | |||
| Fenestration Conduction | 900.14 | 900.14 | 5.38 | |||
| Fenestration Solar | 13306.77 | 13306.77 | 79.53 | |||
| Opaque Door | 0.00 | 0.00 | 0.00 | |||
| Grand Total | 2635.03 | 12348.85 | 892.38 | 854.49 | 16730.76 |
| Value | |
| Time of Peak Load | 7/21 13:10:00 |
| Outside Dry Bulb Temperature [C] | 30.75 |
| Outside Wet Bulb Temperature [C] | 25.68 |
| Outside Humidity Ratio at Peak [kgWater/kgAir] | 0.01878 |
| Zone Dry Bulb Temperature [C] | 24.00 |
| Zone Relative Humdity [%] | 47.33 |
| Zone Humidity Ratio at Peak [kgWater/kgAir] | 0.00879 |
| Peak Design Sensible Load [W] | 13048.52 |
| Estimated Instant + Delayed Sensible Load [W] | 14983.89 |
| Difference [W] | -1935.4 |
| Sensible - Instant [W] | Sensible - Delayed [W] | Sensible - Return Air [W] | Latent [W] | Total [W] | %Grand Total | |
| People | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Lights | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Equipment | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Water Use Equipment | 0.00 | 0.00 | 0.00 | -0.00 | ||
| HVAC Equipment Losses | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Power Generation Equipment | 0.00 | 0.00 | 0.00 | -0.00 | ||
| DOAS | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Infiltration | -2363.8 | -831.6 | -3195.5 | 40.27 | ||
| Zone Ventilation | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Interzone Mixing | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Roof | 0.00 | 0.00 | -0.00 | |||
| Interzone Ceiling | -318.5 | -318.5 | 4.01 | |||
| Other Roof | 0.00 | 0.00 | -0.00 | |||
| Exterior Wall | -706.1 | -706.1 | 8.90 | |||
| Interzone Wall | 271.11 | 271.11 | -3.4 | |||
| Ground Contact Wall | 0.00 | 0.00 | -0.00 | |||
| Other Wall | 0.00 | 0.00 | -0.00 | |||
| Exterior Floor | 0.00 | 0.00 | -0.00 | |||
| Interzone Floor | 49.13 | 49.13 | -0.6 | |||
| Ground Contact Floor | 0.00 | 0.00 | -0.00 | |||
| Other Floor | 0.00 | 0.00 | -0.00 | |||
| Fenestration Conduction | -4034.8 | -4034.8 | 50.85 | |||
| Fenestration Solar | 0.00 | 0.00 | -0.00 | |||
| Opaque Door | 0.00 | 0.00 | -0.00 | |||
| Grand Total | -6398.7 | -704.4 | 0.00 | -831.6 | -7934.7 |
| Value | |
| Time of Peak Load | 1/21 06:00:00 |
| Outside Dry Bulb Temperature [C] | -20.6 |
| Outside Wet Bulb Temperature [C] | -20.6 |
| Outside Humidity Ratio at Peak [kgWater/kgAir] | 0.00061 |
| Zone Dry Bulb Temperature [C] | 20.99 |
| Zone Relative Humdity [%] | 42.75 |
| Zone Humidity Ratio at Peak [kgWater/kgAir] | 0.00659 |
| Peak Design Sensible Load [W] | -7106.6 |
| Estimated Instant + Delayed Sensible Load [W] | -7103.0 |
| Difference [W] | -3.6 |
Report: Zone Component Load Summary
For: PERIMETER_MID_ZN_2
Timestamp: 2018-02-13 16:27:46
Estimated Cooling Peak Load Components| Sensible - Instant [W] | Sensible - Delayed [W] | Sensible - Return Air [W] | Latent [W] | Total [W] | %Grand Total | |
| People | 343.92 | 333.95 | 356.44 | 1034.32 | 8.57 | |
| Lights | 0.00 | 2260.73 | 564.95 | 2825.68 | 23.42 | |
| Equipment | 706.19 | 2369.92 | 0.00 | 3076.11 | 25.50 | |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Water Use Equipment | 0.00 | 0.00 | 0.00 | 0.00 | ||
| HVAC Equipment Losses | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Power Generation Equipment | 0.00 | 0.00 | 0.00 | 0.00 | ||
| DOAS Direct to Zone | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Infiltration | 0.85 | 197.46 | 198.31 | 1.64 | ||
| Zone Ventilation | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Interzone Mixing | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Roof | 0.00 | 0.00 | 0.00 | |||
| Interzone Ceiling | -826.7 | -826.7 | -6.9 | |||
| Other Roof | 0.00 | 0.00 | 0.00 | |||
| Exterior Wall | -655.0 | -655.0 | -5.4 | |||
| Interzone Wall | -3090.1 | -3090.1 | -25.6 | |||
| Ground Contact Wall | 0.00 | 0.00 | 0.00 | |||
| Other Wall | 0.00 | 0.00 | 0.00 | |||
| Exterior Floor | 0.00 | 0.00 | 0.00 | |||
| Interzone Floor | -1743.6 | -1743.6 | -14.5 | |||
| Ground Contact Floor | 0.00 | 0.00 | 0.00 | |||
| Other Floor | 0.00 | 0.00 | 0.00 | |||
| Fenestration Conduction | 471.53 | 471.53 | 3.91 | |||
| Fenestration Solar | 10772.88 | 10772.88 | 89.30 | |||
| Opaque Door | 0.00 | 0.00 | 0.00 | |||
| Grand Total | 1522.49 | 9422.14 | 564.95 | 553.90 | 12063.49 |
| Value | |
| Time of Peak Load | 7/21 08:50:00 |
| Outside Dry Bulb Temperature [C] | 24.98 |
| Outside Wet Bulb Temperature [C] | 24.20 |
| Outside Humidity Ratio at Peak [kgWater/kgAir] | 0.01878 |
| Zone Dry Bulb Temperature [C] | 24.00 |
| Zone Relative Humdity [%] | 47.09 |
| Zone Humidity Ratio at Peak [kgWater/kgAir] | 0.00875 |
| Peak Design Sensible Load [W] | 10012.89 |
| Estimated Instant + Delayed Sensible Load [W] | 10944.63 |
| Difference [W] | -931.7 |
| Sensible - Instant [W] | Sensible - Delayed [W] | Sensible - Return Air [W] | Latent [W] | Total [W] | %Grand Total | |
| People | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Lights | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Equipment | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Water Use Equipment | 0.00 | 0.00 | 0.00 | -0.00 | ||
| HVAC Equipment Losses | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Power Generation Equipment | 0.00 | 0.00 | 0.00 | -0.00 | ||
| DOAS | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Infiltration | -1575.9 | -553.5 | -2129.4 | 40.58 | ||
| Zone Ventilation | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Interzone Mixing | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Roof | 0.00 | 0.00 | -0.00 | |||
| Interzone Ceiling | -179.2 | -179.2 | 3.41 | |||
| Other Roof | 0.00 | 0.00 | -0.00 | |||
| Exterior Wall | -471.1 | -471.1 | 8.98 | |||
| Interzone Wall | 156.87 | 156.87 | -3.0 | |||
| Ground Contact Wall | 0.00 | 0.00 | -0.00 | |||
| Other Wall | 0.00 | 0.00 | -0.00 | |||
| Exterior Floor | 0.00 | 0.00 | -0.00 | |||
| Interzone Floor | 51.98 | 51.98 | -1.0 | |||
| Ground Contact Floor | 0.00 | 0.00 | -0.00 | |||
| Other Floor | 0.00 | 0.00 | -0.00 | |||
| Fenestration Conduction | -2677.2 | -2677.2 | 51.01 | |||
| Fenestration Solar | 0.00 | 0.00 | -0.00 | |||
| Opaque Door | 0.00 | 0.00 | -0.00 | |||
| Grand Total | -4253.1 | -441.4 | 0.00 | -553.5 | -5248.0 |
| Value | |
| Time of Peak Load | 1/21 06:00:00 |
| Outside Dry Bulb Temperature [C] | -20.6 |
| Outside Wet Bulb Temperature [C] | -20.6 |
| Outside Humidity Ratio at Peak [kgWater/kgAir] | 0.00061 |
| Zone Dry Bulb Temperature [C] | 20.99 |
| Zone Relative Humdity [%] | 42.69 |
| Zone Humidity Ratio at Peak [kgWater/kgAir] | 0.00658 |
| Peak Design Sensible Load [W] | -4697.6 |
| Estimated Instant + Delayed Sensible Load [W] | -4694.4 |
| Difference [W] | -3.2 |
Report: Zone Component Load Summary
For: PERIMETER_MID_ZN_3
Timestamp: 2018-02-13 16:27:46
Estimated Cooling Peak Load Components| Sensible - Instant [W] | Sensible - Delayed [W] | Sensible - Return Air [W] | Latent [W] | Total [W] | %Grand Total | |
| People | 525.77 | 229.44 | 588.00 | 1343.21 | 12.95 | |
| Lights | 0.00 | 3185.82 | 892.38 | 4078.20 | 39.31 | |
| Equipment | 1115.48 | 3353.97 | 0.00 | 4469.45 | 43.08 | |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Water Use Equipment | 0.00 | 0.00 | 0.00 | 0.00 | ||
| HVAC Equipment Losses | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Power Generation Equipment | 0.00 | 0.00 | 0.00 | 0.00 | ||
| DOAS Direct to Zone | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Infiltration | -35.1 | 215.32 | 180.21 | 1.74 | ||
| Zone Ventilation | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Interzone Mixing | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Roof | 0.00 | 0.00 | 0.00 | |||
| Interzone Ceiling | -272.8 | -272.8 | -2.6 | |||
| Other Roof | 0.00 | 0.00 | 0.00 | |||
| Exterior Wall | -664.0 | -664.0 | -6.4 | |||
| Interzone Wall | -1676.8 | -1676.8 | -16.2 | |||
| Ground Contact Wall | 0.00 | 0.00 | 0.00 | |||
| Other Wall | 0.00 | 0.00 | 0.00 | |||
| Exterior Floor | 0.00 | 0.00 | 0.00 | |||
| Interzone Floor | -232.1 | -232.1 | -2.2 | |||
| Ground Contact Floor | 0.00 | 0.00 | 0.00 | |||
| Other Floor | 0.00 | 0.00 | 0.00 | |||
| Fenestration Conduction | -358.3 | -358.3 | -3.5 | |||
| Fenestration Solar | 3508.28 | 3508.28 | 33.81 | |||
| Opaque Door | 0.00 | 0.00 | 0.00 | |||
| Grand Total | 1247.86 | 7431.78 | 892.38 | 803.32 | 10375.35 |
| Value | |
| Time of Peak Load | 7/21 07:00:00 |
| Outside Dry Bulb Temperature [C] | 21.46 |
| Outside Wet Bulb Temperature [C] | 21.46 |
| Outside Humidity Ratio at Peak [kgWater/kgAir] | 0.01650 |
| Zone Dry Bulb Temperature [C] | 24.00 |
| Zone Relative Humdity [%] | 47.90 |
| Zone Humidity Ratio at Peak [kgWater/kgAir] | 0.00890 |
| Peak Design Sensible Load [W] | 9833.38 |
| Estimated Instant + Delayed Sensible Load [W] | 8679.65 |
| Difference [W] | 1153.74 |
| Sensible - Instant [W] | Sensible - Delayed [W] | Sensible - Return Air [W] | Latent [W] | Total [W] | %Grand Total | |
| People | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Lights | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Equipment | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Water Use Equipment | 0.00 | 0.00 | 0.00 | -0.00 | ||
| HVAC Equipment Losses | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Power Generation Equipment | 0.00 | 0.00 | 0.00 | -0.00 | ||
| DOAS | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Infiltration | -2363.8 | -830.0 | -3193.8 | 40.64 | ||
| Zone Ventilation | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Interzone Mixing | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Roof | 0.00 | 0.00 | -0.00 | |||
| Interzone Ceiling | -272.9 | -272.9 | 3.47 | |||
| Other Roof | 0.00 | 0.00 | -0.00 | |||
| Exterior Wall | -706.5 | -706.5 | 8.99 | |||
| Interzone Wall | 262.42 | 262.42 | -3.3 | |||
| Ground Contact Wall | 0.00 | 0.00 | -0.00 | |||
| Other Wall | 0.00 | 0.00 | -0.00 | |||
| Exterior Floor | 0.00 | 0.00 | -0.00 | |||
| Interzone Floor | 92.52 | 92.52 | -1.2 | |||
| Ground Contact Floor | 0.00 | 0.00 | -0.00 | |||
| Other Floor | 0.00 | 0.00 | -0.00 | |||
| Fenestration Conduction | -4041.5 | -4041.5 | 51.42 | |||
| Fenestration Solar | 0.00 | 0.00 | -0.00 | |||
| Opaque Door | 0.00 | 0.00 | -0.00 | |||
| Grand Total | -6405.3 | -624.5 | 0.00 | -830.0 | -7859.7 |
| Value | |
| Time of Peak Load | 1/21 06:00:00 |
| Outside Dry Bulb Temperature [C] | -20.6 |
| Outside Wet Bulb Temperature [C] | -20.6 |
| Outside Humidity Ratio at Peak [kgWater/kgAir] | 0.00061 |
| Zone Dry Bulb Temperature [C] | 20.99 |
| Zone Relative Humdity [%] | 42.67 |
| Zone Humidity Ratio at Peak [kgWater/kgAir] | 0.00658 |
| Peak Design Sensible Load [W] | -7033.1 |
| Estimated Instant + Delayed Sensible Load [W] | -7029.8 |
| Difference [W] | -3.3 |
Report: Zone Component Load Summary
For: PERIMETER_MID_ZN_4
Timestamp: 2018-02-13 16:27:46
Estimated Cooling Peak Load Components| Sensible - Instant [W] | Sensible - Delayed [W] | Sensible - Return Air [W] | Latent [W] | Total [W] | %Grand Total | |
| People | 343.90 | 529.64 | 356.42 | 1229.96 | 9.28 | |
| Lights | 0.00 | 2706.78 | 564.92 | 3271.70 | 24.68 | |
| Equipment | 706.14 | 2841.62 | 0.00 | 3547.77 | 26.76 | |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Water Use Equipment | 0.00 | 0.00 | 0.00 | 0.00 | ||
| HVAC Equipment Losses | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Power Generation Equipment | 0.00 | 0.00 | 0.00 | 0.00 | ||
| DOAS Direct to Zone | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Infiltration | 48.90 | 195.50 | 244.40 | 1.84 | ||
| Zone Ventilation | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Interzone Mixing | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Roof | 0.00 | 0.00 | 0.00 | |||
| Interzone Ceiling | -1115.2 | -1115.2 | -8.4 | |||
| Other Roof | 0.00 | 0.00 | 0.00 | |||
| Exterior Wall | -732.6 | -732.6 | -5.5 | |||
| Interzone Wall | -2819.6 | -2819.6 | -21.3 | |||
| Ground Contact Wall | 0.00 | 0.00 | 0.00 | |||
| Other Wall | 0.00 | 0.00 | 0.00 | |||
| Exterior Floor | 0.00 | 0.00 | 0.00 | |||
| Interzone Floor | -2750.9 | -2750.9 | -20.8 | |||
| Ground Contact Floor | 0.00 | 0.00 | 0.00 | |||
| Other Floor | 0.00 | 0.00 | 0.00 | |||
| Fenestration Conduction | 898.83 | 898.83 | 6.78 | |||
| Fenestration Solar | 11481.18 | 11481.18 | 86.61 | |||
| Opaque Door | 0.00 | 0.00 | 0.00 | |||
| Grand Total | 1997.78 | 10140.88 | 564.92 | 551.92 | 13255.49 |
| Value | |
| Time of Peak Load | 7/21 16:50:00 |
| Outside Dry Bulb Temperature [C] | 29.84 |
| Outside Wet Bulb Temperature [C] | 25.45 |
| Outside Humidity Ratio at Peak [kgWater/kgAir] | 0.01878 |
| Zone Dry Bulb Temperature [C] | 24.00 |
| Zone Relative Humdity [%] | 47.03 |
| Zone Humidity Ratio at Peak [kgWater/kgAir] | 0.00874 |
| Peak Design Sensible Load [W] | 10355.29 |
| Estimated Instant + Delayed Sensible Load [W] | 12138.66 |
| Difference [W] | -1783.4 |
| Sensible - Instant [W] | Sensible - Delayed [W] | Sensible - Return Air [W] | Latent [W] | Total [W] | %Grand Total | |
| People | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Lights | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Equipment | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Water Use Equipment | 0.00 | 0.00 | 0.00 | -0.00 | ||
