Morphological properties of HSCs inside their niche is not well studied. This project aimed to quantify various measurements of HSC morphology using 4d cell data from in vivo microscope images.
The first measure of morphology to be considered was the aspect ratio, which is a measure of how elongated a shape is. For regular shapes, aspect ratio is the longest axis divided by the shortest axis. Thus a larger value indicates a more elongated shape, while values close to one indicate a more round or square shape. It was hypothesised that the HSCs should get more elongated when they move faster, and the following analysis tests this hypothesis.
To obtain the aspect ratio of the cell, we first calculated its minimum volume bounding ellipsoid (MVBE). This is the ellipsoid that contains all points in the cell while having the least wasted volume [8]. See the simulation to the right for a visualization of this concept. The MVBE provides a convenient way to quantify the "axes" of a cell: these are just the major and minor axes of the ellipsoid which is fitted and thus the aspect ratio of the cell is the longest of these axes divided by the shorter. The speed of the cell was calculated by considering the difference in position of the center of mass of the cell at each time step and dividing by the length of the time step.
The graphs to the left show the results of plotting the aspect ratio against the speed for cells in two different microscopy sessions (labelled Sort 5 and Sort 6). Both show what seems to be a random distribution of points. There does not seem to be any correlation betweent the aspect ratio of these cells and the speed at which they move. This is surprising as we had assumed elongation at speed to be a fairly safe assumption.
The randomness of the analysis above is thought to have arisen from a lack of resolution in the z dimension of the microscopy data. Each pixel in the images represents ~0.5 microns in the x and y dimensions, but ~5 microns in the z dimension. This can be seen when plotting the detected points in 3d space as in the diagram below; there are large gaps between the "slices" in the z-axis. To test this idea, we tried considering only the aspect ratio in the x-y plane.
To get the aspect ratio in 2d, we projected the points of the cell onto the x-y plane and then calculated the MVBE (which is just an ellipse in 2d). The aspect ratio is then the major axis divided by the minor axis. The speed was calculated by finding the difference in centroid coordinates at adjacent timesteps and dividing by the length of the timestep.
The graphs to the left show the relationship between the 2d aspect ratio and speed for the cells in Sort 5 and Sort 6. Once again, there does not seem to be any correlation. These cells do not show any trend between their elongation and the speed at which they move.
After the inconclusive results of the preceding attempts at considering aspect ratio, we decided to try a more exploratory approach. Instead of speed, we plotted the aspect ratio against time to see if there were any patterns that could be discened.
The graphs to the left show the results of this attempt. In both 2d and 3d, using both ways of calculating aspect ratio, there did not seem to be any significant patterns. Finally, this line of enquiry was abandoned.
Moving forward from aspect ratio, we look at the polarity of the cell and how this relates to its direction of movement. The polarity of a cell is loosely defined as the directon in which the cell is oriented. We tested the hypothesis that the polarity of a cell should line up with the direction in which it is moving.
Once again we start with the bounding ellipsoid of the cell. Consider the vector given by the longest axis of the ellipsoid, as shown in red in the simulation to the right. This vector can be considered the direction in which the cell is facing. The direction of movement is the vector between the current center of mass and the next center of mass, shown in green on the simulation. We then take the angle between these two vectors in 3d and this is the metric we are tracking. Note that the angle is at most ~1.6 radians (180 degrees) as the symmetry in the ellipsoid means that we can always invert the polarity of the cell.
The bar charts to the left show the results of the above analysis. The x-axis is the angle between polarity and direction of movement, while the y-axis is the number of cells that fell into that category. All angles up the the maximum seem to be represented uniformly, meaning that these cells did not show any preference for facing their direction of movement.


1 For it is plain to see that the Colchians are Egyptians; and what I say, I myself noted before I heard it from others. When it occurred to me, I inquired of both peoples; and the Colchians remembered the Egyptians better than the Egyptians remembered the Colchians;
2 the Egyptians said that they considered the Colchians part of Sesostris' army. I myself guessed it, partly because they are dark-skinned and woolly-haired; though that indeed counts for nothing, since other peoples are, too; but my better proof was that the Colchians and Egyptians and Ethiopians are the only nations that have from the first practised circumcision.
3 The Phoenicians and the Syrians of Palestine acknowledge that they learned the custom from the Egyptians, and the Syrians of the valleys of the Thermodon and the Parthenius, as well as their neighbors the Macrones, say that they learned it lately from the Colchians. These are the only nations that circumcise, and it is seen that they do just as the Egyptians.
4 But as to the Egyptians and Ethiopians themselves, I cannot say which nation learned it from the other; for it is evidently a very ancient custom. That the others learned it through traffic with Egypt, I consider clearly proved by this: that Phoenicians who traffic with Hellas cease to imitate the Egyptians in this matter and do not circumcise their children.


The base class for Substance highlight painters is
org.pushingpixels.substance.api.painter.highlight.SubstanceHighlightPainter
.
Highlight painter is used to paint the highlights of renderer-based
UI components (such as trees, tables, lists), as well as highlights
of menu items. It can also be used to paint visuals of third-party
components (see skinning primer for
more information). This allows providing a consistent and pluggable
appearance to those components. In addition, it provides an external API
for applications that wish to skin custom components in a visually
consistent manner.
The only painting method in
org.pushingpixels.substance.api.painter.highlight.SubstanceHighlightPainter
is
/**
* Paints the highlight.
*
* @param graphics
* Graphics context.
* @param comp
* Component.
* @param width
* Width.
* @param height
* Height.
* @param colorScheme
* The color scheme for painting the highlight.
*/
public void paintHighlight(Graphics2D graphics, Component comp, int width,
int height, SubstanceColorScheme colorScheme);


Examples¶
Simple illustrative examples on how you can quickly start using the Paralytics in your projects.
Discretization¶
Let’s suppose that we want to discretize continuous variables. With use of the Discretization transformer we can do it right away, because the transformer will recognize which variables are of the continuous type.
import numpy as np
import pandas as pd
import paralytics as prl
# Fix the seed for reproducibility.
SEED = 42
np.random.seed(SEED)
# Create available categories for non-numeric variable.
sexes = ['female', 'male', 'child']
# Generate example DataFrame.
X = pd.DataFrame({
'NormalVariable': np.random.normal(loc=0, scale=10, size=100),
'UniformVariable': np.random.uniform(low=0, high=100, size=100),
'IntVariable': np.random.randint(low=0, high=100, size=100),
'Sex': np.random.choice(sexes, 100, p=[.5, .3, .2])
})
# Generate response variable.
y = np.random.randint(low=0, high=2, size=100)
# Do discretization.
discretizer = prl.Discretizer(max_bins=5, random_state=SEED)
X_discretized = discretizer.fit_transform(X, y)
The X_discretized
dataframe is already a fully discretized equivalent of the
input dataframe X
. First five rows will look like presented below.
NormalVariable |
UniformVariable |
IntVariable |
Sex |
|
|---|---|---|---|---|
0 |
(-3.886, inf] |
(33.151, inf] |
(63.5, inf] |
child |
1 |
(-3.886, inf] |
(-inf, 24.071] |
(-inf, 28.0] |
female |
2 |
(-3.886, inf] |
(-inf, 24.071] |
(28.0, 63.5] |
female |
3 |
(-3.886, inf] |
(33.151, inf] |
(63.5, inf] |
male |
4 |
(-3.886, inf] |
(33.151, inf] |
(-inf, 28.0] |
male |
Forcing Context Manager¶
Let’s suppose that we want to create a class which methods will only be available if the instance is created using the context manager. We will get this functionality in the following way.
from paralytics import force_context_manager
@force_context_manager
class ExamplePrinter(object):
def __init__(self):
print('You just initiated me.')
def open(self):
print('I am opened.')
def __exit__(exc_type, exc_value, traceback):
print('...and now I am closed.')
if __name__ == '__main__':
example = ExamplePrinter()
try:
# Access methods without prior instance creation using the context
# manager results in raising an exception.
example.open()
except RuntimeError as e:
print(
'Error message without using the context manager: \n\n"{}"\n\n'
'Now we will try to do the same but with use of the '
'`with` statement:\n'
.format(e)
)
# This time no exception occurs.
with ExamplePrinter() as example:
example.open()
Assuming the Python code above is saved into a file called example.py
it can be run at the
command line with the result below:
$ python example.py
Error message without using the context manager:
"Object of the ExamplePrinter should only be initialized with the `with` statement.
Otherwise, the ExamplePrinter methods will not be available."
Now we will try to do the same but with use of the `with` statement:
You just initialized me.
I am opened.
...and now I am closed.
Main advantage of using the force_context_manager
function as a decorator allows to enforce
good practices and call the closing method __exit__ without worrying about remembering it.


Error Handler in angular
Angular allows us to set up a custom error handler that can be used to control the different errors and them in a correct way. Using a global error handler will avoid mistakes and provide a use friendly interface allowing us to indicate the user what problem is happening.
What is ErrorHandler
ErrorHandler
is the class that Angular
uses by default to control the errors. This means that, even if the application doesnt have a ErrorHandler
it is going to use the one setup by default in Angular
. This can be tested by trying to find a page not existing in any app, instantly Angular
will print the error in the console.
Creating your custom ErrorHandler step by step
In order to create a custom ErrorHandler
three steps are going to be needed:
Creating the custom ErrorHandler class
In this first step the custom ErrorHandler
class is going to be created inside the folder /app/core/errors/errors-handler.ts
:
import { ErrorHandler, Injectable, Injector } from '@angular/core';
import { HttpErrorResponse } from '@angular/common/http';
@Injectable()
export class ErrorsHandler implements ErrorHandler {
constructor(private injector: Injector) {}
handleError(error: Error | HttpErrorResponse) {
// To do: Use injector to get the necessary services to redirect or
// show a message to the user
const classname = error.constructor.name;
switch ( classname ) {
case 'HttpErrorResponse':
console.error('HttpError:' + error.message);
if (!navigator.onLine) {
console.error('Theres no internet connection');
// To do: control here in internet what you wanna do if user has no internet
} else {
console.error('Server Error:' + error.message);
// To do: control here if the server gave an error
}
break;
default:
console.error('Error:' + error.message);
// To do: control here if the client/other things gave an error
}
}
}
This class can be used to control the different type of errors. If wanted, the classname
variable could be used to add more switch cases. This would allow control of more specific situations.
Creating a ErrorInterceptor
Inside the same folder created in the last step we are going to create the ErrorInterceptor
(errors-handler-interceptor.ts
). This ErrorInterceptor
is going to retry any failed calls to the server to make sure it is not being found before showing the error:
import { HttpInterceptor, HttpRequest, HttpHandler, HttpEvent } from '@angular/common/http';
import { Injectable } from '@angular/core';
import { Observable } from 'rxjs';
import { retry } from 'rxjs/operators';
@Injectable()
export class ErrorsHandlerInterceptor implements HttpInterceptor {
constructor() {}
intercept(req: HttpRequest<any>, next: HttpHandler): Observable<HttpEvent<any>> {
return next.handle(req).pipe(
retryWhen((errors: Observable<any>) => errors.pipe(
delay(500),
take(5),
concatMap((error: any, retryIndex: number) => {
if (++retryIndex === 5) {
throw error;
}
return of(error);
})
))
);
}
}
This custom made interceptor is implementing the HttpInterceptor
and inside the method intercept
using the method pipe
,retryWhen
,delay
,take
and concatMap
from RxJs it is going to do the next things if there is errors:
-
With
delay(500)
do a delay to allow some time in between requests -
With
take(5)
retry five times. -
With
concatMap
if the index thattake()
gives is not 5 it returns the error, else, it throws the error.
Creating a Error Module
Finally, creating a module(errors-handler.module.ts
) is necessary to include the interceptor
and the custom error handler. In this case, the module is going to be created in the same folder as the last two:
import { NgModule, ErrorHandler } from '@angular/core';
import { CommonModule } from '@angular/common';
import { ErrorsHandler } from './errors-handler';
import { HTTP_INTERCEPTORS } from '@angular/common/http';
import { ErrorsHandlerInterceptor } from './errors-handler-interceptor';
@NgModule({
declarations: [], // Declare here component if you want to use routing to error component
imports: [
CommonModule
],
providers: [
{
provide: ErrorHandler,
useClass: ErrorsHandler,
},
{
provide: HTTP_INTERCEPTORS,
useClass: ErrorsHandlerInterceptor,
multi: true,
}
]
})
export class ErrorsHandlerModule { }
This module simply is providing the services that are implemented by our custom classes and then telling angular to use our custom made classes instead of the default ones. After doing this, the module has to be included in the app module app.module.ts
in order to be used.
....
imports: [
ErrorsHandlerModule,
....
Handling Errors
As a final step, handling these errors is necessary. Theres different ways that can be used to control the errors, here are a few:
-
Creating a custom page and using with
Router
to redirect to a page showing an error. -
Creating a service in the server side or
Backend
to create a log with the error and calling it withHttpClient
. -
Showing a custom made
SnackBar
with the error message.
Using SnackBarService
and NgZone
If the SnackBar is used directly, some errors can ocurr, this is due to SnackBar
being out of the Angular
zone. In order to use this service properly, NgZone is necessary. The method run()
from NgZone
will allow the service to be inside the Angular Zone
. An example on how to use it:
import { ErrorHandler, Injectable, Injector, NgZone } from '@angular/core';
import { HttpErrorResponse } from '@angular/common/http';
import { MatSnackBar } from '@angular/material';
@Injectable()
export class ErrorsHandler implements ErrorHandler {
constructor(private injector: Injector, private zone: NgZone) {}
handleError(error: Error | HttpErrorResponse) {
// Use injector to get the necessary services to redirect or
const snackBar: MatSnackBar = this.injector.get(MatSnackBar);
const classname = error.constructor.name;
let message: string;
switch ( classname ) {
case 'HttpErrorResponse':
message = !(navigator.onLine) ? 'There is no internet connection' : error.message;
break;
default:
message = error.message;
}
this.zone.run(
() => snackBar.open(message, 'danger', { duration : 4000})
);
}
}
Using Injector
the MatSnackBar
is obtained, then the correct message is obtained inside the switch. Finally, using NgZone
and run()
, we open the SnackBar
passing the message, and the paremeters wanted.


