Program Version:EnergyPlus, Version 8.9.0-40101eaafd, YMD=2018.06.04 13:40
Tabular Output Report in Format: HTML
Building: KA2 A Flatroof Sample Building
Environment: RUN PERIOD 1 ** Anchorage Elmendorf AK USA TMY3 WMO#=702720
Simulation Timestamp: 2018-06-04 13:40:50
Report: Annual Building Utility Performance Summary
For: Entire Facility
Timestamp: 2018-06-04 13:40:50
Values gathered over 8760.00 hours| Total Energy [GJ] | Energy Per Total Building Area [MJ/m2] | Energy Per Conditioned Building Area [MJ/m2] | |
| Total Site Energy | 311.20 | 314.12 | 314.12 |
| Net Site Energy | 311.20 | 314.12 | 314.12 |
| Total Source Energy | 985.57 | 994.81 | 994.81 |
| Net Source Energy | 985.57 | 994.81 | 994.81 |
| Site=>Source Conversion Factor | |
| Electricity | 3.167 |
| Natural Gas | 1.084 |
| District Cooling | 1.056 |
| District Heating | 3.613 |
| Steam | 0.300 |
| Gasoline | 1.050 |
| Diesel | 1.050 |
| Coal | 1.050 |
| Fuel Oil #1 | 1.050 |
| Fuel Oil #2 | 1.050 |
| Propane | 1.050 |
| Other Fuel 1 | 1.000 |
| Other Fuel 2 | 1.000 |
| Area [m2] | |
| Total Building Area | 990.72 |
| Net Conditioned Building Area | 990.72 |
| Unconditioned Building Area | 0.00 |
| Electricity [GJ] | Natural Gas [GJ] | Additional Fuel [GJ] | District Cooling [GJ] | District Heating [GJ] | Water [m3] | |
| Heating | 143.65 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | 9.52 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 11.42 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 83.21 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 63.41 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total End Uses | 311.20 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Subcategory | Electricity [GJ] | Natural Gas [GJ] | Additional Fuel [GJ] | District Cooling [GJ] | District Heating [GJ] | Water [m3] | |
| Heating | General | 143.65 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | General | 9.52 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | General | 11.42 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | General | 83.21 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | General | 63.41 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Electricity Intensity [MJ/m2] | Natural Gas Intensity [MJ/m2] | Additional Fuel Intensity [MJ/m2] | District Cooling Intensity [MJ/m2] | District Heating Intensity [MJ/m2] | Water Intensity [m3/m2] | |
| Lighting | 11.52 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| HVAC | 218.61 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Other | 83.98 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total | 314.12 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Electricity Intensity [MJ/m2] | Natural Gas Intensity [MJ/m2] | Additional Fuel Intensity [MJ/m2] | District Cooling Intensity [MJ/m2] | District Heating Intensity [MJ/m2] | Water Intensity [m3/m2] | |
| Lighting | 11.52 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| HVAC | 218.61 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Other | 83.98 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total | 314.12 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Electricity [GJ] | Percent Electricity [%] | |
| Fuel-Fired Power Generation | 0.000 | 0.00 |
| High Temperature Geothermal* | 0.000 | 0.00 |
| Photovoltaic Power | 0.000 | 0.00 |
| Wind Power | 0.000 | 0.00 |
| Power Conversion | 0.000 | 0.00 |
| Net Decrease in On-Site Storage | 0.000 | 0.00 |
| Total On-Site Electric Sources | 0.000 | 0.00 |
| Electricity Coming From Utility | 311.201 | 100.00 |
| Surplus Electricity Going To Utility | 0.000 | 0.00 |
| Net Electricity From Utility | 311.201 | 100.00 |
| Total On-Site and Utility Electric Sources | 311.201 | 100.00 |
| Total Electricity End Uses | 311.201 | 100.00 |
| Heat [GJ] | Percent Heat [%] | |
| Water-Side Heat Recovery | 0.00 | |
| Air to Air Heat Recovery for Cooling | 0.00 | |
| Air to Air Heat Recovery for Heating | 0.00 | |
| High-Temperature Geothermal* | 0.00 | |
| Solar Water Thermal | 0.00 | |
| Solar Air Thermal | 0.00 | |
| Total On-Site Thermal Sources | 0.00 |
| Water [m3] | Percent Water [%] | |
| Rainwater Collection | 0.00 | - |
| Condensate Collection | 0.00 | - |
| Groundwater Well | 0.00 | - |
| Total On Site Water Sources | 0.00 | - |
| - | - | - |
| Initial Storage | 0.00 | - |
| Final Storage | 0.00 | - |
| Change in Storage | 0.00 | - |
| - | - | - |
| Water Supplied by Utility | 0.00 | - |
| - | - | - |
| Total On Site, Change in Storage, and Utility Water Sources | 0.00 | - |
| Total Water End Uses | 0.00 | - |
| Degrees [deltaC] | |
| Tolerance for Zone Heating Setpoint Not Met Time | 0.20 |
| Tolerance for Zone Cooling Setpoint Not Met Time | 0.20 |
| Facility [Hours] | |
| Time Setpoint Not Met During Occupied Heating | 907.50 |
| Time Setpoint Not Met During Occupied Cooling | 0.00 |
| Time Not Comfortable Based on Simple ASHRAE 55-2004 | 6372.33 |
Table of Contents
TopLife-Cycle Cost Report
| Entire Facility |Report: Input Verification and Results Summary
For: Entire Facility
Timestamp: 2018-06-04 13:40:50
General| Value | |
| Program Version and Build | EnergyPlus, Version 8.9.0-40101eaafd, YMD=2018.06.04 13:40 |
| RunPeriod | RUN PERIOD 1 |
| Weather File | Anchorage Elmendorf AK USA TMY3 WMO#=702720 |
| Latitude [deg] | 61.25 |
| Longitude [deg] | -149.8 |
| Elevation [m] | 59.00 |
| Time Zone | -9.0 |
| North Axis Angle [deg] | 0.00 |
| Rotation for Appendix G [deg] | 0.00 |
| Hours Simulated [hrs] | 8760.00 |
| Total | North (315 to 45 deg) | East (45 to 135 deg) | South (135 to 225 deg) | West (225 to 315 deg) | |
| Gross Wall Area [m2] | 1014.78 | 295.85 | 211.54 | 295.85 | 211.54 |
| Above Ground Wall Area [m2] | 1014.78 | 295.85 | 211.54 | 295.85 | 211.54 |
| Window Opening Area [m2] | 135.80 | 38.65 | 52.45 | 6.69 | 38.01 |
| Gross Window-Wall Ratio [%] | 13.38 | 13.07 | 24.79 | 2.26 | 17.97 |
| Above Ground Window-Wall Ratio [%] | 13.38 | 13.07 | 24.79 | 2.26 | 17.97 |
| Total | North (315 to 45 deg) | East (45 to 135 deg) | South (135 to 225 deg) | West (225 to 315 deg) | |
| Gross Wall Area [m2] | 1014.78 | 295.85 | 211.54 | 295.85 | 211.54 |
| Above Ground Wall Area [m2] | 1014.78 | 295.85 | 211.54 | 295.85 | 211.54 |
| Window Opening Area [m2] | 135.80 | 38.65 | 52.45 | 6.69 | 38.01 |
| Gross Window-Wall Ratio [%] | 13.38 | 13.07 | 24.79 | 2.26 | 17.97 |
| Above Ground Window-Wall Ratio [%] | 13.38 | 13.07 | 24.79 | 2.26 | 17.97 |
| Total | |
| Gross Roof Area [m2] | 330.24 |
| Skylight Area [m2] | 0.00 |
| Skylight-Roof Ratio [%] | 0.00 |
| Area [m2] | Conditioned (Y/N) | Part of Total Floor Area (Y/N) | Volume [m3] | Multipliers | Above Ground Gross Wall Area [m2] | Underground Gross Wall Area [m2] | Window Glass Area [m2] | Opening Area [m2] | Lighting [W/m2] | People [m2 per person] | Plug and Process [W/m2] | |
| 01_A1 | 57.60 | Yes | Yes | 193.12 | 1.00 | 56.55 | 0.00 | 6.31 | 6.31 | 4.1269 | 37.16 | 87.2678 |
| 01_A2 | 62.25 | Yes | Yes | 208.70 | 1.00 | 85.84 | 0.00 | 6.83 | 6.83 | 3.7286 | 40.16 | 80.7553 |
| 01_B2 | 96.77 | Yes | Yes | 324.46 | 1.00 | 99.13 | 0.00 | 13.20 | 13.20 | 3.2604 | 39.18 | 56.0447 |
| 01_C1 | 113.62 | Yes | Yes | 380.95 | 1.00 | 96.74 | 0.00 | 14.63 | 14.63 | 3.0849 | 33.52 | 49.6765 |
| 02_A1 | 57.60 | Yes | Yes | 193.12 | 1.00 | 56.55 | 0.00 | 6.79 | 6.79 | 4.1269 | 37.16 | 87.2678 |
| 02_A2 | 62.25 | Yes | Yes | 208.70 | 1.00 | 85.84 | 0.00 | 7.56 | 7.56 | 3.7286 | 40.16 | 80.7553 |
| 02_B2 | 96.77 | Yes | Yes | 324.46 | 1.00 | 99.13 | 0.00 | 15.49 | 15.49 | 3.2604 | 39.18 | 56.0447 |
| 02_C1 | 113.62 | Yes | Yes | 380.95 | 1.00 | 96.74 | 0.00 | 17.58 | 17.58 | 3.0849 | 33.52 | 49.6765 |
| 03_A1 | 57.60 | Yes | Yes | 193.12 | 1.00 | 56.55 | 0.00 | 6.79 | 6.79 | 4.1269 | 37.16 | 87.2678 |
| 03_A2 | 62.25 | Yes | Yes | 208.70 | 1.00 | 85.84 | 0.00 | 7.56 | 7.56 | 3.7286 | 40.16 | 80.7553 |
| 03_B2 | 96.77 | Yes | Yes | 324.46 | 1.00 | 99.13 | 0.00 | 15.49 | 15.49 | 3.2604 | 39.18 | 56.0447 |
| 03_C1 | 113.62 | Yes | Yes | 380.95 | 1.00 | 96.74 | 0.00 | 17.58 | 17.58 | 3.0849 | 33.52 | 49.6765 |
| Total | 990.72 | 3321.68 | 1014.78 | 0.00 | 135.80 | 135.80 | 3.4394 | 36.86 | 63.9571 | |||
| Conditioned Total | 990.72 | 3321.68 | 1014.78 | 0.00 | 135.80 | 135.80 | 3.4394 | 36.86 | 63.9571 | |||
| Unconditioned Total | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | ||||||
| Not Part of Total | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
Report: Demand End Use Components Summary
For: Entire Facility
Timestamp: 2018-06-04 13:40:50
End Uses| Electricity [W] | Natural Gas [W] | Propane [W] | District Cooling [W] | Steam [W] | Water [m3/s] | |
| Time of Peak | 16-DEC-19:10 | - | - | - | - | - |
| Heating | 28621.54 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 1090.40 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 3863.90 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 2010.80 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total End Uses | 35586.64 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Subcategory | Electricity [W] | Natural Gas [W] | Propane [W] | District Cooling [W] | Steam [W] | Water [m3/s] | |
| Heating | General | 28621.54 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | General | 1090.40 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | General | 3863.90 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | General | 2010.80 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
Report: Source Energy End Use Components Summary
For: Entire Facility
Timestamp: 2018-06-04 13:40:50
Values gathered over 8760.00 hours| Source Electricity [GJ] | Source Natural Gas [GJ] | Source Additional Fuel [GJ] | Source District Cooling [GJ] | Source District Heating [GJ] | |
| Heating | 454.93 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | 30.14 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 36.16 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 263.51 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 200.83 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total Source Energy End Use Components | 985.57 | 0.00 | 0.00 | 0.00 | 0.00 |
| Source Electricity [MJ/m2] | Source Natural Gas [MJ/m2] | Source Additional Fuel [MJ/m2] | Source District Cooling [MJ/m2] | Source District Heating [MJ/m2] | |
| Heating | 459.20 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | 30.42 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 36.50 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 265.98 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 202.71 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total Source Energy End Use Components | 994.81 | 0.00 | 0.00 | 0.00 | 0.00 |
| Source Electricity [MJ/m2] | Source Natural Gas [MJ/m2] | Source Additional Fuel [MJ/m2] | Source District Cooling [MJ/m2] | Source District Heating [MJ/m2] | |
| Heating | 459.20 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | 30.42 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 36.50 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 265.98 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 202.71 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total Source Energy End Use Components | 994.81 | 0.00 | 0.00 | 0.00 | 0.00 |
Report: Component Sizing Summary
For: Entire Facility
Timestamp: 2018-06-04 13:40:50
AirTerminal:SingleDuct:Uncontrolled| Design Size Maximum Air Flow Rate [m3/s] | |
| DIFFUSER | 0.195785 |
| DIFFUSER 1 | 0.324700 |
| DIFFUSER 2 | 0.257075 |
| DIFFUSER 3 | 0.192704 |
| DIFFUSER 4 | 0.324700 |
| DIFFUSER 5 | 0.372097 |
| DIFFUSER 11 | 0.423900 |
| DIFFUSER 6 | 0.371155 |
| DIFFUSER 7 | 0.324700 |
| DIFFUSER 8 | 0.388147 |
| DIFFUSER 9 | 0.453092 |
| DIFFUSER 10 | 0.393552 |
| Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | Sum of Air Terminal Maximum Flow Rates [m3/s] | Adjusted Heating Design Air Flow Rate [m3/s] | Adjusted Cooling Design Air Flow Rate [m3/s] | Adjusted Main Design Air Flow Rate [m3/s] | User Heating Air Flow Ratio [] | Calculated Heating Air Flow Ratio [] | Design Supply Air Flow Rate [m3/s] | |
| AIR LOOP HVAC 1 | 0.195785 | 0.195785 | 0.195785 | 0.195785 | 0.195785 | 0.195785 | 0.300000 | 1.00 | 0.195785 |
| AIR LOOP HVAC 10 | 0.388147 | 0.388147 | 0.388147 | 0.388147 | 0.388147 | 0.388147 | 0.300000 | 1.00 | 0.388147 |
| AIR LOOP HVAC 11 | 0.453092 | 0.453092 | 0.453092 | 0.453092 | 0.453092 | 0.453092 | 0.300000 | 1.000000 | 0.453092 |
| AIR LOOP HVAC 12 | 0.393552 | 0.393552 | 0.393552 | 0.393552 | 0.393552 | 0.393552 | 0.300000 | 1.00 | 0.393552 |
| AIR LOOP HVAC 2 | 0.324700 | 0.324700 | 0.324700 | 0.324700 | 0.324700 | 0.324700 | 0.300000 | 1.00 | 0.324700 |
| AIR LOOP HVAC 3 | 0.257075 | 0.257075 | 0.257075 | 0.257075 | 0.257075 | 0.257075 | 0.300000 | 1.00 | 0.257075 |