| HVAC Equipment Losses | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Power Generation Equipment | 0.00 | 0.00 | 0.00 | -0.00 | ||
| DOAS | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Infiltration | -1575.9 | -553.7 | -2129.6 | 40.51 | ||
| Zone Ventilation | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Interzone Mixing | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Roof | 0.00 | 0.00 | -0.00 | |||
| Interzone Ceiling | -178.3 | -178.3 | 3.39 | |||
| Other Roof | 0.00 | 0.00 | -0.00 | |||
| Exterior Wall | -470.5 | -470.5 | 8.95 | |||
| Interzone Wall | 157.65 | 157.65 | -3.0 | |||
| Ground Contact Wall | 0.00 | 0.00 | -0.00 | |||
| Other Wall | 0.00 | 0.00 | -0.00 | |||
| Exterior Floor | 0.00 | 0.00 | -0.00 | |||
| Interzone Floor | 52.80 | 52.80 | -1.0 | |||
| Ground Contact Floor | 0.00 | 0.00 | -0.00 | |||
| Other Floor | 0.00 | 0.00 | -0.00 | |||
| Fenestration Conduction | -2689.0 | -2689.0 | 51.15 | |||
| Fenestration Solar | 0.00 | 0.00 | -0.00 | |||
| Opaque Door | 0.00 | 0.00 | -0.00 | |||
| Grand Total | -4264.8 | -438.3 | 0.00 | -553.7 | -5256.9 |
| Value | |
| Time of Peak Load | 1/21 06:00:00 |
| Outside Dry Bulb Temperature [C] | -20.6 |
| Outside Wet Bulb Temperature [C] | -20.6 |
| Outside Humidity Ratio at Peak [kgWater/kgAir] | 0.00061 |
| Zone Dry Bulb Temperature [C] | 20.99 |
| Zone Relative Humdity [%] | 42.70 |
| Zone Humidity Ratio at Peak [kgWater/kgAir] | 0.00659 |
| Peak Design Sensible Load [W] | -4706.4 |
| Estimated Instant + Delayed Sensible Load [W] | -4703.2 |
| Difference [W] | -3.2 |
Report: Zone Component Load Summary
For: PERIMETER_TOP_ZN_1
Timestamp: 2018-02-13 16:27:46
Estimated Cooling Peak Load Components| Sensible - Instant [W] | Sensible - Delayed [W] | Sensible - Return Air [W] | Latent [W] | Total [W] | %Grand Total | |
| People | 543.26 | 941.21 | 563.02 | 2047.49 | 11.37 | |
| Lights | 0.00 | 5207.13 | 892.38 | 6099.52 | 33.86 | |
| Equipment | 1115.48 | 5476.66 | 0.00 | 6592.14 | 36.59 | |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Water Use Equipment | 0.00 | 0.00 | 0.00 | 0.00 | ||
| HVAC Equipment Losses | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Power Generation Equipment | 0.00 | 0.00 | 0.00 | 0.00 | ||
| DOAS Direct to Zone | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Infiltration | 75.86 | 291.53 | 367.38 | 2.04 | ||
| Zone Ventilation | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Interzone Mixing | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Roof | 0.00 | 0.00 | 0.00 | |||
| Interzone Ceiling | -2422.9 | -2422.9 | -13.4 | |||
| Other Roof | 0.00 | 0.00 | 0.00 | |||
| Exterior Wall | -1431.4 | -1431.4 | -7.9 | |||
| Interzone Wall | -4920.7 | -4920.7 | -27.3 | |||
| Ground Contact Wall | 0.00 | 0.00 | 0.00 | |||
| Other Wall | 0.00 | 0.00 | 0.00 | |||
| Exterior Floor | 0.00 | 0.00 | 0.00 | |||
| Interzone Floor | -5462.1 | -5462.1 | -30.3 | |||
| Ground Contact Floor | 0.00 | 0.00 | 0.00 | |||
| Other Floor | 0.00 | 0.00 | 0.00 | |||
| Fenestration Conduction | 904.18 | 904.18 | 5.02 | |||
| Fenestration Solar | 16240.86 | 16240.86 | 90.15 | |||
| Opaque Door | 0.00 | 0.00 | 0.00 | |||
| Grand Total | 2638.77 | 13628.80 | 892.38 | 854.55 | 18014.50 |
| Value | |
| Time of Peak Load | 7/21 13:10:00 |
| Outside Dry Bulb Temperature [C] | 30.75 |
| Outside Wet Bulb Temperature [C] | 25.68 |
| Outside Humidity Ratio at Peak [kgWater/kgAir] | 0.01878 |
| Zone Dry Bulb Temperature [C] | 24.00 |
| Zone Relative Humdity [%] | 47.32 |
| Zone Humidity Ratio at Peak [kgWater/kgAir] | 0.00879 |
| Peak Design Sensible Load [W] | 13106.86 |
| Estimated Instant + Delayed Sensible Load [W] | 16267.57 |
| Difference [W] | -3160.7 |
| Sensible - Instant [W] | Sensible - Delayed [W] | Sensible - Return Air [W] | Latent [W] | Total [W] | %Grand Total | |
| People | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Lights | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Equipment | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Water Use Equipment | 0.00 | 0.00 | 0.00 | -0.00 | ||
| HVAC Equipment Losses | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Power Generation Equipment | 0.00 | 0.00 | 0.00 | -0.00 | ||
| DOAS | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Infiltration | -2365.6 | -886.3 | -3251.9 | 28.41 | ||
| Zone Ventilation | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Interzone Mixing | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Roof | 0.00 | 0.00 | -0.00 | |||
| Interzone Ceiling | -3946.5 | -3946.5 | 34.48 | |||
| Other Roof | 0.00 | 0.00 | -0.00 | |||
| Exterior Wall | -689.3 | -689.3 | 6.02 | |||
| Interzone Wall | 239.89 | 239.89 | -2.1 | |||
| Ground Contact Wall | 0.00 | 0.00 | -0.00 | |||
| Other Wall | 0.00 | 0.00 | -0.00 | |||
| Exterior Floor | 0.00 | 0.00 | -0.00 | |||
| Interzone Floor | 199.84 | 199.84 | -1.7 | |||
| Ground Contact Floor | 0.00 | 0.00 | -0.00 | |||
| Other Floor | 0.00 | 0.00 | -0.00 | |||
| Fenestration Conduction | -3999.2 | -3999.2 | 34.94 | |||
| Fenestration Solar | 0.00 | 0.00 | -0.00 | |||
| Opaque Door | 0.00 | 0.00 | -0.00 | |||
| Grand Total | -6364.7 | -4196.1 | 0.00 | -886.3 | -11447.2 |
| Value | |
| Time of Peak Load | 1/21 06:00:00 |
| Outside Dry Bulb Temperature [C] | -20.6 |
| Outside Wet Bulb Temperature [C] | -20.6 |
| Outside Humidity Ratio at Peak [kgWater/kgAir] | 0.00061 |
| Zone Dry Bulb Temperature [C] | 20.99 |
| Zone Relative Humdity [%] | 45.27 |
| Zone Humidity Ratio at Peak [kgWater/kgAir] | 0.00699 |
| Peak Design Sensible Load [W] | -10512.3 |
| Estimated Instant + Delayed Sensible Load [W] | -10560.9 |
| Difference [W] | 48.60 |
Report: Zone Component Load Summary
For: PERIMETER_TOP_ZN_2
Timestamp: 2018-02-13 16:27:46
Estimated Cooling Peak Load Components| Sensible - Instant [W] | Sensible - Delayed [W] | Sensible - Return Air [W] | Latent [W] | Total [W] | %Grand Total | |
| People | 343.92 | 413.96 | 356.44 | 1114.33 | 8.74 | |
| Lights | 0.00 | 2909.03 | 564.95 | 3473.99 | 27.26 | |
| Equipment | 706.19 | 3053.53 | 0.00 | 3759.72 | 29.50 | |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Water Use Equipment | 0.00 | 0.00 | 0.00 | 0.00 | ||
| HVAC Equipment Losses | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Power Generation Equipment | 0.00 | 0.00 | 0.00 | 0.00 | ||
| DOAS Direct to Zone | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Infiltration | 0.64 | 197.49 | 198.14 | 1.55 | ||
| Zone Ventilation | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Interzone Mixing | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Roof | 0.00 | 0.00 | 0.00 | |||
| Interzone Ceiling | -1599.0 | -1599.0 | -12.5 | |||
| Other Roof | 0.00 | 0.00 | 0.00 | |||
| Exterior Wall | -830.3 | -830.3 | -6.5 | |||
| Interzone Wall | -4228.1 | -4228.1 | -33.2 | |||
| Ground Contact Wall | 0.00 | 0.00 | 0.00 | |||
| Other Wall | 0.00 | 0.00 | 0.00 | |||
| Exterior Floor | 0.00 | 0.00 | 0.00 | |||
| Interzone Floor | -2601.7 | -2601.7 | -20.4 | |||
| Ground Contact Floor | 0.00 | 0.00 | 0.00 | |||
| Other Floor | 0.00 | 0.00 | 0.00 | |||
| Fenestration Conduction | 466.08 | 466.08 | 3.66 | |||
| Fenestration Solar | 12991.21 | 12991.21 | 101.94 | |||
| Opaque Door | 0.00 | 0.00 | 0.00 | |||
| Grand Total | 1516.84 | 10108.56 | 564.95 | 553.94 | 12744.29 |
| Value | |
| Time of Peak Load | 7/21 08:50:00 |
| Outside Dry Bulb Temperature [C] | 24.98 |
| Outside Wet Bulb Temperature [C] | 24.20 |
| Outside Humidity Ratio at Peak [kgWater/kgAir] | 0.01878 |
| Zone Dry Bulb Temperature [C] | 24.00 |
| Zone Relative Humdity [%] | 47.08 |
| Zone Humidity Ratio at Peak [kgWater/kgAir] | 0.00875 |
| Peak Design Sensible Load [W] | 10061.40 |
| Estimated Instant + Delayed Sensible Load [W] | 11625.40 |
| Difference [W] | -1564.0 |
| Sensible - Instant [W] | Sensible - Delayed [W] | Sensible - Return Air [W] | Latent [W] | Total [W] | %Grand Total | |
| People | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Lights | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Equipment | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Water Use Equipment | 0.00 | 0.00 | 0.00 | -0.00 | ||
| HVAC Equipment Losses | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Power Generation Equipment | 0.00 | 0.00 | 0.00 | -0.00 | ||
| DOAS | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Infiltration | -1577.0 | -589.0 | -2166.1 | 28.99 | ||
| Zone Ventilation | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Interzone Mixing | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Roof | 0.00 | 0.00 | -0.00 | |||
| Interzone Ceiling | -2481.2 | -2481.2 | 33.21 | |||
| Other Roof | 0.00 | 0.00 | -0.00 | |||
| Exterior Wall | -460.0 | -460.0 | 6.16 | |||
| Interzone Wall | 129.66 | 129.66 | -1.7 | |||
| Ground Contact Wall | 0.00 | 0.00 | -0.00 | |||
| Other Wall | 0.00 | 0.00 | -0.00 | |||
| Exterior Floor | 0.00 | 0.00 | -0.00 | |||
| Interzone Floor | 151.80 | 151.80 | -2.0 | |||
| Ground Contact Floor | 0.00 | 0.00 | -0.00 | |||
| Other Floor | 0.00 | 0.00 | -0.00 | |||
| Fenestration Conduction | -2644.7 | -2644.7 | 35.40 | |||
| Fenestration Solar | 0.00 | 0.00 | -0.00 | |||
| Opaque Door | 0.00 | 0.00 | -0.00 | |||
| Grand Total | -4221.7 | -2659.7 | 0.00 | -589.0 | -7470.5 |
| Value | |
| Time of Peak Load | 1/21 06:00:00 |
| Outside Dry Bulb Temperature [C] | -20.6 |
| Outside Wet Bulb Temperature [C] | -20.6 |
| Outside Humidity Ratio at Peak [kgWater/kgAir] | 0.00061 |
| Zone Dry Bulb Temperature [C] | 20.99 |
| Zone Relative Humdity [%] | 45.14 |
| Zone Humidity Ratio at Peak [kgWater/kgAir] | 0.00697 |
| Peak Design Sensible Load [W] | -6852.5 |
| Estimated Instant + Delayed Sensible Load [W] | -6881.4 |
| Difference [W] | 28.98 |
Report: Zone Component Load Summary
For: PERIMETER_TOP_ZN_3
Timestamp: 2018-02-13 16:27:46
Estimated Cooling Peak Load Components| Sensible - Instant [W] | Sensible - Delayed [W] | Sensible - Return Air [W] | Latent [W] | Total [W] | %Grand Total | |
| People | 525.77 | 245.16 | 588.00 | 1358.94 | 12.46 | |
| Lights | 0.00 | 4105.45 | 892.38 | 4997.83 | 45.82 | |
| Equipment | 1115.48 | 4327.39 | 0.00 | 5442.87 | 49.90 | |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Water Use Equipment | 0.00 | 0.00 | 0.00 | 0.00 | ||
| HVAC Equipment Losses | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Power Generation Equipment | 0.00 | 0.00 | 0.00 | 0.00 | ||
| DOAS Direct to Zone | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Infiltration | -35.4 | 215.61 | 180.19 | 1.65 | ||
| Zone Ventilation | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Interzone Mixing | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Roof | 0.00 | 0.00 | 0.00 | |||
| Interzone Ceiling | -899.5 | -899.5 | -8.2 | |||
| Other Roof | 0.00 | 0.00 | 0.00 | |||
| Exterior Wall | -874.4 | -874.4 | -8.0 | |||
| Interzone Wall | -2371.2 | -2371.2 | -21.7 | |||
| Ground Contact Wall | 0.00 | 0.00 | 0.00 | |||
| Other Wall | 0.00 | 0.00 | 0.00 | |||
| Exterior Floor | 0.00 | 0.00 | 0.00 | |||
| Interzone Floor | -527.5 | -527.5 | -4.8 | |||
| Ground Contact Floor | 0.00 | 0.00 | 0.00 | |||
| Other Floor | 0.00 | 0.00 | 0.00 | |||
| Fenestration Conduction | -361.2 | -361.2 | -3.3 | |||
| Fenestration Solar | 3961.69 | 3961.69 | 36.32 | |||
| Opaque Door | 0.00 | 0.00 | 0.00 | |||
| Grand Total | 1244.63 | 7967.01 | 892.38 | 803.62 | 10907.63 |
| Value | |
| Time of Peak Load | 7/21 07:00:00 |
| Outside Dry Bulb Temperature [C] | 21.46 |
| Outside Wet Bulb Temperature [C] | 21.46 |
| Outside Humidity Ratio at Peak [kgWater/kgAir] | 0.01650 |
| Zone Dry Bulb Temperature [C] | 24.00 |
| Zone Relative Humdity [%] | 47.87 |
| Zone Humidity Ratio at Peak [kgWater/kgAir] | 0.00890 |
| Peak Design Sensible Load [W] | 9922.02 |
| Estimated Instant + Delayed Sensible Load [W] | 9211.63 |
| Difference [W] | 710.39 |
| Sensible - Instant [W] | Sensible - Delayed [W] | Sensible - Return Air [W] | Latent [W] | Total [W] | %Grand Total | |
| People | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Lights | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Equipment | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Water Use Equipment | 0.00 | 0.00 | 0.00 | -0.00 | ||
| HVAC Equipment Losses | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Power Generation Equipment | 0.00 | 0.00 | 0.00 | -0.00 | ||
| DOAS | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Infiltration | -2365.6 | -885.9 | -3251.4 | 28.50 | ||
| Zone Ventilation | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Interzone Mixing | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Roof | 0.00 | 0.00 | -0.00 | |||
| Interzone Ceiling | -3900.2 | -3900.2 | 34.18 | |||
| Other Roof | 0.00 | 0.00 | -0.00 | |||
| Exterior Wall | -688.1 | -688.1 | 6.03 | |||
| Interzone Wall | 186.15 | 186.15 | -1.6 | |||
| Ground Contact Wall | 0.00 | 0.00 | -0.00 | |||
| Other Wall | 0.00 | 0.00 | -0.00 | |||
| Exterior Floor | 0.00 | 0.00 | -0.00 | |||
| Interzone Floor | 240.73 | 240.73 | -2.1 | |||
| Ground Contact Floor | 0.00 | 0.00 | -0.00 | |||
| Other Floor | 0.00 | 0.00 | -0.00 | |||
| Fenestration Conduction | -3996.8 | -3996.8 | 35.03 | |||
| Fenestration Solar | 0.00 | 0.00 | -0.00 | |||