Hi,
After upgrading my Ubuntu server from oem_gate to emonhub I see that my /dev/ttyUSB0 jeelink v3c is switching from time to time to /dev/ttyUSB1 causing my emonhub.conf to be wrong. Once I reconfigure emonhub.conf the set-up is working again...until...it switches back to /dev/ttyUSB0 again. So how do I stop ttyUSB0/1 from switching in Linux/Ubuntu so my config emonhub.conf can stay the same. Strangely I never had this problem before with oem_gate. That set-up was running for more than 2 years but it all started with the use of emonhub....strange...
So all help welcome...
Re: emonhub /dev/ttyUSB0 switching /dev/ttyUSB1
Im not sure about this, I dont think there should be any difference in the way its selected, could it be a temperamental physical connection issue? This might be useful I havent tried it myself http://hintshop.ludvig.co.nz/show/persistent-names-usb-serial-devices/
Re: emonhub /dev/ttyUSB0 switching /dev/ttyUSB1
Also just as an addition to Trystan's points,
Do you have more than one usb device connected (ie both the JeeLink and JeeNode)? Due to the way the OS assigns the refs dynamically, there is no guarantee which order they will get numbered at boot.
This is a big issue for Pi's booting to hdd when they have any other usb device connected at boot and is the reason the uuid is used rather than the assigned ref in fstab and cmdline.txt.
The persistent ref for your jeelink would be highly advisable. I cannot vouch for the guide Trystan has linked to, but the idea of a persistent usb ref is a must unless you only ever have one device connected, the connection is 100% sound and you never remove/refit it on the live system, only when shut down.
Paul
Re: emonhub /dev/ttyUSB0 switching /dev/ttyUSB1
Hello both,
See my other topic on http://openenergymonitor.org/emon/node/11851 .
It looks stable now. I think that due to the fact that I used a wrong interfacer the operating system was always resetting the port for some reason. After reinstalling emonhub RC1.2 and configuring it with the correct interfacer it is now stable (2 days) So I will further monitor it but I think this is solved now.
Herbert


Format
Steam Upgrade Calculator
Best damage to cost ratio
Made by opl (
Twitter
,
Reddit
,
Steam
)
Update
Bought next
Name
Lvl
Cost
Cost Sum
EDPS


Port Ghalib is on the southern part of Egypt's Red Sea coast, 85 km from Kusier and 60 km from Marsa Alam.
The Port Ghalib Marina is an artificial harbour, part of a tourist resort. Located in a quiet desert-looking landscape, it opened in 2002 and can accommodate up to 1000 yachts. Now part of the Camper & Nicholsons group, facilities are greatly improved with Harbor Master, Customs and Immigration offices on site and a fully equipped repair and fueling facility.
Position 25°32'N, 34°38'E (entrance channel)
Port Ghalib is an official port of entry to Egypt.
See Egypt Formalities for full details on clearing into and out of Egypt.
Call port control on VHF Ch:10 or 16, preferably 2 hours before arrival, otherwise well before reaching the entrance channel.
This is an easy place to clear in to the country and get visas as all entry formalities can be completed at the marina office without the need to hire an agent or travel to any other place.
The Marina provides clearance formalities at these costs:
Government fee - formalities for foreign yachts up to 18 metres (valid 1 mth): USD 30 (USD 50 for larger yachts);
Immigration stamps - Egyptian visa (per person): USD 25
Processing fee (marina acts as agent): USD 80 per yacht
Berthing up to 8 hours in the marina (to complete formalities): USD 13 (15 m LOA).
Note:
Fees are payable only once per visit to Egypt at at any licensed port of entry. The marina will issue a receipt which should be shown at subsequent ports or marinas so as not to have to pay additional fees for formalities.
This applies to tourist marinas (such as Port Ghalib, Abu Tig Marina, Wadi Dome, Hurghada Marina). It does not apply to Sharm El Sheikh, where you will be liable for further fees.
Yachts owners should only fill a Customs declaration form and present it to the marina management for processing.
See Agents for details of any Clearance agents.
Last updated June 2016.
Entrance to the channel is at 25°32.1'N 034°38.6'E. The channel is well marked with buoys on both port and starboard sides, free of danger with depths in excess of 25m. The channel to the marina runs E/W through the reef.
A prior reservation is required before entering the marina. Entrance is permitted after sunset.
Berthing is stern-to the quay with electricity and water on the quay. Slipway service for boats up to 20m. Very limited repair services available.
Last updated June 2016.


Machine Learning
Endorsed by Kirk Borne and 7 others who are highly skilled at this
Endorsed by 2 of Karthik’s colleagues at LogBase Technologies
Hadoop
Endorsed by Sal Uryasev and 5 others who are highly skilled at this
Computer Security
Endorsed by 3 of Karthik’s colleagues at LinkedIn


LIFE STYLE
RUNNING
FOOTBALL
SKATEBOARDING
huarache
new
the running has just begun
$200
Size
7
8
9
10
11
add to cart
wishlist


Home
Recipes
History of food
Recipe Book
Healthy-Food
Junk-Food
The history of Junk-Food
Vegetarian-Food


--- action: 'shop:receipt' template: main protocol: all published: true name: Receipt url: '/receipt/:paymenthash' --- {% if invoice %}
Your order number is {{ invoice.order.number }}. Look for a confirmation email soon. Questions?
Customer Service<EMAIL_ADDRESS>or 1-855-332-0555
Order Date: {{ invoice.order.created_at.format('M jS, Y') }}
Payment method: {{ payment.guessPaymentMethod().name }}
Product |
Qty |
Total |
| {{ item.product.name }} | {{ item.quantity|number_format(0) }} | {{ (item.quantity *item.pivot.price)|currency }} |
Invoice not found.


Formatting text
Paragraphs and line breaks
Users of HTML are sometimes surprised to find that HTML gives them little control over the way that a page is
displayed.
It should be remembered that HTML was developed as a means of marking up the structure of a document
not as away of determining its presentation. Formatting text to appear on a Web page is therefore different from
formatting text to appear
in a printed document.
- Monday
- Tuesday
- Wednesday
- Thursday
- Friday
- Saturday
- Sunday
- January
- February
- March
- April
- May
- June
- July
- August
- September
- October
- November
- December
- Spring
- First season of the year: March - May
- Summer
- Second season of the year: June - August
- Autumn
- Third season of the year: September - November
- Winter
- Fourth season of the year: December - February
- Spring
- March
- April
- May
- Summer
- June
- July
- August
- Autumn
- September
- October
- November
- Winter
- December
- January
- February


WITNESS LIST Ways & Means Committee April 14, 1999-2:00P HB 767 For: Sweeden, John (City of Richardson, City Council) Vela, Rosie (City of Richardson) HB 1164 For: Dingmore, Lindsey (Texas Independent Producers and Royalty Owners) Key, Robert (Association of Energy Service Companies) Landreth, Bob (Independent Oil Producer) Stevens, Bill (West Central Texas Oil & Gas Association) On: Garza, Tony (RailRoad Commission) Matthews, Charles (RailRoad Commission, Commissioner) Williams, Michael (RailRoad Commission, Commissioner) HB 1273 Against: Courtney, Chuck (Texas Retailers Association) HB 1310 For: Dingmore, Lindsey (Texas Independent Producers and Royalty Owners) Key, Robert (Association of Energy Service Companies) Landreth, Bob (Independent Oil Producer) Stevens, Bill (West Central Texas Oil & Gas Association) On: Garza, Tony (RailRoad Commission) Matthews, Charles (RailRoad Commission, Commissioner) Williams, Michael (RailRoad Commission, Commissioner) HB 1761 For: Kobdish, George (Self and Attorney) Tiffin, David (Richardson ISD) On: Barton, Kery (Comptroller of Public Accounts) HB 2429 On: Semple, Chas (Comptroller of Public Accounts) HB 2737 For: Tucker, Durwood (Texas Farm Bureau) On: Combs, Susan (Texas Department of Agriculture, Commissioner) HB 2999 For: Allday, Marty (The Coastal Corporation) Hammerlein, George (Harris County Tax Assessor-Collector) Handy, David (Harris County) HB 3034 For: Lee, Donald (Texas Conference of Urban Counties) HB 3082 For: Maxey, Merlin (Maxey Energy Co. / T.P.C.A.) Newton, Chris (Texas Petroleum Marketers & Convenience Store Association) On: Barton, Kery (Comptroller of Public Accounts) Nichols, Robert (Texas Transportation Commission) HB 3211 On: McLeskey, Kenny (Comptroller of Public Accounts) HB 3212 On: Barton, Kery (Comptroller of Public Accounts) HB 3252 For: Hansen, Don (Texas Hotel & Motel Association) HB 3460 For: Gilman, Holly (Water Oriented District of Comal County) Inman, Jim (Comal County Water Oriented Recreation District) Scheel, Danny (County Judge for Comal County) On: Barton, Kery (Comptroller of Public Accounts) HB 3541 For: Buckalew, James (Texas Oil & Gas Association) Vernon, Roger (Texas Oil & Gas Association) HB 3549 For: Anderson, Bruce (Linebarger,Heard law firm) HB 3567 For: Jacobs, Sandy (Denton County) Leonard, Tom (Denton County) Against: Croker, Katie (City of Little Elm) Knowler, Del (Citizens United for a Rural Environment) Pelley, Jim (City of Little Elm, Mayor) Wilkinson, Bill (Mayor Pro Tempore, Double Oak, Tx.) HB 3600 For: Ratcliff, Joe (Texas Association of Wholesale Distributors) On: Fox, Jeannene (Texas Alcohol & Beverage Commission) LeBas, James (Comptroller of Public Accounts) HB 3623 For: Smith, Patrick (Texas Society of Professional Surveyors) HB 3659 For: Jackson, Lee (Texas Transportation Funding Coalition) Newton, Chris (Texas Petroleum Marketers & Convenience Store Association) Against: Maxey, Merlin (Maxey Energy Co. / T.P.C.A.) On: Barton, Kery (Comptroller of Public Accounts) Nichols, Robert (Texas Transportation Commission) Steffens, Peter (Florida Department of Revenue) HJR 81 For: Anderson, Wilma (Texas Shrimp Association) Turner, William (Matagorda County Navigation District No. 1)


Use any of the available button classes to quickly create a styled button.
If You want larger or smaller buttons You can add .btn-lg
, .btn-sm
, or .btn-xs
class.
Create block level buttons or outline buttons, by adding .btn-block
or .btn-outline
.
To add three diminsion to buttons You can add .dim
class to button.
Droppdowns buttons are avalible with any color and any size.
To buttons with any color or any size you can add extra icon on the left or the right side.
This is a group of buttons, ideal for sytuation where many actions are related to same element.
Page: {{main.bigCurrentPage}}
Button groups can act as a radio or a switch or even a single toggle. Below are some examples click to see what happens
{{main.singleModel}}
{{main.checkModel}}
{{main.radioModel || 'null'}}


BFP admin
Logout
flash_on
Posts
description
Documents
group
Users
warning
Reports
equalizer
Charts
receipt
Generate Recommendations


Latest News
The latest super interested link in web for developers. Add a link now!
Jon Doe
- Git Tutorial by Atlassian
- 3 Books to Inspire Your Career Change
- 4 best JavaScript or JQuery books for beginners
- Getting Started ASP .NET
- 19 Creatice CV/Resume Website Examples You Need To See
- The 9 Most In-Demand Programming Languages of 2016
- HOW TO KEEP UP TO DATE ON FRONT-END TECHNOLOGIES
- The most important skill in software development
- State of the Art JavaScript in 2016
- Ember.js 2 Tutorial - Building a complex web application


Labour pledges to save free TV licences as general election campaign hots up
Tom Watson unveiled the eye-catching policy exclusively to the Mirror
by Ben Glaze, https://www.facebook.com/MirrorPoliticsMorning,
It's a (sadly, old-fashioned) mark of decency, honour and virtue that if you say you're going to do something, you should do it.
That includes when it becomes uncomfortable, unpalatable or personally inconvenient.
So when the Conservatives promised to maintain free TV licences for the over-75s in the 2017 general election , there were no caveats or get-out clauses; it seemed a straight pledge that millions of pensioners took at face value.
But they reckoned without the sneakiness of the Tories, seeking to evade responsibility for their own commitments.
And so began one of the more unedifying spectacles of this Parliament: Conservative ministers desperately trying to wriggle out of their own manifesto vow.
Slippery Boris Johnson, who is obviously wary of the row brewing as the election campaign hots up, said at the weekend: "This needs sorting out urgently and I'll be talking to the BBC about how to sort that out."
Well, for starters it “needed sorting out urgently” more than a year ago when the Mirror began warning of the threat to the benefit.
Secondly, he has repeatedly tried to blame the BBC for Conservatives breaking a manifesto pledge.
Labour, which introduced free licences in 1999, has seized on the Tory betrayal and campaigned, along with the Mirror and pensioner groups, to save them.
Deputy Leader Tom Watson is unequivocal in his pledge: “Our message is clear, vote Labour to save free TV licences."
Today hundreds of MPs will elect the new Commons Speaker to replace John Bercow .
Bercow was a divisive figure who did much to modernise Parliament but was accused of partisanship.
Westminster watchers all have their favourites of who they would like to succeed him .
But one thing we should all agree on is the new Speaker should be less of a star and more of an impartial umpire.
As one of the candidates said, observers want to remember the game, not the referee.
On today:
2pm - Nigel Farage unveils Brexit Party election candidates
2.30pm - MPs begin electing John Bercow's successor
What I am reading:
OAPs on the streets of Leeds welcoming Labour's pledge to save free TV licences
* If you would like the newsletter sent to your inbox sign up here : http://www.mirror.co.uk/newsletters/politics-newsletter/


Instructions, source code, everything you need ☞ https://github.com/bpierre/webkit-svg-fixer.
Images missing? Fix SVG images.