| AIR LOOP HVAC 4 | 0.192704 | 0.192704 | 0.192704 | 0.192704 | 0.192704 | 0.192704 | 0.300000 | 1.00 | 0.192704 |
| AIR LOOP HVAC 5 | 0.324700 | 0.324700 | 0.324700 | 0.324700 | 0.324700 | 0.324700 | 0.300000 | 1.00 | 0.324700 |
| AIR LOOP HVAC 6 | 0.372097 | 0.372097 | 0.372097 | 0.372097 | 0.372097 | 0.372097 | 0.300000 | 1.00 | 0.372097 |
| AIR LOOP HVAC 7 | 0.423900 | 0.423900 | 0.423900 | 0.423900 | 0.423900 | 0.423900 | 0.300000 | 1.00 | 0.423900 |
| AIR LOOP HVAC 8 | 0.371155 | 0.371155 | 0.371155 | 0.371155 | 0.371155 | 0.371155 | 0.300000 | 1.000000 | 0.371155 |
| AIR LOOP HVAC 9 | 0.324700 | 0.324700 | 0.324700 | 0.324700 | 0.324700 | 0.324700 | 0.300000 | 1.00 | 0.324700 |
| Maximum Outdoor Air Flow Rate [m3/s] | Minimum Outdoor Air Flow Rate [m3/s] | |
| OUTDOOR AIR CONTROLLER | 0.195785 | 0.023597 |
| OUTDOOR AIR CONTROLLER 9 | 0.388147 | 0.023597 |
| OUTDOOR AIR CONTROLLER 10 | 0.453092 | 0.023597 |
| OUTDOOR AIR CONTROLLER 11 | 0.393552 | 0.023597 |
| OUTDOOR AIR CONTROLLER 1 | 0.324700 | 0.023597 |
| OUTDOOR AIR CONTROLLER 2 | 0.257075 | 0.023597 |
| OUTDOOR AIR CONTROLLER 3 | 0.192704 | 0.023597 |
| OUTDOOR AIR CONTROLLER 4 | 0.324700 | 0.023597 |
| OUTDOOR AIR CONTROLLER 5 | 0.372097 | 0.023597 |
| OUTDOOR AIR CONTROLLER 6 | 0.423900 | 0.023597 |
| OUTDOOR AIR CONTROLLER 7 | 0.371155 | 0.023597 |
| OUTDOOR AIR CONTROLLER 8 | 0.324700 | 0.023597 |
| Design Size Supply Air Flow Rate [m3/s] | Design Size Heating Supply Air Flow Rate [m3/s] | Design Size Cooling Supply Air Flow Rate [m3/s] | Design Size No Load Supply Air Flow Rate [m3/s] | Design Size Nominal Cooling Capacity [W] | Design Size Nominal Heating Capacity [W] | Design Size Maximum Supply Air Temperature [C] | User-Specified Maximum Supply Air Temperature [C] | Design Size Supplemental Heating Coil Nominal Capacity [W] | User-Specified Supplemental Heating Coil Nominal Capacity [W] | Fraction of Supply Air Flow That Goes Through the Controlling Zone | |
| UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT | 0.195785 | 0.195785 | 0.195785 | 0.195785 | 4861.80 | 4861.80 | 16.70 | 80.00 | 4861.80 | 4861.80 | 1.00 |
| UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 9 | 0.388147 | 0.388147 | 0.388147 | 0.388147 | 9638.61 | 9638.61 | 16.70 | 80.00 | 9638.61 | 9638.61 | 1.00 |
| UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 10 | 0.453092 | 0.453092 | 0.453092 | 0.453092 | 11251.35 | 11251.35 | 16.70 | 80.00 | 11251.35 | 11251.35 | 1.00 |
| UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 11 | 0.393552 | 0.393552 | 0.393552 | 0.393552 | 9772.83 | 9772.83 | 16.70 | 80.00 | 9772.83 | 9772.83 | 1.00 |
| UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 1 | 0.324700 | 0.324700 | 0.324700 | 0.324700 | 8063.07 | 8063.07 | 16.70 | 80.00 | 8063.07 | 8063.07 | 1.00 |
| UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 2 | 0.257075 | 0.257075 | 0.257075 | 0.257075 | 6383.80 | 6383.80 | 16.70 | 80.00 | 6383.80 | 6383.80 | 1.00 |
| UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 3 | 0.192704 | 0.192704 | 0.192704 | 0.192704 | 4785.29 | 4785.29 | 16.70 | 80.00 | 4785.29 | 4785.29 | 1.00 |
| UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 4 | 0.324700 | 0.324700 | 0.324700 | 0.324700 | 8063.07 | 8063.07 | 16.70 | 80.00 | 8063.07 | 8063.07 | 1.00 |
| UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 5 | 0.372097 | 0.372097 | 0.372097 | 0.372097 | 9240.05 | 9240.05 | 16.70 | 80.00 | 9240.05 | 9240.05 | 1.00 |
| UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 6 | 0.423900 | 0.423900 | 0.423900 | 0.423900 | 10526.44 | 10526.44 | 16.70 | 80.00 | 10526.44 | 10526.44 | 1.00 |
| UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 7 | 0.371155 | 0.371155 | 0.371155 | 0.371155 | 9216.66 | 9216.66 | 16.70 | 80.00 | 9216.66 | 9216.66 | 1.00 |
| UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 8 | 0.324700 | 0.324700 | 0.324700 | 0.324700 | 8063.07 | 8063.07 | 16.70 | 80.00 | 8063.07 | 8063.07 | 1.00 |
| Design Size Maximum Flow Rate [m3/s] | |
| FAN ON OFF 5 | 0.195785 |
| FAN ON OFF 14 | 0.388147 |
| FAN ON OFF 15 | 0.453092 |
| FAN ON OFF 16 | 0.393552 |
| FAN ON OFF 6 | 0.324700 |
| FAN ON OFF 7 | 0.257075 |
| FAN ON OFF 8 | 0.192704 |
| FAN ON OFF 9 | 0.324700 |
| FAN ON OFF 10 | 0.372097 |
| FAN ON OFF 11 | 0.423900 |
| FAN ON OFF 12 | 0.371155 |
| FAN ON OFF 13 | 0.324700 |
| Design Size Rated Air Flow Rate [m3/s] | Design Size Gross Rated Total Cooling Capacity [W] | Design Size Gross Rated Sensible Heat Ratio | |
| 1 SPD DX CLG COIL 4 | 0.195785 | 4861.80 | 0.698083 |
| 1 SPD DX CLG COIL 13 | 0.388147 | 9638.61 | 0.698083 |
| 1 SPD DX CLG COIL 14 | 0.453092 | 11251.35 | 0.698083 |
| 1 SPD DX CLG COIL 15 | 0.393552 | 9772.83 | 0.698083 |
| 1 SPD DX CLG COIL 5 | 0.324700 | 8063.07 | 0.698083 |
| 1 SPD DX CLG COIL 6 | 0.257075 | 6383.80 | 0.698083 |
| 1 SPD DX CLG COIL 7 | 0.192704 | 4785.29 | 0.698083 |
| 1 SPD DX CLG COIL 8 | 0.324700 | 8063.07 | 0.698083 |
| 1 SPD DX CLG COIL 9 | 0.372097 | 9240.05 | 0.698083 |
| 1 SPD DX CLG COIL 10 | 0.423900 | 10526.44 | 0.698083 |
| 1 SPD DX CLG COIL 11 | 0.371155 | 9216.66 | 0.698083 |
| 1 SPD DX CLG COIL 12 | 0.324700 | 8063.07 | 0.698083 |
| Design Size Rated Air Flow Rate [m3/s] | Design Size Gross Rated Heating Capacity [W] | Design Size Resistive Defrost Heater Capacity [W] | User-Specified Resistive Defrost Heater Capacity [W] | |
| 1 SPD DX HTG COIL 3 | 0.195785 | 4861.80 | 4861.80 | 2000.00 |
| 1 SPD DX HTG COIL 12 | 0.388147 | 9638.61 | 9638.61 | 2000.00 |
| 1 SPD DX HTG COIL 13 | 0.453092 | 11251.35 | 11251.35 | 2000.00 |
| 1 SPD DX HTG COIL 14 | 0.393552 | 9772.83 | 9772.83 | 2000.00 |
| 1 SPD DX HTG COIL 4 | 0.324700 | 8063.07 | 8063.07 | 2000.00 |
| 1 SPD DX HTG COIL 5 | 0.257075 | 6383.80 | 6383.80 | 2000.00 |
| 1 SPD DX HTG COIL 6 | 0.192704 | 4785.29 | 4785.29 | 2000.00 |
| 1 SPD DX HTG COIL 7 | 0.324700 | 8063.07 | 8063.07 | 2000.00 |
| 1 SPD DX HTG COIL 8 | 0.372097 | 9240.05 | 9240.05 | 2000.00 |
| 1 SPD DX HTG COIL 9 | 0.423900 | 10526.44 | 10526.44 | 2000.00 |
| 1 SPD DX HTG COIL 10 | 0.371155 | 9216.66 | 9216.66 | 2000.00 |
| 1 SPD DX HTG COIL 11 | 0.324700 | 8063.07 | 8063.07 | 2000.00 |
| Design Size Nominal Capacity [W] | |
| ELEC HTG COIL 5 | 4861.80 |
| ELEC HTG COIL 14 | 9638.61 |
| ELEC HTG COIL 15 | 11251.35 |
| ELEC HTG COIL 16 | 9772.83 |
| ELEC HTG COIL 6 | 8063.07 |
| ELEC HTG COIL 7 | 6383.80 |
| ELEC HTG COIL 8 | 4785.29 |
| ELEC HTG COIL 9 | 8063.07 |
| ELEC HTG COIL 10 | 9240.05 |
| ELEC HTG COIL 11 | 10526.44 |
| ELEC HTG COIL 12 | 9216.66 |
| ELEC HTG COIL 13 | 8063.07 |
Report: Surface Shadowing Summary
For: Entire Facility
Timestamp: 2018-06-04 13:40:50
Surfaces (Walls, Roofs, etc) that may be Shadowed by Other Surfaces| Possible Shadow Receivers | |
| SHADING SURFACE 4 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 7 | Mir-SHADING SURFACE 1 | SURFACE 50 | SURFACE 69 | SURFACE 71 | SURFACE 53 | SURFACE 56 | SURFACE 59 | SURFACE 86 | SURFACE 105 | SURFACE 107 | SURFACE 89 | SURFACE 92 | SURFACE 95 | |
| SHADING SURFACE 2 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 7 | Mir-SHADING SURFACE 1 | SURFACE 38 | SURFACE 42 | SURFACE 43 | SURFACE 66 | SURFACE 69 | SURFACE 70 | SURFACE 71 | SURFACE 56 | SURFACE 58 | SURFACE 59 | SURFACE 74 | SURFACE 78 | SURFACE 79 | SURFACE 102 | SURFACE 105 | SURFACE 106 | SURFACE 107 | SURFACE 92 | SURFACE 94 | SURFACE 95 | |
| SHADING SURFACE 8 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 7 | Mir-SHADING SURFACE 1 | SURFACE 48 | SURFACE 38 | SURFACE 39 | SURFACE 42 | SURFACE 65 | SURFACE 66 | SURFACE 67 | SURFACE 70 | SURFACE 54 | SURFACE 58 | SURFACE 61 | SURFACE 84 | SURFACE 74 | SURFACE 75 | SURFACE 78 | SURFACE 101 | SURFACE 102 | SURFACE 103 | SURFACE 106 | SURFACE 90 | SURFACE 94 | SURFACE 97 | |
| SHADING SURFACE 6 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 7 | Mir-SHADING SURFACE 1 | SURFACE 48 | SURFACE 50 | SURFACE 39 | SURFACE 65 | SURFACE 53 | SURFACE 54 | SURFACE 84 | SURFACE 86 | SURFACE 75 | SURFACE 101 | SURFACE 89 | SURFACE 90 | |
| SHADING SURFACE 5 | Mir-SHADING SURFACE 1 | SURFACE 86 | SURFACE 105 | SURFACE 107 | SURFACE 89 | SURFACE 92 | SURFACE 95 | |
| SHADING SURFACE 3 | Mir-SHADING SURFACE 1 | SURFACE 74 | SURFACE 78 | SURFACE 79 | SURFACE 102 | SURFACE 105 | SURFACE 106 | SURFACE 107 | SURFACE 92 | SURFACE 94 | SURFACE 95 | |
| SHADING SURFACE 9 | Mir-SHADING SURFACE 1 | SURFACE 84 | SURFACE 74 | SURFACE 75 | SURFACE 78 | SURFACE 101 | SURFACE 102 | SURFACE 103 | SURFACE 106 | SURFACE 90 | SURFACE 94 | SURFACE 97 | |
| SHADING SURFACE 7 | Mir-SHADING SURFACE 1 | SURFACE 84 | SURFACE 86 | SURFACE 75 | SURFACE 101 | SURFACE 89 | SURFACE 90 | |
| SURFACE 12 | Mir-SHADING SURFACE 8 | Mir-SHADING SURFACE 6 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 7 | Mir-SHADING SURFACE 1 | SURFACE 33 | SURFACE 35 | SURFACE 22 | SURFACE 23 | SURFACE 69 | SURFACE 71 | SURFACE 58 | SURFACE 59 | SURFACE 105 | SURFACE 107 | SURFACE 94 | SURFACE 95 | |
| SURFACE 14 | Mir-SHADING SURFACE 4 | Mir-SHADING SURFACE 6 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 7 | SURFACE 20 | SURFACE 56 | SURFACE 92 | |
| SURFACE 2 | Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 8 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 9 | SURFACE 35 | SURFACE 71 | SURFACE 107 | |
| SURFACE 3 | Mir-SHADING SURFACE 8 | Mir-SHADING SURFACE 6 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 7 | Mir-SHADING SURFACE 1 | SURFACE 30 | SURFACE 33 | SURFACE 35 | SURFACE 22 | SURFACE 23 | SURFACE 66 | SURFACE 69 | SURFACE 71 | SURFACE 58 | SURFACE 59 | SURFACE 102 | SURFACE 105 | SURFACE 107 | SURFACE 94 | SURFACE 95 | |
| SURFACE 6 | Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 8 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 9 | SURFACE 7 | SURFACE 33 | SURFACE 35 | SURFACE 43 | SURFACE 69 | SURFACE 71 | SURFACE 79 | SURFACE 105 | SURFACE 107 | |
| SURFACE 7 | Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 3 | SURFACE 6 | SURFACE 42 | SURFACE 78 | |
| SURFACE 29 | Mir-SHADING SURFACE 8 | Mir-SHADING SURFACE 6 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 7 | SURFACE 30 | SURFACE 66 | SURFACE 102 | |
| SURFACE 30 | Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 8 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 1 | SURFACE 3 | SURFACE 29 | SURFACE 39 | SURFACE 65 | SURFACE 75 | SURFACE 101 | |
| SURFACE 31 | Mir-SHADING SURFACE 8 | Mir-SHADING SURFACE 9 | |
| SURFACE 33 | Mir-SHADING SURFACE 4 | Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 1 | SURFACE 12 | SURFACE 3 | SURFACE 6 | SURFACE 22 | SURFACE 48 | SURFACE 39 | SURFACE 42 | SURFACE 58 | SURFACE 84 | SURFACE 75 | SURFACE 78 | SURFACE 94 | |
| SURFACE 34 | Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 8 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 9 | SURFACE 35 | SURFACE 71 | SURFACE 107 | |
| SURFACE 35 | Mir-SHADING SURFACE 4 | Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 1 | SURFACE 12 | SURFACE 2 | SURFACE 3 | SURFACE 6 | SURFACE 34 | SURFACE 22 | SURFACE 48 | SURFACE 38 | SURFACE 39 | SURFACE 42 | SURFACE 70 | SURFACE 58 | SURFACE 84 | SURFACE 74 | SURFACE 75 | SURFACE 78 | SURFACE 106 | SURFACE 94 | |
| SURFACE 17 | Mir-SHADING SURFACE 4 | Mir-SHADING SURFACE 6 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 7 | SURFACE 18 | SURFACE 54 | SURFACE 90 | |
| SURFACE 18 | Mir-SHADING SURFACE 8 | Mir-SHADING SURFACE 6 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 7 | SURFACE 17 | SURFACE 53 | SURFACE 89 | |
| SURFACE 20 | Mir-SHADING SURFACE 4 | Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 3 | SURFACE 14 | SURFACE 50 | SURFACE 86 | |
| SURFACE 22 | Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 8 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 1 | SURFACE 12 | SURFACE 3 | SURFACE 33 | SURFACE 35 | SURFACE 23 | SURFACE 48 | SURFACE 39 | SURFACE 69 | SURFACE 71 | SURFACE 59 | SURFACE 84 | SURFACE 75 | SURFACE 105 | SURFACE 107 | SURFACE 95 | |
| SURFACE 23 | Mir-SHADING SURFACE 4 | Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 1 | SURFACE 12 | SURFACE 3 | SURFACE 22 | SURFACE 48 | SURFACE 39 | SURFACE 58 | SURFACE 84 | SURFACE 75 | SURFACE 94 | |
| SURFACE 25 | Mir-SHADING SURFACE 8 | Mir-SHADING SURFACE 9 | |
| SURFACE 48 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 7 | Mir-SHADING SURFACE 1 | SURFACE 69 | SURFACE 71 | SURFACE 58 | SURFACE 59 | SURFACE 105 | SURFACE 107 | SURFACE 94 | SURFACE 95 | |
| SURFACE 50 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 7 | SURFACE 56 | SURFACE 92 | |
| SURFACE 38 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 9 | SURFACE 71 | SURFACE 107 | |
| SURFACE 39 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 7 | Mir-SHADING SURFACE 1 | SURFACE 66 | SURFACE 69 | SURFACE 71 | SURFACE 58 | SURFACE 59 | SURFACE 102 | SURFACE 105 | SURFACE 107 | SURFACE 94 | SURFACE 95 | |