| Opaque Door | 0.00 | 0.00 | -0.00 | |||
| Grand Total | -6362.4 | -4161.4 | 0.00 | -885.9 | -11409.7 |
| Value | |
| Time of Peak Load | 1/21 06:00:00 |
| Outside Dry Bulb Temperature [C] | -20.6 |
| Outside Wet Bulb Temperature [C] | -20.6 |
| Outside Humidity Ratio at Peak [kgWater/kgAir] | 0.00061 |
| Zone Dry Bulb Temperature [C] | 20.99 |
| Zone Relative Humdity [%] | 45.25 |
| Zone Humidity Ratio at Peak [kgWater/kgAir] | 0.00698 |
| Peak Design Sensible Load [W] | -10473.9 |
| Estimated Instant + Delayed Sensible Load [W] | -10523.8 |
| Difference [W] | 49.92 |
Report: Zone Component Load Summary
For: PERIMETER_TOP_ZN_4
Timestamp: 2018-02-13 16:27:46
Estimated Cooling Peak Load Components| Sensible - Instant [W] | Sensible - Delayed [W] | Sensible - Return Air [W] | Latent [W] | Total [W] | %Grand Total | |
| People | 343.90 | 669.84 | 356.42 | 1370.16 | 9.66 | |
| Lights | 0.00 | 3359.42 | 564.92 | 3924.34 | 27.68 | |
| Equipment | 706.14 | 3529.55 | 0.00 | 4235.70 | 29.88 | |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Water Use Equipment | 0.00 | 0.00 | 0.00 | 0.00 | ||
| HVAC Equipment Losses | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Power Generation Equipment | 0.00 | 0.00 | 0.00 | 0.00 | ||
| DOAS Direct to Zone | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Infiltration | 48.70 | 195.54 | 244.25 | 1.72 | ||
| Zone Ventilation | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Interzone Mixing | 0.00 | 0.00 | 0.00 | 0.00 | ||
| Roof | 0.00 | 0.00 | 0.00 | |||
| Interzone Ceiling | -1863.1 | -1863.1 | -13.1 | |||
| Other Roof | 0.00 | 0.00 | 0.00 | |||
| Exterior Wall | -938.9 | -938.9 | -6.6 | |||
| Interzone Wall | -3606.7 | -3606.7 | -25.4 | |||
| Ground Contact Wall | 0.00 | 0.00 | 0.00 | |||
| Other Wall | 0.00 | 0.00 | 0.00 | |||
| Exterior Floor | 0.00 | 0.00 | 0.00 | |||
| Interzone Floor | -3901.9 | -3901.9 | -27.5 | |||
| Ground Contact Floor | 0.00 | 0.00 | 0.00 | |||
| Other Floor | 0.00 | 0.00 | 0.00 | |||
| Fenestration Conduction | 895.98 | 895.98 | 6.32 | |||
| Fenestration Solar | 13817.62 | 13817.62 | 97.46 | |||
| Opaque Door | 0.00 | 0.00 | 0.00 | |||
| Grand Total | 1994.73 | 11065.81 | 564.92 | 551.96 | 14177.42 |
| Value | |
| Time of Peak Load | 7/21 16:50:00 |
| Outside Dry Bulb Temperature [C] | 29.84 |
| Outside Wet Bulb Temperature [C] | 25.45 |
| Outside Humidity Ratio at Peak [kgWater/kgAir] | 0.01878 |
| Zone Dry Bulb Temperature [C] | 24.00 |
| Zone Relative Humdity [%] | 47.02 |
| Zone Humidity Ratio at Peak [kgWater/kgAir] | 0.00874 |
| Peak Design Sensible Load [W] | 10429.93 |
| Estimated Instant + Delayed Sensible Load [W] | 13060.54 |
| Difference [W] | -2630.6 |
| Sensible - Instant [W] | Sensible - Delayed [W] | Sensible - Return Air [W] | Latent [W] | Total [W] | %Grand Total | |
| People | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Lights | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Equipment | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | |
| Water Use Equipment | 0.00 | 0.00 | 0.00 | -0.00 | ||
| HVAC Equipment Losses | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Power Generation Equipment | 0.00 | 0.00 | 0.00 | -0.00 | ||
| DOAS | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Infiltration | -1577.0 | -589.2 | -2166.2 | 28.94 | ||
| Zone Ventilation | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Interzone Mixing | 0.00 | 0.00 | 0.00 | -0.00 | ||
| Roof | 0.00 | 0.00 | -0.00 | |||
| Interzone Ceiling | -2479.8 | -2479.8 | 33.13 | |||
| Other Roof | 0.00 | 0.00 | -0.00 | |||
| Exterior Wall | -459.1 | -459.1 | 6.13 | |||
| Interzone Wall | 130.81 | 130.81 | -1.7 | |||
| Ground Contact Wall | 0.00 | 0.00 | -0.00 | |||
| Other Wall | 0.00 | 0.00 | -0.00 | |||
| Exterior Floor | 0.00 | 0.00 | -0.00 | |||
| Interzone Floor | 153.01 | 153.01 | -2.0 | |||
| Ground Contact Floor | 0.00 | 0.00 | -0.00 | |||
| Other Floor | 0.00 | 0.00 | -0.00 | |||
| Fenestration Conduction | -2663.9 | -2663.9 | 35.59 | |||
| Fenestration Solar | 0.00 | 0.00 | -0.00 | |||
| Opaque Door | 0.00 | 0.00 | -0.00 | |||
| Grand Total | -4240.9 | -2655.0 | 0.00 | -589.2 | -7485.2 |
| Value | |
| Time of Peak Load | 1/21 06:00:00 |
| Outside Dry Bulb Temperature [C] | -20.6 |
| Outside Wet Bulb Temperature [C] | -20.6 |
| Outside Humidity Ratio at Peak [kgWater/kgAir] | 0.00061 |
| Zone Dry Bulb Temperature [C] | 20.99 |
| Zone Relative Humdity [%] | 45.15 |
| Zone Humidity Ratio at Peak [kgWater/kgAir] | 0.00697 |
| Peak Design Sensible Load [W] | -6867.0 |
| Estimated Instant + Delayed Sensible Load [W] | -6896.0 |
| Difference [W] | 28.94 |
Report: COMPONENTS OF PEAK ELECTRICAL DEMAND
For: Meter
Timestamp: 2018-02-13 16:27:46
Custom Monthly Report| ELECTRICITY:FACILITY [J] | ELECTRICITY:FACILITY {Maximum}[W] | ELECTRICITY:FACILITY {TIMESTAMP} | INTERIORLIGHTS:ELECTRICITY {AT MAX/MIN} [W] | INTERIOREQUIPMENT:ELECTRICITY {AT MAX/MIN} [W] | FANS:ELECTRICITY {AT MAX/MIN} [W] | HEATING:ELECTRICITY {AT MAX/MIN} [W] | COOLING:ELECTRICITY {AT MAX/MIN} [W] | EXTERIORLIGHTS:ELECTRICITY {AT MAX/MIN} [W] | PUMPS:ELECTRICITY {AT MAX/MIN} [W] | HEATREJECTION:ELECTRICITY [Invalid/Undefined] | EXTERIOREQUIPMENT:ELECTRICITY [Invalid/Undefined] | HUMIDIFICATION:ELECTRICITY [Invalid/Undefined] | HEATRECOVERY:ELECTRICITY [Invalid/Undefined] | WATERSYSTEMS:ELECTRICITY [Invalid/Undefined] | REFRIGERATION:ELECTRICITY [Invalid/Undefined] | GENERATORS:ELECTRICITY [Invalid/Undefined] | ELECTRICITYPRODUCED:FACILITY [Invalid/Undefined] | |
| January | 0.240147E+12 | 310294.498 | 02-JAN-06:19 | 5360.832 | 21443.328 | 3839.191 | 264838.707 | 0.000 | 14804.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| February | 0.197654E+12 | 298546.740 | 06-FEB-06:10 | 5360.832 | 21443.328 | 3839.191 | 253090.949 | 0.000 | 14804.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| March | 0.199309E+12 | 223240.067 | 06-MAR-06:10 | 5360.832 | 21443.328 | 3839.191 | 177784.276 | 0.000 | 14804.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| April | 0.185848E+12 | 194741.673 | 18-APR-12:00 | 48247.488 | 63660.235 | 8218.245 | 0.000 | 74607.264 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| May | 0.196687E+12 | 189550.611 | 30-MAY-12:50 | 48247.488 | 63660.235 | 6211.549 | 0.000 | 71422.899 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| June | 0.227353E+12 | 215097.063 | 08-JUN-12:00 | 48247.488 | 63660.235 | 7996.751 | 0.000 | 95184.148 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| July | 0.245631E+12 | 221264.426 | 19-JUL-15:09 | 48247.488 | 63018.038 | 8755.881 | 0.000 | 101234.579 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| August | 0.244412E+12 | 211605.379 | 04-AUG-15:30 | 48247.488 | 63018.038 | 8064.089 | 0.000 | 92267.324 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| September | 0.203400E+12 | 185812.512 | 06-SEP-10:00 | 48247.488 | 62054.741 | 7276.514 | 0.000 | 68225.329 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| October | 0.182743E+12 | 152498.247 | 02-OCT-12:00 | 48247.488 | 63660.235 | 5413.085 | 0.000 | 35168.999 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| November | 0.200656E+12 | 262116.299 | 27-NOV-06:10 | 5360.832 | 21443.328 | 3839.191 | 216660.508 | 0.000 | 14804.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| December | 0.226793E+12 | 297288.110 | 18-DEC-06:10 | 5360.832 | 21443.328 | 3839.191 | 251832.318 | 0.000 | 14804.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| Annual Sum or Average | 0.255063E+13 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | |||||||||
| Minimum of Months | 0.182743E+12 | 152498.247 | 5360.832 | 21443.328 | 3839.191 | 0.000 | 0.000 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | |
| Maximum of Months | 0.245631E+12 | 310294.498 | 48247.488 | 63660.235 | 8755.881 | 264838.707 | 101234.579 | 14804.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
Report: COOLING PART LOAD PERFORMANCE
For: VAV_1_COOLC DXCOIL
Timestamp: 2018-02-13 16:27:46
Custom Monthly Report| COOLING COIL ELECTRIC POWER [W] | COOLING COIL ELECTRIC POWER {Maximum}[W] | COOLING COIL ELECTRIC POWER {TIMESTAMP} | |
| January | 0. | 0. | 01-JAN-00:02 |
| February | 31. | 2707. | 23-FEB-12:00 |
| March | 157. | 10389. | 27-MAR-15:10 |
| April | 1970. | 26933. | 18-APR-13:00 |
| May | 4003. | 27037. | 30-MAY-12:50 |
| June | 8863. | 43857. | 20-JUN-05:02 |
| July | 11302. | 44156. | 05-JUL-05:02 |
| August | 9793. | 43332. | 04-AUG-05:02 |
| September | 6102. | 26923. | 07-SEP-05:02 |
| October | 1133. | 14027. | 02-OCT-13:00 |
| November | 895. | 14756. | 02-NOV-13:00 |
| December | 0. | 0. | 01-DEC-00:10 |
| Annual Sum or Average | 3709. | ||
| Minimum of Months | 0. | 0. | |
| Maximum of Months | 11302. | 44156. |
Report: COOLING PART LOAD PERFORMANCE
For: VAV_2_COOLC DXCOIL
Timestamp: 2018-02-13 16:27:46
Custom Monthly Report| COOLING COIL ELECTRIC POWER [W] | COOLING COIL ELECTRIC POWER {Maximum}[W] | COOLING COIL ELECTRIC POWER {TIMESTAMP} | |
| January | 0. | 0. | 01-JAN-00:02 |
| February | 26. | 2304. | 23-FEB-12:00 |
| March | 113. | 8309. | 27-MAR-15:00 |
| April | 1687. | 25816. | 18-APR-05:02 |
| May | 3308. | 25156. | 30-MAY-05:02 |
| June | 7558. | 38335. | 20-JUN-05:02 |
| July | 9948. | 38597. | 05-JUL-05:02 |
| August | 8296. | 37666. | 04-AUG-05:02 |
| September | 5031. | 26843. | 16-SEP-05:02 |
| October | 885. | 11040. | 21-OCT-11:40 |
| November | 713. | 10759. | 02-NOV-13:00 |
| December | 0. | 0. | 01-DEC-00:10 |
| Annual Sum or Average | 3149. | ||
| Minimum of Months | 0. | 0. | |
| Maximum of Months | 9948. | 38597. |
Report: COOLING PART LOAD PERFORMANCE
For: VAV_3_COOLC DXCOIL
Timestamp: 2018-02-13 16:27:46
Custom Monthly Report| COOLING COIL ELECTRIC POWER [W] | COOLING COIL ELECTRIC POWER {Maximum}[W] | COOLING COIL ELECTRIC POWER {TIMESTAMP} | |
| January | 0. | 0. | 01-JAN-00:02 |
| February | 27. | 2325. | 23-FEB-12:00 |
| March | 103. | 8380. | 27-MAR-15:00 |
| April | 1710. | 26318. | 18-APR-05:02 |
| May | 3263. | 24794. | 30-MAY-05:02 |
| June | 7639. | 38611. | 20-JUN-05:02 |
| July | 10425. | 38874. | 05-JUL-05:02 |
| August | 8421. | 36760. | 28-AUG-05:02 |
| September | 4963. | 26755. | 16-SEP-05:02 |
| October | 852. | 10671. | 21-OCT-14:00 |
| November | 718. | 10663. | 02-NOV-13:00 |
| December | 0. | 0. | 01-DEC-00:10 |
| Annual Sum or Average | 3196. | ||
| Minimum of Months | 0. | 0. | |
| Maximum of Months | 10425. | 38874. |
Report: EMISSIONS DATA SUMMARY
For: Meter
Timestamp: 2018-02-13 16:27:46
Custom Monthly Report| CO2:FACILITY [kg] | NOX:FACILITY [kg] | SO2:FACILITY [kg] | PM:FACILITY [kg] | HG:FACILITY [kg] | WATERENVIRONMENTALFACTORS:FACILITY [L] | CARBON EQUIVALENT:FACILITY [kg] | |
| January | 84461.5829 | 151.6015 | 449.5681 | 0.0000 | 0.0014 |<PHONE_NUMBER> | 24318.1228 |
| February | 69136.4094 | 124.4312 | 370.0172 | 0.0000 | 0.0011 | 85180.2581 | 19910.8211 |
| March | 68494.8975 | 124.3651 | 373.1089 | 0.0000 | 0.0011 | 85893.4426 | 19742.5733 |
| April | 63738.8424 | 115.8476 | 347.9086 | 0.0000 | 0.0010 | 80092.2205 | 18373.5038 |
| May | 67369.8016 | 122.5255 | 368.1981 | 0.0000 | 0.0011 | 84763.1797 | 19421.3623 |
| June | 77832.9417 | 141.5920 | 425.6055 | 0.0000 | 0.0013 | 97979.0284 | 22438.2394 |
| July | 84066.1041 | 152.9533 | 459.8224 | 0.0000 | 0.0014 |<PHONE_NUMBER> | 24235.5160 |
| August | 83654.6491 | 152.1995 | 457.5404 | 0.0000 | 0.0014 |<PHONE_NUMBER> | 24116.8178 |
| September | 69634.0182 | 126.6756 | 380.7657 | 0.0000 | 0.0011 | 87656.4311 | 20074.5785 |
| October | 62591.8357 | 113.8375 | 342.0955 | 0.0000 | 0.0010 | 78754.0808 | 18043.9972 |
| November | 69264.6500 | 125.4842 | 375.6322 | 0.0000 | 0.0011 | 86473.9622 | 19960.2191 |
| December | 79494.0394 | 142.9254 | 424.5676 | 0.0000 | 0.0013 | 97737.8920 | 22891.5142 |
| Annual Sum or Average |<PHONE_NUMBER> | 1594.4384 | 4774.8303 | 0.0000 | 0.0144 | 0.109921E+07 |<PHONE_NUMBER> |
| Minimum of Months | 62591.8357 | 113.8375 | 342.0955 | 0.0000 | 0.0010 | 78754.0808 | 18043.9972 |
| Maximum of Months | 84461.5829 | 152.9533 | 459.8224 | 0.0000 | 0.0014 |<PHONE_NUMBER> | 24318.1228 |
Report: FAN PART LOAD PERFORMANCE
For: VAV_1_FAN
Timestamp: 2018-02-13 16:27:46
Custom Monthly Report| FAN ELECTRIC POWER [W] | FAN ELECTRIC POWER {Maximum}[W] | FAN ELECTRIC POWER {TIMESTAMP} | |
| January | 820. | 1707. | 05-JAN-13:10 |
| February | 779. | 1941. | 10-FEB-13:40 |
| March | 870. | 2224. | 15-MAR-15:20 |
| April | 896. | 5860. | 18-APR-05:02 |
| May | 1000. | 4840. | 31-MAY-05:02 |
| June | 1175. | 11091. | 20-JUN-05:02 |
| July | 1178. | 13123. | 05-JUL-05:02 |
| August | 1180. | 12511. | 04-AUG-05:02 |
| September | 1026. | 6069. | 07-SEP-05:02 |
| October | 864. | 2641. | 03-OCT-05:02 |
| November | 777. | 2175. | 03-NOV-05:02 |
| December | 741. | 1825. | 05-DEC-13:30 |
| Annual Sum or Average | 943. | ||
| Minimum of Months | 741. | 1707. | |
| Maximum of Months | 1180. | 13123. |
Report: FAN PART LOAD PERFORMANCE
For: VAV_2_FAN
Timestamp: 2018-02-13 16:27:46
Custom Monthly Report| FAN ELECTRIC POWER [W] | FAN ELECTRIC POWER {Maximum}[W] | FAN ELECTRIC POWER {TIMESTAMP} | |
| January | 696. | 1240. | 10-JAN-13:30 |
| February | 652. | 1332. | 10-FEB-13:30 |
| March | 695. | 1420. | 09-MAR-13:30 |