This class implements a patterned string.
For a list of all members of this type, see PatternString Members.
System.Object
log4net.Util.PatternString
This type is not safe for multithreaded operations.
This string has embedded patterns that are resolved and expanded when the string is formatted.
This class functions similarly to the PatternLayout in that it accepts a pattern and renders it to a string. Unlike the PatternLayout however the PatternString
does not render the properties of a specific LoggingEvent but of the process in general.
The recognized conversion pattern names are:
| Conversion Pattern Name | Effect |
|---|---|
| appdomain |
Used to output the friendly name of the current AppDomain. |
| date |
Used to output the date of the logging event in the local time zone. To output the date in universal time use the The date format specifier admits the same syntax as the time pattern string of the ToString. For better results it is recommended to use the log4net date formatters. These can be specified using one of the strings "ABSOLUTE", "DATE" and "ISO8601" for specifying AbsoluteTimeDateFormatter, DateTimeDateFormatter and respectively Iso8601DateFormatter. For example, %date{ISO8601} or %date{ABSOLUTE}. These dedicated date formatters perform significantly better than ToString. |
| env |
Used to output the a specific environment variable. The key to lookup must be specified within braces and directly following the pattern specifier, e.g. %env{COMPUTERNAME} would include the value of the The |
| identity |
Used to output the user name for the currently active user (Principal.Identity.Name). |
| newline |
Outputs the platform dependent line separator character or characters. This conversion pattern name offers the same performance as using non-portable line separator strings such as "\n", or "\r\n". Thus, it is the preferred way of specifying a line separator. |
| processid |
Used to output the system process ID for the current process. |
| property |
Used to output a specific context property. The key to lookup must be specified within braces and directly following the pattern specifier, e.g. %property{user} would include the value from the property that is keyed by the string 'user'. Each property value that is to be included in the log must be specified separately. Properties are stored in logging contexts. By default the If no key is specified, e.g. %property then all the keys and their values are printed in a comma separated list. The properties of an event are combined from a number of different contexts. These are listed below in the order in which they are searched.
|
| random |
Used to output a random string of characters. The string is made up of uppercase letters and numbers. By default the string is 4 characters long. The length of the string can be specified within braces directly following the pattern specifier, e.g. %random{8} would output an 8 character string. |
| username |
Used to output the WindowsIdentity for the currently active user. |
| utcdate |
Used to output the date of the logging event in universal time. The date conversion specifier may be followed by a date format specifier enclosed between braces. For example, %utcdate{HH:mm:ss,fff} or %utcdate{dd MMM yyyy HH:mm:ss,fff}. If no date format specifier is given then ISO8601 format is assumed (Iso8601DateFormatter). The date format specifier admits the same syntax as the time pattern string of the ToString. For better results it is recommended to use the log4net date formatters. These can be specified using one of the strings "ABSOLUTE", "DATE" and "ISO8601" for specifying AbsoluteTimeDateFormatter, DateTimeDateFormatter and respectively Iso8601DateFormatter. For example, %utcdate{ISO8601} or %utcdate{ABSOLUTE}. These dedicated date formatters perform significantly better than ToString. |
| % |
The sequence %% outputs a single percent sign. |
Additional pattern converters may be registered with a specific PatternString instance using AddConverter or AddConverter.
See the PatternLayout for details on the format modifiers supported by the patterns.
Namespace: log4net.Util
Assembly: log4net (in log4net.dll)
PatternString Members | log4net.Util Namespace


Ni Lao
"In this report I will first briefly survey the current state of programming by demonstration (PbD) research, and then I will describe a PbD framework called Verbal Programming Architecture (VPA)"
Unread