| SURFACE 42 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 9 | SURFACE 43 | SURFACE 69 | SURFACE 71 | SURFACE 79 | SURFACE 105 | SURFACE 107 | |
| SURFACE 43 | Mir-SHADING SURFACE 3 | SURFACE 42 | SURFACE 78 | |
| SURFACE 65 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 7 | SURFACE 66 | SURFACE 102 | |
| SURFACE 66 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 1 | SURFACE 39 | SURFACE 65 | SURFACE 75 | SURFACE 101 | |
| SURFACE 67 | Mir-SHADING SURFACE 9 | |
| SURFACE 69 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 1 | SURFACE 48 | SURFACE 39 | SURFACE 42 | SURFACE 58 | SURFACE 84 | SURFACE 75 | SURFACE 78 | SURFACE 94 | |
| SURFACE 70 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 9 | SURFACE 71 | SURFACE 107 | |
| SURFACE 71 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 1 | SURFACE 48 | SURFACE 38 | SURFACE 39 | SURFACE 42 | SURFACE 70 | SURFACE 58 | SURFACE 84 | SURFACE 74 | SURFACE 75 | SURFACE 78 | SURFACE 106 | SURFACE 94 | |
| SURFACE 53 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 7 | SURFACE 54 | SURFACE 90 | |
| SURFACE 54 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 7 | SURFACE 53 | SURFACE 89 | |
| SURFACE 56 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 3 | SURFACE 50 | SURFACE 86 | |
| SURFACE 58 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 1 | SURFACE 48 | SURFACE 39 | SURFACE 69 | SURFACE 71 | SURFACE 59 | SURFACE 84 | SURFACE 75 | SURFACE 105 | SURFACE 107 | SURFACE 95 | |
| SURFACE 59 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 1 | SURFACE 48 | SURFACE 39 | SURFACE 58 | SURFACE 84 | SURFACE 75 | SURFACE 94 | |
| SURFACE 61 | Mir-SHADING SURFACE 9 | |
| SURFACE 84 | Mir-SHADING SURFACE 1 | SURFACE 105 | SURFACE 107 | SURFACE 94 | SURFACE 95 | |
| SURFACE 86 | SURFACE 92 | |
| SURFACE 74 | SURFACE 107 | |
| SURFACE 75 | Mir-SHADING SURFACE 1 | SURFACE 102 | SURFACE 105 | SURFACE 107 | SURFACE 94 | SURFACE 95 | |
| SURFACE 78 | SURFACE 79 | SURFACE 105 | SURFACE 107 | |
| SURFACE 79 | SURFACE 78 | |
| SURFACE 101 | SURFACE 102 | |
| SURFACE 102 | Mir-SHADING SURFACE 1 | SURFACE 75 | SURFACE 101 | |
| SURFACE 105 | Mir-SHADING SURFACE 1 | SURFACE 84 | SURFACE 75 | SURFACE 78 | SURFACE 94 | |
| SURFACE 106 | SURFACE 107 | |
| SURFACE 107 | Mir-SHADING SURFACE 1 | SURFACE 84 | SURFACE 74 | SURFACE 75 | SURFACE 78 | SURFACE 106 | SURFACE 94 | |
| SURFACE 89 | SURFACE 90 | |
| SURFACE 90 | SURFACE 89 | |
| SURFACE 92 | SURFACE 86 | |
| SURFACE 94 | Mir-SHADING SURFACE 1 | SURFACE 84 | SURFACE 75 | SURFACE 105 | SURFACE 107 | SURFACE 95 | |
| SURFACE 95 | Mir-SHADING SURFACE 1 | SURFACE 84 | SURFACE 75 | SURFACE 94 | |
| Possible Shadow Receivers | |
| SURFACE 12 | SUB SURFACE 63 | |
| SURFACE 14 | SUB SURFACE 51 | SUB SURFACE 54 | |
| SURFACE 2 | SUB SURFACE 42 | |
| SURFACE 3 | SUB SURFACE 66 | |
| SURFACE 6 | SUB SURFACE 48 | |
| SURFACE 7 | SUB SURFACE 45 | |
| SURFACE 28 | SUB SURFACE 37 | |
| SURFACE 29 | SUB SURFACE 30 | |
| SURFACE 31 | SUB SURFACE 26 | SUB SURFACE 27 | |
| SURFACE 33 | SUB SURFACE 57 | |
| SURFACE 34 | SUB SURFACE 38 | SUB SURFACE 39 | |
| SURFACE 17 | SUB SURFACE 6 | |
| SURFACE 18 | SUB SURFACE 3 | |
| SURFACE 19 | SUB SURFACE 13 | SUB SURFACE 14 | SUB SURFACE 15 | |
| SURFACE 23 | SUB SURFACE 60 | |
| SURFACE 25 | SUB SURFACE 18 | SUB SURFACE 19 | |
| SURFACE 48 | SUB SURFACE 62 | |
| SURFACE 50 | SUB SURFACE 50 | SUB SURFACE 53 | |
| SURFACE 38 | SUB SURFACE 41 | |
| SURFACE 39 | SUB SURFACE 65 | |
| SURFACE 42 | SUB SURFACE 47 | |
| SURFACE 43 | SUB SURFACE 44 | |
| SURFACE 64 | SUB SURFACE 34 | |
| SURFACE 65 | SUB SURFACE 29 | |
| SURFACE 67 | SUB SURFACE 24 | SUB SURFACE 25 | |
| SURFACE 69 | SUB SURFACE 56 | |
| SURFACE 70 | SUB SURFACE 35 | SUB SURFACE 36 | |
| SURFACE 53 | SUB SURFACE 5 | |
| SURFACE 54 | SUB SURFACE 2 | |
| SURFACE 55 | SUB SURFACE 10 | SUB SURFACE 11 | SUB SURFACE 12 | |
| SURFACE 59 | SUB SURFACE 59 | |
| SURFACE 61 | SUB SURFACE 17 | SUB SURFACE 20 | |
| SURFACE 84 | SUB SURFACE 61 | |
| SURFACE 86 | SUB SURFACE 49 | SUB SURFACE 52 | |
| SURFACE 74 | SUB SURFACE 40 | |
| SURFACE 75 | SUB SURFACE 64 | |
| SURFACE 78 | SUB SURFACE 46 | |
| SURFACE 79 | SUB SURFACE 43 | |
| SURFACE 100 | SUB SURFACE 33 | |
| SURFACE 101 | SUB SURFACE 28 | |
| SURFACE 103 | SUB SURFACE 22 | SUB SURFACE 23 | |
| SURFACE 105 | SUB SURFACE 55 | |
| SURFACE 106 | SUB SURFACE 31 | SUB SURFACE 32 | |
| SURFACE 89 | SUB SURFACE 4 | |
| SURFACE 90 | SUB SURFACE 1 | |
| SURFACE 91 | SUB SURFACE 7 | SUB SURFACE 8 | SUB SURFACE 9 | |
| SURFACE 95 | SUB SURFACE 58 | |
| SURFACE 97 | SUB SURFACE 16 | SUB SURFACE 21 | |
Report: Adaptive Comfort Summary
For: Entire Facility
Timestamp: 2018-06-04 13:40:50
Time Not Meeting the Adaptive Comfort Models during Occupied Hours| ASHRAE55 90% Acceptability Limits [Hours] | ASHRAE55 80% Acceptability Limits [Hours] | CEN15251 Category I Acceptability Limits [Hours] | CEN15251 Category II Acceptability Limits [Hours] | CEN15251 Category III Acceptability Limits [Hours] |
Report: Initialization Summary
For: Entire Facility
Timestamp: 2018-06-04 13:40:50
Version| Version ID | |
| 1 | 8.9 |
| #TimeSteps | Minutes per TimeStep {minutes} | |
| 1 | 6 | 10 |
| Minimum System TimeStep {minutes} | Max HVAC Iterations | Minimum Plant Iterations | Maximum Plant Iterations | |
| 1 | 1 | 20 | 2 | 8 |
| Do Zone Sizing | Do System Sizing | Do Plant Sizing | Do Design Days | Do Weather Simulation | Do HVAC Sizing Simulation | |
| 1 | Yes | Yes | No | Yes | Yes | No |
| Tolerance for Time Heating Setpoint Not Met | Tolerance for Zone Cooling Setpoint Not Met Time | |
| 1 | 0.200 | 0.200 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | 18.00 | 18.00 | 18.00 | 18.00 | 18.00 | 18.00 | 18.00 | 18.00 | 18.00 | 18.00 | 18.00 | 18.00 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | -5.05 | -3.21 | 0.37 | 3.76 | 10.17 | 13.55 | 14.48 | 12.77 | 8.81 | 3.88 | -0.97 | -4.18 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 |
| Jan{dimensionless} | Feb{dimensionless} | Mar{dimensionless} | Apr{dimensionless} | May{dimensionless} | Jun{dimensionless} | Jul{dimensionless} | Aug{dimensionless} | Sep{dimensionless} | Oct{dimensionless} | Nov{dimensionless} | Dec{dimensionless} | |
| 1 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 |
| Normal | Daylighting {dimensionless} | |
| 1 | 1.000 | 1.000 |
| Jan{dimensionless} | Feb{dimensionless} | Mar{dimensionless} | Apr{dimensionless} | May{dimensionless} | Jun{dimensionless} | Jul{dimensionless} | Aug{dimensionless} | Sep{dimensionless} | Oct{dimensionless} | Nov{dimensionless} | Dec{dimensionless} | |
| 1 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 |
| Jan{dimensionless} | Feb{dimensionless} | Mar{dimensionless} | Apr{dimensionless} | May{dimensionless} | Jun{dimensionless} | Jul{dimensionless} | Aug{dimensionless} | Sep{dimensionless} | Oct{dimensionless} | Nov{dimensionless} | Dec{dimensionless} | |
| 1 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 |
| Wind Sensor Height Above Ground {m} | Wind Speed Profile Exponent {} | Wind Speed Profile Boundary Layer Thickness {m} | Air Temperature Sensor Height Above Ground {m} | Wind Speed Modifier Coefficient-Internal | Temperature Modifier Coefficient-Internal | |
| 1 | 10.000 | 0.140 | 270.000 | 1.500 | 1.586 | 9.750E-003 |
| Location Name | Latitude {N+/S- Deg} | Longitude {E+/W- Deg} | Time Zone Number {GMT+/-} | Elevation {m} | Standard Pressure at Elevation {Pa} | Standard RhoAir at Elevation | |
| 1 | Anchorage Elmendorf AK USA TMY3 WMO#=702720 | 61.25 | -149.80 | -9.00 | 59.00 | 100618 | 1.1959 |
| Building Name | North Axis {deg} | Terrain | Loads Convergence Tolerance Value | Temperature Convergence Tolerance Value | Solar Distribution | Maximum Number of Warmup Days | Minimum Number of Warmup Days | |
| 1 | KA2 A Flatroof Sample Building | 0.000 | Suburbs | 4.00000E-002 | 0.40000 | FullExterior | 25 | 6 |
| Algorithm {Simple TARP CeilingDiffuser AdaptiveConvectionAlgorithm} |
|
| 1 | TARP |
| Algorithm {SimpleCombined TARP MoWitt DOE-2 AdaptiveConvectionAlgorithm} |
|
| 1 | DOE-2 |
| Value {Anisotropic} | |
| 1 | Anisotropic |
| Value {ThirdOrderBackwardDifference AnalyticalSolution EulerMethod} |
|
| 1 | ThirdOrderBackwardDifference |
| Simulation {Yes/No} | Carbon Dioxide Concentration | |
| 1 | No | N/A |
| Simulation {Yes/No} | Generic Contaminant Concentration | |
| 1 | No | N/A |
| Enforce Mass Balance |
Adjust Zone Mixing |
Adjust Zone Infiltration {AddInfiltration AdjustInfiltration None} |
Infiltration Zones {MixingSourceZonesOnly AllZones} |
|
| 1 | No | N/A | N/A | N/A |
| Value {RegulaFalsi Bisection BisectionThenRegulaFalsi RegulaFalsiThenBisection} |
|
| 1 | RegulaFalsi |
| Wind Speed Profile Exponent {} | Wind Speed Profile Boundary Layer Thickness {m} | Air Temperature Gradient Coefficient {K/m} | |
| 1 | 0.220 | 370.000 | 6.500000E-003 |
| Starting Corner | Vertex Input Direction | Coordinate System | Daylight Reference Point Coordinate System | Rectangular (Simple) Surface Coordinate System | |
| 1 | UpperLeftCorner | Counterclockwise | RelativeCoordinateSystem | RelativeCoordinateSystem | RelativeToZoneOrigin |
| Value {CTF - ConductionTransferFunction EMPD - MoisturePenetrationDepthConductionTransferFunction CondFD - ConductionFiniteDifference HAMT - CombinedHeatAndMoistureFiniteElement} - Description |
Inside Surface Max Temperature Limit{C} |
Surface Convection Coefficient Lower Limit {W/m2-K} |
Surface Convection Coefficient Upper Limit {W/m2-K} |
|
| 1 | CTF - ConductionTransferFunction | 200 | 0.10 | 1000.0 |
| Number of Fixed Detached Shades | Number of Building Detached Shades | Number of Attached Shades | |
| 1 | 0 | 0 | 18 |
| Number of Zones | Number of Zone Surfaces | Number of SubSurfaces | |
| 1 | 12 | 174 | 66 |
| Zone Name | North Axis {deg} | Origin X-Coordinate {m} | Origin Y-Coordinate {m} | Origin Z-Coordinate {m} | Centroid X-Coordinate {m} | Centroid Y-Coordinate {m} | Centroid Z-Coordinate {m} | Type | Zone Multiplier | Zone List Multiplier | Minimum X {m} | Maximum X {m} | Minimum Y {m} | Maximum Y {m} | Minimum Z {m} | Maximum Z {m} | Ceiling Height {m} | Volume {m3} | Zone Inside Convection Algorithm {Simple-Detailed-CeilingDiffuser-TrombeWall} | Zone Outside Convection Algorithm {Simple-Detailed-Tarp-MoWitt-DOE-2-BLAST} | Floor Area {m2} | Exterior Gross Wall Area {m2} | Exterior Net Wall Area {m2} | Exterior Window Area {m2} | Number of Surfaces | Number of SubSurfaces | Number of Shading SubSurfaces | Part of Total Building Area | |
| 1 | 01_A1 | 0.0 | 19.48 | 4.60 | 0.00 | 15.54 | 8.26 | 1.68 | 1 | 1 | 1 | 11.61 | 19.48 | 4.60 | 11.91 | 0.00 | 3.35 | 3.35 | 193.12 | CeilingDiffuser | DOE-2 | 57.60 | 56.55 | 48.29 | 6.31 | 7 | 3 | 2 | Yes |
| 2 | 01_A2 | 0.0 | 2.46 | 8.26 | 0.00 | 6.52 | 8.32 | 1.68 | 1 | 1 | 1 | 2.46 | 11.61 | 4.60 | 11.91 | 0.00 | 3.35 | 3.35 | 208.70 | TARP | DOE-2 | 62.25 | 85.84 | 77.06 | 6.83 | 8 | 4 | 2 | Yes |
| 3 | 01_B2 | 0.0 | 2.16 | 21.21 | 0.00 | 6.09 | 21.12 | 1.68 | 1 | 1 | 1 | 2.16 | 11.61 | 14.96 | 25.63 | 0.00 | 3.35 | 3.35 | 324.46 | CeilingDiffuser | DOE-2 | 96.77 | 99.13 | 83.98 | 13.20 | 10 | 7 | 2 | Yes |
| 4 | 01_C1 | 0.0 | 18.92 | 25.63 | 1.26E-030 | 16.14 | 18.67 | 1.68 | 1 | 1 | 1 | 11.61 | 20.75 | 11.91 | 25.63 | 6.28E-031 | 3.35 | 3.35 | 380.95 | CeilingDiffuser | DOE-2 | 113.62 | 96.74 | 80.17 | 14.63 | 11 | 8 | 2 | Yes |
| 5 | 02_A1 | 0.0 | 19.48 | 4.60 | 3.35 | 15.54 | 8.26 | 5.03 | 1 | 1 | 1 | 11.61 | 19.48 | 4.60 | 11.91 | 3.35 | 6.71 | 3.35 | 193.12 | CeilingDiffuser | DOE-2 | 57.60 | 56.55 | 47.80 | 6.79 | 7 | 3 | 2 | Yes |
| 6 | 02_A2 | 0.0 | 2.46 | 8.26 | 3.35 | 6.52 | 8.32 | 5.03 | 1 | 1 | 1 | 2.46 | 11.61 | 4.60 | 11.91 | 3.35 | 6.71 | 3.35 | 208.70 | TARP | DOE-2 | 62.25 | 85.84 | 76.33 | 7.56 | 8 | 4 | 2 | Yes |
| 7 | 02_B2 | 0.0 | 2.16 | 21.21 | 3.35 | 6.09 | 21.12 | 5.03 | 1 | 1 | 1 | 2.16 | 11.61 | 14.96 | 25.63 | 3.35 | 6.71 | 3.35 | 324.46 | CeilingDiffuser | DOE-2 | 96.77 | 99.13 | 81.69 | 15.49 | 10 | 7 | 2 | Yes |
| 8 | 02_C1 | 0.0 | 18.92 | 25.63 | 3.35 | 16.14 | 18.67 | 5.03 | 1 | 1 | 1 | 11.61 | 20.75 | 11.91 | 25.63 | 3.35 | 6.71 | 3.35 | 380.95 | CeilingDiffuser | DOE-2 | 113.62 | 96.74 | 77.21 | 17.58 | 11 | 8 | 2 | Yes |
| 9 | 03_A1 | 0.0 | 19.48 | 4.60 | 6.71 | 15.54 | 8.26 | 8.38 | 1 | 1 | 1 | 11.61 | 19.48 | 4.60 | 11.91 | 6.71 | 10.06 | 3.35 | 193.12 | CeilingDiffuser | DOE-2 | 57.60 | 56.55 | 47.80 | 6.79 | 7 | 3 | 0 | Yes |
| 10 | 03_A2 | 0.0 | 2.46 | 8.26 | 6.71 | 6.52 | 8.32 | 8.38 | 1 | 1 | 1 | 2.46 | 11.61 | 4.60 | 11.91 | 6.71 | 10.06 | 3.35 | 208.70 | CeilingDiffuser | DOE-2 | 62.25 | 85.84 | 76.33 | 7.56 | 8 | 4 | 0 | Yes |
| 11 | 03_B2 | 0.0 | 2.16 | 21.21 | 6.71 | 6.09 | 21.12 | 8.38 | 1 | 1 | 1 | 2.16 | 11.61 | 14.96 | 25.63 | 6.71 | 10.06 | 3.35 | 324.46 | CeilingDiffuser | DOE-2 | 96.77 | 99.13 | 81.69 | 15.49 | 10 | 7 | 0 | Yes |