| April | 718. | 7733. | 18-APR-05:02 |
| May | 785. | 6659. | 30-MAY-05:02 |
| June | 945. | 12617. | 20-JUN-05:02 |
| July | 965. | 13873. | 05-JUL-05:02 |
| August | 931. | 12411. | 04-AUG-05:02 |
| September | 801. | 6791. | 07-SEP-05:02 |
| October | 666. | 3802. | 03-OCT-05:02 |
| November | 634. | 2630. | 03-NOV-05:02 |
| December | 630. | 1303. | 05-DEC-13:05 |
| Annual Sum or Average | 761. | ||
| Minimum of Months | 630. | 1240. | |
| Maximum of Months | 965. | 13873. |
Report: FAN PART LOAD PERFORMANCE
For: VAV_3_FAN
Timestamp: 2018-02-13 16:27:46
Custom Monthly Report| FAN ELECTRIC POWER [W] | FAN ELECTRIC POWER {Maximum}[W] | FAN ELECTRIC POWER {TIMESTAMP} | |
| January | 808. | 1233. | 01-JAN-00:02 |
| February | 735. | 1266. | 10-FEB-13:30 |
| March | 704. | 1361. | 09-MAR-13:30 |
| April | 714. | 8029. | 18-APR-05:02 |
| May | 764. | 6310. | 30-MAY-05:02 |
| June | 944. | 12788. | 20-JUN-05:02 |
| July | 993. | 14158. | 05-JUL-05:02 |
| August | 927. | 9241. | 23-AUG-05:02 |
| September | 780. | 6860. | 07-SEP-05:02 |
| October | 653. | 1846. | 03-OCT-05:02 |
| November | 677. | 1363. | 02-NOV-12:20 |
| December | 758. | 1241. | 05-DEC-13:20 |
| Annual Sum or Average | 789. | ||
| Minimum of Months | 653. | 1233. | |
| Maximum of Months | 993. | 14158. |
Report: HEATING PART LOAD PERFORMANCE
For: VAV_1_HEATC
Timestamp: 2018-02-13 16:27:46
Custom Monthly Report| HEATING COIL GAS RATE [W] | HEATING COIL GAS RATE {Maximum}[W] | HEATING COIL GAS RATE {TIMESTAMP} | |
| January | 3174. | 39334. | 07-JAN-07:10 |
| February | 1950. | 39557. | 06-FEB-07:05 |
| March | 74. | 12468. | 18-MAR-06:10 |
| April | 19. | 6661. | 05-APR-06:05 |
| May | 0. | 0. | 01-MAY-00:10 |
| June | 0. | 0. | 01-JUN-00:10 |
| July | 0. | 0. | 01-JUL-00:10 |
| August | 0. | 0. | 01-AUG-00:10 |
| September | 0. | 0. | 01-SEP-00:10 |
| October | 0. | 0. | 01-OCT-00:10 |
| November | 680. | 23555. | 28-NOV-07:05 |
| December | 2409. | 32086. | 20-DEC-07:05 |
| Annual Sum or Average | 688. | ||
| Minimum of Months | 0. | 0. | |
| Maximum of Months | 3174. | 39557. |
Report: HEATING PART LOAD PERFORMANCE
For: VAV_2_HEATC
Timestamp: 2018-02-13 16:27:46
Custom Monthly Report| HEATING COIL GAS RATE [W] | HEATING COIL GAS RATE {Maximum}[W] | HEATING COIL GAS RATE {TIMESTAMP} | |
| January | 5462. | 44046. | 07-JAN-07:10 |
| February | 3960. | 44371. | 06-FEB-07:05 |
| March | 446. | 16966. | 18-MAR-06:10 |
| April | 155. | 11341. | 05-APR-06:05 |
| May | 0. | 0. | 01-MAY-00:10 |
| June | 0. | 0. | 01-JUN-00:10 |
| July | 0. | 0. | 01-JUL-00:10 |
| August | 0. | 0. | 01-AUG-00:10 |
| September | 0. | 0. | 01-SEP-00:10 |
| October | 2. | 1744. | 17-OCT-06:03 |
| November | 1365. | 28365. | 28-NOV-07:05 |
| December | 4618. | 36886. | 20-DEC-07:05 |
| Annual Sum or Average | 1323. | ||
| Minimum of Months | 0. | 0. | |
| Maximum of Months | 5462. | 44371. |
Report: HEATING PART LOAD PERFORMANCE
For: VAV_3_HEATC
Timestamp: 2018-02-13 16:27:46
Custom Monthly Report| HEATING COIL GAS RATE [W] | HEATING COIL GAS RATE {Maximum}[W] | HEATING COIL GAS RATE {TIMESTAMP} | |
| January | 7298. | 51896. | 07-JAN-07:10 |
| February | 5450. | 51383. | 06-FEB-07:05 |
| March | 927. | 22915. | 18-MAR-06:10 |
| April | 342. | 16116. | 05-APR-06:05 |
| May | 0. | 0. | 01-MAY-00:10 |
| June | 0. | 0. | 01-JUN-00:10 |
| July | 0. | 0. | 01-JUL-00:10 |
| August | 0. | 0. | 01-AUG-00:10 |
| September | 0. | 0. | 01-SEP-00:10 |
| October | 19. | 5604. | 17-OCT-06:03 |
| November | 1996. | 34033. | 28-NOV-07:05 |
| December | 6093. | 44084. | 20-DEC-07:05 |
| Annual Sum or Average | 1828. | ||
| Minimum of Months | 0. | 0. | |
| Maximum of Months | 7298. | 51896. |
Report: ZONE AIR RELATIVE HUMIDITY [%]
For: CORE_BOTTOM
Timestamp: 2018-02-13 16:27:46
Values in table are in hours.| - [hr] | 1 [hr] | 2 [hr] | 3 [hr] | 4 [hr] | - [hr] | - [hr] | |
| Interval Start | less than | 60.<= | 70.<= | 80.<= | 90.<= | equal to or more than | Row |
| Interval End | 60. | 70.> | 80.> | 90.> | 100.> | 100. | Total |
| January | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| February | 672.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 672.00 |
| March | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| April | 720.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| May | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| June | 720.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| July | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| August | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| September | 720.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| October | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| November | 720.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| December | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| 12:01 to 1:00 am | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 am | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 am | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 am | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 am | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 am | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 am | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 am | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 am | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 am | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 am | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 pm | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 12:01 to 1:00 pm | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 pm | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 pm | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 pm | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 pm | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 pm | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 pm | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 pm | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 pm | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 pm | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 pm | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 am | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| Total | 8760.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 8760.00 |
| Statistic | |
| Minimum | 3.00 |
| Mean minus two standard deviations | 4.75 |
| Mean | 30.78 |
| Mean plus two standard deviations | 56.81 |
| Maximum | 57.00 |
| Standard deviation | 13.01 |
Report: ZONE AIR RELATIVE HUMIDITY [%]
For: CORE_MID
Timestamp: 2018-02-13 16:27:46
Values in table are in hours.| - [hr] | 1 [hr] | 2 [hr] | 3 [hr] | 4 [hr] | - [hr] | - [hr] | |
| Interval Start | less than | 60.<= | 70.<= | 80.<= | 90.<= | equal to or more than | Row |
| Interval End | 60. | 70.> | 80.> | 90.> | 100.> | 100. | Total |
| January | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| February | 672.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 672.00 |
| March | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| April | 720.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| May | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| June | 720.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| July | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| August | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| September | 720.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| October | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| November | 720.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| December | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| 12:01 to 1:00 am | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 am | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 am | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 am | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 am | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 am | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 am | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 am | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 am | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 am | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 am | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 pm | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 12:01 to 1:00 pm | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 pm | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 pm | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 pm | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 pm | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 pm | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 pm | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 pm | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 pm | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 pm | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 pm | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 am | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| Total | 8760.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 8760.00 |
| Statistic | |
| Minimum | 4.00 |
| Mean minus two standard deviations | 6.35 |
| Mean | 31.38 |
| Mean plus two standard deviations | 56.41 |
| Maximum | 56.00 |
| Standard deviation | 12.52 |
Report: ZONE AIR RELATIVE HUMIDITY [%]
For: CORE_TOP
Timestamp: 2018-02-13 16:27:46
Values in table are in hours.| - [hr] | 1 [hr] | 2 [hr] | 3 [hr] | 4 [hr] | - [hr] | - [hr] | |
| Interval Start | less than | 60.<= | 70.<= | 80.<= | 90.<= | equal to or more than | Row |
| Interval End | 60. | 70.> | 80.> | 90.> | 100.> | 100. | Total |
| January | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| February | 672.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 672.00 |
| March | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| April | 713.00 | 7.00 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| May | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| June | 720.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| July | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| August | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| September | 720.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| October | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| November | 720.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| December | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| 12:01 to 1:00 am | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 am | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 am | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 am | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 am | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 am | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 am | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 am | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 am | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 am | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 am | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 pm | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 12:01 to 1:00 pm | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 pm | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 pm | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 pm | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 pm | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 pm | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 pm | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 pm | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 pm | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 pm | 365.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 am | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| Total | 8753.00 | 7.00 | 0.00 | 0.00 | 0.00 | 0.00 | 8760.00 |
| Statistic | |
| Minimum | 3.00 |
| Mean minus two standard deviations | 6.11 |
| Mean | 32.22 |
| Mean plus two standard deviations | 58.32 |
| Maximum | 62.00 |
| Standard deviation | 13.05 |
Report: ZONE AIR RELATIVE HUMIDITY [%]
For: FIRSTFLOOR_PLENUM
Timestamp: 2018-02-13 16:27:46
Values in table are in hours.| - [hr] | 1 [hr] | 2 [hr] | 3 [hr] | 4 [hr] | - [hr] | - [hr] | |
| Interval Start | less than | 60.<= | 70.<= | 80.<= | 90.<= | equal to or more than | Row |
| Interval End | 60. | 70.> | 80.> | 90.> | 100.> | 100. | Total |
| January | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| February | 672.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 672.00 |
| March | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| April | 720.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| May | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| June | 718.33 | 1.67 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| July | 706.66 | 29.54 | 7.80 | 0.00 | 0.00 | 0.00 | 744.00 |