Program Version:EnergyPlus, Version 9.1.0-08d2e308bb, YMD=2021.07.16 12:27
Tabular Output Report in Format: HTML
Building: Ref Bldg Medium Office New2004_v1.3_5.0
Environment: PHILADELPHIA 2014 ** PHILADELPHIA - USA Custom-720304 WMO#=720304
Simulation Timestamp: 2021-07-16 12:27:59
Report: Annual Building Utility Performance Summary
For: Entire Facility
Timestamp: 2021-07-16 12:27:59
Values gathered over 8760.00 hours| Total Energy [GJ] | Energy Per Total Building Area [MJ/m2] | Energy Per Conditioned Building Area [MJ/m2] | |
| Total Site Energy | 2059.86 | 413.44 | 413.44 |
| Net Site Energy | 2059.86 | 413.44 | 413.44 |
| Total Source Energy | 7018.50 | 1408.72 | 1408.72 |
| Net Source Energy | 7018.50 | 1408.72 | 1408.72 |
| Site=>Source Conversion Factor | |
| Electricity | 3.546 |
| Natural Gas | 1.092 |
| District Cooling | 0.848 |
| District Heating | 1.647 |
| Steam | 0.585 |
| Gasoline | 1.050 |
| Diesel | 1.050 |
| Coal | 1.050 |
| Fuel Oil #1 | 1.050 |
| Fuel Oil #2 | 1.050 |
| Propane | 1.050 |
| Other Fuel 1 | 1.000 |
| Other Fuel 2 | 1.000 |
| Area [m2] | |
| Total Building Area | 4982.19 |
| Net Conditioned Building Area | 4982.19 |
| Unconditioned Building Area | 0.00 |
| Electricity [GJ] | Natural Gas [GJ] | Additional Fuel [GJ] | District Cooling [GJ] | District Heating [GJ] | Water [m3] | |
| Heating | 74.98 | 80.32 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | 334.04 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 699.56 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 232.69 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 512.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 89.88 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 0.27 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 36.13 | 0.00 | 0.00 | 0.00 | 174.75 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total End Uses | 1943.41 | 116.45 | 0.00 | 0.00 | 0.00 | 174.75 |
| Subcategory | Electricity [GJ] | Natural Gas [GJ] | Additional Fuel [GJ] | District Cooling [GJ] | District Heating [GJ] | Water [m3] | |
| Heating | General | 74.98 | 80.32 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | General | 334.04 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | General | 699.56 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | Exterior Facade Lighting | 232.69 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | General | 347.08 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Elevators | 164.92 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Exterior Equipment | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | Fan Energy | 89.88 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | General | 0.27 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | Water Heater | 0.00 | 36.13 | 0.00 | 0.00 | 0.00 | 0.00 |
| General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 174.75 | |
| Refrigeration | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Electricity Intensity [MJ/m2] | Natural Gas Intensity [MJ/m2] | Additional Fuel Intensity [MJ/m2] | District Cooling Intensity [MJ/m2] | District Heating Intensity [MJ/m2] | Water Intensity [m3/m2] | |
| Lighting | 187.12 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| HVAC | 100.19 | 23.37 | 0.00 | 0.00 | 0.00 | 0.04 |
| Other | 102.77 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total | 390.07 | 23.37 | 0.00 | 0.00 | 0.00 | 0.04 |
| Electricity Intensity [MJ/m2] | Natural Gas Intensity [MJ/m2] | Additional Fuel Intensity [MJ/m2] | District Cooling Intensity [MJ/m2] | District Heating Intensity [MJ/m2] | Water Intensity [m3/m2] | |
| Lighting | 187.12 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| HVAC | 100.19 | 23.37 | 0.00 | 0.00 | 0.00 | 0.04 |
| Other | 102.77 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total | 390.07 | 23.37 | 0.00 | 0.00 | 0.00 | 0.04 |
| Electricity [GJ] | Percent Electricity [%] | |
| Fuel-Fired Power Generation | 0.000 | 0.00 |
| High Temperature Geothermal* | 0.000 | 0.00 |
| Photovoltaic Power | 0.000 | 0.00 |
| Wind Power | 0.000 | 0.00 |
| Power Conversion | 0.000 | 0.00 |
| Net Decrease in On-Site Storage | 0.000 | 0.00 |
| Total On-Site Electric Sources | 0.000 | 0.00 |
| Electricity Coming From Utility | 1943.412 | 100.00 |
| Surplus Electricity Going To Utility | 0.000 | 0.00 |
| Net Electricity From Utility | 1943.412 | 100.00 |
| Total On-Site and Utility Electric Sources | 1943.412 | 100.00 |
| Total Electricity End Uses | 1943.412 | 100.00 |
| Heat [GJ] | Percent Heat [%] | |
| Water-Side Heat Recovery | 0.00 | |
| Air to Air Heat Recovery for Cooling | 0.00 | |
| Air to Air Heat Recovery for Heating | 0.00 | |
| High-Temperature Geothermal* | 0.00 | |
| Solar Water Thermal | 0.00 | |
| Solar Air Thermal | 0.00 | |
| Total On-Site Thermal Sources | 0.00 |
| Water [m3] | Percent Water [%] | |
| Rainwater Collection | 0.00 | 0.00 |
| Condensate Collection | 0.00 | 0.00 |
| Groundwater Well | 0.00 | 0.00 |
| Total On Site Water Sources | 0.00 | 0.00 |
| - | - | - |
| Initial Storage | 0.00 | 0.00 |
| Final Storage | 0.00 | 0.00 |
| Change in Storage | 0.00 | 0.00 |
| - | - | - |
| Water Supplied by Utility | 174.75 | 100.00 |
| - | - | - |
| Total On Site, Change in Storage, and Utility Water Sources | 174.75 | 100.00 |
| Total Water End Uses | 174.75 | 100.00 |
| Degrees [deltaC] | |
| Tolerance for Zone Heating Setpoint Not Met Time | 0.56 |
| Tolerance for Zone Cooling Setpoint Not Met Time | 0.56 |
| Facility [Hours] | |
| Time Setpoint Not Met During Occupied Heating | 20.00 |
| Time Setpoint Not Met During Occupied Cooling | 0.00 |
| Time Not Comfortable Based on Simple ASHRAE 55-2004 | 3180.67 |
Table of Contents
TopEMISSIONS DATA SUMMARY
| Meter |COMPONENTS OF PEAK ELECTRICAL DEMAND
| Meter |HEATING PART LOAD PERFORMANCE
| VAV_1_HEATC | VAV_2_HEATC | VAV_3_HEATC |COOLING PART LOAD PERFORMANCE
| VAV_1_COOLC DXCOIL | VAV_2_COOLC DXCOIL | VAV_3_COOLC DXCOIL |FAN PART LOAD PERFORMANCE
| VAV_1_FAN | VAV_2_FAN | VAV_3_FAN |Report: Input Verification and Results Summary
For: Entire Facility
Timestamp: 2021-07-16 12:27:59
General| Value | |
| Program Version and Build | EnergyPlus, Version 9.1.0-08d2e308bb, YMD=2021.07.16 12:27 |
| RunPeriod | PHILADELPHIA 2014 |
| Weather File | PHILADELPHIA - USA Custom-720304 WMO#=720304 |
| Latitude [deg] | 40.14 |
| Longitude [deg] | -75.3 |
| Elevation [m] | 92.00 |
| Time Zone | -5.0 |
| North Axis Angle [deg] | 0.00 |
| Rotation for Appendix G [deg] | 0.00 |
| Hours Simulated [hrs] | 8760.00 |
| Total | North (315 to 45 deg) | East (45 to 135 deg) | South (135 to 225 deg) | West (225 to 315 deg) | |
| Gross Wall Area [m2] | 1977.67 | 593.30 | 395.53 | 593.30 | 395.53 |
| Above Ground Wall Area [m2] | 1977.67 | 593.30 | 395.53 | 593.30 | 395.53 |
| Window Opening Area [m2] | 652.83 | 195.85 | 130.57 | 195.85 | 130.57 |
| Gross Window-Wall Ratio [%] | 33.01 | 33.01 | 33.01 | 33.01 | 33.01 |
| Above Ground Window-Wall Ratio [%] | 33.01 | 33.01 | 33.01 | 33.01 | 33.01 |
| Total | North (315 to 45 deg) | East (45 to 135 deg) | South (135 to 225 deg) | West (225 to 315 deg) | |
| Gross Wall Area [m2] | 1977.67 | 593.30 | 395.53 | 593.30 | 395.53 |
| Above Ground Wall Area [m2] | 1977.67 | 593.30 | 395.53 | 593.30 | 395.53 |
| Window Opening Area [m2] | 652.83 | 195.85 | 130.57 | 195.85 | 130.57 |
| Gross Window-Wall Ratio [%] | 33.01 | 33.01 | 33.01 | 33.01 | 33.01 |
| Above Ground Window-Wall Ratio [%] | 33.01 | 33.01 | 33.01 | 33.01 | 33.01 |
| Total | |
| Gross Roof Area [m2] | 1660.73 |
| Skylight Area [m2] | 0.00 |
| Skylight-Roof Ratio [%] | 0.00 |
| Area [m2] | Conditioned (Y/N) | Part of Total Floor Area (Y/N) | Volume [m3] | Multipliers | Above Ground Gross Wall Area [m2] | Underground Gross Wall Area [m2] | Window Glass Area [m2] | Opening Area [m2] | Lighting [W/m2] | People [m2 per person] | Plug and Process [W/m2] | |
| CORE_BOTTOM | 983.54 | Yes | Yes | 2698.04 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 12.4040 | 20.64 | 36.7874 |
| CORE_MID | 983.54 | Yes | Yes | 2698.04 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 12.4040 | 20.64 | 4.1400 |
| CORE_TOP | 983.54 | Yes | Yes | 2698.04 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 12.4040 | 20.64 | 4.1400 |
| FIRSTFLOOR_PLENUM | 1660.73 | Yes | No | 2024.76 | 1.00 | 202.84 | 0.00 | 0.00 | 0.00 | 0.0000 | 0.0000 | |
| MIDFLOOR_PLENUM | 1660.73 | Yes | No | 2024.76 | 1.00 | 202.84 | 0.00 | 0.00 | 0.00 | 0.0000 | 0.0000 | |
| PERIMETER_BOT_ZN_1 | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 12.4040 | 20.64 | 4.1400 |
| PERIMETER_BOT_ZN_2 | 131.26 | Yes | Yes | 360.08 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 12.4040 | 20.64 | 4.1400 |
| PERIMETER_BOT_ZN_3 | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 12.4040 | 20.64 | 4.1400 |
| PERIMETER_BOT_ZN_4 | 131.25 | Yes | Yes | 360.05 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 12.4040 | 20.64 | 4.1400 |
| PERIMETER_MID_ZN_1 | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 12.4040 | 20.64 | 4.1400 |
| PERIMETER_MID_ZN_2 | 131.26 | Yes | Yes | 360.08 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 12.4040 | 20.64 | 4.1400 |
| PERIMETER_MID_ZN_3 | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 12.4040 | 20.64 | 4.1400 |
| PERIMETER_MID_ZN_4 | 131.25 | Yes | Yes | 360.05 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 12.4040 | 20.64 | 4.1400 |
| PERIMETER_TOP_ZN_1 | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 12.4040 | 20.64 | 4.1400 |
| PERIMETER_TOP_ZN_2 | 131.26 | Yes | Yes | 360.08 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 12.4040 | 20.64 | 4.1400 |
| PERIMETER_TOP_ZN_3 | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 12.4040 | 20.64 | 4.1400 |
| PERIMETER_TOP_ZN_4 | 131.25 | Yes | Yes | 360.05 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 12.4040 | 20.64 | 4.1400 |
| TOPFLOOR_PLENUM | 1660.73 | Yes | No | 2024.76 | 1.00 | 202.84 | 0.00 | 0.00 | 0.00 | 0.0000 | 0.0000 | |
| Total | 4982.19 | 13667.13 | 1369.16 | 0.00 | 652.83 | 652.83 | 12.4040 | 20.64 | 10.5849 | |||
| Conditioned Total | 4982.19 | 13667.13 | 1369.16 | 0.00 | 652.83 | 652.83 | 12.4040 | 20.64 | 10.5849 | |||
| Unconditioned Total | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | ||||||
| Not Part of Total | 4982.19 | 6074.28 | 608.51 | 0.00 | 0.00 | 0.00 | 0.0000 | 0.0000 |
Report: Component Sizing Summary
For: Entire Facility
Timestamp: 2021-07-16 12:27:59
AirTerminal:SingleDuct:VAV:Reheat| Design Size Maximum Air Flow Rate [m3/s] | Design Size Constant Minimum Air Flow Fraction | User-Specified Constant Minimum Air Flow Fraction | Design Size Minimum Air Flow Rate [m3/s] | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | Design Size Maximum Flow Fraction during Reheat [] | |
| CORE_BOTTOM VAV BOX COMPONENT | 3.56 | 0.210301 | 0.300000 | 1.07 | 0.001087 | 0.300000 |
| CORE_MID VAV BOX COMPONENT | 3.32 | 0.225664 | 0.300000 | 0.996335 | 0.001013 | 0.300000 |
| CORE_TOP VAV BOX COMPONENT | 3.52 | 0.212969 | 0.300000 | 1.06 | 0.001073 | 0.300000 |
| PERIMETER_BOT_ZN_1 VAV BOX COMPONENT | 1.22 | 0.200000 | 0.300000 | 0.365655 | 0.001764 | 0.300000 |
| PERIMETER_BOT_ZN_2 VAV BOX COMPONENT | 1.39 | 0.200000 | 0.300000 | 0.418001 | 0.003184 | 0.300000 |
| PERIMETER_BOT_ZN_3 VAV BOX COMPONENT | 0.725839 | 0.217668 | 0.300000 | 0.217752 | 0.001050 | 0.300000 |
| PERIMETER_BOT_ZN_4 VAV BOX COMPONENT | 1.50 | 0.200000 | 0.300000 | 0.450863 | 0.003435 | 0.300000 |
| PERIMETER_MID_ZN_1 VAV BOX COMPONENT | 1.38 | 0.200000 | 0.300000 | 0.414169 | 0.001998 | 0.300000 |
| PERIMETER_MID_ZN_2 VAV BOX COMPONENT | 1.51 | 0.200000 | 0.300000 | 0.453513 | 0.003455 | 0.300000 |
| PERIMETER_MID_ZN_3 VAV BOX COMPONENT | 0.908614 | 0.200000 | 0.300000 | 0.272584 | 0.001315 | 0.300000 |
| PERIMETER_MID_ZN_4 VAV BOX COMPONENT | 1.60 | 0.200000 | 0.300000 | 0.479321 | 0.003652 | 0.300000 |
| PERIMETER_TOP_ZN_1 VAV BOX COMPONENT | 1.42 | 0.200000 | 0.300000 | 0.426171 | 0.002055 | 0.300000 |
| PERIMETER_TOP_ZN_2 VAV BOX COMPONENT | 1.51 | 0.200000 | 0.300000 | 0.452553 | 0.003448 | 0.300000 |
| PERIMETER_TOP_ZN_3 VAV BOX COMPONENT | 1.01 | 0.200000 | 0.300000 | 0.301888 | 0.001456 | 0.300000 |
| PERIMETER_TOP_ZN_4 VAV BOX COMPONENT | 1.67 | 0.200000 | 0.300000 | 0.499789 | 0.003808 | 0.300000 |
| Design Size Nominal Capacity [W] | |
| CORE_BOTTOM VAV BOX REHEAT COIL | 43245.78 |
| CORE_MID VAV BOX REHEAT COIL | 40301.65 |
| CORE_TOP VAV BOX REHEAT COIL | 42704.01 |
| PERIMETER_BOT_ZN_1 VAV BOX REHEAT COIL | 14790.73 |
| PERIMETER_BOT_ZN_2 VAV BOX REHEAT COIL | 16908.11 |
| PERIMETER_BOT_ZN_3 VAV BOX REHEAT COIL | 8808.03 |
| PERIMETER_BOT_ZN_4 VAV BOX REHEAT COIL | 18237.36 |
| PERIMETER_MID_ZN_1 VAV BOX REHEAT COIL | 16753.11 |
| PERIMETER_MID_ZN_2 VAV BOX REHEAT COIL | 18344.54 |
| PERIMETER_MID_ZN_3 VAV BOX REHEAT COIL | 11026.00 |
| PERIMETER_MID_ZN_4 VAV BOX REHEAT COIL | 19388.47 |
| PERIMETER_TOP_ZN_1 VAV BOX REHEAT COIL | 17238.57 |
| PERIMETER_TOP_ZN_2 VAV BOX REHEAT COIL | 18305.74 |
| PERIMETER_TOP_ZN_3 VAV BOX REHEAT COIL | 12596.66 |
| PERIMETER_TOP_ZN_4 VAV BOX REHEAT COIL | 20216.42 |
| Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | Sum of Air Terminal Maximum Flow Rates [m3/s] | Adjusted Heating Design Air Flow Rate [m3/s] | Adjusted Cooling Design Air Flow Rate [m3/s] | Adjusted Main Design Air Flow Rate [m3/s] | User Heating Air Flow Ratio [] | Calculated Heating Air Flow Ratio [] | Design Supply Air Flow Rate [m3/s] | |
| VAV_1 | 2.52 | 2.52 | 8.40 | 2.52 | 8.40 | 8.40 | 0.300000 | 0.300000 | 8.40 |
| VAV_2 | 2.62 | 2.62 | 8.72 | 2.62 | 8.72 | 8.72 | 0.300000 | 0.300000 | 8.72 |
| VAV_3 | 2.74 | 2.74 | 9.12 | 2.74 | 9.12 | 9.12 | 0.300000 | 0.300000 | 9.12 |
| Maximum Outdoor Air Flow Rate [m3/s] | Minimum Outdoor Air Flow Rate [m3/s] | |
| VAV_1_OA_CONTROLLER | 8.40 | 1.01 |
| VAV_2_OA_CONTROLLER | 8.72 | 1.01 |
| VAV_3_OA_CONTROLLER | 9.12 | 1.01 |
| Design Size High Speed Rated Air Flow Rate [m3/s] | Design Size High Speed Gross Rated Total Cooling Capacity [W] | Design Size High Speed Rated Sensible Heat Ratio | Design Size Low Speed Rated Air Flow Rate [m3/s] | Design Size Low Speed Gross Rated Total Cooling Capacity [W] | Design Size Low Speed Gross Rated Sensible Heat Ratio | |
| VAV_1_COOLC DXCOIL | 8.40 | 161052.58 | 0.789602 | 2.80 | 53678.83 | 0.789602 |
| VAV_2_COOLC DXCOIL | 8.72 | 161113.11 | 0.800386 | 2.91 | 53699.00 | 0.800386 |
| VAV_3_COOLC DXCOIL | 9.12 | 168674.56 | 0.800077 | 3.04 | 56219.23 | 0.800077 |
| Design Size Design Maximum Air Flow Rate [m3/s] | Design Electric Power Consumption [W] | |
| VAV_1_FAN | 8.40 | 15767.01 |
| Design Size Nominal Capacity [W] | |
| VAV_1_HEATC | 47924.25 |
| VAV_2_HEATC | 48112.99 |
| VAV_3_HEATC | 48353.00 |
| Design Size Maximum Flow Rate [m3/s] | |
| VAV_2_FAN | 8.72 |
| VAV_3_FAN | 9.12 |
| Maximum Loop Flow Rate [m3/s] | Plant Loop Volume [m3] | |
| SWHSYS1 | 0.000031 | 0.003744 |
| Design Flow Rate [m3/s] | Design Power Consumption [W] | |
| SWHSYS1 PUMP | 0.000031 | 8.44 |
| Use Side Design Flow Rate [m3/s] | |