| 12 | 03_C1 | 0.0 | 18.92 | 25.63 | 6.71 | 16.14 | 18.67 | 8.38 | 1 | 1 | 1 | 11.61 | 20.75 | 11.91 | 25.63 | 6.71 | 10.06 | 3.35 | 380.95 | CeilingDiffuser | DOE-2 | 113.62 | 96.74 | 77.21 | 17.58 | 11 | 8 | 2 | Yes |
| Zone Name | Floor Area {m2} | # Occupants | Area per Occupant {m2/person} | Occupant per Area {person/m2} | Interior Lighting {W/m2} | Electric Load {W/m2} | Gas Load {W/m2} | Other Load {W/m2} | Hot Water Eq {W/m2} | Steam Equipment {W/m2} | Sum Loads per Area {W/m2} | Outdoor Controlled Baseboard Heat | |
| 1 | 01_A1 | 57.60 | 1.6 | 37.161 | 2.691E-002 | 4.127 | 87.268 | 0.000 | 0.000 | 0.000 | 0.000 | 91.395 | No |
| 2 | 01_A2 | 62.25 | 1.6 | 40.158 | 2.490E-002 | 3.729 | 80.755 | 0.000 | 0.000 | 0.000 | 0.000 | 84.484 | No |
| 3 | 01_B2 | 96.77 | 2.5 | 39.180 | 2.552E-002 | 3.260 | 56.045 | 0.000 | 0.000 | 0.000 | 0.000 | 59.305 | No |
| 4 | 01_C1 | 113.62 | 3.4 | 33.516 | 2.984E-002 | 3.085 | 49.676 | 0.000 | 0.000 | 0.000 | 0.000 | 52.761 | No |
| 5 | 02_A1 | 57.60 | 1.6 | 37.161 | 2.691E-002 | 4.127 | 87.268 | 0.000 | 0.000 | 0.000 | 0.000 | 91.395 | No |
| 6 | 02_A2 | 62.25 | 1.6 | 40.158 | 2.490E-002 | 3.729 | 80.755 | 0.000 | 0.000 | 0.000 | 0.000 | 84.484 | No |
| 7 | 02_B2 | 96.77 | 2.5 | 39.180 | 2.552E-002 | 3.260 | 56.045 | 0.000 | 0.000 | 0.000 | 0.000 | 59.305 | No |
| 8 | 02_C1 | 113.62 | 3.4 | 33.516 | 2.984E-002 | 3.085 | 49.676 | 0.000 | 0.000 | 0.000 | 0.000 | 52.761 | No |
| 9 | 03_A1 | 57.60 | 1.6 | 37.161 | 2.691E-002 | 4.127 | 87.268 | 0.000 | 0.000 | 0.000 | 0.000 | 91.395 | No |
| 10 | 03_A2 | 62.25 | 1.6 | 40.158 | 2.490E-002 | 3.729 | 80.755 | 0.000 | 0.000 | 0.000 | 0.000 | 84.484 | No |
| 11 | 03_B2 | 96.77 | 2.5 | 39.180 | 2.552E-002 | 3.260 | 56.045 | 0.000 | 0.000 | 0.000 | 0.000 | 59.305 | No |
| 12 | 03_C1 | 113.62 | 3.4 | 33.516 | 2.984E-002 | 3.085 | 49.676 | 0.000 | 0.000 | 0.000 | 0.000 | 52.761 | No |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Number of People {} | People/Floor Area {person/m2} | Floor Area per person {m2/person} | Fraction Radiant | Fraction Convected | Sensible Fraction Calculation | Activity level | ASHRAE 55 Warnings | Carbon Dioxide Generation Rate | Nominal Minimum Number of People | Nominal Maximum Number of People | |
| 1 | 01_A1 PEOPLE 1 | OCCPROTOCOL | 01_A1 | 57.60 | 1.6 | 1.6 | 2.691E-002 | 37.161 | 0.300 | 0.700 | AutoCalculate | MIDRISEAPARTMENT ACTIVITYDOE | No | 3.8200E-008 | 0 | 2 |
| 2 | 02_A1 PEOPLE 1 | OCCPROTOCOL | 02_A1 | 57.60 | 1.6 | 1.6 | 2.691E-002 | 37.161 | 0.300 | 0.700 | AutoCalculate | MIDRISEAPARTMENT ACTIVITYDOE | No | 3.8200E-008 | 0 | 2 |
| 3 | 03_A1 PEOPLE 1 | OCCPROTOCOL | 03_A1 | 57.60 | 1.6 | 1.6 | 2.691E-002 | 37.161 | 0.300 | 0.700 | AutoCalculate | MIDRISEAPARTMENT ACTIVITYDOE | No | 3.8200E-008 | 0 | 2 |
| 4 | 01_A2 PEOPLE 2 | OCCPROTOCOL | 01_A2 | 62.25 | 1.6 | 1.6 | 2.490E-002 | 40.158 | 0.300 | 0.700 | AutoCalculate | MIDRISEAPARTMENT ACTIVITYDOE | No | 3.8200E-008 | 0 | 2 |
| 5 | 02_A2 PEOPLE 2 | OCCPROTOCOL | 02_A2 | 62.25 | 1.6 | 1.6 | 2.490E-002 | 40.158 | 0.300 | 0.700 | AutoCalculate | MIDRISEAPARTMENT ACTIVITYDOE | No | 3.8200E-008 | 0 | 2 |
| 6 | 03_A2 PEOPLE 2 | OCCPROTOCOL | 03_A2 | 62.25 | 1.6 | 1.6 | 2.490E-002 | 40.158 | 0.300 | 0.700 | AutoCalculate | MIDRISEAPARTMENT ACTIVITYDOE | No | 3.8200E-008 | 0 | 2 |
| 7 | 01_B2 PEOPLE 6 | OCCPROTOCOL | 01_B2 | 96.77 | 2.5 | 2.5 | 2.552E-002 | 39.180 | 0.300 | 0.700 | AutoCalculate | MIDRISEAPARTMENT ACTIVITYDOE | No | 3.8200E-008 | 1 | 2 |
| 8 | 02_B2 PEOPLE 6 | OCCPROTOCOL | 02_B2 | 96.77 | 2.5 | 2.5 | 2.552E-002 | 39.180 | 0.300 | 0.700 | AutoCalculate | MIDRISEAPARTMENT ACTIVITYDOE | No | 3.8200E-008 | 1 | 2 |
| 9 | 03_B2 PEOPLE 6 | OCCPROTOCOL | 03_B2 | 96.77 | 2.5 | 2.5 | 2.552E-002 | 39.180 | 0.300 | 0.700 | AutoCalculate | MIDRISEAPARTMENT ACTIVITYDOE | No | 3.8200E-008 | 1 | 2 |
| 10 | 01_C1 PEOPLE 7 | OCCPROTOCOL | 01_C1 | 113.62 | 3.4 | 3.4 | 2.984E-002 | 33.516 | 0.300 | 0.700 | AutoCalculate | MIDRISEAPARTMENT ACTIVITYDOE | No | 3.8200E-008 | 1 | 3 |
| 11 | 02_C1 PEOPLE 7 | OCCPROTOCOL | 02_C1 | 113.62 | 3.4 | 3.4 | 2.984E-002 | 33.516 | 0.300 | 0.700 | AutoCalculate | MIDRISEAPARTMENT ACTIVITYDOE | No | 3.8200E-008 | 1 | 3 |
| 12 | 03_C1 PEOPLE 7 | OCCPROTOCOL | 03_C1 | 113.62 | 3.4 | 3.4 | 2.984E-002 | 33.516 | 0.300 | 0.700 | AutoCalculate | MIDRISEAPARTMENT ACTIVITYDOE | No | 3.8200E-008 | 1 | 3 |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Lighting Level {W} | Lights/Floor Area {W/m2} | Lights per person {W/person} | Fraction Return Air | Fraction Radiant | Fraction Short Wave | Fraction Convected | Fraction Replaceable | End-Use Category | Nominal Minimum Lighting Level {W} | Nominal Maximum Lighting Level {W} | |
| 1 | 01_A1 LIGHTS 2 | MIDRISEAPARTMENT APARTMENT LIGHTDOE | 01_A1 | 57.60 | 1.6 | 237.708 | 4.127 | 153.360 | 0.000 | 0.000 | 0.000 | 1.000 | 1.000 | General | 4.754 | 237.708 |
| 2 | 02_A1 LIGHTS 2 | MIDRISEAPARTMENT APARTMENT LIGHTDOE | 02_A1 | 57.60 | 1.6 | 237.708 | 4.127 | 153.360 | 0.000 | 0.000 | 0.000 | 1.000 | 1.000 | General | 4.754 | 237.708 |
| 3 | 03_A1 LIGHTS 2 | MIDRISEAPARTMENT APARTMENT LIGHTDOE | 03_A1 | 57.60 | 1.6 | 237.708 | 4.127 | 153.360 | 0.000 | 0.000 | 0.000 | 1.000 | 1.000 | General | 4.754 | 237.708 |
| 4 | 01_A2 LIGHTS 3 | MIDRISEAPARTMENT APARTMENT LIGHTDOE | 01_A2 | 62.25 | 1.6 | 232.088 | 3.729 | 149.734 | 0.000 | 0.000 | 0.000 | 1.000 | 1.000 | General | 4.642 | 232.088 |
| 5 | 02_A2 LIGHTS 3 | MIDRISEAPARTMENT APARTMENT LIGHTDOE | 02_A2 | 62.25 | 1.6 | 232.088 | 3.729 | 149.734 | 0.000 | 0.000 | 0.000 | 1.000 | 1.000 | General | 4.642 | 232.088 |
| 6 | 03_A2 LIGHTS 3 | MIDRISEAPARTMENT APARTMENT LIGHTDOE | 03_A2 | 62.25 | 1.6 | 232.088 | 3.729 | 149.734 | 0.000 | 0.000 | 0.000 | 1.000 | 1.000 | General | 4.642 | 232.088 |
| 7 | 01_B2 LIGHTS 7 | MIDRISEAPARTMENT APARTMENT LIGHTDOE | 01_B2 | 96.77 | 2.5 | 315.521 | 3.260 | 127.741 | 0.000 | 0.000 | 0.000 | 1.000 | 1.000 | General | 6.310 | 315.521 |
| 8 | 02_B2 LIGHTS 7 | MIDRISEAPARTMENT APARTMENT LIGHTDOE | 02_B2 | 96.77 | 2.5 | 315.521 | 3.260 | 127.741 | 0.000 | 0.000 | 0.000 | 1.000 | 1.000 | General | 6.310 | 315.521 |
| 9 | 03_B2 LIGHTS 7 | MIDRISEAPARTMENT APARTMENT LIGHTDOE | 03_B2 | 96.77 | 2.5 | 315.521 | 3.260 | 127.741 | 0.000 | 0.000 | 0.000 | 1.000 | 1.000 | General | 6.310 | 315.521 |
| 10 | 01_C1 LIGHTS 8 | MIDRISEAPARTMENT APARTMENT LIGHTDOE | 01_C1 | 113.62 | 3.4 | 350.512 | 3.085 | 103.396 | 0.000 | 0.000 | 0.000 | 1.000 | 1.000 | General | 7.010 | 350.512 |
| 11 | 02_C1 LIGHTS 8 | MIDRISEAPARTMENT APARTMENT LIGHTDOE | 02_C1 | 113.62 | 3.4 | 350.512 | 3.085 | 103.396 | 0.000 | 0.000 | 0.000 | 1.000 | 1.000 | General | 7.010 | 350.512 |
| 12 | 03_C1 LIGHTS 8 | MIDRISEAPARTMENT APARTMENT LIGHTDOE | 03_C1 | 113.62 | 3.4 | 350.512 | 3.085 | 103.396 | 0.000 | 0.000 | 0.000 | 1.000 | 1.000 | General | 7.010 | 350.512 |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Equipment Level {W} | Equipment/Floor Area {W/m2} | Equipment per person {W/person} | Fraction Latent | Fraction Radiant | Fraction Lost | Fraction Convected | End-Use SubCategory | Nominal Minimum Equipment Level {W} | Nominal Maximum Equipment Level {W} | |
| 1 | 01_A1 ELECTRIC EQUIPMENT 19 | APARTMENTMIDRISE EQP_CLOTHESDRYER | 01_A1 | 57.60 | 1.6 | 1699.556 | 29.506 | 1096.487 | 5.000E-002 | 0.150 | 0.000 | 0.800 | General | 3.399 | 1699.556 |
| 2 | 02_A1 ELECTRIC EQUIPMENT 19 | APARTMENTMIDRISE EQP_CLOTHESDRYER | 02_A1 | 57.60 | 1.6 | 1699.556 | 29.506 | 1096.487 | 5.000E-002 | 0.150 | 0.000 | 0.800 | General | 3.399 | 1699.556 |
| 3 | 03_A1 ELECTRIC EQUIPMENT 19 | APARTMENTMIDRISE EQP_CLOTHESDRYER | 03_A1 | 57.60 | 1.6 | 1699.556 | 29.506 | 1096.487 | 5.000E-002 | 0.150 | 0.000 | 0.800 | General | 3.399 | 1699.556 |
| 4 | 01_A1 ELECTRIC EQUIPMENT 20 | APARTMENTMIDRISE EQP_CLOTHESWASHER | 01_A1 | 57.60 | 1.6 | 350.000 | 6.076 | 225.806 | 0.000 | 0.800 | 0.000 | 0.200 | General | 1.225 | 350.000 |
| 5 | 02_A1 ELECTRIC EQUIPMENT 20 | APARTMENTMIDRISE EQP_CLOTHESWASHER | 02_A1 | 57.60 | 1.6 | 350.000 | 6.076 | 225.806 | 0.000 | 0.800 | 0.000 | 0.200 | General | 1.225 | 350.000 |
| 6 | 03_A1 ELECTRIC EQUIPMENT 20 | APARTMENTMIDRISE EQP_CLOTHESWASHER | 03_A1 | 57.60 | 1.6 | 350.000 | 6.076 | 225.806 | 0.000 | 0.800 | 0.000 | 0.200 | General | 1.225 | 350.000 |
| 7 | 01_A1 ELECTRIC EQUIPMENT 22 | APARTMENTMIDRISE EQP_DISHWASHER | 01_A1 | 57.60 | 1.6 | 780.000 | 13.542 | 503.226 | 0.150 | 0.600 | 0.000 | 0.250 | General | 2.730 | 780.000 |
| 8 | 02_A1 ELECTRIC EQUIPMENT 22 | APARTMENTMIDRISE EQP_DISHWASHER | 02_A1 | 57.60 | 1.6 | 780.000 | 13.542 | 503.226 | 0.150 | 0.600 | 0.000 | 0.250 | General | 2.730 | 780.000 |
| 9 | 03_A1 ELECTRIC EQUIPMENT 22 | APARTMENTMIDRISE EQP_DISHWASHER | 03_A1 | 57.60 | 1.6 | 780.000 | 13.542 | 503.226 | 0.150 | 0.600 | 0.000 | 0.250 | General | 2.730 | 780.000 |
| 10 | 01_A1 ELECTRIC EQUIPMENT 23 | APARTMENTMIDRISE EQP_RANGE | 01_A1 | 57.60 | 1.6 | 250.000 | 4.340 | 161.290 | 0.200 | 0.730 | 0.000 | 7.000E-002 | General | 0.800 | 250.000 |
| 11 | 02_A1 ELECTRIC EQUIPMENT 23 | APARTMENTMIDRISE EQP_RANGE | 02_A1 | 57.60 | 1.6 | 250.000 | 4.340 | 161.290 | 0.200 | 0.730 | 0.000 | 7.000E-002 | General | 0.800 | 250.000 |
| 12 | 03_A1 ELECTRIC EQUIPMENT 23 | APARTMENTMIDRISE EQP_RANGE | 03_A1 | 57.60 | 1.6 | 250.000 | 4.340 | 161.290 | 0.200 | 0.730 | 0.000 | 7.000E-002 | General | 0.800 | 250.000 |
| 13 | 01_A1 ELECTRIC EQUIPMENT 24 | APARTMENTMIDRISE EQP_RANGE | 01_A1 | 57.60 | 1.6 | 176.471 | 3.064 | 113.852 | 0.300 | 0.400 | 0.000 | 0.300 | General | 0.565 | 176.471 |
| 14 | 02_A1 ELECTRIC EQUIPMENT 24 | APARTMENTMIDRISE EQP_RANGE | 02_A1 | 57.60 | 1.6 | 176.471 | 3.064 | 113.852 | 0.300 | 0.400 | 0.000 | 0.300 | General | 0.565 | 176.471 |
| 15 | 03_A1 ELECTRIC EQUIPMENT 24 | APARTMENTMIDRISE EQP_RANGE | 03_A1 | 57.60 | 1.6 | 176.471 | 3.064 | 113.852 | 0.300 | 0.400 | 0.000 | 0.300 | General | 0.565 | 176.471 |
| 16 | 01_A1 ELECTRIC EQUIPMENT 25 | APARTMENTMIDRISE EQP_REFRIGERATOR | 01_A1 | 57.60 | 1.6 | 1200.000 | 20.833 | 774.194 | 0.000 | 1.000 | 0.000 | 0.000 | General | 43.476 | 1200.000 |
| 17 | 02_A1 ELECTRIC EQUIPMENT 25 | APARTMENTMIDRISE EQP_REFRIGERATOR | 02_A1 | 57.60 | 1.6 | 1200.000 | 20.833 | 774.194 | 0.000 | 1.000 | 0.000 | 0.000 | General | 43.476 | 1200.000 |
| 18 | 03_A1 ELECTRIC EQUIPMENT 25 | APARTMENTMIDRISE EQP_REFRIGERATOR | 03_A1 | 57.60 | 1.6 | 1200.000 | 20.833 | 774.194 | 0.000 | 1.000 | 0.000 | 0.000 | General | 43.476 | 1200.000 |
| 19 | 01_A1 ELECTRIC EQUIPMENT 26 | APARTMENTMIDRISE EQP_APT_SCH | 01_A1 | 57.60 | 1.6 | 350.000 | 6.076 | 225.806 | 0.200 | 0.730 | 0.000 | 7.000E-002 | General | 8.540 | 350.000 |
| 20 | 02_A1 ELECTRIC EQUIPMENT 26 | APARTMENTMIDRISE EQP_APT_SCH | 02_A1 | 57.60 | 1.6 | 350.000 | 6.076 | 225.806 | 0.200 | 0.730 | 0.000 | 7.000E-002 | General | 8.540 | 350.000 |
| 21 | 03_A1 ELECTRIC EQUIPMENT 26 | APARTMENTMIDRISE EQP_APT_SCH | 03_A1 | 57.60 | 1.6 | 350.000 | 6.076 | 225.806 | 0.200 | 0.730 | 0.000 | 7.000E-002 | General | 8.540 | 350.000 |
| 22 | 01_A1 ELECTRIC EQUIPMENT 3 | APARTMENTMIDRISE EQP_RANGE | 01_A1 | 57.60 | 1.6 | 220.588 | 3.830 | 142.315 | 0.300 | 0.400 | 0.000 | 0.300 | General | 0.706 | 220.588 |
| 23 | 02_A1 ELECTRIC EQUIPMENT 3 | APARTMENTMIDRISE EQP_RANGE | 02_A1 | 57.60 | 1.6 | 220.588 | 3.830 | 142.315 | 0.300 | 0.400 | 0.000 | 0.300 | General | 0.706 | 220.588 |
| 24 | 03_A1 ELECTRIC EQUIPMENT 3 | APARTMENTMIDRISE EQP_RANGE | 03_A1 | 57.60 | 1.6 | 220.588 | 3.830 | 142.315 | 0.300 | 0.400 | 0.000 | 0.300 | General | 0.706 | 220.588 |
| 25 | 01_A2 ELECTRIC EQUIPMENT 13 | APARTMENTMIDRISE EQP_RANGE | 01_A2 | 62.25 | 1.6 | 176.471 | 2.835 | 113.852 | 0.300 | 0.400 | 0.000 | 0.300 | General | 0.565 | 176.471 |
| 26 | 02_A2 ELECTRIC EQUIPMENT 13 | APARTMENTMIDRISE EQP_RANGE | 02_A2 | 62.25 | 1.6 | 176.471 | 2.835 | 113.852 | 0.300 | 0.400 | 0.000 | 0.300 | General | 0.565 | 176.471 |
| 27 | 03_A2 ELECTRIC EQUIPMENT 13 | APARTMENTMIDRISE EQP_RANGE | 03_A2 | 62.25 | 1.6 | 176.471 | 2.835 | 113.852 | 0.300 | 0.400 | 0.000 | 0.300 | General | 0.565 | 176.471 |
| 28 | 01_A2 ELECTRIC EQUIPMENT 27 | APARTMENTMIDRISE EQP_CLOTHESDRYER | 01_A2 | 62.25 | 1.6 | 1699.556 | 27.304 | 1096.487 | 5.000E-002 | 0.150 | 0.000 | 0.800 | General | 3.399 | 1699.556 |
| 29 | 02_A2 ELECTRIC EQUIPMENT 27 | APARTMENTMIDRISE EQP_CLOTHESDRYER | 02_A2 | 62.25 | 1.6 | 1699.556 | 27.304 | 1096.487 | 5.000E-002 | 0.150 | 0.000 | 0.800 | General | 3.399 | 1699.556 |
| 30 | 03_A2 ELECTRIC EQUIPMENT 27 | APARTMENTMIDRISE EQP_CLOTHESDRYER | 03_A2 | 62.25 | 1.6 | 1699.556 | 27.304 | 1096.487 | 5.000E-002 | 0.150 | 0.000 | 0.800 | General | 3.399 | 1699.556 |