| August | 721.29 | 22.71 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| September | 688.67 | 31.33 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| October | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| November | 720.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| December | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| 12:01 to 1:00 am | 360.67 | 4.33 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 am | 358.44 | 6.56 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 am | 354.67 | 10.33 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 am | 350.43 | 12.73 | 1.83 | 0.00 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 am | 345.77 | 17.23 | 2.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 am | 358.78 | 4.92 | 1.30 | 0.00 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 am | 361.00 | 3.00 | 1.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 am | 361.56 | 2.44 | 1.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 am | 362.67 | 1.67 | 0.67 | 0.00 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 am | 363.47 | 1.53 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 am | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 12:01 to 1:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 pm | 363.17 | 1.83 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 pm | 361.33 | 3.67 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 am | 361.00 | 4.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| Total | 8666.95 | 85.25 | 7.80 | 0.00 | 0.00 | 0.00 | 8760.00 |
| Statistic | |
| Minimum | 3.00 |
| Mean minus two standard deviations | 2.50 |
| Mean | 30.14 |
| Mean plus two standard deviations | 57.78 |
| Maximum | 72.00 |
| Standard deviation | 13.82 |
Report: ZONE AIR RELATIVE HUMIDITY [%]
For: MIDFLOOR_PLENUM
Timestamp: 2018-02-13 16:27:46
Values in table are in hours.| - [hr] | 1 [hr] | 2 [hr] | 3 [hr] | 4 [hr] | - [hr] | - [hr] | |
| Interval Start | less than | 60.<= | 70.<= | 80.<= | 90.<= | equal to or more than | Row |
| Interval End | 60. | 70.> | 80.> | 90.> | 100.> | 100. | Total |
| January | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| February | 672.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 672.00 |
| March | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| April | 720.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| May | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| June | 719.67 | 0.33 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| July | 716.98 | 26.38 | 0.63 | 0.00 | 0.00 | 0.00 | 744.00 |
| August | 725.95 | 18.05 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| September | 690.33 | 29.67 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| October | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| November | 720.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| December | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| 12:01 to 1:00 am | 361.00 | 4.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 am | 359.50 | 5.50 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 am | 358.50 | 6.50 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 am | 354.92 | 10.08 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 am | 350.30 | 14.20 | 0.50 | 0.00 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 am | 360.13 | 4.73 | 0.13 | 0.00 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 am | 361.00 | 4.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 am | 361.56 | 3.44 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 am | 362.63 | 2.38 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 am | 363.57 | 1.43 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 am | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 12:01 to 1:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 pm | 363.50 | 1.50 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 pm | 363.00 | 2.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 am | 361.33 | 3.67 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| Total | 8684.93 | 74.44 | 0.63 | 0.00 | 0.00 | 0.00 | 8760.00 |
| Statistic | |
| Minimum | 3.00 |
| Mean minus two standard deviations | 3.61 |
| Mean | 30.47 |
| Mean plus two standard deviations | 57.33 |
| Maximum | 70.00 |
| Standard deviation | 13.43 |
Report: ZONE AIR RELATIVE HUMIDITY [%]
For: PERIMETER_BOT_ZN_1
Timestamp: 2018-02-13 16:27:46
Values in table are in hours.| - [hr] | 1 [hr] | 2 [hr] | 3 [hr] | 4 [hr] | - [hr] | - [hr] | |
| Interval Start | less than | 60.<= | 70.<= | 80.<= | 90.<= | equal to or more than | Row |
| Interval End | 60. | 70.> | 80.> | 90.> | 100.> | 100. | Total |
| January | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| February | 672.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 672.00 |
| March | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| April | 719.43 | 0.57 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| May | 734.77 | 9.23 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| June | 703.57 | 15.88 | 0.56 | 0.00 | 0.00 | 0.00 | 720.00 |
| July | 622.17 | 91.24 | 30.46 | 0.13 | 0.00 | 0.00 | 744.00 |
| August | 678.08 | 53.80 | 12.12 | 0.00 | 0.00 | 0.00 | 744.00 |
| September | 669.32 | 49.96 | 0.72 | 0.00 | 0.00 | 0.00 | 720.00 |
| October | 743.97 | 0.03 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| November | 719.07 | 0.93 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| December | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| 12:01 to 1:00 am | 339.67 | 23.33 | 2.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 am | 331.17 | 30.83 | 3.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 am | 327.17 | 32.08 | 5.75 | 0.00 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 am | 325.50 | 29.00 | 10.50 | 0.00 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 am | 324.92 | 29.58 | 10.50 | 0.00 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 am | 337.06 | 22.30 | 5.51 | 0.13 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 am | 359.02 | 4.98 | 1.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 am | 361.30 | 2.57 | 1.13 | 0.00 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 am | 361.77 | 2.93 | 0.30 | 0.00 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 am | 363.40 | 1.60 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 am | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 12:01 to 1:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 pm | 364.50 | 0.50 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 pm | 364.17 | 0.83 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 pm | 361.67 | 3.33 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 pm | 360.17 | 4.83 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 pm | 358.67 | 5.50 | 0.83 | 0.00 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 pm | 357.07 | 6.60 | 1.33 | 0.00 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 am | 349.17 | 13.83 | 2.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| Total | 8494.37 | 221.64 | 43.86 | 0.13 | 0.00 | 0.00 | 8760.00 |
| Statistic | |
| Minimum | 3.00 |
| Mean minus two standard deviations | 0.75 |
| Mean | 32.13 |
| Mean plus two standard deviations | 63.50 |
| Maximum | 81.00 |
| Standard deviation | 15.69 |
Report: ZONE AIR RELATIVE HUMIDITY [%]
For: PERIMETER_BOT_ZN_2
Timestamp: 2018-02-13 16:27:46
Values in table are in hours.| - [hr] | 1 [hr] | 2 [hr] | 3 [hr] | 4 [hr] | - [hr] | - [hr] | |
| Interval Start | less than | 60.<= | 70.<= | 80.<= | 90.<= | equal to or more than | Row |
| Interval End | 60. | 70.> | 80.> | 90.> | 100.> | 100. | Total |
| January | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| February | 672.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 672.00 |
| March | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| April | 718.83 | 1.17 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| May | 736.17 | 7.83 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| June | 702.43 | 16.08 | 1.49 | 0.00 | 0.00 | 0.00 | 720.00 |
| July | 613.23 | 97.78 | 32.99 | 0.00 | 0.00 | 0.00 | 744.00 |
| August | 667.00 | 57.46 | 19.54 | 0.00 | 0.00 | 0.00 | 744.00 |
| September | 663.29 | 51.02 | 5.69 | 0.00 | 0.00 | 0.00 | 720.00 |
| October | 743.90 | 0.10 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| November | 718.70 | 1.30 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| December | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| 12:01 to 1:00 am | 333.33 | 29.33 | 2.33 | 0.00 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 am | 326.17 | 32.47 | 6.37 | 0.00 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 am | 323.83 | 29.67 | 11.50 | 0.00 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 am | 323.17 | 29.67 | 12.17 | 0.00 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 am | 323.17 | 28.50 | 13.33 | 0.00 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 am | 336.46 | 21.13 | 7.41 | 0.00 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 am | 360.57 | 3.43 | 1.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 am | 361.61 | 2.56 | 0.83 | 0.00 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 am | 362.54 | 2.36 | 0.10 | 0.00 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 am | 362.43 | 2.57 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 am | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 12:01 to 1:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 pm | 363.67 | 1.33 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 pm | 360.83 | 4.17 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 pm | 359.33 | 5.67 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 pm | 358.67 | 5.33 | 1.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 pm | 355.67 | 7.67 | 1.67 | 0.00 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 am | 344.11 | 18.89 | 2.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| Total | 8467.56 | 232.73 | 59.71 | 0.00 | 0.00 | 0.00 | 8760.00 |
| Statistic | |
| Minimum | 3.00 |
| Mean minus two standard deviations | 1.35 |
| Mean | 32.80 |
| Mean plus two standard deviations | 64.25 |
| Maximum | 79.00 |
| Standard deviation | 15.72 |
Report: ZONE AIR RELATIVE HUMIDITY [%]
For: PERIMETER_BOT_ZN_3
Timestamp: 2018-02-13 16:27:46
Values in table are in hours.| - [hr] | 1 [hr] | 2 [hr] | 3 [hr] | 4 [hr] | - [hr] | - [hr] | |
| Interval Start | less than | 60.<= | 70.<= | 80.<= | 90.<= | equal to or more than | Row |
| Interval End | 60. | 70.> | 80.> | 90.> | 100.> | 100. | Total |
| January | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| February | 672.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 672.00 |
| March | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| April | 718.52 | 1.48 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| May | 733.54 | 10.46 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| June | 704.31 | 15.52 | 0.17 | 0.00 | 0.00 | 0.00 | 720.00 |
| July | 620.86 | 91.54 | 31.60 | 0.00 | 0.00 | 0.00 | 744.00 |
| August | 674.83 | 52.54 | 16.62 | 0.00 | 0.00 | 0.00 | 744.00 |
| September | 667.86 | 51.92 | 0.22 | 0.00 | 0.00 | 0.00 | 720.00 |
| October | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| November | 719.64 | 0.36 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| December | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| 12:01 to 1:00 am | 337.17 | 25.50 | 2.33 | 0.00 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 am | 328.83 | 31.61 | 4.56 | 0.00 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 am | 327.33 | 30.37 | 7.30 | 0.00 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 am | 326.00 | 28.50 | 10.50 | 0.00 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 am | 325.33 | 29.17 | 10.50 | 0.00 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 am | 337.83 | 21.34 | 5.82 | 0.00 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 am | 358.79 | 4.37 | 1.83 | 0.00 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 am | 361.17 | 2.73 | 1.10 | 0.00 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 am | 362.18 | 2.65 | 0.17 | 0.00 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 am | 363.28 | 1.72 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 am | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 12:01 to 1:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 pm | 361.67 | 3.33 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 pm | 359.17 | 5.83 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 pm | 358.00 | 6.17 | 0.83 | 0.00 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 pm | 356.20 | 7.13 | 1.67 | 0.00 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 am | 348.61 | 14.39 | 2.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| Total | 8487.57 | 223.82 | 48.61 | 0.00 | 0.00 | 0.00 | 8760.00 |
| Statistic | |
| Minimum | 3.00 |
| Mean minus two standard deviations | 2.31 |
| Mean | 33.00 |
| Mean plus two standard deviations | 63.69 |
| Maximum | 79.00 |
| Standard deviation | 15.34 |
Report: ZONE AIR RELATIVE HUMIDITY [%]
For: PERIMETER_BOT_ZN_4
Timestamp: 2018-02-13 16:27:46
Values in table are in hours.| - [hr] | 1 [hr] | 2 [hr] | 3 [hr] | 4 [hr] | - [hr] | - [hr] | |
| Interval Start | less than | 60.<= | 70.<= | 80.<= | 90.<= | equal to or more than | Row |
| Interval End | 60. | 70.> | 80.> | 90.> | 100.> | 100. | Total |
| January | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| February | 672.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 672.00 |