| SWHSYS1 WATER HEATER | 0.000031 |
Report: Climatic Data Summary
For: Entire Facility
Timestamp: 2021-07-16 12:27:59
SizingPeriod:DesignDay| Maximum Dry Bulb [C] | Daily Temperature Range [deltaC] | Humidity Value | Humidity Type | Wind Speed [m/s] | Wind Direction | |
| CHICAGO ANN HTG 99.6% CONDNS DB | -20.60 | 0.00 | -20.60 | Wetbulb [C] | 4.90 | 270.00 |
| CHICAGO ANN CLG .4% CONDNS WB=>MDB | 31.20 | 10.70 | 25.50 | Wetbulb [C] | 5.30 | 230.00 |
| Value | |
| None |
Report: Envelope Summary
For: Entire Facility
Timestamp: 2021-07-16 12:27:59
Opaque Exterior| Construction | Reflectance | U-Factor with Film [W/m2-K] | U-Factor no Film [W/m2-K] | Gross Area [m2] | Net Area [m2] | Azimuth [deg] | Tilt [deg] | Cardinal Direction | |
| CORE_BOT_ZN_5_FLOOR | EXT-SLAB | 0.30 | 2.193 | 3.401 | 983.54 | 983.54 | 0.00 | 180.00 | |
| PERIMETER_BOT_PLENUM_WALL_EAST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.270 | 0.281 | 40.57 | 40.57 | 90.00 | 90.00 | E |
| PERIMETER_BOT_PLENUM_WALL_NORTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.270 | 0.281 | 60.85 | 60.85 | 0.00 | 90.00 | N |
| PERIMETER_BOT_PLENUM_WALL_SOUTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.270 | 0.281 | 60.85 | 60.85 | 180.00 | 90.00 | S |
| PERIMETER_BOT_PLENUM_WALL_WEST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.270 | 0.281 | 40.57 | 40.57 | 270.00 | 90.00 | W |
| PERIMETER_MID_PLENUM_WALL_EAST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.270 | 0.281 | 40.57 | 40.57 | 90.00 | 90.00 | E |
| PERIMETER_MID_PLENUM_WALL_NORTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.270 | 0.281 | 60.85 | 60.85 | 0.00 | 90.00 | N |
| PERIMETER_MID_PLENUM_WALL_SOUTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.270 | 0.281 | 60.85 | 60.85 | 180.00 | 90.00 | S |
| PERIMETER_MID_PLENUM_WALL_WEST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.270 | 0.281 | 40.57 | 40.57 | 270.00 | 90.00 | W |
| PERIMETER_BOT_ZN_1_WALL_SOUTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.270 | 0.281 | 136.92 | 71.63 | 180.00 | 90.00 | S |
| PERIMETER_BOT_ZN_1_FLOOR | EXT-SLAB | 0.30 | 2.193 | 3.401 | 207.34 | 207.34 | 180.00 | 180.00 | |
| PERIMETER_BOT_ZN_2_WALL_EAST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.270 | 0.281 | 91.28 | 47.75 | 90.00 | 90.00 | E |
| PERIMETER_BOT_ZN_2_FLOOR | EXT-SLAB | 0.30 | 2.193 | 3.401 | 131.26 | 131.26 | 90.00 | 180.00 | |
| PERIMETER_BOT_ZN_3_WALL_NORTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.270 | 0.281 | 136.92 | 71.63 | 0.00 | 90.00 | N |
| PERIMETER_BOT_ZN_3_FLOOR | EXT-SLAB | 0.30 | 2.193 | 3.401 | 207.34 | 207.34 | 0.00 | 180.00 | |
| PERIMETER_BOT_ZN_4_WALL_WEST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.270 | 0.281 | 91.28 | 47.75 | 270.00 | 90.00 | W |
| PERIMETER_BOT_ZN_4_FLOOR | EXT-SLAB | 0.30 | 2.193 | 3.401 | 131.25 | 131.25 | 270.00 | 180.00 | |
| PERIMETER_MID_ZN_1_WALL_SOUTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.270 | 0.281 | 136.92 | 71.63 | 180.00 | 90.00 | S |
| PERIMETER_MID_ZN_2_WALL_EAST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.270 | 0.281 | 91.28 | 47.75 | 90.00 | 90.00 | E |
| PERIMETER_MID_ZN_3_WALL_NORTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.270 | 0.281 | 136.92 | 71.63 | 0.00 | 90.00 | N |
| PERIMETER_MID_ZN_4_WALL_WEST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.270 | 0.281 | 91.28 | 47.75 | 270.00 | 90.00 | W |
| PERIMETER_TOP_ZN_1_WALL_SOUTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.270 | 0.281 | 136.92 | 71.63 | 180.00 | 90.00 | S |
| PERIMETER_TOP_ZN_2_WALL_EAST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.270 | 0.281 | 91.28 | 47.75 | 90.00 | 90.00 | E |
| PERIMETER_TOP_ZN_3_WALL_NORTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.270 | 0.281 | 136.92 | 71.63 | 0.00 | 90.00 | N |
| PERIMETER_TOP_ZN_4_WALL_WEST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.270 | 0.281 | 91.28 | 47.75 | 270.00 | 90.00 | W |
| PERIMETER_TOP_PLENUM_WALL_EAST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.270 | 0.281 | 40.57 | 40.57 | 90.00 | 90.00 | E |
| PERIMETER_TOP_PLENUM_WALL_NORTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.270 | 0.281 | 60.85 | 60.85 | 0.00 | 90.00 | N |
| PERIMETER_TOP_PLENUM_WALL_SOUTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.270 | 0.281 | 60.85 | 60.85 | 180.00 | 90.00 | S |
| PERIMETER_TOP_PLENUM_WALL_WEST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.270 | 0.281 | 40.57 | 40.57 | 270.00 | 90.00 | W |
| BUILDING_ROOF | IEAD NON-RES ROOF | 0.30 | 0.358 | 0.376 | 1660.73 | 1660.73 | 0.00 | 0.00 |
| Construction | Glass Area [m2] | Frame Area [m2] | Divider Area [m2] | Area of One Opening [m2] | Area of Multiplied Openings [m2] | Glass U-Factor [W/m2-K] | Glass SHGC | Glass Visible Transmittance | Frame Conductance [W/m2-K] | Divider Conductance [W/m2-K] | Shade Control | Parent Surface | Azimuth [deg] | Tilt [deg] | Cardinal Direction | |
| PERIMETER_BOT_ZN_1_WALL_SOUTH_WINDOW | WINDOW NON-RES FIXED | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 4.598 | 0.516 | 0.357 | No | PERIMETER_BOT_ZN_1_WALL_SOUTH | 180.00 | 90.00 | S | ||
| PERIMETER_BOT_ZN_2_WALL_EAST_WINDOW | WINDOW NON-RES FIXED | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 4.598 | 0.516 | 0.357 | No | PERIMETER_BOT_ZN_2_WALL_EAST | 90.00 | 90.00 | E | ||
| PERIMETER_BOT_ZN_3_WALL_NORTH_WINDOW | WINDOW NON-RES FIXED | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 4.598 | 0.516 | 0.357 | No | PERIMETER_BOT_ZN_3_WALL_NORTH | 0.00 | 90.00 | N | ||
| PERIMETER_BOT_ZN_4_WALL_WEST_WINDOW | WINDOW NON-RES FIXED | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 4.598 | 0.516 | 0.357 | No | PERIMETER_BOT_ZN_4_WALL_WEST | 270.00 | 90.00 | W | ||
| PERIMETER_MID_ZN_1_WALL_SOUTH_WINDOW | WINDOW NON-RES FIXED | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 4.598 | 0.516 | 0.357 | No | PERIMETER_MID_ZN_1_WALL_SOUTH | 180.00 | 90.00 | S | ||
| PERIMETER_MID_ZN_2_WALL_EAST_WINDOW | WINDOW NON-RES FIXED | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 4.598 | 0.516 | 0.357 | No | PERIMETER_MID_ZN_2_WALL_EAST | 90.00 | 90.00 | E | ||
| PERIMETER_MID_ZN_3_WALL_NORTH_WINDOW | WINDOW NON-RES FIXED | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 4.598 | 0.516 | 0.357 | No | PERIMETER_MID_ZN_3_WALL_NORTH | 0.00 | 90.00 | N | ||
| PERIMETER_MID_ZN_4_WALL_WEST_WINDOW | WINDOW NON-RES FIXED | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 4.598 | 0.516 | 0.357 | No | PERIMETER_MID_ZN_4_WALL_WEST | 270.00 | 90.00 | W | ||
| PERIMETER_TOP_ZN_1_WALL_SOUTH_WINDOW | WINDOW NON-RES FIXED | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 4.598 | 0.516 | 0.357 | No | PERIMETER_TOP_ZN_1_WALL_SOUTH | 180.00 | 90.00 | S | ||
| PERIMETER_TOP_ZN_2_WALL_EAST_WINDOW | WINDOW NON-RES FIXED | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 4.598 | 0.516 | 0.357 | No | PERIMETER_TOP_ZN_2_WALL_EAST | 90.00 | 90.00 | E | ||
| PERIMETER_TOP_ZN_3_WALL_NORTH_WINDOW | WINDOW NON-RES FIXED | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 4.598 | 0.516 | 0.357 | No | PERIMETER_TOP_ZN_3_WALL_NORTH | 0.00 | 90.00 | N | ||
| PERIMETER_TOP_ZN_4_WALL_WEST_WINDOW | WINDOW NON-RES FIXED | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 4.598 | 0.516 | 0.357 | No | PERIMETER_TOP_ZN_4_WALL_WEST | 270.00 | 90.00 | W | ||
| Total or Average | 652.83 | 4.598 | 0.516 | 0.357 | ||||||||||||
| North Total or Average | 195.85 | 4.598 | 0.516 | 0.357 | ||||||||||||
| Non-North Total or Average | 456.98 | 4.598 | 0.516 | 0.357 |
| Construction | Area of One Opening [m2] | Area of Openings [m2] | Glass U-Factor [W/m2-K] | Glass SHGC | Glass Visible Transmittance | Parent Surface | |
| Total or Average | 0.00 | - | - | - |
| Construction | U-Factor with Film [W/m2-K] | U-Factor no Film [W/m2-K] | Gross Area [m2] | Parent Surface | |
| None |
Report: Equipment Summary
For: Entire Facility
Timestamp: 2021-07-16 12:27:59
Central Plant| Type | Nominal Capacity [W] | Nominal Efficiency [W/W] | IPLV in SI Units [W/W] | IPLV in IP Units [Btu/W-h] | |
| None |
| Type | Design Coil Load [W] | Nominal Total Capacity [W] | Nominal Sensible Capacity [W] | Nominal Latent Capacity [W] | Nominal Sensible Heat Ratio | Nominal Efficiency [W/W] | Nominal Coil UA Value [W/C] | Nominal Coil Surface Area [m2] | |
| VAV_1_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | 161052.58 | 127167.44 | 33885.14 | 0.79 | 3.23 | |||
| VAV_2_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | 161113.11 | 128952.61 | 32160.50 | 0.80 | 3.23 | |||
| VAV_3_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | 168674.56 | 134952.63 | 33721.94 | 0.80 | 3.23 |
| DX Cooling Coil Type | Standard Rated Net Cooling Capacity [W] | Standard Rated Net COP [W/W] | EER [Btu/W-h] | SEER [Btu/W-h] | IEER [Btu/W-h] | |
| VAV_1_COOLC DXCOIL | 159967.3 | 2.76 | 9.42 | N/A | 12.57 | |
| VAV_2_COOLC DXCOIL | 160027.7 | 2.75 | 9.37 | N/A | 12.53 | |
| VAV_3_COOLC DXCOIL | 167577.9 | 2.75 | 9.37 | N/A | 12.53 |
| DX Cooling Coil Type | Rated Net Cooling Capacity Test A [W] | Rated Electric Power Test A [W] | Rated Net Cooling Capacity Test B [W] | Rated Electric Power Test B [W] | Rated Net Cooling Capacity Test C [W] | Rated Electric Power Test C [W] | Rated Net Cooling Capacity Test D [W] | Rated Electric Power Test D [W] | |
| VAV_1_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | ||||||||
| VAV_2_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | ||||||||
| VAV_3_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed |
| DX Heating Coil Type | High Temperature Heating (net) Rating Capacity [W] | Low Temperature Heating (net) Rating Capacity [W] | HSPF [Btu/W-h] | Region Number | |
| None |
| Type | Design Coil Load [W] | Nominal Total Capacity [W] | Nominal Efficiency [W/W] | |
| CORE_BOTTOM VAV BOX REHEAT COIL | Coil:Heating:Electric | 43245.78 | 1.00 | |
| CORE_MID VAV BOX REHEAT COIL | Coil:Heating:Electric | 40301.65 | 1.00 | |
| CORE_TOP VAV BOX REHEAT COIL | Coil:Heating:Electric | 42704.01 | 1.00 | |
| PERIMETER_BOT_ZN_1 VAV BOX REHEAT COIL | Coil:Heating:Electric | 14790.73 | 1.00 | |
| PERIMETER_BOT_ZN_2 VAV BOX REHEAT COIL | Coil:Heating:Electric | 16908.11 | 1.00 | |
| PERIMETER_BOT_ZN_3 VAV BOX REHEAT COIL | Coil:Heating:Electric | 8808.03 | 1.00 | |
| PERIMETER_BOT_ZN_4 VAV BOX REHEAT COIL | Coil:Heating:Electric | 18237.36 | 1.00 | |
| PERIMETER_MID_ZN_1 VAV BOX REHEAT COIL | Coil:Heating:Electric | 16753.11 | 1.00 | |
| PERIMETER_MID_ZN_2 VAV BOX REHEAT COIL | Coil:Heating:Electric | 18344.54 | 1.00 | |
| PERIMETER_MID_ZN_3 VAV BOX REHEAT COIL | Coil:Heating:Electric | 11026.00 | 1.00 | |
| PERIMETER_MID_ZN_4 VAV BOX REHEAT COIL | Coil:Heating:Electric | 19388.47 | 1.00 | |
| PERIMETER_TOP_ZN_1 VAV BOX REHEAT COIL | Coil:Heating:Electric | 17238.57 | 1.00 | |
| PERIMETER_TOP_ZN_2 VAV BOX REHEAT COIL | Coil:Heating:Electric | 18305.74 | 1.00 | |
| PERIMETER_TOP_ZN_3 VAV BOX REHEAT COIL | Coil:Heating:Electric | 12596.66 | 1.00 | |
| PERIMETER_TOP_ZN_4 VAV BOX REHEAT COIL | Coil:Heating:Electric | 20216.42 | 1.00 | |
| VAV_1_HEATC | Coil:Heating:Fuel | 47924.25 | 0.80 | |
| VAV_2_HEATC | Coil:Heating:Fuel | 48112.99 | 0.80 | |
| VAV_3_HEATC | Coil:Heating:Fuel | 48353.00 | 0.80 |
| Type | Total Efficiency [W/W] | Delta Pressure [pa] | Max Air Flow Rate [m3/s] | Rated Electric Power [W] | Rated Power Per Max Air Flow Rate [W-s/m3] | Motor Heat In Air Fraction | Fan Energy Index | End Use Subcategory | Design Day Name for Fan Sizing Peak | Date/Time for Fan Sizing Peak | |
| VAV_1_FAN | Fan:SystemModel | 0.59 | 1109.65 | 8.40 | 15767.01 | 1875.99 | 1.00 | 1.12 | Fan Energy | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 09:00:00 |
| VAV_2_FAN | Fan:VariableVolume | 0.59 | 1109.65 | 8.72 | 16358.14 | 1875.99 | 1.00 | 1.11 | Fan Energy | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 07:00:00 |
| VAV_3_FAN | Fan:VariableVolume | 0.59 | 1109.65 | 9.12 | 17109.83 | 1875.99 | 1.00 | 1.11 | Fan Energy | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 16:40:00 |
| Type | Control | Head [pa] | Water Flow [m3/s] | Electric Power [W] | Power Per Water Flow Rate [W-s/m3] | Motor Efficiency [W/W] | End Use Subcategory | |
| SWHSYS1 PUMP | Pump:ConstantSpeed | Intermittent | 179352.00 | 0.000031 | 8.44 | 270515.84 | 0.85 | General |
| Type | Storage Volume [m3] | Input [W] | Thermal Efficiency [W/W] | Recovery Efficiency [W/W] | Energy Factor | |
| SWHSYS1 WATER HEATER | WaterHeater:Mixed | 0.38 | 845000.00 | 0.80 | 1.83 | 0.57 |
| DX Cooling Coil Type | Assocated Fan | Net Cooling Capacity [W] | COP [W/W] | EER [Btu/W-h] | IEER [Btu/W-h] | Supply Air Flow 100% [kg/s] | COP 75% Capacity [W/W] | EER 75% Capacity [Btu/W-h] | Supply Air Flow 75% [kg/s] | COP 50% Capacity [W/W] | EER 50% Capacity [Btu/W-h] | Supply Air Flow 50% [kg/s] | COP 25% Capacity [W/W] | EER 25% Capacity [Btu/W-h] | Supply Air Flow 25% [kg/s] | |
| VAV_1_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | VAV_1_FAN | 159967.29 | 2.76 | 9.42 | 12.57 | 9.6155 | 3.42 | 11.67 | 7.7788 | 4.13 | 14.10 | 5.2192 | 4.27 | 14.58 | 2.0793 |
| VAV_2_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | VAV_2_FAN | 160027.72 | 2.75 | 9.37 | 12.53 | 9.9760 | 3.41 | 11.62 | 8.0466 | 4.13 | 14.08 | 5.3864 | 4.27 | 14.56 | 2.1519 |
| VAV_3_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | VAV_3_FAN | 167577.92 | 2.75 | 9.37 | 12.53 | 10.4344 | 3.41 | 11.63 | 8.4167 | 4.13 | 14.08 | 5.6344 | 4.27 | 14.56 | 2.2508 |
Report: HVAC Sizing Summary
For: Entire Facility
Timestamp: 2021-07-16 12:27:59
Zone Sensible Cooling| Calculated Design Load [W] | User Design Load [W] | User Design Load per Area [W/m2] | Calculated Design Air Flow [m3/s] | User Design Air Flow [m3/s] | Design Day Name | Date/Time Of Peak {TIMESTAMP} | Thermostat Setpoint Temperature at Peak Load [C] | Indoor Temperature at Peak Load [C] | Indoor Humidity Ratio at Peak Load [kgWater/kgAir] | Outdoor Temperature at Peak Load [C] | Outdoor Humidity Ratio at Peak Load [kgWater/kgAir] | Minimum Outdoor Air Flow Rate [m3/s] | Heat Gain Rate from DOAS [W] | |
| CORE_BOTTOM | 32145.28 | 42753.23 | 43.47 | 2.679 | 3.564 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 09:00:00 | 22.67 | 22.67 | 0.00876 | 25.31 | 0.01878 | 0.596 | 0.00 |
| CORE_MID | 31136.60 | 41411.68 | 42.10 | 2.497 | 3.321 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 07:00:00 | 22.67 | 22.67 | 0.00879 | 21.46 | 0.01650 | 0.596 | 0.00 |
| CORE_TOP | 32961.59 | 43838.91 | 44.57 | 2.646 | 3.519 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 07:00:00 | 22.67 | 22.67 | 0.00877 | 21.46 | 0.01650 | 0.596 | 0.00 |
| PERIMETER_BOT_ZN_1 | 10994.74 | 14623.01 | 70.53 | 0.916 | 1.219 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 13:00:00 | 22.67 | 22.67 | 0.00866 | 30.66 | 0.01878 | 0.126 | 0.00 |
| PERIMETER_BOT_ZN_2 | 12568.90 | 16716.63 | 127.35 | 1.048 | 1.393 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 08:40:00 | 22.67 | 22.67 | 0.00859 | 24.64 | 0.01878 | 0.079 | 0.00 |