| 31 | 01_A2 ELECTRIC EQUIPMENT 28 | APARTMENTMIDRISE EQP_CLOTHESWASHER | 01_A2 | 62.25 | 1.6 | 350.000 | 5.623 | 225.806 | 0.000 | 0.800 | 0.000 | 0.200 | General | 1.225 | 350.000 |
| 32 | 02_A2 ELECTRIC EQUIPMENT 28 | APARTMENTMIDRISE EQP_CLOTHESWASHER | 02_A2 | 62.25 | 1.6 | 350.000 | 5.623 | 225.806 | 0.000 | 0.800 | 0.000 | 0.200 | General | 1.225 | 350.000 |
| 33 | 03_A2 ELECTRIC EQUIPMENT 28 | APARTMENTMIDRISE EQP_CLOTHESWASHER | 03_A2 | 62.25 | 1.6 | 350.000 | 5.623 | 225.806 | 0.000 | 0.800 | 0.000 | 0.200 | General | 1.225 | 350.000 |
| 34 | 01_A2 ELECTRIC EQUIPMENT 30 | APARTMENTMIDRISE EQP_DISHWASHER | 01_A2 | 62.25 | 1.6 | 780.000 | 12.531 | 503.226 | 0.150 | 0.600 | 0.000 | 0.250 | General | 2.730 | 780.000 |
| 35 | 02_A2 ELECTRIC EQUIPMENT 30 | APARTMENTMIDRISE EQP_DISHWASHER | 02_A2 | 62.25 | 1.6 | 780.000 | 12.531 | 503.226 | 0.150 | 0.600 | 0.000 | 0.250 | General | 2.730 | 780.000 |
| 36 | 03_A2 ELECTRIC EQUIPMENT 30 | APARTMENTMIDRISE EQP_DISHWASHER | 03_A2 | 62.25 | 1.6 | 780.000 | 12.531 | 503.226 | 0.150 | 0.600 | 0.000 | 0.250 | General | 2.730 | 780.000 |
| 37 | 01_A2 ELECTRIC EQUIPMENT 31 | APARTMENTMIDRISE EQP_RANGE | 01_A2 | 62.25 | 1.6 | 250.000 | 4.016 | 161.290 | 0.200 | 0.730 | 0.000 | 7.000E-002 | General | 0.800 | 250.000 |
| 38 | 02_A2 ELECTRIC EQUIPMENT 31 | APARTMENTMIDRISE EQP_RANGE | 02_A2 | 62.25 | 1.6 | 250.000 | 4.016 | 161.290 | 0.200 | 0.730 | 0.000 | 7.000E-002 | General | 0.800 | 250.000 |
| 39 | 03_A2 ELECTRIC EQUIPMENT 31 | APARTMENTMIDRISE EQP_RANGE | 03_A2 | 62.25 | 1.6 | 250.000 | 4.016 | 161.290 | 0.200 | 0.730 | 0.000 | 7.000E-002 | General | 0.800 | 250.000 |
| 40 | 01_A2 ELECTRIC EQUIPMENT 32 | APARTMENTMIDRISE EQP_RANGE | 01_A2 | 62.25 | 1.6 | 220.588 | 3.544 | 142.315 | 0.300 | 0.400 | 0.000 | 0.300 | General | 0.706 | 220.588 |
| 41 | 02_A2 ELECTRIC EQUIPMENT 32 | APARTMENTMIDRISE EQP_RANGE | 02_A2 | 62.25 | 1.6 | 220.588 | 3.544 | 142.315 | 0.300 | 0.400 | 0.000 | 0.300 | General | 0.706 | 220.588 |
| 42 | 03_A2 ELECTRIC EQUIPMENT 32 | APARTMENTMIDRISE EQP_RANGE | 03_A2 | 62.25 | 1.6 | 220.588 | 3.544 | 142.315 | 0.300 | 0.400 | 0.000 | 0.300 | General | 0.706 | 220.588 |
| 43 | 01_A2 ELECTRIC EQUIPMENT 33 | APARTMENTMIDRISE EQP_REFRIGERATOR | 01_A2 | 62.25 | 1.6 | 1200.000 | 19.279 | 774.194 | 0.000 | 1.000 | 0.000 | 0.000 | General | 43.476 | 1200.000 |
| 44 | 02_A2 ELECTRIC EQUIPMENT 33 | APARTMENTMIDRISE EQP_REFRIGERATOR | 02_A2 | 62.25 | 1.6 | 1200.000 | 19.279 | 774.194 | 0.000 | 1.000 | 0.000 | 0.000 | General | 43.476 | 1200.000 |
| 45 | 03_A2 ELECTRIC EQUIPMENT 33 | APARTMENTMIDRISE EQP_REFRIGERATOR | 03_A2 | 62.25 | 1.6 | 1200.000 | 19.279 | 774.194 | 0.000 | 1.000 | 0.000 | 0.000 | General | 43.476 | 1200.000 |
| 46 | 01_A2 ELECTRIC EQUIPMENT 34 | APARTMENTMIDRISE EQP_APT_SCH | 01_A2 | 62.25 | 1.6 | 350.000 | 5.623 | 225.806 | 0.200 | 0.730 | 0.000 | 7.000E-002 | General | 8.540 | 350.000 |
| 47 | 02_A2 ELECTRIC EQUIPMENT 34 | APARTMENTMIDRISE EQP_APT_SCH | 02_A2 | 62.25 | 1.6 | 350.000 | 5.623 | 225.806 | 0.200 | 0.730 | 0.000 | 7.000E-002 | General | 8.540 | 350.000 |
| 48 | 03_A2 ELECTRIC EQUIPMENT 34 | APARTMENTMIDRISE EQP_APT_SCH | 03_A2 | 62.25 | 1.6 | 350.000 | 5.623 | 225.806 | 0.200 | 0.730 | 0.000 | 7.000E-002 | General | 8.540 | 350.000 |
| 49 | 01_B2 ELECTRIC EQUIPMENT 45 | APARTMENTMIDRISE EQP_RANGE | 01_B2 | 96.77 | 2.5 | 397.059 | 4.103 | 160.753 | 0.300 | 0.400 | 0.000 | 0.300 | General | 1.271 | 397.059 |
| 50 | 02_B2 ELECTRIC EQUIPMENT 45 | APARTMENTMIDRISE EQP_RANGE | 02_B2 | 96.77 | 2.5 | 397.059 | 4.103 | 160.753 | 0.300 | 0.400 | 0.000 | 0.300 | General | 1.271 | 397.059 |
| 51 | 03_B2 ELECTRIC EQUIPMENT 45 | APARTMENTMIDRISE EQP_RANGE | 03_B2 | 96.77 | 2.5 | 397.059 | 4.103 | 160.753 | 0.300 | 0.400 | 0.000 | 0.300 | General | 1.271 | 397.059 |
| 52 | 01_B2 ELECTRIC EQUIPMENT 60 | APARTMENTMIDRISE EQP_CLOTHESDRYER | 01_B2 | 96.77 | 2.5 | 1699.556 | 17.562 | 688.079 | 5.000E-002 | 0.150 | 0.000 | 0.800 | General | 3.399 | 1699.556 |
| 53 | 02_B2 ELECTRIC EQUIPMENT 60 | APARTMENTMIDRISE EQP_CLOTHESDRYER | 02_B2 | 96.77 | 2.5 | 1699.556 | 17.562 | 688.079 | 5.000E-002 | 0.150 | 0.000 | 0.800 | General | 3.399 | 1699.556 |
| 54 | 03_B2 ELECTRIC EQUIPMENT 60 | APARTMENTMIDRISE EQP_CLOTHESDRYER | 03_B2 | 96.77 | 2.5 | 1699.556 | 17.562 | 688.079 | 5.000E-002 | 0.150 | 0.000 | 0.800 | General | 3.399 | 1699.556 |
| 55 | 01_B2 ELECTRIC EQUIPMENT 61 | APARTMENTMIDRISE EQP_CLOTHESWASHER | 01_B2 | 96.77 | 2.5 | 350.000 | 3.617 | 141.700 | 0.000 | 0.800 | 0.000 | 0.200 | General | 1.225 | 350.000 |
| 56 | 02_B2 ELECTRIC EQUIPMENT 61 | APARTMENTMIDRISE EQP_CLOTHESWASHER | 02_B2 | 96.77 | 2.5 | 350.000 | 3.617 | 141.700 | 0.000 | 0.800 | 0.000 | 0.200 | General | 1.225 | 350.000 |
| 57 | 03_B2 ELECTRIC EQUIPMENT 61 | APARTMENTMIDRISE EQP_CLOTHESWASHER | 03_B2 | 96.77 | 2.5 | 350.000 | 3.617 | 141.700 | 0.000 | 0.800 | 0.000 | 0.200 | General | 1.225 | 350.000 |
| 58 | 01_B2 ELECTRIC EQUIPMENT 63 | APARTMENTMIDRISE EQP_DISHWASHER | 01_B2 | 96.77 | 2.5 | 780.000 | 8.060 | 315.789 | 0.150 | 0.600 | 0.000 | 0.250 | General | 2.730 | 780.000 |
| 59 | 02_B2 ELECTRIC EQUIPMENT 63 | APARTMENTMIDRISE EQP_DISHWASHER | 02_B2 | 96.77 | 2.5 | 780.000 | 8.060 | 315.789 | 0.150 | 0.600 | 0.000 | 0.250 | General | 2.730 | 780.000 |
| 60 | 03_B2 ELECTRIC EQUIPMENT 63 | APARTMENTMIDRISE EQP_DISHWASHER | 03_B2 | 96.77 | 2.5 | 780.000 | 8.060 | 315.789 | 0.150 | 0.600 | 0.000 | 0.250 | General | 2.730 | 780.000 |
| 61 | 01_B2 ELECTRIC EQUIPMENT 64 | APARTMENTMIDRISE EQP_RANGE | 01_B2 | 96.77 | 2.5 | 250.000 | 2.583 | 101.215 | 0.200 | 0.730 | 0.000 | 7.000E-002 | General | 0.800 | 250.000 |
| 62 | 02_B2 ELECTRIC EQUIPMENT 64 | APARTMENTMIDRISE EQP_RANGE | 02_B2 | 96.77 | 2.5 | 250.000 | 2.583 | 101.215 | 0.200 | 0.730 | 0.000 | 7.000E-002 | General | 0.800 | 250.000 |
| 63 | 03_B2 ELECTRIC EQUIPMENT 64 | APARTMENTMIDRISE EQP_RANGE | 03_B2 | 96.77 | 2.5 | 250.000 | 2.583 | 101.215 | 0.200 | 0.730 | 0.000 | 7.000E-002 | General | 0.800 | 250.000 |
| 64 | 01_B2 ELECTRIC EQUIPMENT 65 | APARTMENTMIDRISE EQP_RANGE | 01_B2 | 96.77 | 2.5 | 220.588 | 2.279 | 89.307 | 0.300 | 0.400 | 0.000 | 0.300 | General | 0.706 | 220.588 |
| 65 | 02_B2 ELECTRIC EQUIPMENT 65 | APARTMENTMIDRISE EQP_RANGE | 02_B2 | 96.77 | 2.5 | 220.588 | 2.279 | 89.307 | 0.300 | 0.400 | 0.000 | 0.300 | General | 0.706 | 220.588 |
| 66 | 03_B2 ELECTRIC EQUIPMENT 65 | APARTMENTMIDRISE EQP_RANGE | 03_B2 | 96.77 | 2.5 | 220.588 | 2.279 | 89.307 | 0.300 | 0.400 | 0.000 | 0.300 | General | 0.706 | 220.588 |
| 67 | 01_B2 ELECTRIC EQUIPMENT 66 | APARTMENTMIDRISE EQP_RANGE | 01_B2 | 96.77 | 2.5 | 176.471 | 1.824 | 71.446 | 0.300 | 0.400 | 0.000 | 0.300 | General | 0.565 | 176.471 |
| 68 | 02_B2 ELECTRIC EQUIPMENT 66 | APARTMENTMIDRISE EQP_RANGE | 02_B2 | 96.77 | 2.5 | 176.471 | 1.824 | 71.446 | 0.300 | 0.400 | 0.000 | 0.300 | General | 0.565 | 176.471 |
| 69 | 03_B2 ELECTRIC EQUIPMENT 66 | APARTMENTMIDRISE EQP_RANGE | 03_B2 | 96.77 | 2.5 | 176.471 | 1.824 | 71.446 | 0.300 | 0.400 | 0.000 | 0.300 | General | 0.565 | 176.471 |
| 70 | 01_B2 ELECTRIC EQUIPMENT 67 | APARTMENTMIDRISE EQP_REFRIGERATOR | 01_B2 | 96.77 | 2.5 | 1200.000 | 12.400 | 485.830 | 0.000 | 1.000 | 0.000 | 0.000 | General | 43.476 | 1200.000 |
| 71 | 02_B2 ELECTRIC EQUIPMENT 67 | APARTMENTMIDRISE EQP_REFRIGERATOR | 02_B2 | 96.77 | 2.5 | 1200.000 | 12.400 | 485.830 | 0.000 | 1.000 | 0.000 | 0.000 | General | 43.476 | 1200.000 |
| 72 | 03_B2 ELECTRIC EQUIPMENT 67 | APARTMENTMIDRISE EQP_REFRIGERATOR | 03_B2 | 96.77 | 2.5 | 1200.000 | 12.400 | 485.830 | 0.000 | 1.000 | 0.000 | 0.000 | General | 43.476 | 1200.000 |
| 73 | 01_B2 ELECTRIC EQUIPMENT 68 | APARTMENTMIDRISE EQP_APT_SCH | 01_B2 | 96.77 | 2.5 | 350.000 | 3.617 | 141.700 | 0.200 | 0.730 | 0.000 | 7.000E-002 | General | 8.540 | 350.000 |
| 74 | 02_B2 ELECTRIC EQUIPMENT 68 | APARTMENTMIDRISE EQP_APT_SCH | 02_B2 | 96.77 | 2.5 | 350.000 | 3.617 | 141.700 | 0.200 | 0.730 | 0.000 | 7.000E-002 | General | 8.540 | 350.000 |
| 75 | 03_B2 ELECTRIC EQUIPMENT 68 | APARTMENTMIDRISE EQP_APT_SCH | 03_B2 | 96.77 | 2.5 | 350.000 | 3.617 | 141.700 | 0.200 | 0.730 | 0.000 | 7.000E-002 | General | 8.540 | 350.000 |
| 76 | 01_C1 ELECTRIC EQUIPMENT 1 | APARTMENTMIDRISE EQP_CLOTHESDRYER | 01_C1 | 113.62 | 3.4 | 1699.556 | 14.958 | 501.344 | 5.000E-002 | 0.150 | 0.000 | 0.800 | General | 3.399 | 1699.556 |
| 77 | 02_C1 ELECTRIC EQUIPMENT 1 | APARTMENTMIDRISE EQP_CLOTHESDRYER | 02_C1 | 113.62 | 3.4 | 1699.556 | 14.958 | 501.344 | 5.000E-002 | 0.150 | 0.000 | 0.800 | General | 3.399 | 1699.556 |
| 78 | 03_C1 ELECTRIC EQUIPMENT 1 | APARTMENTMIDRISE EQP_CLOTHESDRYER | 03_C1 | 113.62 | 3.4 | 1699.556 | 14.958 | 501.344 | 5.000E-002 | 0.150 | 0.000 | 0.800 | General | 3.399 | 1699.556 |
| 79 | 01_C1 ELECTRIC EQUIPMENT 10 | APARTMENTMIDRISE EQP_RANGE | 01_C1 | 113.62 | 3.4 | 397.059 | 3.495 | 117.126 | 0.300 | 0.400 | 0.000 | 0.300 | General | 1.271 | 397.059 |
| 80 | 02_C1 ELECTRIC EQUIPMENT 10 | APARTMENTMIDRISE EQP_RANGE | 02_C1 | 113.62 | 3.4 | 397.059 | 3.495 | 117.126 | 0.300 | 0.400 | 0.000 | 0.300 | General | 1.271 | 397.059 |
| 81 | 03_C1 ELECTRIC EQUIPMENT 10 | APARTMENTMIDRISE EQP_RANGE | 03_C1 | 113.62 | 3.4 | 397.059 | 3.495 | 117.126 | 0.300 | 0.400 | 0.000 | 0.300 | General | 1.271 | 397.059 |
| 82 | 01_C1 ELECTRIC EQUIPMENT 2 | APARTMENTMIDRISE EQP_CLOTHESWASHER | 01_C1 | 113.62 | 3.4 | 350.000 | 3.080 | 103.245 | 0.000 | 0.800 | 0.000 | 0.200 | General | 1.225 | 350.000 |
| 83 | 02_C1 ELECTRIC EQUIPMENT 2 | APARTMENTMIDRISE EQP_CLOTHESWASHER | 02_C1 | 113.62 | 3.4 | 350.000 | 3.080 | 103.245 | 0.000 | 0.800 | 0.000 | 0.200 | General | 1.225 | 350.000 |
| 84 | 03_C1 ELECTRIC EQUIPMENT 2 | APARTMENTMIDRISE EQP_CLOTHESWASHER | 03_C1 | 113.62 | 3.4 | 350.000 | 3.080 | 103.245 | 0.000 | 0.800 | 0.000 | 0.200 | General | 1.225 | 350.000 |
| 85 | 01_C1 ELECTRIC EQUIPMENT 4 | APARTMENTMIDRISE EQP_DISHWASHER | 01_C1 | 113.62 | 3.4 | 780.000 | 6.865 | 230.088 | 0.150 | 0.600 | 0.000 | 0.250 | General | 2.730 | 780.000 |
| 86 | 02_C1 ELECTRIC EQUIPMENT 4 | APARTMENTMIDRISE EQP_DISHWASHER | 02_C1 | 113.62 | 3.4 | 780.000 | 6.865 | 230.088 | 0.150 | 0.600 | 0.000 | 0.250 | General | 2.730 | 780.000 |
| 87 | 03_C1 ELECTRIC EQUIPMENT 4 | APARTMENTMIDRISE EQP_DISHWASHER | 03_C1 | 113.62 | 3.4 | 780.000 | 6.865 | 230.088 | 0.150 | 0.600 | 0.000 | 0.250 | General | 2.730 | 780.000 |
| 88 | 01_C1 ELECTRIC EQUIPMENT 5 | APARTMENTMIDRISE EQP_RANGE | 01_C1 | 113.62 | 3.4 | 220.588 | 1.941 | 65.070 | 0.300 | 0.400 | 0.000 | 0.300 | General | 0.706 | 220.588 |
| 89 | 02_C1 ELECTRIC EQUIPMENT 5 | APARTMENTMIDRISE EQP_RANGE | 02_C1 | 113.62 | 3.4 | 220.588 | 1.941 | 65.070 | 0.300 | 0.400 | 0.000 | 0.300 | General | 0.706 | 220.588 |
| 90 | 03_C1 ELECTRIC EQUIPMENT 5 | APARTMENTMIDRISE EQP_RANGE | 03_C1 | 113.62 | 3.4 | 220.588 | 1.941 | 65.070 | 0.300 | 0.400 | 0.000 | 0.300 | General | 0.706 | 220.588 |
| 91 | 01_C1 ELECTRIC EQUIPMENT 53 | APARTMENTMIDRISE EQP_RANGE | 01_C1 | 113.62 | 3.4 | 220.588 | 1.941 | 65.070 | 0.300 | 0.400 | 0.000 | 0.300 | General | 0.706 | 220.588 |
| 92 | 02_C1 ELECTRIC EQUIPMENT 53 | APARTMENTMIDRISE EQP_RANGE | 02_C1 | 113.62 | 3.4 | 220.588 | 1.941 | 65.070 | 0.300 | 0.400 | 0.000 | 0.300 | General | 0.706 | 220.588 |
| 93 | 03_C1 ELECTRIC EQUIPMENT 53 | APARTMENTMIDRISE EQP_RANGE | 03_C1 | 113.62 | 3.4 | 220.588 | 1.941 | 65.070 | 0.300 | 0.400 | 0.000 | 0.300 | General | 0.706 | 220.588 |
| 94 | 01_C1 ELECTRIC EQUIPMENT 6 | APARTMENTMIDRISE EQP_RANGE | 01_C1 | 113.62 | 3.4 | 250.000 | 2.200 | 73.746 | 0.200 | 0.730 | 0.000 | 7.000E-002 | General | 0.800 | 250.000 |
| 95 | 02_C1 ELECTRIC EQUIPMENT 6 | APARTMENTMIDRISE EQP_RANGE | 02_C1 | 113.62 | 3.4 | 250.000 | 2.200 | 73.746 | 0.200 | 0.730 | 0.000 | 7.000E-002 | General | 0.800 | 250.000 |
| 96 | 03_C1 ELECTRIC EQUIPMENT 6 | APARTMENTMIDRISE EQP_RANGE | 03_C1 | 113.62 | 3.4 | 250.000 | 2.200 | 73.746 | 0.200 | 0.730 | 0.000 | 7.000E-002 | General | 0.800 | 250.000 |
| 97 | 01_C1 ELECTRIC EQUIPMENT 7 | APARTMENTMIDRISE EQP_RANGE | 01_C1 | 113.62 | 3.4 | 176.471 | 1.553 | 52.056 | 0.300 | 0.400 | 0.000 | 0.300 | General | 0.565 | 176.471 |
| 98 | 02_C1 ELECTRIC EQUIPMENT 7 | APARTMENTMIDRISE EQP_RANGE | 02_C1 | 113.62 | 3.4 | 176.471 | 1.553 | 52.056 | 0.300 | 0.400 | 0.000 | 0.300 | General | 0.565 | 176.471 |
| 99 | 03_C1 ELECTRIC EQUIPMENT 7 | APARTMENTMIDRISE EQP_RANGE | 03_C1 | 113.62 | 3.4 | 176.471 | 1.553 | 52.056 | 0.300 | 0.400 | 0.000 | 0.300 | General | 0.565 | 176.471 |
| 100 | 01_C1 ELECTRIC EQUIPMENT 8 | APARTMENTMIDRISE EQP_REFRIGERATOR | 01_C1 | 113.62 | 3.4 | 1200.000 | 10.561 | 353.982 | 0.000 | 1.000 | 0.000 | 0.000 | General | 43.476 | 1200.000 |
| 101 | 02_C1 ELECTRIC EQUIPMENT 8 | APARTMENTMIDRISE EQP_REFRIGERATOR | 02_C1 | 113.62 | 3.4 | 1200.000 | 10.561 | 353.982 | 0.000 | 1.000 | 0.000 | 0.000 | General | 43.476 | 1200.000 |