| March | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| April | 719.22 | 0.78 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| May | 733.79 | 10.21 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| June | 703.20 | 15.98 | 0.82 | 0.00 | 0.00 | 0.00 | 720.00 |
| July | 620.07 | 93.25 | 30.58 | 0.10 | 0.00 | 0.00 | 744.00 |
| August | 673.08 | 53.76 | 17.16 | 0.00 | 0.00 | 0.00 | 744.00 |
| September | 664.54 | 50.43 | 5.02 | 0.00 | 0.00 | 0.00 | 720.00 |
| October | 743.90 | 0.10 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| November | 718.87 | 1.13 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| December | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| 12:01 to 1:00 am | 338.67 | 24.33 | 2.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 am | 329.50 | 32.08 | 3.42 | 0.00 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 am | 324.33 | 32.33 | 8.33 | 0.00 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 am | 324.00 | 29.00 | 12.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 am | 323.92 | 29.08 | 12.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 am | 334.60 | 22.36 | 7.94 | 0.10 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 am | 358.69 | 4.14 | 2.17 | 0.00 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 am | 361.01 | 2.77 | 1.22 | 0.00 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 am | 362.32 | 2.52 | 0.17 | 0.00 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 am | 362.46 | 2.54 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 am | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 12:01 to 1:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 pm | 361.33 | 3.67 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 pm | 359.83 | 5.17 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 pm | 358.17 | 6.00 | 0.83 | 0.00 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 pm | 357.17 | 6.33 | 1.50 | 0.00 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 am | 348.68 | 14.32 | 2.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| Total | 8480.67 | 225.65 | 53.58 | 0.10 | 0.00 | 0.00 | 8760.00 |
| Statistic | |
| Minimum | 3.00 |
| Mean minus two standard deviations | 1.13 |
| Mean | 32.97 |
| Mean plus two standard deviations | 64.80 |
| Maximum | 82.00 |
| Standard deviation | 15.92 |
Report: ZONE AIR RELATIVE HUMIDITY [%]
For: PERIMETER_MID_ZN_1
Timestamp: 2018-02-13 16:27:46
Values in table are in hours.| - [hr] | 1 [hr] | 2 [hr] | 3 [hr] | 4 [hr] | - [hr] | - [hr] | |
| Interval Start | less than | 60.<= | 70.<= | 80.<= | 90.<= | equal to or more than | Row |
| Interval End | 60. | 70.> | 80.> | 90.> | 100.> | 100. | Total |
| January | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| February | 672.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 672.00 |
| March | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| April | 719.71 | 0.29 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| May | 740.62 | 3.37 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| June | 706.07 | 13.63 | 0.30 | 0.00 | 0.00 | 0.00 | 720.00 |
| July | 645.81 | 77.86 | 20.33 | 0.00 | 0.00 | 0.00 | 744.00 |
| August | 686.80 | 56.34 | 0.87 | 0.00 | 0.00 | 0.00 | 744.00 |
| September | 678.54 | 41.32 | 0.13 | 0.00 | 0.00 | 0.00 | 720.00 |
| October | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| November | 719.75 | 0.25 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| December | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| 12:01 to 1:00 am | 346.83 | 16.17 | 2.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 am | 340.78 | 22.22 | 2.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 am | 333.83 | 28.83 | 2.33 | 0.00 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 am | 330.00 | 32.00 | 3.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 am | 328.92 | 31.92 | 4.16 | 0.00 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 am | 345.32 | 16.45 | 3.23 | 0.00 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 am | 360.03 | 3.97 | 1.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 am | 361.30 | 2.93 | 0.77 | 0.00 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 am | 362.50 | 2.37 | 0.13 | 0.00 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 am | 363.50 | 1.50 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 am | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 12:01 to 1:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 pm | 364.50 | 0.50 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 pm | 363.00 | 2.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 pm | 362.00 | 3.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 pm | 360.00 | 4.50 | 0.50 | 0.00 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 pm | 357.72 | 6.28 | 1.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 am | 353.08 | 10.42 | 1.50 | 0.00 | 0.00 | 0.00 | 365.00 |
| Total | 8545.31 | 193.06 | 21.63 | 0.00 | 0.00 | 0.00 | 8760.00 |
| Statistic | |
| Minimum | 2.00 |
| Mean minus two standard deviations | 1.25 |
| Mean | 31.71 |
| Mean plus two standard deviations | 62.18 |
| Maximum | 79.00 |
| Standard deviation | 15.23 |
Report: ZONE AIR RELATIVE HUMIDITY [%]
For: PERIMETER_MID_ZN_2
Timestamp: 2018-02-13 16:27:46
Values in table are in hours.| - [hr] | 1 [hr] | 2 [hr] | 3 [hr] | 4 [hr] | - [hr] | - [hr] | |
| Interval Start | less than | 60.<= | 70.<= | 80.<= | 90.<= | equal to or more than | Row |
| Interval End | 60. | 70.> | 80.> | 90.> | 100.> | 100. | Total |
| January | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| February | 672.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 672.00 |
| March | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| April | 719.75 | 0.25 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| May | 741.42 | 2.58 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| June | 705.02 | 14.81 | 0.17 | 0.00 | 0.00 | 0.00 | 720.00 |
| July | 640.03 | 82.47 | 21.50 | 0.00 | 0.00 | 0.00 | 744.00 |
| August | 682.72 | 55.84 | 5.43 | 0.00 | 0.00 | 0.00 | 744.00 |
| September | 674.16 | 45.67 | 0.17 | 0.00 | 0.00 | 0.00 | 720.00 |
| October | 743.97 | 0.03 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| November | 718.23 | 1.77 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| December | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| 12:01 to 1:00 am | 344.50 | 18.37 | 2.13 | 0.00 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 am | 336.89 | 26.11 | 2.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 am | 330.83 | 31.33 | 2.83 | 0.00 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 am | 328.33 | 30.83 | 5.83 | 0.00 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 am | 328.42 | 30.35 | 6.23 | 0.00 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 am | 346.55 | 15.15 | 3.30 | 0.00 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 am | 360.60 | 3.40 | 1.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 am | 361.61 | 3.06 | 0.33 | 0.00 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 am | 362.00 | 2.90 | 0.10 | 0.00 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 am | 362.53 | 2.47 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 am | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 12:01 to 1:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 pm | 362.50 | 2.50 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 pm | 361.00 | 4.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 pm | 359.33 | 5.00 | 0.67 | 0.00 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 pm | 357.20 | 6.80 | 1.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 am | 351.00 | 12.17 | 1.83 | 0.00 | 0.00 | 0.00 | 365.00 |
| Total | 8529.30 | 203.43 | 27.26 | 0.00 | 0.00 | 0.00 | 8760.00 |
| Statistic | |
| Minimum | 2.00 |
| Mean minus two standard deviations | 1.68 |
| Mean | 32.22 |
| Mean plus two standard deviations | 62.77 |
| Maximum | 77.00 |
| Standard deviation | 15.27 |
Report: ZONE AIR RELATIVE HUMIDITY [%]
For: PERIMETER_MID_ZN_3
Timestamp: 2018-02-13 16:27:46
Values in table are in hours.| - [hr] | 1 [hr] | 2 [hr] | 3 [hr] | 4 [hr] | - [hr] | - [hr] | |
| Interval Start | less than | 60.<= | 70.<= | 80.<= | 90.<= | equal to or more than | Row |
| Interval End | 60. | 70.> | 80.> | 90.> | 100.> | 100. | Total |
| January | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| February | 672.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 672.00 |
| March | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| April | 719.68 | 0.32 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| May | 739.29 | 4.71 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| June | 706.23 | 13.60 | 0.17 | 0.00 | 0.00 | 0.00 | 720.00 |
| July | 641.85 | 80.96 | 21.20 | 0.00 | 0.00 | 0.00 | 744.00 |
| August | 683.54 | 57.63 | 2.83 | 0.00 | 0.00 | 0.00 | 744.00 |
| September | 677.40 | 42.47 | 0.13 | 0.00 | 0.00 | 0.00 | 720.00 |
| October | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| November | 719.97 | 0.03 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| December | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| 12:01 to 1:00 am | 345.50 | 17.50 | 2.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 am | 337.50 | 25.50 | 2.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 am | 332.10 | 30.40 | 2.50 | 0.00 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 am | 329.50 | 31.00 | 4.50 | 0.00 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 am | 329.00 | 30.67 | 5.33 | 0.00 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 am | 346.03 | 15.97 | 3.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 am | 360.53 | 3.47 | 1.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 am | 361.27 | 3.20 | 0.53 | 0.00 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 am | 362.33 | 2.53 | 0.13 | 0.00 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 am | 363.43 | 1.57 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 am | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 12:01 to 1:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 pm | 363.00 | 2.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 pm | 361.50 | 3.50 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 pm | 358.50 | 6.00 | 0.50 | 0.00 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 pm | 357.27 | 6.73 | 1.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 am | 352.50 | 10.67 | 1.83 | 0.00 | 0.00 | 0.00 | 365.00 |
| Total | 8535.96 | 199.71 | 24.33 | 0.00 | 0.00 | 0.00 | 8760.00 |
| Statistic | |
| Minimum | 3.00 |
| Mean minus two standard deviations | 2.38 |
| Mean | 32.46 |
| Mean plus two standard deviations | 62.53 |
| Maximum | 77.00 |
| Standard deviation | 15.04 |
Report: ZONE AIR RELATIVE HUMIDITY [%]
For: PERIMETER_MID_ZN_4
Timestamp: 2018-02-13 16:27:46
Values in table are in hours.| - [hr] | 1 [hr] | 2 [hr] | 3 [hr] | 4 [hr] | - [hr] | - [hr] | |
| Interval Start | less than | 60.<= | 70.<= | 80.<= | 90.<= | equal to or more than | Row |
| Interval End | 60. | 70.> | 80.> | 90.> | 100.> | 100. | Total |
| January | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| February | 672.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 672.00 |
| March | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| April | 719.58 | 0.42 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| May | 739.43 | 4.57 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| June | 705.84 | 13.86 | 0.30 | 0.00 | 0.00 | 0.00 | 720.00 |
| July | 646.99 | 76.67 | 20.30 | 0.03 | 0.00 | 0.00 | 744.00 |
| August | 684.97 | 56.43 | 2.60 | 0.00 | 0.00 | 0.00 | 744.00 |
| September | 676.26 | 43.57 | 0.17 | 0.00 | 0.00 | 0.00 | 720.00 |
| October | 743.97 | 0.03 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| November | 718.07 | 1.93 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| December | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| 12:01 to 1:00 am | 345.33 | 17.53 | 2.13 | 0.00 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 am | 340.33 | 22.67 | 2.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 am | 334.00 | 28.50 | 2.50 | 0.00 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 am | 330.00 | 31.67 | 3.33 | 0.00 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 am | 328.92 | 31.19 | 4.90 | 0.00 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 am | 344.91 | 16.62 | 3.43 | 0.03 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 am | 360.01 | 3.99 | 1.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 am | 361.23 | 3.13 | 0.63 | 0.00 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 am | 361.85 | 2.98 | 0.17 | 0.00 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 am | 362.53 | 2.37 | 0.10 | 0.00 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 am | 363.83 | 1.17 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 12:01 to 1:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 pm | 362.83 | 2.17 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 pm | 361.33 | 3.67 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 pm | 359.33 | 5.17 | 0.50 | 0.00 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 pm | 357.68 | 6.32 | 1.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 am | 352.98 | 10.35 | 1.67 | 0.00 | 0.00 | 0.00 | 365.00 |