| PERIMETER_BOT_ZN_3 | 6811.04 | 9058.68 | 43.69 | 0.546 | 0.726 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 07:00:00 | 22.67 | 22.67 | 0.00881 | 21.46 | 0.01650 | 0.126 | 0.00 |
| PERIMETER_BOT_ZN_4 | 13557.02 | 18030.83 | 137.37 | 1.130 | 1.503 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 17:00:00 | 22.67 | 22.67 | 0.00858 | 29.70 | 0.01878 | 0.079 | 0.00 |
| PERIMETER_MID_ZN_1 | 12453.53 | 16563.20 | 79.88 | 1.038 | 1.381 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 13:00:00 | 22.67 | 22.67 | 0.00864 | 30.66 | 0.01878 | 0.126 | 0.00 |
| PERIMETER_MID_ZN_2 | 13636.71 | 18136.83 | 138.17 | 1.137 | 1.512 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 08:30:00 | 22.67 | 22.67 | 0.00858 | 24.30 | 0.01878 | 0.079 | 0.00 |
| PERIMETER_MID_ZN_3 | 8462.93 | 11255.70 | 54.29 | 0.683 | 0.909 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 07:00:00 | 22.67 | 22.67 | 0.00873 | 21.46 | 0.01650 | 0.126 | 0.00 |
| PERIMETER_MID_ZN_4 | 14412.74 | 19168.95 | 146.05 | 1.201 | 1.598 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 17:00:00 | 22.67 | 22.67 | 0.00858 | 29.70 | 0.01878 | 0.079 | 0.00 |
| PERIMETER_TOP_ZN_1 | 12814.42 | 17043.18 | 82.20 | 1.068 | 1.421 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 13:10:00 | 22.67 | 22.67 | 0.00864 | 30.75 | 0.01878 | 0.126 | 0.00 |
| PERIMETER_TOP_ZN_2 | 13607.87 | 18098.47 | 137.88 | 1.134 | 1.509 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 08:30:00 | 22.67 | 22.67 | 0.00858 | 24.30 | 0.01878 | 0.079 | 0.00 |
| PERIMETER_TOP_ZN_3 | 9077.31 | 12072.82 | 58.23 | 0.757 | 1.006 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 18:30:00 | 22.67 | 22.67 | 0.00869 | 27.83 | 0.01878 | 0.126 | 0.00 |
| PERIMETER_TOP_ZN_4 | 15028.23 | 19987.54 | 152.28 | 1.253 | 1.666 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 17:00:00 | 22.67 | 22.67 | 0.00857 | 29.70 | 0.01878 | 0.079 | 0.00 |
| Calculated Design Load [W] | User Design Load [W] | User Design Load per Area [W/m2] | Calculated Design Air Flow [m3/s] | User Design Air Flow [m3/s] | Design Day Name | Date/Time Of Peak {TIMESTAMP} | Thermostat Setpoint Temperature at Peak Load [C] | Indoor Temperature at Peak Load [C] | Indoor Humidity Ratio at Peak Load [kgWater/kgAir] | Outdoor Temperature at Peak Load [C] | Outdoor Humidity Ratio at Peak Load [kgWater/kgAir] | Minimum Outdoor Air Flow Rate [m3/s] | Heat Gain Rate from DOAS [W] | |
| CORE_BOTTOM | 0.00 | 0.00 | 0.00 | 0.000 | 0.596 | CHICAGO ANN HTG 99.6% CONDNS DB | 0.00 | 15.03 | 0.00800 | -20.60 | 0.00061 | 0.596 | 0.00 | |
| CORE_MID | 4112.41 | 5469.50 | 5.56 | 0.097 | 0.596 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:40:00 | 15.03 | 15.03 | 0.00800 | -20.60 | 0.00061 | 0.596 | 0.00 |
| CORE_TOP | 14826.01 | 19718.59 | 20.05 | 0.349 | 0.596 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 15.03 | 15.03 | 0.00800 | -20.60 | 0.00061 | 0.596 | 0.00 |
| PERIMETER_BOT_ZN_1 | 4700.52 | 6251.69 | 30.15 | 0.111 | 0.147 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | 15.03 | 15.03 | 0.00800 | -20.60 | 0.00061 | 0.126 | 0.00 |
| PERIMETER_BOT_ZN_2 | 3209.04 | 4268.03 | 32.52 | 0.076 | 0.100 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | 15.03 | 15.03 | 0.00800 | -20.60 | 0.00061 | 0.079 | 0.00 |
| PERIMETER_BOT_ZN_3 | 4546.02 | 6046.20 | 29.16 | 0.107 | 0.142 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | 15.03 | 15.03 | 0.00800 | -20.60 | 0.00061 | 0.126 | 0.00 |
| PERIMETER_BOT_ZN_4 | 3194.67 | 4248.91 | 32.37 | 0.075 | 0.100 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | 15.03 | 15.03 | 0.00800 | -20.60 | 0.00061 | 0.079 | 0.00 |
| PERIMETER_MID_ZN_1 | 7465.97 | 9929.74 | 47.89 | 0.176 | 0.234 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:30:00 | 15.03 | 15.03 | 0.00800 | -20.60 | 0.00061 | 0.126 | 0.00 |
| PERIMETER_MID_ZN_2 | 4914.60 | 6536.42 | 49.80 | 0.116 | 0.154 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:30:00 | 15.03 | 15.03 | 0.00800 | -20.60 | 0.00061 | 0.079 | 0.00 |
| PERIMETER_MID_ZN_3 | 7334.50 | 9754.89 | 47.05 | 0.173 | 0.230 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:30:00 | 15.03 | 15.03 | 0.00800 | -20.60 | 0.00061 | 0.126 | 0.00 |
| PERIMETER_MID_ZN_4 | 4962.54 | 6600.18 | 50.29 | 0.117 | 0.155 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:30:00 | 15.03 | 15.03 | 0.00800 | -20.60 | 0.00061 | 0.079 | 0.00 |
| PERIMETER_TOP_ZN_1 | 10058.27 | 13377.50 | 64.52 | 0.237 | 0.315 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 15.03 | 15.03 | 0.00800 | -20.60 | 0.00061 | 0.126 | 0.00 |
| PERIMETER_TOP_ZN_2 | 6524.14 | 8677.11 | 66.11 | 0.154 | 0.204 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 15.03 | 15.03 | 0.00800 | -20.60 | 0.00061 | 0.079 | 0.00 |
| PERIMETER_TOP_ZN_3 | 9945.59 | 13227.63 | 63.80 | 0.234 | 0.311 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 15.03 | 15.03 | 0.00800 | -20.60 | 0.00061 | 0.126 | 0.00 |
| PERIMETER_TOP_ZN_4 | 6607.94 | 8788.56 | 66.96 | 0.156 | 0.207 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 15.03 | 15.03 | 0.00800 | -20.60 | 0.00061 | 0.079 | 0.00 |
| Calculated cooling [m3/s] | User cooling [m3/s] | Calculated heating [m3/s] | User heating [m3/s] | Adjusted cooling [m3/s] | Adjusted heating [m3/s] | Adjusted main [m3/s] | Calculated Heating Air Flow Ratio [] | User Heating Air Flow Ratio [] | |
| VAV_1 | 8.40 | 8.40 | 1.09 | 1.09 | 8.4046 | 2.5214 | 8.4046 | 0.3000 | 0.3000 |
| VAV_2 | 8.72 | 8.72 | 1.37 | 1.37 | 8.7197 | 2.6159 | 8.7197 | 0.3000 | 0.3000 |
| VAV_3 | 9.12 | 9.12 | 1.63 | 1.63 | 9.1204 | 2.7361 | 9.1204 | 0.3000 | 0.3000 |
| Previous Design Volume Flow Rate [m3/s] | Algorithm Volume Flow Rate [m3/s] | Coincident Design Volume Flow Rate [m3/s] | Coincident Size Adjusted | Peak Sizing Period Name | Peak Day into Period {TIMESTAMP}[day] | Peak Hour Of Day {TIMESTAMP}[hr] | Peak Step Start Minute {TIMESTAMP}[min] | |
| None |
| Coil Type | HVAC Type | HVAC Name | Coil Final Gross Total Capacity [W] | Coil Final Gross Sensible Capacity [W] | Coil Final Reference Air Volume Flow Rate [m3/s] | Coil Final Reference Plant Fluid Volume Flow Rate [m3/s] | Coil U-value Times Area Value [W/K] | Design Day Name at Sensible Ideal Loads Peak | Date/Time at Sensible Ideal Loads Peak | Design Day Name at Air Flow Ideal Loads Peak | Date/Time at Air Flow Ideal Loads Peak | Coil Total Capacity at Ideal Loads Peak [W] | Coil Sensible Capacity at Ideal Loads Peak [W] | Coil Air Volume Flow Rate at Ideal Loads Peak [m3/s] | Coil Entering Air Drybulb at Ideal Loads Peak [C] | Coil Entering Air Wetbulb at Ideal Loads Peak [C] | Coil Entering Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Coil Leaving Air Drybulb at Ideal Loads Peak [C] | Coil Leaving Air Wetbulb at Ideal Loads Peak [C] | Coil Leaving Air Humidity Ratio at Ideal Loads Peak [C] | Outdoor Air Drybulb at Ideal Loads Peak [C] | Outdoor Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Outdoor Air Wetbulb at Ideal Loads Peak [C] | Outdoor Air Flow Percentage at Ideal Loads Peak [%] | Zone Air Drybulb at Ideal Loads Peak [C] | Zone Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Zone Air Relative Humidity at Ideal Loads Peak [%] | Zone Sensible Heat Gain at Ideal Loads Peak [W] | Zone Latent Heat Gain at Ideal Loads Peak [W] | Coil Total Capacity at Rating Conditions [W] | Coil Sensible Capacity at Rating Conditions [W] | |
| CORE_BOTTOM VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | CORE_BOTTOM VAV BOX | 43245.780 | 43245.780 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 00:10:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 00:10:00 | 43245.78 | 24089.29 | 0.595534 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 15.03 | 0.00800000 | 74.4740 | 0.00 | 0.00 | -999.00 | -999.00 |
| CORE_MID VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | CORE_MID VAV BOX | 40301.647 | 40301.647 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:40:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:40:00 | 40301.65 | 24089.29 | 0.595534 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 15.03 | 0.00799972 | 74.4714 | 5469.50 | 0.00 | -999.00 | -999.00 |
| CORE_TOP VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | CORE_TOP VAV BOX | 42704.014 | 42704.014 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 42704.01 | 24089.29 | 0.595534 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 15.03 | 0.00800000 | 74.4740 | 19718.59 | 0.00 | -999.00 | -999.00 |
| PERIMETER_BOT_ZN_1 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_BOT_ZN_1 VAV BOX | 14790.726 | 14790.726 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | 14790.73 | 5953.48 | 0.147182 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 15.03 | 0.00800000 | 74.4740 | 6251.69 | 0.00 | -999.00 | -999.00 |
| PERIMETER_BOT_ZN_2 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_BOT_ZN_2 VAV BOX | 16908.110 | 16908.110 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | 16908.11 | 4064.44 | 0.100481 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 15.03 | 0.00800000 | 74.4740 | 4268.03 | 0.00 | -999.00 | -999.00 |
| PERIMETER_BOT_ZN_3 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_BOT_ZN_3 VAV BOX | 8808.033 | 8808.033 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | 8808.03 | 5757.79 | 0.142344 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 15.03 | 0.00800000 | 74.4740 | 6046.20 | 0.00 | -999.00 | -999.00 |
| PERIMETER_BOT_ZN_4 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_BOT_ZN_4 VAV BOX | 18237.357 | 18237.357 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | 18237.36 | 4046.23 | 0.100031 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 15.03 | 0.00800000 | 74.4740 | 4248.91 | 0.00 | -999.00 | -999.00 |
| PERIMETER_MID_ZN_1 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_MID_ZN_1 VAV BOX | 16753.105 | 16753.105 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:30:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:30:00 | 16753.11 | 9456.08 | 0.233773 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 15.03 | 0.00800000 | 74.4740 | 9929.74 | 0.00 | -999.00 | -999.00 |
| PERIMETER_MID_ZN_2 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_MID_ZN_2 VAV BOX | 18344.539 | 18344.539 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:30:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:30:00 | 18344.54 | 6224.63 | 0.153885 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 15.03 | 0.00800000 | 74.4740 | 6536.42 | 0.00 | -999.00 | -999.00 |
| PERIMETER_MID_ZN_3 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_MID_ZN_3 VAV BOX | 11026.002 | 11026.002 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:30:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:30:00 | 11026.00 | 9289.57 | 0.229656 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 15.03 | 0.00800000 | 74.4740 | 9754.89 | 0.00 | -999.00 | -999.00 |
| PERIMETER_MID_ZN_4 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_MID_ZN_4 VAV BOX | 19388.468 | 19388.468 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:30:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:30:00 | 19388.47 | 6285.34 | 0.155386 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 15.03 | 0.00800000 | 74.4740 | 6600.18 | 0.00 | -999.00 | -999.00 |
| PERIMETER_TOP_ZN_1 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_TOP_ZN_1 VAV BOX | 17238.572 | 17238.572 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 17238.57 | 12739.38 | 0.314942 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 15.03 | 0.00800000 | 74.4740 | 13377.50 | 0.00 | -999.00 | -999.00 |
| PERIMETER_TOP_ZN_2 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_TOP_ZN_2 VAV BOX | 18305.737 | 18305.737 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 18305.74 | 8263.20 | 0.204282 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 15.03 | 0.00800000 | 74.4740 | 8677.11 | 0.00 | -999.00 | -999.00 |
| PERIMETER_TOP_ZN_3 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_TOP_ZN_3 VAV BOX | 12596.663 | 12596.663 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 12596.66 | 12596.66 | 0.311414 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 15.03 | 0.00800000 | 74.4740 | 13227.63 | 0.00 | -999.00 | -999.00 |
| PERIMETER_TOP_ZN_4 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_TOP_ZN_4 VAV BOX | 20216.418 | 20216.418 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 20216.42 | 8369.34 | 0.206906 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 15.03 | 0.00800000 | 74.4740 | 8788.56 | 0.00 | -999.00 | -999.00 |
| VAV_1_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | AirLoopHVAC | VAV_1 | 161052.584 | 127167.442 | 8.404637 | -999.0 | -999.000 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 14:00:00 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 09:00:00 | 160417.03 | 126193.31 | 8.404637 | 24.08 | 17.44 | 0.00987483 | 11.26 | 11.26 | 0.00850000 | 26.43 | 0.01858532 | 24.32 | 11.9645 | 22.67 | 0.00869103 | 50.1438 | 101182.39 | 0.00 | 161036.88 | 126994.91 |
| VAV_1_HEATC | Coil:Heating:Fuel | AirLoopHVAC | VAV_1 | 47924.250 | 47924.250 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | 47924.25 | 47924.25 | 2.521391 | -17.97 | -17.97 | 0.00115695 | 16.70 | 13.08 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 39.8818 | 15.03 | 0.00800000 | 74.4740 | 20814.83 | 0.00 | -999.00 | -999.00 |
| VAV_2_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | AirLoopHVAC | VAV_2 | 161113.111 | 128952.609 | 8.719739 | -999.0 | -999.000 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 06:40:00 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 07:00:00 | 159614.28 | 128374.59 | 8.719739 | 23.95 | 17.28 | 0.00972156 | 11.26 | 11.26 | 0.00850000 | 24.92 | 0.01767327 | 23.35 | 11.5322 | 22.67 | 0.00868502 | 50.1092 | 106536.36 | 0.00 | 161097.40 | 128773.46 |
| VAV_2_HEATC | Coil:Heating:Fuel | AirLoopHVAC | VAV_2 | 48112.992 | 48112.992 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:30:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:30:00 | 48112.99 | 48112.99 | 2.615922 | -11.16 | -11.16 | 0.00257062 | 16.70 | 13.08 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 38.4406 | 15.03 | 0.00799988 | 74.4728 | 38290.73 | 0.00 | -999.00 | -999.00 |
| VAV_3_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | AirLoopHVAC | VAV_3 | 168674.563 | 134952.628 | 9.120425 | -999.0 | -999.000 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 16:20:00 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 16:40:00 | 168071.79 | 135804.83 | 9.120425 | 23.95 | 17.25 | 0.00969232 | 11.26 | 11.26 | 0.00850000 | 25.59 | 0.01790026 | 23.67 | 11.0255 | 22.67 | 0.00867521 | 50.0533 | 111040.92 | 0.00 | 168658.11 | 134761.40 |
| VAV_3_HEATC | Coil:Heating:Fuel | AirLoopHVAC | VAV_3 | 48352.998 | 48352.998 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 48353.00 | 48353.00 | 2.736128 | -6.91 | -6.91 | 0.00345116 | 16.70 | 13.08 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 36.7518 | 15.03 | 0.00800000 | 74.4740 | 63789.39 | 0.00 | -999.00 | -999.00 |