| 102 | 03_C1 ELECTRIC EQUIPMENT 8 | APARTMENTMIDRISE EQP_REFRIGERATOR | 03_C1 | 113.62 | 3.4 | 1200.000 | 10.561 | 353.982 | 0.000 | 1.000 | 0.000 | 0.000 | General | 43.476 | 1200.000 |
| 103 | 01_C1 ELECTRIC EQUIPMENT 9 | APARTMENTMIDRISE EQP_APT_SCH | 01_C1 | 113.62 | 3.4 | 350.000 | 3.080 | 103.245 | 0.200 | 0.730 | 0.000 | 7.000E-002 | General | 8.540 | 350.000 |
| 104 | 02_C1 ELECTRIC EQUIPMENT 9 | APARTMENTMIDRISE EQP_APT_SCH | 02_C1 | 113.62 | 3.4 | 350.000 | 3.080 | 103.245 | 0.200 | 0.730 | 0.000 | 7.000E-002 | General | 8.540 | 350.000 |
| 105 | 03_C1 ELECTRIC EQUIPMENT 9 | APARTMENTMIDRISE EQP_APT_SCH | 03_C1 | 113.62 | 3.4 | 350.000 | 3.080 | 103.245 | 0.200 | 0.730 | 0.000 | 7.000E-002 | General | 8.540 | 350.000 |
| Calculation Method | Value {days} | Allowable Number Figures in Shadow Overlap {} | Polygon Clipping Algorithm | Sky Diffuse Modeling Algorithm | External Shading Calculation Method | Output External Shading Calculation Results | Disable Self-Shading Within Shading Zone Groups | Disable Self-Shading From Shading Zone Groups to Other Zones | |
| 1 | AverageOverDaysInFrequency | 20 | 15000 | SutherlandHodgman | SimpleSkyDiffuseModeling | InternalCalculation | No | No | No |
| Zone Name | Mixing/Mundt/UCSDDV/UCSDCV/UCSDUFI/UCSDUFE/User Defined | |
| 1 | 01_A1 | Mixing/Well-Stirred |
| 2 | 01_A2 | Mixing/Well-Stirred |
| 3 | 01_B2 | Mixing/Well-Stirred |
| 4 | 01_C1 | Mixing/Well-Stirred |
| 5 | 02_A1 | Mixing/Well-Stirred |
| 6 | 02_A2 | Mixing/Well-Stirred |
| 7 | 02_B2 | Mixing/Well-Stirred |
| 8 | 02_C1 | Mixing/Well-Stirred |
| 9 | 03_A1 | Mixing/Well-Stirred |
| 10 | 03_A2 | Mixing/Well-Stirred |
| 11 | 03_B2 | Mixing/Well-Stirred |
| 12 | 03_C1 | Mixing/Well-Stirred |
| No Multizone or Distribution/Multizone with Distribution/Multizone without Distribution/Multizone with Distribution only during Fan Operation | |
| 1 | NoMultizoneOrDistribution |
| Sensible Heat Capacity Multiplier | Moisture Capacity Multiplier | Carbon Dioxide Capacity Multiplier | Generic Contaminant Capacity Multiplier | |
| 1 | 1.000 | 1.000 | 1.000 | 1.000 |
| Zone Name | DOAS Design Control Strategy | DOAS Design Low Setpoint Temperature {C} | DOAS Design High Setpoint Temperature {C} | |
| 1 | 01_A1 | NeutralSupplyAir | 21.100 | 23.900 |
| Value | |
| 1 | 6 |
| Sizing Factor ID | Value | |
| 1 | Global | 1.2500 |
| 2 | Zone 01_A1 | 1.2500 |
| 3 | Zone 01_A2 | 1.2500 |
| 4 | Zone 01_B2 | 1.2500 |
| 5 | Zone 01_C1 | 1.2500 |
| 6 | Zone 02_A1 | 1.2500 |
| 7 | Zone 02_A2 | 1.2500 |
| 8 | Zone 02_B2 | 1.2500 |
| 9 | Zone 02_C1 | 1.2500 |
| 10 | Zone 03_A1 | 1.2500 |
| 11 | Zone 03_A2 | 1.2500 |
| 12 | Zone 03_B2 | 1.2500 |
| 13 | Zone 03_C1 | 1.2500 |
| Sizing Factor ID | Value | |
| 1 | Global | 1.1500 |
| 2 | Zone 01_A1 | 1.1500 |
| 3 | Zone 01_A2 | 1.1500 |
| 4 | Zone 01_B2 | 1.1500 |
| 5 | Zone 01_C1 | 1.1500 |
| 6 | Zone 02_A1 | 1.1500 |
| 7 | Zone 02_A2 | 1.1500 |
| 8 | Zone 02_B2 | 1.1500 |
| 9 | Zone 02_C1 | 1.1500 |
| 10 | Zone 03_A1 | 1.1500 |
| 11 | Zone 03_A2 | 1.1500 |
| 12 | Zone 03_B2 | 1.1500 |
| 13 | Zone 03_C1 | 1.1500 |
| Zone Name | Load Type | Calc Des Load {W} | User Des Load {W} | Calc Des Air Flow Rate {m3/s} | User Des Air Flow Rate {m3/s} | Design Day Name | Date/Time of Peak | Temperature at Peak {C} | Humidity Ratio at Peak {kgWater/kgDryAir} | Floor Area {m2} | # Occupants | Calc Outdoor Air Flow Rate {m3/s} | Calc DOAS Heat Addition Rate {W} | |
| 1 | 01_A1 | Cooling | 2888.32746 | 3321.57658 | 0.17025 | 0.19578 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 20.27500 | 7.02465E-003 | 57.59988 | 1.55000 | 2.35974E-002 | -66.78904 |
| 2 | 01_A1 | Heating | 25.11708 | 31.39635 | 1.85544E-003 | 2.35974E-002 | ANCHORAGEELMENDORFANNHUM_N99.6CONDNSDPMCDB | 1/21 01:40:00 | -23.70000 | 2.37546E-004 | 57.59988 | 1.55000 | 2.35974E-002 | -66.40649 |
| 3 | 01_A2 | Cooling | 3669.22772 | 4219.61188 | 0.21633 | 0.24878 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 20.27500 | 7.02465E-003 | 62.24504 | 1.55000 | 2.35974E-002 | 0.00000 |
| 4 | 01_A2 | Heating | 0.00000 | 0.00000 | 0.00000 | 0.32470 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | -26.00000 | 3.54096E-004 | 62.24504 | 1.55000 | 2.35974E-002 | 0.00000 | |
| 5 | 01_B2 | Cooling | 3791.76895 | 4360.53430 | 0.22354 | 0.25708 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 20.27500 | 7.02465E-003 | 96.77400 | 2.47000 | 2.35974E-002 | 0.00000 |
| 6 | 01_B2 | Heating | 141.23549 | 176.54436 | 8.33271E-003 | 2.35974E-002 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 05:00:00 | -26.00000 | 3.54096E-004 | 96.77400 | 2.47000 | 2.35974E-002 | 0.00000 |
| 7 | 01_C1 | Cooling | 2842.30087 | 3268.64600 | 0.16757 | 0.19270 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 20.27500 | 7.02465E-003 | 113.62042 | 3.39000 | 2.35974E-002 | 0.00000 |
| 8 | 01_C1 | Heating | 101.74354 | 127.17943 | 6.00256E-003 | 2.35974E-002 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 05:00:00 | -26.00000 | 3.54096E-004 | 113.62042 | 3.39000 | 2.35974E-002 | 0.00000 |
| 9 | 02_A1 | Cooling | 4487.79665 | 5160.96615 | 0.26459 | 0.30428 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 20.27500 | 7.02465E-003 | 57.59988 | 1.55000 | 2.35974E-002 | 0.00000 |
| 10 | 02_A1 | Heating | 0.00000 | 0.00000 | 0.00000 | 0.32470 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | -26.00000 | 3.54096E-004 | 57.59988 | 1.55000 | 2.35974E-002 | 0.00000 | |
| 11 | 02_A2 | Cooling | 5488.08492 | 6311.29766 | 0.32356 | 0.37210 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 20.27500 | 7.02465E-003 | 62.24504 | 1.55000 | 2.35974E-002 | 0.00000 |
| 12 | 02_A2 | Heating | 0.00000 | 0.00000 | 0.00000 | 0.32470 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | -26.00000 | 3.54096E-004 | 62.24504 | 1.55000 | 2.35974E-002 | 0.00000 | |
| 13 | 02_B2 | Cooling | 6252.36041 | 7190.21447 | 0.36861 | 0.42390 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 20.27500 | 7.02465E-003 | 96.77400 | 2.47000 | 2.35974E-002 | 0.00000 |
| 14 | 02_B2 | Heating | 0.00000 | 0.00000 | 0.00000 | 0.32470 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | -26.00000 | 3.54096E-004 | 96.77400 | 2.47000 | 2.35974E-002 | 0.00000 | |
| 15 | 02_C1 | Cooling | 5474.43380 | 6295.59887 | 0.32274 | 0.37116 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 20.27500 | 7.02465E-003 | 113.62042 | 3.39000 | 2.35974E-002 | 0.00000 |
| 16 | 02_C1 | Heating | 0.00000 | 0.00000 | 0.00000 | 0.32470 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | -26.00000 | 3.54096E-004 | 113.62042 | 3.39000 | 2.35974E-002 | 0.00000 | |
| 17 | 03_A1 | Cooling | 4717.02441 | 5424.57807 | 0.27811 | 0.31983 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 20.27500 | 7.02465E-003 | 57.59988 | 1.55000 | 2.35974E-002 | 0.00000 |
| 18 | 03_A1 | Heating | 0.00000 | 0.00000 | 0.00000 | 0.32470 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | -26.00000 | 3.54096E-004 | 57.59988 | 1.55000 | 2.35974E-002 | 0.00000 | |
| 19 | 03_A2 | Cooling | 5724.80005 | 6583.52006 | 0.33752 | 0.38815 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 20.27500 | 7.02465E-003 | 62.24504 | 1.55000 | 2.35974E-002 | 0.00000 |
| 20 | 03_A2 | Heating | 0.00000 | 0.00000 | 0.00000 | 0.32470 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | -26.00000 | 3.54096E-004 | 62.24504 | 1.55000 | 2.35974E-002 | 0.00000 | |
| 21 | 03_B2 | Cooling | 6682.94041 | 7685.38148 | 0.39399 | 0.45309 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 20.27500 | 7.02465E-003 | 96.77400 | 2.47000 | 2.35974E-002 | 0.00000 |
| 22 | 03_B2 | Heating | 0.00000 | 0.00000 | 0.00000 | 0.32470 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | -26.00000 | 3.54096E-004 | 96.77400 | 2.47000 | 2.35974E-002 | 0.00000 | |
| 23 | 03_C1 | Cooling | 5804.78697 | 6675.50502 | 0.34222 | 0.39355 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 20.27500 | 7.02465E-003 | 113.62042 | 3.39000 | 2.35974E-002 | 0.00000 |
| 24 | 03_C1 | Heating | 0.00000 | 0.00000 | 0.00000 | 0.32470 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | -26.00000 | 3.54096E-004 | 113.62042 | 3.39000 | 2.35974E-002 | 0.00000 |
| System Name | Load Type | Peak Load Kind | User Design Capacity | Calc Des Air Flow Rate [m3/s] | User Des Air Flow Rate [m3/s] | Design Day Name | Date/Time of Peak | |
| 1 | AIR LOOP HVAC 1 | Cooling | Sensible | 1758.71 | 0.19578 | 0.19578 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 05:00:00 |
| 2 | AIR LOOP HVAC 1 | Heating | Sensible | 1145.64 | 2.35974E-002 | 2.35974E-002 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 |
| 3 | AIR LOOP HVAC 10 | Cooling | Sensible | 3486.67 | 0.38815 | 0.38815 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 05:00:00 |
| 4 | AIR LOOP HVAC 10 | Heating | Sensible | 16661.45 | 0.32470 | 0.32470 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 |
| 5 | AIR LOOP HVAC 11 | Cooling | Sensible | 4070.05 | 0.45309 | 0.45309 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 05:00:00 |
| 6 | AIR LOOP HVAC 11 | Heating | Sensible | 16661.45 | 0.32470 | 0.32470 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 |
| 7 | AIR LOOP HVAC 12 | Cooling | Sensible | 3535.22 | 0.39355 | 0.39355 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 05:00:00 |
| 8 | AIR LOOP HVAC 12 | Heating | Sensible | 16661.45 | 0.32470 | 0.32470 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 |
| 9 | AIR LOOP HVAC 2 | Cooling | Sensible | 2234.78 | 0.24878 | 0.24878 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 05:00:00 |
| 10 | AIR LOOP HVAC 2 | Heating | Sensible | 16661.45 | 0.32470 | 0.32470 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 |
| 11 | AIR LOOP HVAC 3 | Cooling | Sensible | 2309.27 | 0.25708 | 0.25708 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 05:00:00 |
| 12 | AIR LOOP HVAC 3 | Heating | Sensible | 1210.86 | 2.35974E-002 | 2.35974E-002 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 03:20:00 |
| 13 | AIR LOOP HVAC 4 | Cooling | Sensible | 1731.03 | 0.19270 | 0.19270 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 05:00:00 |
| 14 | AIR LOOP HVAC 4 | Heating | Sensible | 1210.86 | 2.35974E-002 | 2.35974E-002 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 04:20:00 |
| 15 | AIR LOOP HVAC 5 | Cooling | Sensible | 2733.34 | 0.30428 | 0.30428 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 05:00:00 |
| 16 | AIR LOOP HVAC 5 | Heating | Sensible | 16661.45 | 0.32470 | 0.32470 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 |
| 17 | AIR LOOP HVAC 6 | Cooling | Sensible | 3342.49 | 0.37210 | 0.37210 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 05:00:00 |
| 18 | AIR LOOP HVAC 6 | Heating | Sensible | 16661.45 | 0.32470 | 0.32470 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 |
| 19 | AIR LOOP HVAC 7 | Cooling | Sensible | 3807.83 | 0.42390 | 0.42390 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 05:00:00 |
| 20 | AIR LOOP HVAC 7 | Heating | Sensible | 16661.45 | 0.32470 | 0.32470 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 |
| 21 | AIR LOOP HVAC 8 | Cooling | Sensible | 3334.03 | 0.37116 | 0.37116 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 05:00:00 |
| 22 | AIR LOOP HVAC 8 | Heating | Sensible | 16661.45 | 0.32470 | 0.32470 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 |
| 23 | AIR LOOP HVAC 9 | Cooling | Sensible | 2872.95 | 0.31983 | 0.31983 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 05:00:00 |
| 24 | AIR LOOP HVAC 9 | Heating | Sensible | 16661.45 | 0.32470 | 0.32470 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 |
| Component Type | Component Name | Input Field Description | Value | |
| 1 | AirTerminal:SingleDuct:Uncontrolled | DIFFUSER | Design Size Maximum Air Flow Rate [m3/s] | 0.19578 |
| 2 | AirTerminal:SingleDuct:Uncontrolled | DIFFUSER 1 | Design Size Maximum Air Flow Rate [m3/s] | 0.32470 |
| 3 | AirTerminal:SingleDuct:Uncontrolled | DIFFUSER 2 | Design Size Maximum Air Flow Rate [m3/s] | 0.25708 |
| 4 | AirTerminal:SingleDuct:Uncontrolled | DIFFUSER 3 | Design Size Maximum Air Flow Rate [m3/s] | 0.19270 |
| 5 | AirTerminal:SingleDuct:Uncontrolled | DIFFUSER 4 | Design Size Maximum Air Flow Rate [m3/s] | 0.32470 |
| 6 | AirTerminal:SingleDuct:Uncontrolled | DIFFUSER 5 | Design Size Maximum Air Flow Rate [m3/s] | 0.37210 |
| 7 | AirTerminal:SingleDuct:Uncontrolled | DIFFUSER 11 | Design Size Maximum Air Flow Rate [m3/s] | 0.42390 |
| 8 | AirTerminal:SingleDuct:Uncontrolled | DIFFUSER 6 | Design Size Maximum Air Flow Rate [m3/s] | 0.37116 |
| 9 | AirTerminal:SingleDuct:Uncontrolled | DIFFUSER 7 | Design Size Maximum Air Flow Rate [m3/s] | 0.32470 |
| 10 | AirTerminal:SingleDuct:Uncontrolled | DIFFUSER 8 | Design Size Maximum Air Flow Rate [m3/s] | 0.38815 |
| 11 | AirTerminal:SingleDuct:Uncontrolled | DIFFUSER 9 | Design Size Maximum Air Flow Rate [m3/s] | 0.45309 |