| Total | 8539.12 | 197.48 | 23.36 | 0.03 | 0.00 | 0.00 | 8760.00 |
| Statistic | |
| Minimum | 2.00 |
| Mean minus two standard deviations | 1.50 |
| Mean | 32.37 |
| Mean plus two standard deviations | 63.24 |
| Maximum | 80.00 |
| Standard deviation | 15.43 |
Report: ZONE AIR RELATIVE HUMIDITY [%]
For: PERIMETER_TOP_ZN_1
Timestamp: 2018-02-13 16:27:46
Values in table are in hours.| - [hr] | 1 [hr] | 2 [hr] | 3 [hr] | 4 [hr] | - [hr] | - [hr] | |
| Interval Start | less than | 60.<= | 70.<= | 80.<= | 90.<= | equal to or more than | Row |
| Interval End | 60. | 70.> | 80.> | 90.> | 100.> | 100. | Total |
| January | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| February | 672.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 672.00 |
| March | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| April | 719.76 | 0.24 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| May | 740.68 | 3.32 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| June | 706.17 | 13.57 | 0.27 | 0.00 | 0.00 | 0.00 | 720.00 |
| July | 672.38 | 55.92 | 15.70 | 0.00 | 0.00 | 0.00 | 744.00 |
| August | 695.08 | 48.19 | 0.73 | 0.00 | 0.00 | 0.00 | 744.00 |
| September | 678.01 | 41.86 | 0.13 | 0.00 | 0.00 | 0.00 | 720.00 |
| October | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| November | 717.55 | 2.45 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| December | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| 12:01 to 1:00 am | 350.58 | 12.42 | 2.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 am | 346.83 | 16.17 | 2.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 am | 341.12 | 21.88 | 2.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 am | 335.05 | 27.95 | 2.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 am | 335.94 | 26.96 | 2.10 | 0.00 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 am | 348.24 | 14.33 | 2.43 | 0.00 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 am | 359.94 | 4.06 | 1.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 am | 361.33 | 3.23 | 0.43 | 0.00 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 am | 361.77 | 3.10 | 0.13 | 0.00 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 am | 362.63 | 2.30 | 0.07 | 0.00 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 am | 363.67 | 1.33 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 12:01 to 1:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 pm | 363.17 | 1.83 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 pm | 361.50 | 3.50 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 pm | 359.67 | 5.00 | 0.33 | 0.00 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 pm | 357.70 | 6.30 | 1.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 am | 356.50 | 7.17 | 1.33 | 0.00 | 0.00 | 0.00 | 365.00 |
| Total | 8577.63 | 165.54 | 16.83 | 0.00 | 0.00 | 0.00 | 8760.00 |
| Statistic | |
| Minimum | 3.00 |
| Mean minus two standard deviations | 2.36 |
| Mean | 32.38 |
| Mean plus two standard deviations | 62.41 |
| Maximum | 79.00 |
| Standard deviation | 15.01 |
Report: ZONE AIR RELATIVE HUMIDITY [%]
For: PERIMETER_TOP_ZN_2
Timestamp: 2018-02-13 16:27:46
Values in table are in hours.| - [hr] | 1 [hr] | 2 [hr] | 3 [hr] | 4 [hr] | - [hr] | - [hr] | |
| Interval Start | less than | 60.<= | 70.<= | 80.<= | 90.<= | equal to or more than | Row |
| Interval End | 60. | 70.> | 80.> | 90.> | 100.> | 100. | Total |
| January | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| February | 672.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 672.00 |
| March | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| April | 719.76 | 0.24 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| May | 741.75 | 2.25 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| June | 705.26 | 14.58 | 0.17 | 0.00 | 0.00 | 0.00 | 720.00 |
| July | 664.23 | 63.67 | 16.10 | 0.00 | 0.00 | 0.00 | 744.00 |
| August | 689.76 | 50.17 | 4.07 | 0.00 | 0.00 | 0.00 | 744.00 |
| September | 672.59 | 47.24 | 0.17 | 0.00 | 0.00 | 0.00 | 720.00 |
| October | 743.93 | 0.07 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| November | 717.57 | 2.43 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| December | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| 12:01 to 1:00 am | 348.85 | 14.15 | 2.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 am | 343.50 | 19.50 | 2.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 am | 335.20 | 27.80 | 2.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 am | 331.65 | 30.35 | 3.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 am | 334.54 | 25.79 | 4.67 | 0.00 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 am | 348.68 | 13.98 | 2.33 | 0.00 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 am | 360.40 | 3.60 | 1.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 am | 361.56 | 3.28 | 0.17 | 0.00 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 am | 362.00 | 2.87 | 0.13 | 0.00 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 am | 362.70 | 2.27 | 0.03 | 0.00 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 am | 363.83 | 1.17 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 12:01 to 1:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 pm | 363.83 | 1.17 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 pm | 363.83 | 1.17 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 pm | 362.67 | 2.33 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 pm | 360.50 | 4.50 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 pm | 359.00 | 5.50 | 0.50 | 0.00 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 pm | 357.27 | 6.73 | 1.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 am | 354.83 | 8.50 | 1.67 | 0.00 | 0.00 | 0.00 | 365.00 |
| Total | 8558.84 | 180.66 | 20.50 | 0.00 | 0.00 | 0.00 | 8760.00 |
| Statistic | |
| Minimum | 3.00 |
| Mean minus two standard deviations | 2.63 |
| Mean | 32.84 |
| Mean plus two standard deviations | 63.05 |
| Maximum | 77.00 |
| Standard deviation | 15.11 |
Report: ZONE AIR RELATIVE HUMIDITY [%]
For: PERIMETER_TOP_ZN_3
Timestamp: 2018-02-13 16:27:46
Values in table are in hours.| - [hr] | 1 [hr] | 2 [hr] | 3 [hr] | 4 [hr] | - [hr] | - [hr] | |
| Interval Start | less than | 60.<= | 70.<= | 80.<= | 90.<= | equal to or more than | Row |
| Interval End | 60. | 70.> | 80.> | 90.> | 100.> | 100. | Total |
| January | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| February | 672.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 672.00 |
| March | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| April | 719.68 | 0.32 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| May | 739.06 | 4.94 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| June | 706.49 | 13.34 | 0.17 | 0.00 | 0.00 | 0.00 | 720.00 |
| July | 666.30 | 61.86 | 15.83 | 0.00 | 0.00 | 0.00 | 744.00 |
| August | 689.56 | 52.24 | 2.20 | 0.00 | 0.00 | 0.00 | 744.00 |
| September | 677.34 | 42.52 | 0.13 | 0.00 | 0.00 | 0.00 | 720.00 |
| October | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| November | 719.16 | 0.84 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| December | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| 12:01 to 1:00 am | 350.17 | 12.83 | 2.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 am | 343.80 | 19.20 | 2.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 am | 336.00 | 27.00 | 2.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 am | 332.83 | 29.67 | 2.50 | 0.00 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 am | 335.44 | 26.53 | 3.03 | 0.00 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 am | 349.26 | 13.47 | 2.27 | 0.00 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 am | 359.94 | 4.06 | 1.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 am | 361.20 | 3.40 | 0.40 | 0.00 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 am | 362.02 | 2.85 | 0.13 | 0.00 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 am | 363.60 | 1.40 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 am | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 12:01 to 1:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 pm | 363.00 | 2.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 pm | 360.83 | 4.17 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 pm | 358.50 | 6.17 | 0.33 | 0.00 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 pm | 357.17 | 6.83 | 1.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 am | 355.83 | 7.50 | 1.67 | 0.00 | 0.00 | 0.00 | 365.00 |
| Total | 8565.59 | 176.07 | 18.33 | 0.00 | 0.00 | 0.00 | 8760.00 |
| Statistic | |
| Minimum | 3.00 |
| Mean minus two standard deviations | 3.31 |
| Mean | 33.15 |
| Mean plus two standard deviations | 62.98 |
| Maximum | 77.00 |
| Standard deviation | 14.92 |
Report: ZONE AIR RELATIVE HUMIDITY [%]
For: PERIMETER_TOP_ZN_4
Timestamp: 2018-02-13 16:27:46
Values in table are in hours.| - [hr] | 1 [hr] | 2 [hr] | 3 [hr] | 4 [hr] | - [hr] | - [hr] | |
| Interval Start | less than | 60.<= | 70.<= | 80.<= | 90.<= | equal to or more than | Row |
| Interval End | 60. | 70.> | 80.> | 90.> | 100.> | 100. | Total |
| January | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| February | 672.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 672.00 |
| March | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| April | 719.59 | 0.41 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| May | 739.39 | 4.61 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| June | 705.78 | 13.92 | 0.30 | 0.00 | 0.00 | 0.00 | 720.00 |
| July | 673.86 | 54.11 | 15.97 | 0.07 | 0.00 | 0.00 | 744.00 |
| August | 694.81 | 46.90 | 2.29 | 0.00 | 0.00 | 0.00 | 744.00 |
| September | 675.26 | 44.58 | 0.17 | 0.00 | 0.00 | 0.00 | 720.00 |
| October | 743.90 | 0.10 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| November | 717.73 | 2.27 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| December | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| 12:01 to 1:00 am | 349.05 | 13.95 | 2.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 am | 346.08 | 16.92 | 2.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 am | 341.28 | 21.72 | 2.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 am | 335.93 | 26.73 | 2.33 | 0.00 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 am | 337.29 | 24.41 | 3.30 | 0.00 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 am | 346.76 | 15.71 | 2.47 | 0.07 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 am | 359.98 | 4.02 | 1.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 am | 361.27 | 3.21 | 0.52 | 0.00 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 am | 361.78 | 3.05 | 0.17 | 0.00 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 am | 362.61 | 2.29 | 0.10 | 0.00 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 am | 363.83 | 1.17 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 12:01 to 1:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 pm | 363.83 | 1.17 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 pm | 363.00 | 2.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 pm | 361.00 | 4.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 pm | 359.00 | 5.67 | 0.33 | 0.00 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 pm | 357.37 | 6.63 | 1.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 am | 356.25 | 7.25 | 1.50 | 0.00 | 0.00 | 0.00 | 365.00 |
| Total | 8574.32 | 166.89 | 18.72 | 0.07 | 0.00 | 0.00 | 8760.00 |
| Statistic | |
| Minimum | 3.00 |
| Mean minus two standard deviations | 2.43 |
| Mean | 32.98 |
| Mean plus two standard deviations | 63.53 |
| Maximum | 80.00 |
| Standard deviation | 15.28 |
Report: ZONE AIR RELATIVE HUMIDITY [%]
For: TOPFLOOR_PLENUM
Timestamp: 2018-02-13 16:27:46
Values in table are in hours.| - [hr] | 1 [hr] | 2 [hr] | 3 [hr] | 4 [hr] | - [hr] | - [hr] | |
| Interval Start | less than | 60.<= | 70.<= | 80.<= | 90.<= | equal to or more than | Row |
| Interval End | 60. | 70.> | 80.> | 90.> | 100.> | 100. | Total |
| January | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| February | 672.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 672.00 |
| March | 742.17 | 1.83 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| April | 712.28 | 7.72 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| May | 723.73 | 20.27 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| June | 693.78 | 11.56 | 14.67 | 0.00 | 0.00 | 0.00 | 720.00 |
| July | 561.95 | 122.69 | 49.36 | 10.00 | 0.00 | 0.00 | 744.00 |
| August | 624.26 | 64.57 | 55.17 | 0.00 | 0.00 | 0.00 | 744.00 |
| September | 637.54 | 55.62 | 26.83 | 0.00 | 0.00 | 0.00 | 720.00 |
| October | 740.67 | 3.33 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| November | 686.36 | 33.64 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| December | 744.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 744.00 |