Report: System Summary
For: Entire Facility
Timestamp: 2021-07-16 12:27:59
Economizer| High Limit Shutoff Control | Minimum Outdoor Air [m3/s] | Maximum Outdoor Air [m3/s] | Return Air Temp Limit | Return Air Enthalpy Limit | Outdoor Air Temperature Limit [C] | Outdoor Air Enthalpy Limit [C] | |
| VAV_1_OA_CONTROLLER | DifferentialDryBulb | 1.01 | 8.40 | - | |||
| VAV_2_OA_CONTROLLER | DifferentialDryBulb | 1.01 | 8.72 | - | |||
| VAV_3_OA_CONTROLLER | DifferentialDryBulb | 1.01 | 9.12 | - |
| Controller:MechanicalVentilation Name | Outdoor Air Per Person [m3/s-person] | Outdoor Air Per Area [m3/s-m2] | Outdoor Air Per Zone [m3/s] | Outdoor Air ACH [ach] | Outdoor Air Method | Outdoor Air Schedule Name | Air Distribution Effectiveness in Cooling Mode | Air Distribution Effectiveness in Heating Mode | Air Distribution Effectiveness Schedule Name | |
| None |
| Winter Clothes [hr] | Summer Clothes [hr] | Summer or Winter Clothes [hr] | |
| CORE_BOTTOM | 1310.33 | 5108.00 | 1310.33 |
| CORE_MID | 2082.00 | 5028.50 | 2070.00 |
| CORE_TOP | 2461.00 | 4982.67 | 2389.50 |
| PERIMETER_BOT_ZN_1 | 1873.67 | 4251.00 | 1588.00 |
| PERIMETER_BOT_ZN_2 | 2870.83 | 4562.17 | 2564.17 |
| PERIMETER_BOT_ZN_3 | 2535.83 | 5011.00 | 2535.67 |
| PERIMETER_BOT_ZN_4 | 3118.17 | 4547.33 | 2737.00 |
| PERIMETER_MID_ZN_1 | 1992.00 | 4069.83 | 1583.33 |
| PERIMETER_MID_ZN_2 | 2908.50 | 4429.67 | 2501.83 |
| PERIMETER_MID_ZN_3 | 2523.33 | 4768.17 | 2507.67 |
| PERIMETER_MID_ZN_4 | 3077.67 | 4459.50 | 2626.00 |
| PERIMETER_TOP_ZN_1 | 2285.33 | 4012.50 | 1816.17 |
| PERIMETER_TOP_ZN_2 | 3033.17 | 4360.33 | 2576.50 |
| PERIMETER_TOP_ZN_3 | 2710.50 | 4585.67 | 2658.17 |
| PERIMETER_TOP_ZN_4 | 3265.00 | 4412.17 | 2761.00 |
| FIRSTFLOOR_PLENUM | 0.00 | 0.00 | 0.00 |
| MIDFLOOR_PLENUM | 0.00 | 0.00 | 0.00 |
| TOPFLOOR_PLENUM | 0.00 | 0.00 | 0.00 |
| Facility | 4302.00 | 5108.00 | 3180.67 |
| During Heating [hr] | During Cooling [hr] | During Occupied Heating [hr] | During Occupied Cooling [hr] | |
| CORE_BOTTOM | 0.00 | 0.00 | 0.00 | 0.00 |
| CORE_MID | 0.00 | 0.00 | 0.00 | 0.00 |
| CORE_TOP | 0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_BOT_ZN_1 | 2.67 | 6.33 | 0.00 | 0.00 |
| PERIMETER_BOT_ZN_2 | 20.67 | 3.50 | 1.17 | 0.00 |
| PERIMETER_BOT_ZN_3 | 12.50 | 0.00 | 0.67 | 0.00 |
| PERIMETER_BOT_ZN_4 | 15.67 | 6.83 | 0.83 | 0.00 |
| PERIMETER_MID_ZN_1 | 24.83 | 7.83 | 0.67 | 0.00 |
| PERIMETER_MID_ZN_2 | 78.17 | 5.67 | 6.33 | 0.00 |
| PERIMETER_MID_ZN_3 | 78.50 | 0.00 | 6.17 | 0.00 |
| PERIMETER_MID_ZN_4 | 64.83 | 10.00 | 5.33 | 0.00 |
| PERIMETER_TOP_ZN_1 | 105.17 | 7.00 | 6.83 | 0.00 |
| PERIMETER_TOP_ZN_2 | 182.17 | 5.83 | 19.17 | 0.00 |
| PERIMETER_TOP_ZN_3 | 198.50 | 0.00 | 19.17 | 0.00 |
| PERIMETER_TOP_ZN_4 | 172.33 | 12.50 | 16.17 | 0.00 |
| FIRSTFLOOR_PLENUM | 0.00 | 0.00 | 0.00 | 0.00 |
| MIDFLOOR_PLENUM | 0.00 | 0.00 | 0.00 | 0.00 |
| TOPFLOOR_PLENUM | 0.00 | 0.00 | 0.00 | 0.00 |
| Facility | 241.33 | 50.33 | 20.00 | 0.00 |
Report: EMISSIONS DATA SUMMARY
For: Meter
Timestamp: 2021-07-16 12:27:59
Custom Monthly Report| CO2:FACILITY [kg] | NOX:FACILITY [kg] | SO2:FACILITY [kg] | PM:FACILITY [kg] | HG:FACILITY [kg] | WATERENVIRONMENTALFACTORS:FACILITY [L] | CARBON EQUIVALENT:FACILITY [kg] | |
| January | 59520.9923 | 106.4568 | 314.5470 | 0.0000 | 0.0010 | 72409.7955 | 17131.5072 |
| February | 47607.5147 | 85.7132 | 254.9719 | 0.0000 | 0.0008 | 58696.1440 | 13711.0919 |
| March | 46844.4130 | 84.7199 | 253.1661 | 0.0000 | 0.0008 | 58280.9541 | 13497.0862 |
| April | 48123.2841 | 87.4659 | 262.6742 | 0.0000 | 0.0008 | 60470.3562 | 13872.1291 |
| May | 57031.1040 | 103.7024 | 311.5732 | 0.0000 | 0.0009 | 71727.5008 | 16440.6184 |
| June | 65211.1543 | 118.6122 | 356.4761 | 0.0000 | 0.0011 | 82064.6596 | 18799.2590 |
| July | 68556.2394 | 124.7114 | 374.8511 | 0.0000 | 0.0011 | 86294.8165 | 19763.8153 |
| August | 68269.8284 | 124.1872 | 373.2660 | 0.0000 | 0.0011 | 85929.8937 | 19681.1986 |
| September | 56834.7961 | 103.3677 | 310.6342 | 0.0000 | 0.0009 | 71511.3519 | 16384.3653 |
| October | 54432.0747 | 98.9613 | 297.2834 | 0.0000 | 0.0009 | 68437.8123 | 15691.1548 |
| November | 45458.2718 | 82.4336 | 246.9973 | 0.0000 | 0.0007 | 56861.1432 | 13101.0479 |
| December | 52241.1942 | 94.3677 | 281.6585 | 0.0000 | 0.0009 | 64839.9874 | 15050.3336 |
| Annual Sum or Average |<PHONE_NUMBER> | 1214.6991 | 3638.0990 | 0.0000 | 0.0110 |<PHONE_NUMBER> |<PHONE_NUMBER> |
| Minimum of Months | 45458.2718 | 82.4336 | 246.9973 | 0.0000 | 0.0007 | 56861.1432 | 13101.0479 |
| Maximum of Months | 68556.2394 | 124.7114 | 374.8511 | 0.0000 | 0.0011 | 86294.8165 | 19763.8153 |
Report: COMPONENTS OF PEAK ELECTRICAL DEMAND
For: Meter
Timestamp: 2021-07-16 12:27:59
Custom Monthly Report| ELECTRICITY:FACILITY [J] | ELECTRICITY:FACILITY {Maximum}[W] | ELECTRICITY:FACILITY {TIMESTAMP} | INTERIORLIGHTS:ELECTRICITY {AT MAX/MIN} [W] | INTERIOREQUIPMENT:ELECTRICITY {AT MAX/MIN} [W] | FANS:ELECTRICITY {AT MAX/MIN} [W] | HEATING:ELECTRICITY {AT MAX/MIN} [W] | COOLING:ELECTRICITY {AT MAX/MIN} [W] | EXTERIORLIGHTS:ELECTRICITY {AT MAX/MIN} [W] | PUMPS:ELECTRICITY {AT MAX/MIN} [W] | HEATREJECTION:ELECTRICITY [] | EXTERIOREQUIPMENT:ELECTRICITY [] | HUMIDIFICATION:ELECTRICITY [] | HEATRECOVERY:ELECTRICITY [] | WATERSYSTEMS:ELECTRICITY [] | REFRIGERATION:ELECTRICITY [] | GENERATORS:ELECTRICITY [] | ELECTRICITYPRODUCED:FACILITY [] | |
| January | 0.168021E+12 | 116433.769 | 22-JAN-08:09 | 55619.130 | 40719.449 | 4238.689 | 15848.060 | 0.000 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| February | 0.136200E+12 | 109211.308 | 12-FEB-08:09 | 55619.130 | 40719.449 | 4238.689 | 8625.599 | 0.000 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| March | 0.135237E+12 | 110015.098 | 12-MAR-11:00 | 55619.130 | 35124.736 | 5111.668 | 0.000 | 14151.123 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| April | 0.140317E+12 | 136128.492 | 15-APR-07:00 | 55619.130 | 40719.449 | 4370.610 | 0.000 | 35410.862 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| May | 0.166438E+12 | 160215.583 | 02-MAY-13:00 | 55619.130 | 30444.284 | 6719.300 | 0.000 | 67424.429 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| June | 0.190425E+12 | 179046.489 | 17-JUN-15:00 | 55619.130 | 33334.174 | 8767.151 | 0.000 | 81317.594 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| July | 0.200241E+12 | 199198.252 | 02-JUL-15:09 | 55619.130 | 33334.174 | 9153.505 | 0.000 | 101083.003 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| August | 0.199394E+12 | 175264.731 | 22-AUG-12:20 | 55619.130 | 33976.372 | 6576.375 | 0.000 | 79084.413 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| September | 0.165937E+12 | 185115.906 | 11-SEP-12:00 | 55619.130 | 33976.372 | 8100.679 | 0.000 | 87411.284 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| October | 0.158805E+12 | 166075.808 | 07-OCT-11:20 | 55619.130 | 35124.736 | 5398.568 | 0.000 | 69924.933 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| November | 0.131942E+12 | 132438.359 | 01-NOV-07:19 | 55619.130 | 40719.449 | 4238.689 | 0.000 | 31852.650 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| December | 0.150456E+12 | 115143.653 | 23-DEC-08:00 | 55619.130 | 40719.449 | 4238.689 | 0.000 | 14557.944 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| Annual Sum or Average | 0.194341E+13 | |||||||||||||||||
| Minimum of Months | 0.131942E+12 | 109211.308 | 55619.130 | 30444.284 | 4238.689 | 0.000 | 0.000 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | |
| Maximum of Months | 0.200241E+12 | 199198.252 | 55619.130 | 40719.449 | 9153.505 | 15848.060 | 101083.003 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
Report: HEATING PART LOAD PERFORMANCE
For: VAV_1_HEATC
Timestamp: 2021-07-16 12:27:59
Custom Monthly Report| HEATING COIL GAS RATE [W] | HEATING COIL GAS RATE {Maximum}[W] | HEATING COIL GAS RATE {TIMESTAMP} | |
| January | 3416. | 34375. | 04-JAN-07:10 |
| February | 1548. | 29881. | 12-FEB-07:03 |
| March | 707. | 23524. | 01-MAR-07:05 |
| April | 3. | 2915. | 01-APR-06:03 |
| May | 0. | 0. | 01-MAY-00:10 |
| June | 0. | 0. | 01-JUN-00:10 |
| July | 0. | 0. | 01-JUL-00:10 |
| August | 0. | 0. | 01-AUG-00:10 |
| September | 0. | 0. | 01-SEP-00:10 |
| October | 15. | 5267. | 26-OCT-06:20 |
| November | 259. | 14269. | 25-NOV-07:03 |
| December | 885. | 20024. | 11-DEC-07:03 |
| Annual Sum or Average | 576. | ||
| Minimum of Months | 0. | 0. | |
| Maximum of Months | 3416. | 34375. |
Report: HEATING PART LOAD PERFORMANCE
For: VAV_2_HEATC
Timestamp: 2021-07-16 12:27:59
Custom Monthly Report| HEATING COIL GAS RATE [W] | HEATING COIL GAS RATE {Maximum}[W] | HEATING COIL GAS RATE {TIMESTAMP} | |
| January | 4306. | 35838. | 04-JAN-07:10 |
| February | 2192. | 31229. | 12-FEB-07:03 |
| March | 910. | 24630. | 01-MAR-07:10 |
| April | 1. | 3156. | 01-APR-06:03 |
| May | 0. | 0. | 01-MAY-00:10 |
| June | 0. | 0. | 01-JUN-00:10 |
| July | 0. | 0. | 01-JUL-00:10 |
| August | 0. | 0. | 01-AUG-00:10 |
| September | 0. | 0. | 01-SEP-00:10 |
| October | 16. | 5548. | 26-OCT-06:27 |
| November | 427. | 15909. | 25-NOV-07:03 |
| December | 1451. | 21615. | 11-DEC-07:03 |
| Annual Sum or Average | 783. | ||
| Minimum of Months | 0. | 0. | |
| Maximum of Months | 4306. | 35838. |
Report: HEATING PART LOAD PERFORMANCE
For: VAV_3_HEATC
Timestamp: 2021-07-16 12:27:59
Custom Monthly Report| HEATING COIL GAS RATE [W] | HEATING COIL GAS RATE {Maximum}[W] | HEATING COIL GAS RATE {TIMESTAMP} | |
| January | 5646. | 44585. | 04-JAN-07:10 |
| February | 3416. | 39235. | 12-FEB-07:03 |
| March | 1629. | 33009. | 01-MAR-07:10 |
| April | 31. | 8293. | 01-APR-06:03 |
| May | 0. | 0. | 01-MAY-00:10 |
| June | 0. | 0. | 01-JUN-00:10 |
| July | 0. | 0. | 01-JUL-00:10 |
| August | 0. | 0. | 01-AUG-00:10 |
| September | 0. | 0. | 01-SEP-00:10 |
| October | 81. | 13002. | 26-OCT-06:30 |
| November | 976. | 22953. | 25-NOV-07:03 |
| December | 2390. | 28269. | 11-DEC-07:03 |
| Annual Sum or Average | 1188. | ||
| Minimum of Months | 0. | 0. | |
| Maximum of Months | 5646. | 44585. |
Report: COOLING PART LOAD PERFORMANCE
For: VAV_1_COOLC DXCOIL
Timestamp: 2021-07-16 12:27:59
Custom Monthly Report| COOLING COIL ELECTRIC POWER [W] | COOLING COIL ELECTRIC POWER {Maximum}[W] | COOLING COIL ELECTRIC POWER {TIMESTAMP} | |
| January | 62. | 7574. | 11-JAN-15:00 |
| February | 0. | 0. | 01-FEB-00:10 |
| March | 203. | 6226. | 22-MAR-15:00 |
| April | 1540. | 13307. | 11-APR-15:10 |
| May | 4795. | 21097. | 02-MAY-14:00 |
| June | 8413. | 26457. | 19-JUN-05:02 |
| July | 9581. | 33117. | 02-JUL-15:10 |
| August | 8694. | 29003. | 22-AUG-05:02 |
| September | 5075. | 29547. | 11-SEP-13:00 |
| October | 2666. | 23153. | 07-OCT-11:20 |
| November | 461. | 10945. | 01-NOV-05:10 |
| December | 150. | 9986. | 22-DEC-12:58 |
| Annual Sum or Average | 3468. | ||
| Minimum of Months | 0. | 0. | |
| Maximum of Months | 9581. | 33117. |
Report: COOLING PART LOAD PERFORMANCE
For: VAV_2_COOLC DXCOIL
Timestamp: 2021-07-16 12:27:59
Custom Monthly Report| COOLING COIL ELECTRIC POWER [W] | COOLING COIL ELECTRIC POWER {Maximum}[W] | COOLING COIL ELECTRIC POWER {TIMESTAMP} | |
| January | 64. | 7864. | 11-JAN-15:00 |
| February | 0. | 0. | 01-FEB-00:10 |
| March | 206. | 6371. | 22-MAR-15:00 |
| April | 1599. | 13418. | 11-APR-15:00 |
| May | 5022. | 26024. | 16-MAY-05:02 |
| June | 8382. | 38980. | 26-JUN-05:02 |
| July | 9471. | 39363. | 08-JUL-05:02 |
| August | 8236. | 37182. | 22-AUG-05:02 |
| September | 4979. | 38461. | 02-SEP-05:02 |
| October | 2735. | 23026. | 07-OCT-11:20 |
| November | 469. | 11314. | 01-NOV-05:15 |
| December | 150. | 10305. | 22-DEC-12:58 |
| Annual Sum or Average | 3441. | ||
| Minimum of Months | 0. | 0. | |
| Maximum of Months | 9471. | 39363. |
Report: COOLING PART LOAD PERFORMANCE
For: VAV_3_COOLC DXCOIL
Timestamp: 2021-07-16 12:27:59
Custom Monthly Report| COOLING COIL ELECTRIC POWER [W] | COOLING COIL ELECTRIC POWER {Maximum}[W] | COOLING COIL ELECTRIC POWER {TIMESTAMP} | |
| January | 72. | 8225. | 11-JAN-15:00 |
| February | 0. | 0. | 01-FEB-00:10 |
| March | 212. | 6453. | 22-MAR-15:00 |
| April | 1672. | 14710. | 11-APR-15:00 |
| May | 5430. | 28326. | 16-MAY-05:02 |
| June | 9228. | 40809. | 26-JUN-05:02 |
| July | 10332. | 41210. | 08-JUL-05:02 |
| August | 8664. | 39692. | 22-AUG-05:02 |
| September | 5198. | 40934. | 02-SEP-05:02 |
| October | 2828. | 23745. | 07-OCT-11:20 |
| November | 456. | 11838. | 01-NOV-05:04 |
| December | 142. | 10780. | 22-DEC-12:58 |
| Annual Sum or Average | 3683. | ||
| Minimum of Months | 0. | 0. | |
| Maximum of Months | 10332. | 41210. |
Report: FAN PART LOAD PERFORMANCE
For: VAV_1_FAN
Timestamp: 2021-07-16 12:27:59
Custom Monthly Report| FAN ELECTRIC POWER [W] | FAN ELECTRIC POWER {Maximum}[W] | FAN ELECTRIC POWER {TIMESTAMP} | |
| January | 848. | 1801. | 13-JAN-13:05 |
| February | 822. | 1707. | 20-FEB-13:10 |
| March | 767. | 1820. | 11-MAR-13:00 |
| April | 822. | 1849. | 14-APR-15:20 |
| May | 866. | 2169. | 02-MAY-13:00 |
| June | 1019. | 4174. | 18-JUN-05:02 |
| July | 1131. | 4885. | 02-JUL-05:02 |
| August | 1077. | 3166. | 21-AUG-15:10 |
| September | 982. | 2971. | 11-SEP-13:00 |
| October | 889. | 2375. | 04-OCT-15:10 |
| November | 751. | 1895. | 18-NOV-12:00 |
| December | 759. | 1811. | 28-DEC-12:40 |
| Annual Sum or Average | 894. | ||
| Minimum of Months | 751. | 1707. | |
| Maximum of Months | 1131. | 4885. |
Report: FAN PART LOAD PERFORMANCE
For: VAV_2_FAN
Timestamp: 2021-07-16 12:27:59
Custom Monthly Report| FAN ELECTRIC POWER [W] | FAN ELECTRIC POWER {Maximum}[W] | FAN ELECTRIC POWER {TIMESTAMP} | |
| January | 1035. | 1703. | 13-JAN-13:05 |
| February | 982. | 1656. | 22-FEB-13:10 |
| March | 810. | 1815. | 11-MAR-13:10 |
| April | 855. | 2360. | 15-APR-05:02 |
| May | 901. | 4468. | 16-MAY-05:02 |
| June | 977. | 9128. | 18-JUN-05:02 |
| July | 1044. | 8599. | 14-JUL-05:02 |
| August | 952. | 5205. | 09-AUG-05:02 |
| September | 930. | 5201. | 02-SEP-05:02 |
| October | 903. | 2932. | 07-OCT-05:02 |
| November | 804. | 1885. | 18-NOV-12:00 |
| December | 929. | 1719. | 28-DEC-12:40 |
| Annual Sum or Average | 927. | ||
| Minimum of Months | 804. | 1656. | |
| Maximum of Months | 1044. | 9128. |
Report: FAN PART LOAD PERFORMANCE
For: VAV_3_FAN
Timestamp: 2021-07-16 12:27:59
Custom Monthly Report| FAN ELECTRIC POWER [W] | FAN ELECTRIC POWER {Maximum}[W] | FAN ELECTRIC POWER {TIMESTAMP} | |
| January | 1214. | 1643. | 13-JAN-13:05 |
| February | 1176. | 1612. | 20-FEB-13:20 |
| March | 913. | 1796. | 11-MAR-13:20 |
| April | 881. | 2548. | 15-APR-05:02 |
| May | 962. | 5586. | 03-MAY-05:02 |
| June | 1078. | 10984. | 18-JUN-05:02 |
| July | 1153. | 11517. | 14-JUL-05:02 |
| August | 1000. | 5590. | 22-AUG-05:02 |
| September | 964. | 6732. | 02-SEP-05:02 |
| October | 922. | 3623. | 07-OCT-05:02 |
| November | 943. | 1893. | 18-NOV-13:05 |
| December | 1146. | 1639. | 28-DEC-13:10 |
| Annual Sum or Average | 1029. | ||
| Minimum of Months | 881. | 1612. | |
| Maximum of Months | 1214. | 11517. |