| 12 | AirTerminal:SingleDuct:Uncontrolled | DIFFUSER 10 | Design Size Maximum Air Flow Rate [m3/s] | 0.39355 |
| 13 | AirLoopHVAC | AIR LOOP HVAC 1 | Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | 0.19578 |
| 14 | AirLoopHVAC | AIR LOOP HVAC 1 | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | 0.19578 |
| 15 | AirLoopHVAC | AIR LOOP HVAC 1 | Sum of Air Terminal Maximum Flow Rates [m3/s] | 0.19578 |
| 16 | AirLoopHVAC | AIR LOOP HVAC 1 | Adjusted Heating Design Air Flow Rate [m3/s] | 0.19578 |
| 17 | AirLoopHVAC | AIR LOOP HVAC 1 | Adjusted Cooling Design Air Flow Rate [m3/s] | 0.19578 |
| 18 | AirLoopHVAC | AIR LOOP HVAC 1 | Adjusted Main Design Air Flow Rate [m3/s] | 0.19578 |
| 19 | AirLoopHVAC | AIR LOOP HVAC 1 | User Heating Air Flow Ratio [] | 0.30000 |
| 20 | AirLoopHVAC | AIR LOOP HVAC 1 | Calculated Heating Air Flow Ratio [] | 1.00000 |
| 21 | AirLoopHVAC | AIR LOOP HVAC 10 | Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | 0.38815 |
| 22 | AirLoopHVAC | AIR LOOP HVAC 10 | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | 0.38815 |
| 23 | AirLoopHVAC | AIR LOOP HVAC 10 | Sum of Air Terminal Maximum Flow Rates [m3/s] | 0.38815 |
| 24 | AirLoopHVAC | AIR LOOP HVAC 10 | Adjusted Heating Design Air Flow Rate [m3/s] | 0.38815 |
| 25 | AirLoopHVAC | AIR LOOP HVAC 10 | Adjusted Cooling Design Air Flow Rate [m3/s] | 0.38815 |
| 26 | AirLoopHVAC | AIR LOOP HVAC 10 | Adjusted Main Design Air Flow Rate [m3/s] | 0.38815 |
| 27 | AirLoopHVAC | AIR LOOP HVAC 10 | User Heating Air Flow Ratio [] | 0.30000 |
| 28 | AirLoopHVAC | AIR LOOP HVAC 10 | Calculated Heating Air Flow Ratio [] | 1.00000 |
| 29 | AirLoopHVAC | AIR LOOP HVAC 11 | Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | 0.45309 |
| 30 | AirLoopHVAC | AIR LOOP HVAC 11 | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | 0.45309 |
| 31 | AirLoopHVAC | AIR LOOP HVAC 11 | Sum of Air Terminal Maximum Flow Rates [m3/s] | 0.45309 |
| 32 | AirLoopHVAC | AIR LOOP HVAC 11 | Adjusted Heating Design Air Flow Rate [m3/s] | 0.45309 |
| 33 | AirLoopHVAC | AIR LOOP HVAC 11 | Adjusted Cooling Design Air Flow Rate [m3/s] | 0.45309 |
| 34 | AirLoopHVAC | AIR LOOP HVAC 11 | Adjusted Main Design Air Flow Rate [m3/s] | 0.45309 |
| 35 | AirLoopHVAC | AIR LOOP HVAC 11 | User Heating Air Flow Ratio [] | 0.30000 |
| 36 | AirLoopHVAC | AIR LOOP HVAC 11 | Calculated Heating Air Flow Ratio [] | 1.00000 |
| 37 | AirLoopHVAC | AIR LOOP HVAC 12 | Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | 0.39355 |
| 38 | AirLoopHVAC | AIR LOOP HVAC 12 | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | 0.39355 |
| 39 | AirLoopHVAC | AIR LOOP HVAC 12 | Sum of Air Terminal Maximum Flow Rates [m3/s] | 0.39355 |
| 40 | AirLoopHVAC | AIR LOOP HVAC 12 | Adjusted Heating Design Air Flow Rate [m3/s] | 0.39355 |
| 41 | AirLoopHVAC | AIR LOOP HVAC 12 | Adjusted Cooling Design Air Flow Rate [m3/s] | 0.39355 |
| 42 | AirLoopHVAC | AIR LOOP HVAC 12 | Adjusted Main Design Air Flow Rate [m3/s] | 0.39355 |
| 43 | AirLoopHVAC | AIR LOOP HVAC 12 | User Heating Air Flow Ratio [] | 0.30000 |
| 44 | AirLoopHVAC | AIR LOOP HVAC 12 | Calculated Heating Air Flow Ratio [] | 1.00000 |
| 45 | AirLoopHVAC | AIR LOOP HVAC 2 | Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | 0.32470 |
| 46 | AirLoopHVAC | AIR LOOP HVAC 2 | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | 0.32470 |
| 47 | AirLoopHVAC | AIR LOOP HVAC 2 | Sum of Air Terminal Maximum Flow Rates [m3/s] | 0.32470 |
| 48 | AirLoopHVAC | AIR LOOP HVAC 2 | Adjusted Heating Design Air Flow Rate [m3/s] | 0.32470 |
| 49 | AirLoopHVAC | AIR LOOP HVAC 2 | Adjusted Cooling Design Air Flow Rate [m3/s] | 0.32470 |
| 50 | AirLoopHVAC | AIR LOOP HVAC 2 | Adjusted Main Design Air Flow Rate [m3/s] | 0.32470 |
| 51 | AirLoopHVAC | AIR LOOP HVAC 2 | User Heating Air Flow Ratio [] | 0.30000 |
| 52 | AirLoopHVAC | AIR LOOP HVAC 2 | Calculated Heating Air Flow Ratio [] | 1.00000 |
| 53 | AirLoopHVAC | AIR LOOP HVAC 3 | Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | 0.25708 |
| 54 | AirLoopHVAC | AIR LOOP HVAC 3 | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | 0.25708 |
| 55 | AirLoopHVAC | AIR LOOP HVAC 3 | Sum of Air Terminal Maximum Flow Rates [m3/s] | 0.25708 |
| 56 | AirLoopHVAC | AIR LOOP HVAC 3 | Adjusted Heating Design Air Flow Rate [m3/s] | 0.25708 |
| 57 | AirLoopHVAC | AIR LOOP HVAC 3 | Adjusted Cooling Design Air Flow Rate [m3/s] | 0.25708 |
| 58 | AirLoopHVAC | AIR LOOP HVAC 3 | Adjusted Main Design Air Flow Rate [m3/s] | 0.25708 |
| 59 | AirLoopHVAC | AIR LOOP HVAC 3 | User Heating Air Flow Ratio [] | 0.30000 |
| 60 | AirLoopHVAC | AIR LOOP HVAC 3 | Calculated Heating Air Flow Ratio [] | 1.00000 |
| 61 | AirLoopHVAC | AIR LOOP HVAC 4 | Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | 0.19270 |
| 62 | AirLoopHVAC | AIR LOOP HVAC 4 | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | 0.19270 |
| 63 | AirLoopHVAC | AIR LOOP HVAC 4 | Sum of Air Terminal Maximum Flow Rates [m3/s] | 0.19270 |
| 64 | AirLoopHVAC | AIR LOOP HVAC 4 | Adjusted Heating Design Air Flow Rate [m3/s] | 0.19270 |
| 65 | AirLoopHVAC | AIR LOOP HVAC 4 | Adjusted Cooling Design Air Flow Rate [m3/s] | 0.19270 |
| 66 | AirLoopHVAC | AIR LOOP HVAC 4 | Adjusted Main Design Air Flow Rate [m3/s] | 0.19270 |
| 67 | AirLoopHVAC | AIR LOOP HVAC 4 | User Heating Air Flow Ratio [] | 0.30000 |
| 68 | AirLoopHVAC | AIR LOOP HVAC 4 | Calculated Heating Air Flow Ratio [] | 1.00000 |
| 69 | AirLoopHVAC | AIR LOOP HVAC 5 | Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | 0.32470 |
| 70 | AirLoopHVAC | AIR LOOP HVAC 5 | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | 0.32470 |
| 71 | AirLoopHVAC | AIR LOOP HVAC 5 | Sum of Air Terminal Maximum Flow Rates [m3/s] | 0.32470 |
| 72 | AirLoopHVAC | AIR LOOP HVAC 5 | Adjusted Heating Design Air Flow Rate [m3/s] | 0.32470 |
| 73 | AirLoopHVAC | AIR LOOP HVAC 5 | Adjusted Cooling Design Air Flow Rate [m3/s] | 0.32470 |
| 74 | AirLoopHVAC | AIR LOOP HVAC 5 | Adjusted Main Design Air Flow Rate [m3/s] | 0.32470 |
| 75 | AirLoopHVAC | AIR LOOP HVAC 5 | User Heating Air Flow Ratio [] | 0.30000 |
| 76 | AirLoopHVAC | AIR LOOP HVAC 5 | Calculated Heating Air Flow Ratio [] | 1.00000 |
| 77 | AirLoopHVAC | AIR LOOP HVAC 6 | Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | 0.37210 |
| 78 | AirLoopHVAC | AIR LOOP HVAC 6 | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | 0.37210 |
| 79 | AirLoopHVAC | AIR LOOP HVAC 6 | Sum of Air Terminal Maximum Flow Rates [m3/s] | 0.37210 |
| 80 | AirLoopHVAC | AIR LOOP HVAC 6 | Adjusted Heating Design Air Flow Rate [m3/s] | 0.37210 |
| 81 | AirLoopHVAC | AIR LOOP HVAC 6 | Adjusted Cooling Design Air Flow Rate [m3/s] | 0.37210 |
| 82 | AirLoopHVAC | AIR LOOP HVAC 6 | Adjusted Main Design Air Flow Rate [m3/s] | 0.37210 |
| 83 | AirLoopHVAC | AIR LOOP HVAC 6 | User Heating Air Flow Ratio [] | 0.30000 |
| 84 | AirLoopHVAC | AIR LOOP HVAC 6 | Calculated Heating Air Flow Ratio [] | 1.00000 |
| 85 | AirLoopHVAC | AIR LOOP HVAC 7 | Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | 0.42390 |
| 86 | AirLoopHVAC | AIR LOOP HVAC 7 | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | 0.42390 |
| 87 | AirLoopHVAC | AIR LOOP HVAC 7 | Sum of Air Terminal Maximum Flow Rates [m3/s] | 0.42390 |
| 88 | AirLoopHVAC | AIR LOOP HVAC 7 | Adjusted Heating Design Air Flow Rate [m3/s] | 0.42390 |
| 89 | AirLoopHVAC | AIR LOOP HVAC 7 | Adjusted Cooling Design Air Flow Rate [m3/s] | 0.42390 |
| 90 | AirLoopHVAC | AIR LOOP HVAC 7 | Adjusted Main Design Air Flow Rate [m3/s] | 0.42390 |
| 91 | AirLoopHVAC | AIR LOOP HVAC 7 | User Heating Air Flow Ratio [] | 0.30000 |
| 92 | AirLoopHVAC | AIR LOOP HVAC 7 | Calculated Heating Air Flow Ratio [] | 1.00000 |
| 93 | AirLoopHVAC | AIR LOOP HVAC 8 | Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | 0.37116 |
| 94 | AirLoopHVAC | AIR LOOP HVAC 8 | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | 0.37116 |
| 95 | AirLoopHVAC | AIR LOOP HVAC 8 | Sum of Air Terminal Maximum Flow Rates [m3/s] | 0.37116 |
| 96 | AirLoopHVAC | AIR LOOP HVAC 8 | Adjusted Heating Design Air Flow Rate [m3/s] | 0.37116 |
| 97 | AirLoopHVAC | AIR LOOP HVAC 8 | Adjusted Cooling Design Air Flow Rate [m3/s] | 0.37116 |
| 98 | AirLoopHVAC | AIR LOOP HVAC 8 | Adjusted Main Design Air Flow Rate [m3/s] | 0.37116 |
| 99 | AirLoopHVAC | AIR LOOP HVAC 8 | User Heating Air Flow Ratio [] | 0.30000 |
| 100 | AirLoopHVAC | AIR LOOP HVAC 8 | Calculated Heating Air Flow Ratio [] | 1.00000 |
| 101 | AirLoopHVAC | AIR LOOP HVAC 9 | Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | 0.32470 |
| 102 | AirLoopHVAC | AIR LOOP HVAC 9 | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | 0.32470 |
| 103 | AirLoopHVAC | AIR LOOP HVAC 9 | Sum of Air Terminal Maximum Flow Rates [m3/s] | 0.32470 |
| 104 | AirLoopHVAC | AIR LOOP HVAC 9 | Adjusted Heating Design Air Flow Rate [m3/s] | 0.32470 |
| 105 | AirLoopHVAC | AIR LOOP HVAC 9 | Adjusted Cooling Design Air Flow Rate [m3/s] | 0.32470 |
| 106 | AirLoopHVAC | AIR LOOP HVAC 9 | Adjusted Main Design Air Flow Rate [m3/s] | 0.32470 |
| 107 | AirLoopHVAC | AIR LOOP HVAC 9 | User Heating Air Flow Ratio [] | 0.30000 |
| 108 | AirLoopHVAC | AIR LOOP HVAC 9 | Calculated Heating Air Flow Ratio [] | 1.00000 |
| 109 | AirLoopHVAC | AIR LOOP HVAC 1 | Design Supply Air Flow Rate [m3/s] | 0.19578 |
| 110 | AirLoopHVAC | AIR LOOP HVAC 10 | Design Supply Air Flow Rate [m3/s] | 0.38815 |
| 111 | AirLoopHVAC | AIR LOOP HVAC 11 | Design Supply Air Flow Rate [m3/s] | 0.45309 |
| 112 | AirLoopHVAC | AIR LOOP HVAC 12 | Design Supply Air Flow Rate [m3/s] | 0.39355 |
| 113 | AirLoopHVAC | AIR LOOP HVAC 2 | Design Supply Air Flow Rate [m3/s] | 0.32470 |
| 114 | AirLoopHVAC | AIR LOOP HVAC 3 | Design Supply Air Flow Rate [m3/s] | 0.25708 |
| 115 | AirLoopHVAC | AIR LOOP HVAC 4 | Design Supply Air Flow Rate [m3/s] | 0.19270 |
| 116 | AirLoopHVAC | AIR LOOP HVAC 5 | Design Supply Air Flow Rate [m3/s] | 0.32470 |
| 117 | AirLoopHVAC | AIR LOOP HVAC 6 | Design Supply Air Flow Rate [m3/s] | 0.37210 |
| 118 | AirLoopHVAC | AIR LOOP HVAC 7 | Design Supply Air Flow Rate [m3/s] | 0.42390 |
| 119 | AirLoopHVAC | AIR LOOP HVAC 8 | Design Supply Air Flow Rate [m3/s] | 0.37116 |
| 120 | AirLoopHVAC | AIR LOOP HVAC 9 | Design Supply Air Flow Rate [m3/s] | 0.32470 |
| 121 | Controller:OutdoorAir | OUTDOOR AIR CONTROLLER | Maximum Outdoor Air Flow Rate [m3/s] | 0.19578 |
| 122 | Controller:OutdoorAir | OUTDOOR AIR CONTROLLER | Minimum Outdoor Air Flow Rate [m3/s] | 2.35974E-002 |
| 123 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT | Design Size Supply Air Flow Rate [m3/s] | 0.19578 |
| 124 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT | Design Size Heating Supply Air Flow Rate [m3/s] | 0.19578 |
| 125 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT | Design Size Cooling Supply Air Flow Rate [m3/s] | 0.19578 |
| 126 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT | Design Size No Load Supply Air Flow Rate [m3/s] | 0.19578 |
| 127 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT | Design Size Nominal Cooling Capacity [W] | 4861.80475 |
| 128 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT | Design Size Nominal Heating Capacity [W] | 4861.80475 |
| 129 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT | Design Size Maximum Supply Air Temperature [C] | 16.70000 |
| 130 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT | User-Specified Maximum Supply Air Temperature [C] | 80.00000 |
| 131 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT | Design Size Supplemental Heating Coil Nominal Capacity [W] | 4861.80475 |
| 132 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT | User-Specified Supplemental Heating Coil Nominal Capacity [W] | 4861.80475 |
| 133 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT | Fraction of Supply Air Flow That Goes Through the Controlling Zone | 1.00000 |
| 134 | Fan:OnOff | FAN ON OFF 5 | Design Size Maximum Flow Rate [m3/s] | 0.19578 |
| 135 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 4 | Design Size Rated Air Flow Rate [m3/s] | 0.19578 |
| 136 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 4 | Design Size Gross Rated Total Cooling Capacity [W] | 4861.80475 |
| 137 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 4 | Design Size Gross Rated Sensible Heat Ratio | 0.69808 |
| 138 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 3 | Design Size Rated Air Flow Rate [m3/s] | 0.19578 |
| 139 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 3 | Design Size Gross Rated Heating Capacity [W] | 4861.80475 |
| 140 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 3 | Design Size Resistive Defrost Heater Capacity [W] | 4861.80475 |
| 141 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 3 | User-Specified Resistive Defrost Heater Capacity [W] | 2000.00000 |