| 12:01 to 1:00 am | 315.14 | 31.18 | 16.68 | 2.00 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 am | 311.27 | 34.70 | 17.37 | 1.67 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 am | 306.50 | 38.60 | 19.57 | 0.33 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 am | 304.77 | 42.37 | 17.03 | 0.83 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 am | 306.53 | 42.59 | 15.38 | 0.50 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 am | 349.80 | 10.94 | 4.27 | 0.00 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 am | 357.86 | 3.14 | 4.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 am | 358.50 | 3.23 | 3.27 | 0.00 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 am | 360.07 | 3.00 | 1.93 | 0.00 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 am | 363.53 | 0.47 | 1.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 am | 364.00 | 0.00 | 1.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 pm | 364.00 | 0.00 | 1.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 12:01 to 1:00 pm | 364.00 | 0.33 | 0.67 | 0.00 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 pm | 364.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 pm | 363.50 | 1.50 | 0.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 pm | 363.80 | 0.70 | 0.50 | 0.00 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 pm | 363.17 | 0.83 | 1.00 | 0.00 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 pm | 360.33 | 3.51 | 1.17 | 0.00 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 pm | 357.44 | 4.39 | 3.17 | 0.00 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 pm | 355.92 | 4.25 | 4.83 | 0.00 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 pm | 354.44 | 5.56 | 4.50 | 0.50 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 pm | 341.32 | 17.85 | 4.83 | 1.00 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 pm | 317.26 | 35.61 | 10.97 | 1.17 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 am | 315.61 | 35.49 | 11.90 | 2.00 | 0.00 | 0.00 | 365.00 |
| Total | 8282.74 | 321.23 | 146.03 | 10.00 | 0.00 | 0.00 | 8760.00 |
| Statistic | |
| Minimum | 4.00 |
| Mean minus two standard deviations | 5.35 |
| Mean | 34.90 |
| Mean plus two standard deviations | 64.46 |
| Maximum | 86.00 |
| Standard deviation | 14.78 |
Report: AVAILABILITY MANAGER NIGHT CYCLE CONTROL STATUS []
For: VAV_1 AVAILABILITY MANAGER
Timestamp: 2018-02-13 16:27:46
Values in table are in hours.| - [hr] | 1 [hr] | 2 [hr] | 3 [hr] | 4 [hr] | - [hr] | - [hr] | |
| Interval Start | less than | 0.00<= | 1.00<= | 2.00<= | 3.00<= | equal to or more than | Row |
| Interval End | 0.00 | 1.00> | 2.00> | 3.00> | 4.00> | 4.00 | Total |
| January | 0.00 | 698.58 | 0.00 | 45.42 | 0.00 | 0.00 | 744.00 |
| February | 0.00 | 663.00 | 0.00 | 9.00 | 0.00 | 0.00 | 672.00 |
| March | 0.00 | 733.86 | 0.00 | 10.14 | 0.00 | 0.00 | 744.00 |
| April | 0.00 | 704.49 | 0.00 | 15.51 | 0.00 | 0.00 | 720.00 |
| May | 0.00 | 715.02 | 0.00 | 28.98 | 0.00 | 0.00 | 744.00 |
| June | 0.00 | 689.77 | 0.00 | 30.23 | 0.00 | 0.00 | 720.00 |
| July | 0.00 | 691.47 | 0.00 | 52.53 | 0.00 | 0.00 | 744.00 |
| August | 0.00 | 716.81 | 0.00 | 27.19 | 0.00 | 0.00 | 744.00 |
| September | 0.00 | 692.06 | 0.00 | 27.94 | 0.00 | 0.00 | 720.00 |
| October | 0.00 | 726.71 | 0.00 | 17.29 | 0.00 | 0.00 | 744.00 |
| November | 0.00 | 716.41 | 0.00 | 3.59 | 0.00 | 0.00 | 720.00 |
| December | 0.00 | 737.22 | 0.00 | 6.78 | 0.00 | 0.00 | 744.00 |
| 12:01 to 1:00 am | 0.00 | 360.20 | 0.00 | 4.80 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 am | 0.00 | 359.67 | 0.00 | 5.33 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 am | 0.00 | 359.83 | 0.00 | 5.17 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 am | 0.00 | 359.67 | 0.00 | 5.33 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 am | 0.00 | 359.83 | 0.00 | 5.17 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 am | 0.00 | 358.38 | 0.00 | 6.62 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 am | 0.00 | 356.30 | 0.00 | 8.70 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 am | 0.00 | 349.89 | 0.00 | 15.11 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 am | 0.00 | 347.68 | 0.00 | 17.32 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 am | 0.00 | 346.97 | 0.00 | 18.03 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 am | 0.00 | 345.63 | 0.00 | 19.38 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 pm | 0.00 | 344.66 | 0.00 | 20.34 | 0.00 | 0.00 | 365.00 |
| 12:01 to 1:00 pm | 0.00 | 343.07 | 0.00 | 21.93 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 pm | 0.00 | 343.20 | 0.00 | 21.80 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 pm | 0.00 | 343.66 | 0.00 | 21.34 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 pm | 0.00 | 346.63 | 0.00 | 18.37 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 pm | 0.00 | 349.52 | 0.00 | 15.48 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 pm | 0.00 | 348.71 | 0.00 | 16.29 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 pm | 0.00 | 353.90 | 0.00 | 11.10 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 pm | 0.00 | 361.61 | 0.00 | 3.39 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 pm | 0.00 | 362.39 | 0.00 | 2.61 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 pm | 0.00 | 361.43 | 0.00 | 3.57 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 pm | 0.00 | 361.40 | 0.00 | 3.60 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 am | 0.00 | 361.17 | 0.00 | 3.83 | 0.00 | 0.00 | 365.00 |
| Total | 0.00 | 8485.40 | 0.00 | 274.60 | 0.00 | 0.00 | 8760.00 |
| Statistic | |
| Minimum | 0.00 |
| Mean minus two standard deviations | -1.0 |
| Mean | 0.18 |
| Mean plus two standard deviations | 1.31 |
| Maximum | 2.00 |
| Standard deviation | 0.57 |
Report: AVAILABILITY MANAGER NIGHT CYCLE CONTROL STATUS []
For: VAV_2 AVAILABILITY MANAGER
Timestamp: 2018-02-13 16:27:46
Values in table are in hours.| - [hr] | 1 [hr] | 2 [hr] | 3 [hr] | 4 [hr] | - [hr] | - [hr] | |
| Interval Start | less than | 0.00<= | 1.00<= | 2.00<= | 3.00<= | equal to or more than | Row |
| Interval End | 0.00 | 1.00> | 2.00> | 3.00> | 4.00> | 4.00 | Total |
| January | 0.00 | 704.34 | 0.00 | 39.66 | 0.00 | 0.00 | 744.00 |
| February | 0.00 | 666.07 | 0.00 | 5.93 | 0.00 | 0.00 | 672.00 |
| March | 0.00 | 740.32 | 0.00 | 3.68 | 0.00 | 0.00 | 744.00 |
| April | 0.00 | 707.99 | 0.00 | 12.01 | 0.00 | 0.00 | 720.00 |
| May | 0.00 | 717.01 | 0.00 | 26.99 | 0.00 | 0.00 | 744.00 |
| June | 0.00 | 690.63 | 0.00 | 29.37 | 0.00 | 0.00 | 720.00 |
| July | 0.00 | 687.57 | 0.00 | 56.43 | 0.00 | 0.00 | 744.00 |
| August | 0.00 | 715.63 | 0.00 | 28.37 | 0.00 | 0.00 | 744.00 |
| September | 0.00 | 692.32 | 0.00 | 27.68 | 0.00 | 0.00 | 720.00 |
| October | 0.00 | 732.26 | 0.00 | 11.74 | 0.00 | 0.00 | 744.00 |
| November | 0.00 | 720.00 | 0.00 | 0.00 | 0.00 | 0.00 | 720.00 |
| December | 0.00 | 740.67 | 0.00 | 3.33 | 0.00 | 0.00 | 744.00 |
| 12:01 to 1:00 am | 0.00 | 360.50 | 0.00 | 4.50 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 am | 0.00 | 360.87 | 0.00 | 4.13 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 am | 0.00 | 360.30 | 0.00 | 4.70 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 am | 0.00 | 360.70 | 0.00 | 4.30 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 am | 0.00 | 358.15 | 0.00 | 6.85 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 am | 0.00 | 359.15 | 0.00 | 5.85 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 am | 0.00 | 357.31 | 0.00 | 7.69 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 am | 0.00 | 351.26 | 0.00 | 13.74 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 am | 0.00 | 349.63 | 0.00 | 15.37 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 am | 0.00 | 349.14 | 0.00 | 15.86 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 am | 0.00 | 348.27 | 0.00 | 16.73 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 pm | 0.00 | 348.14 | 0.00 | 16.86 | 0.00 | 0.00 | 365.00 |
| 12:01 to 1:00 pm | 0.00 | 345.11 | 0.00 | 19.89 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 pm | 0.00 | 345.67 | 0.00 | 19.33 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 pm | 0.00 | 347.57 | 0.00 | 17.43 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 pm | 0.00 | 348.88 | 0.00 | 16.12 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 pm | 0.00 | 350.51 | 0.00 | 14.49 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 pm | 0.00 | 347.07 | 0.00 | 17.93 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 pm | 0.00 | 354.52 | 0.00 | 10.48 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 pm | 0.00 | 362.92 | 0.00 | 2.08 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 pm | 0.00 | 363.47 | 0.00 | 1.53 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 pm | 0.00 | 363.23 | 0.00 | 1.77 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 pm | 0.00 | 361.30 | 0.00 | 3.70 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 am | 0.00 | 361.17 | 0.00 | 3.83 | 0.00 | 0.00 | 365.00 |
| Total | 0.00 | 8514.81 | 0.00 | 245.19 | 0.00 | 0.00 | 8760.00 |
| Statistic | |
| Minimum | 0.00 |
| Mean minus two standard deviations | -0.9 |
| Mean | 0.16 |
| Mean plus two standard deviations | 1.24 |
| Maximum | 2.00 |
| Standard deviation | 0.54 |
Report: AVAILABILITY MANAGER NIGHT CYCLE CONTROL STATUS []
For: VAV_3 AVAILABILITY MANAGER
Timestamp: 2018-02-13 16:27:46
Values in table are in hours.| - [hr] | 1 [hr] | 2 [hr] | 3 [hr] | 4 [hr] | - [hr] | - [hr] | |
| Interval Start | less than | 0.00<= | 1.00<= | 2.00<= | 3.00<= | equal to or more than | Row |
| Interval End | 0.00 | 1.00> | 2.00> | 3.00> | 4.00> | 4.00 | Total |
| January | 0.00 | 640.25 | 0.00 | 103.75 | 0.00 | 0.00 | 744.00 |
| February | 0.00 | 623.67 | 0.00 | 48.33 | 0.00 | 0.00 | 672.00 |
| March | 0.00 | 736.50 | 0.00 | 7.50 | 0.00 | 0.00 | 744.00 |
| April | 0.00 | 709.87 | 0.00 | 10.13 | 0.00 | 0.00 | 720.00 |
| May | 0.00 | 721.89 | 0.00 | 22.11 | 0.00 | 0.00 | 744.00 |
| June | 0.00 | 689.37 | 0.00 | 30.63 | 0.00 | 0.00 | 720.00 |
| July | 0.00 | 678.48 | 0.00 | 65.52 | 0.00 | 0.00 | 744.00 |
| August | 0.00 | 713.19 | 0.00 | 30.81 | 0.00 | 0.00 | 744.00 |
| September | 0.00 | 695.00 | 0.00 | 25.00 | 0.00 | 0.00 | 720.00 |
| October | 0.00 | 739.00 | 0.00 | 5.00 | 0.00 | 0.00 | 744.00 |
| November | 0.00 | 697.50 | 0.00 | 22.50 | 0.00 | 0.00 | 720.00 |
| December | 0.00 | 666.50 | 0.00 | 77.50 | 0.00 | 0.00 | 744.00 |
| 12:01 to 1:00 am | 0.00 | 349.08 | 0.00 | 15.92 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 am | 0.00 | 350.33 | 0.00 | 14.67 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 am | 0.00 | 344.50 | 0.00 | 20.50 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 am | 0.00 | 342.83 | 0.00 | 22.17 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 am | 0.00 | 334.93 | 0.00 | 30.07 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 am | 0.00 | 338.32 | 0.00 | 26.68 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 am | 0.00 | 350.21 | 0.00 | 14.79 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 am | 0.00 | 346.31 | 0.00 | 18.69 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 am | 0.00 | 343.20 | 0.00 | 21.80 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 am | 0.00 | 344.65 | 0.00 | 20.35 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 am | 0.00 | 344.65 | 0.00 | 20.35 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 pm | 0.00 | 345.02 | 0.00 | 19.98 | 0.00 | 0.00 | 365.00 |
| 12:01 to 1:00 pm | 0.00 | 344.94 | 0.00 | 20.06 | 0.00 | 0.00 | 365.00 |
| 1:01 to 2:00 pm | 0.00 | 344.90 | 0.00 | 20.10 | 0.00 | 0.00 | 365.00 |
| 2:01 to 3:00 pm | 0.00 | 345.90 | 0.00 | 19.10 | 0.00 | 0.00 | 365.00 |
| 3:01 to 4:00 pm | 0.00 | 345.87 | 0.00 | 19.13 | 0.00 | 0.00 | 365.00 |
| 4:01 to 5:00 pm | 0.00 | 345.91 | 0.00 | 19.09 | 0.00 | 0.00 | 365.00 |
| 5:01 to 6:00 pm | 0.00 | 340.26 | 0.00 | 24.74 | 0.00 | 0.00 | 365.00 |
| 6:01 to 7:00 pm | 0.00 | 346.17 | 0.00 | 18.83 | 0.00 | 0.00 | 365.00 |
| 7:01 to 8:00 pm | 0.00 | 353.15 | 0.00 | 11.85 | 0.00 | 0.00 | 365.00 |
| 8:01 to 9:00 pm | 0.00 | 353.72 | 0.00 | 11.28 | 0.00 | 0.00 | 365.00 |
| 9:01 to 10:00 pm | 0.00 | 353.70 | 0.00 | 11.30 | 0.00 | 0.00 | 365.00 |
| 10:01 to 11:00 pm | 0.00 | 350.67 | 0.00 | 14.33 | 0.00 | 0.00 | 365.00 |
| 11:01 to 12:00 am | 0.00 | 352.00 | 0.00 | 13.00 | 0.00 | 0.00 | 365.00 |
| Total | 0.00 | 8311.21 | 0.00 | 448.79 | 0.00 | 0.00 | 8760.00 |
| Statistic | |
| Minimum | 0.00 |
| Mean minus two standard deviations | -1.1 |
| Mean | 0.23 |
| Mean plus two standard deviations | 1.52 |
| Maximum | 2.00 |
| Standard deviation | 0.64 |
Report: AIR SYSTEM OUTDOOR AIR FLOW FRACTION []
For: VAV_1
Timestamp: 2018-02-13 16:27:46
Values in table are in hours.| - [hr] | 1 [hr] | 2 [hr] | 3 [hr] | 4 [hr] | 5 [hr] | - [hr] | - [hr] | |
| Interval Start | less than | 0.0000<= | 0.2000<= | 0.4000<= | 0.6000<= | 0.8000<= | equal to or more than | Row |
| Interval End | 0.0000 | 0.2000> | 0.4000> | 0.6000> | 0.8000> | 1.0000> | 1.0000 | Total |
| January | 0.00 | 358.49 | 36.08 | 324.27 | 16.83 | 8.33 | 0.00 | 744.00 |
| February | 0.00 | 322.00 | 30.88 | 273.29 | 23.67 | 9.50 | 12.67 | 672.00 |
| March | 0.00 | 317.86 | 5.90 | 218.03 | 145.27 | 23.08 | 33.86 | 744.00 |
| April | 0.00 | 331.54 | 23.17 | 103.58 | 112.00 | 46.31 | 103.40 | 720.00 |
| May | 0.00 | 328.08 | 31.67 | 10.50 | 22.51 | 61.01 | 290.24 | 744.00 |
| June | 0.00 | 306.10 | 116.83 | 34.33 | 0.00 | 6.00 | 256.73 | 720.00 |
| July | 0.00 | 350.66 | 173.83 | 53.83 | 0.00 | 0.00 | 165.68 | 744.00 |
| August | 0.00 | 321.90 | 106.50 | 36.25 | 0.00 | 1.00 | 278.35 | 744.00 |