THE SPARK ON THE CANDLE.
A BRIGHT spark on the candle-wick indicates a letter coming to the house. The person towards whom it shines will receive it. The time of its arrival is determined by striking the bottom of the candlestick on the table. If the spark comes off on the first blow, it will be received to-morrow; if two blows are required, on the second day,--and so on.


2D Game
This is a simple 2D game where you avoid enemies and try to stay alive to get the highest score. The plot is helping Real Madrid collect as many UCL throphies as possible.
Crime Project
This is a Data App project in which you can pick your community and a type of crime to see the results. Find out what is going out in your community. This project involves AJAX calls, Boostrap, and a Toolbar.
Lane Bus Tracker
Lane Tech students are always in a rush. Especially when trying to get home. This app focuses on the 4 main bus stops. This project involves AJAX calls, Boostrap, and a Toolbar.
Annoying Horn
Want to annoy your favorite teacher? Want be the most disturbing kid in class? This airhorn sure does the job. This app includes the capability to run offline, and was made following a Google Web Dev tutorial.
Daily Activities
This is a simply bar graph showing my daily activities. It is meant to show of the Google Chart tools. It is a simple yet informative graph about my life. It shows what I do in my daily life.
Find Your Car
Did your car get impounded or stolen? Find out with this app. It allows you to search the database of Chicago to know if your car has been impounded. If it was, it tells you where you can find it.
Potholes In My Area
This map uses an interactive google map to show the potholes in my zip code area 60625. The data it retrieves places a marker on where the pothole was reported.
City Council Employees
This website is meant to track the employees that work for City Council using an API call
to the City of Chicago Data Portal. The focus of this project was to work on the DexieDB,
in which I had trouble with.
Custom Bus Tracker
This website is a follow up to the Lane Bus Tracker. It is meant to allow customization for the user. The API call works, and you are able to search any bus for an estimate. But much like the "City Council Employees" website, I had trouble with the DexieDB part of the project.
My Favorite Things
This website is a simple HTML website where I share my favorite topics about life. It's a simple 3-page website. More on the lighter and fun side of me.