| 142 | Coil:Heating:Electric | ELEC HTG COIL 5 | Design Size Nominal Capacity [W] | 4861.80475 |
| 143 | Controller:OutdoorAir | OUTDOOR AIR CONTROLLER 9 | Maximum Outdoor Air Flow Rate [m3/s] | 0.38815 |
| 144 | Controller:OutdoorAir | OUTDOOR AIR CONTROLLER 9 | Minimum Outdoor Air Flow Rate [m3/s] | 2.35974E-002 |
| 145 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 9 | Design Size Supply Air Flow Rate [m3/s] | 0.38815 |
| 146 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 9 | Design Size Heating Supply Air Flow Rate [m3/s] | 0.38815 |
| 147 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 9 | Design Size Cooling Supply Air Flow Rate [m3/s] | 0.38815 |
| 148 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 9 | Design Size No Load Supply Air Flow Rate [m3/s] | 0.38815 |
| 149 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 9 | Design Size Nominal Cooling Capacity [W] | 9638.61459 |
| 150 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 9 | Design Size Nominal Heating Capacity [W] | 9638.61459 |
| 151 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 9 | Design Size Maximum Supply Air Temperature [C] | 16.70000 |
| 152 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 9 | User-Specified Maximum Supply Air Temperature [C] | 80.00000 |
| 153 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 9 | Design Size Supplemental Heating Coil Nominal Capacity [W] | 9638.61459 |
| 154 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 9 | User-Specified Supplemental Heating Coil Nominal Capacity [W] | 9638.61459 |
| 155 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 9 | Fraction of Supply Air Flow That Goes Through the Controlling Zone | 1.00000 |
| 156 | Fan:OnOff | FAN ON OFF 14 | Design Size Maximum Flow Rate [m3/s] | 0.38815 |
| 157 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 13 | Design Size Rated Air Flow Rate [m3/s] | 0.38815 |
| 158 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 13 | Design Size Gross Rated Total Cooling Capacity [W] | 9638.61459 |
| 159 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 13 | Design Size Gross Rated Sensible Heat Ratio | 0.69808 |
| 160 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 12 | Design Size Rated Air Flow Rate [m3/s] | 0.38815 |
| 161 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 12 | Design Size Gross Rated Heating Capacity [W] | 9638.61459 |
| 162 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 12 | Design Size Resistive Defrost Heater Capacity [W] | 9638.61459 |
| 163 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 12 | User-Specified Resistive Defrost Heater Capacity [W] | 2000.00000 |
| 164 | Coil:Heating:Electric | ELEC HTG COIL 14 | Design Size Nominal Capacity [W] | 9638.61459 |
| 165 | Controller:OutdoorAir | OUTDOOR AIR CONTROLLER 10 | Maximum Outdoor Air Flow Rate [m3/s] | 0.45309 |
| 166 | Controller:OutdoorAir | OUTDOOR AIR CONTROLLER 10 | Minimum Outdoor Air Flow Rate [m3/s] | 2.35974E-002 |
| 167 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 10 | Design Size Supply Air Flow Rate [m3/s] | 0.45309 |
| 168 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 10 | Design Size Heating Supply Air Flow Rate [m3/s] | 0.45309 |
| 169 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 10 | Design Size Cooling Supply Air Flow Rate [m3/s] | 0.45309 |
| 170 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 10 | Design Size No Load Supply Air Flow Rate [m3/s] | 0.45309 |
| 171 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 10 | Design Size Nominal Cooling Capacity [W] | 11251.34830 |
| 172 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 10 | Design Size Nominal Heating Capacity [W] | 11251.34830 |
| 173 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 10 | Design Size Maximum Supply Air Temperature [C] | 16.70000 |
| 174 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 10 | User-Specified Maximum Supply Air Temperature [C] | 80.00000 |
| 175 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 10 | Design Size Supplemental Heating Coil Nominal Capacity [W] | 11251.34830 |
| 176 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 10 | User-Specified Supplemental Heating Coil Nominal Capacity [W] | 11251.34830 |
| 177 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 10 | Fraction of Supply Air Flow That Goes Through the Controlling Zone | 1.00000 |
| 178 | Fan:OnOff | FAN ON OFF 15 | Design Size Maximum Flow Rate [m3/s] | 0.45309 |
| 179 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 14 | Design Size Rated Air Flow Rate [m3/s] | 0.45309 |
| 180 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 14 | Design Size Gross Rated Total Cooling Capacity [W] | 11251.34830 |
| 181 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 14 | Design Size Gross Rated Sensible Heat Ratio | 0.69808 |
| 182 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 13 | Design Size Rated Air Flow Rate [m3/s] | 0.45309 |
| 183 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 13 | Design Size Gross Rated Heating Capacity [W] | 11251.34830 |
| 184 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 13 | Design Size Resistive Defrost Heater Capacity [W] | 11251.34830 |
| 185 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 13 | User-Specified Resistive Defrost Heater Capacity [W] | 2000.00000 |
| 186 | Coil:Heating:Electric | ELEC HTG COIL 15 | Design Size Nominal Capacity [W] | 11251.34830 |
| 187 | Controller:OutdoorAir | OUTDOOR AIR CONTROLLER 11 | Maximum Outdoor Air Flow Rate [m3/s] | 0.39355 |
| 188 | Controller:OutdoorAir | OUTDOOR AIR CONTROLLER 11 | Minimum Outdoor Air Flow Rate [m3/s] | 2.35974E-002 |
| 189 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 11 | Design Size Supply Air Flow Rate [m3/s] | 0.39355 |
| 190 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 11 | Design Size Heating Supply Air Flow Rate [m3/s] | 0.39355 |
| 191 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 11 | Design Size Cooling Supply Air Flow Rate [m3/s] | 0.39355 |
| 192 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 11 | Design Size No Load Supply Air Flow Rate [m3/s] | 0.39355 |
| 193 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 11 | Design Size Nominal Cooling Capacity [W] | 9772.82988 |
| 194 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 11 | Design Size Nominal Heating Capacity [W] | 9772.82988 |
| 195 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 11 | Design Size Maximum Supply Air Temperature [C] | 16.70000 |
| 196 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 11 | User-Specified Maximum Supply Air Temperature [C] | 80.00000 |
| 197 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 11 | Design Size Supplemental Heating Coil Nominal Capacity [W] | 9772.82988 |
| 198 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 11 | User-Specified Supplemental Heating Coil Nominal Capacity [W] | 9772.82988 |
| 199 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 11 | Fraction of Supply Air Flow That Goes Through the Controlling Zone | 1.00000 |
| 200 | Fan:OnOff | FAN ON OFF 16 | Design Size Maximum Flow Rate [m3/s] | 0.39355 |
| 201 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 15 | Design Size Rated Air Flow Rate [m3/s] | 0.39355 |
| 202 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 15 | Design Size Gross Rated Total Cooling Capacity [W] | 9772.82988 |
| 203 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 15 | Design Size Gross Rated Sensible Heat Ratio | 0.69808 |
| 204 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 14 | Design Size Rated Air Flow Rate [m3/s] | 0.39355 |
| 205 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 14 | Design Size Gross Rated Heating Capacity [W] | 9772.82988 |
| 206 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 14 | Design Size Resistive Defrost Heater Capacity [W] | 9772.82988 |
| 207 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 14 | User-Specified Resistive Defrost Heater Capacity [W] | 2000.00000 |
| 208 | Coil:Heating:Electric | ELEC HTG COIL 16 | Design Size Nominal Capacity [W] | 9772.82988 |
| 209 | Controller:OutdoorAir | OUTDOOR AIR CONTROLLER 1 | Maximum Outdoor Air Flow Rate [m3/s] | 0.32470 |
| 210 | Controller:OutdoorAir | OUTDOOR AIR CONTROLLER 1 | Minimum Outdoor Air Flow Rate [m3/s] | 2.35974E-002 |
| 211 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 1 | Design Size Supply Air Flow Rate [m3/s] | 0.32470 |
| 212 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 1 | Design Size Heating Supply Air Flow Rate [m3/s] | 0.32470 |
| 213 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 1 | Design Size Cooling Supply Air Flow Rate [m3/s] | 0.32470 |
| 214 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 1 | Design Size No Load Supply Air Flow Rate [m3/s] | 0.32470 |
| 215 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 1 | Design Size Nominal Cooling Capacity [W] | 8063.07030 |
| 216 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 1 | Design Size Nominal Heating Capacity [W] | 8063.07030 |
| 217 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 1 | Design Size Maximum Supply Air Temperature [C] | 16.70000 |
| 218 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 1 | User-Specified Maximum Supply Air Temperature [C] | 80.00000 |
| 219 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 1 | Design Size Supplemental Heating Coil Nominal Capacity [W] | 8063.07030 |
| 220 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 1 | User-Specified Supplemental Heating Coil Nominal Capacity [W] | 8063.07030 |
| 221 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 1 | Fraction of Supply Air Flow That Goes Through the Controlling Zone | 1.00000 |
| 222 | Fan:OnOff | FAN ON OFF 6 | Design Size Maximum Flow Rate [m3/s] | 0.32470 |
| 223 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 5 | Design Size Rated Air Flow Rate [m3/s] | 0.32470 |
| 224 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 5 | Design Size Gross Rated Total Cooling Capacity [W] | 8063.07030 |
| 225 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 5 | Design Size Gross Rated Sensible Heat Ratio | 0.69808 |
| 226 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 4 | Design Size Rated Air Flow Rate [m3/s] | 0.32470 |
| 227 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 4 | Design Size Gross Rated Heating Capacity [W] | 8063.07030 |
| 228 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 4 | Design Size Resistive Defrost Heater Capacity [W] | 8063.07030 |
| 229 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 4 | User-Specified Resistive Defrost Heater Capacity [W] | 2000.00000 |
| 230 | Coil:Heating:Electric | ELEC HTG COIL 6 | Design Size Nominal Capacity [W] | 8063.07030 |
| 231 | Controller:OutdoorAir | OUTDOOR AIR CONTROLLER 2 | Maximum Outdoor Air Flow Rate [m3/s] | 0.25708 |
| 232 | Controller:OutdoorAir | OUTDOOR AIR CONTROLLER 2 | Minimum Outdoor Air Flow Rate [m3/s] | 2.35974E-002 |
| 233 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 2 | Design Size Supply Air Flow Rate [m3/s] | 0.25708 |
| 234 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 2 | Design Size Heating Supply Air Flow Rate [m3/s] | 0.25708 |
| 235 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 2 | Design Size Cooling Supply Air Flow Rate [m3/s] | 0.25708 |
| 236 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 2 | Design Size No Load Supply Air Flow Rate [m3/s] | 0.25708 |
| 237 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 2 | Design Size Nominal Cooling Capacity [W] | 6383.79600 |
| 238 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 2 | Design Size Nominal Heating Capacity [W] | 6383.79600 |
| 239 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 2 | Design Size Maximum Supply Air Temperature [C] | 16.70000 |
| 240 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 2 | User-Specified Maximum Supply Air Temperature [C] | 80.00000 |
| 241 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 2 | Design Size Supplemental Heating Coil Nominal Capacity [W] | 6383.79600 |
| 242 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 2 | User-Specified Supplemental Heating Coil Nominal Capacity [W] | 6383.79600 |
| 243 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 2 | Fraction of Supply Air Flow That Goes Through the Controlling Zone | 1.00000 |
| 244 | Fan:OnOff | FAN ON OFF 7 | Design Size Maximum Flow Rate [m3/s] | 0.25708 |
| 245 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 6 | Design Size Rated Air Flow Rate [m3/s] | 0.25708 |
| 246 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 6 | Design Size Gross Rated Total Cooling Capacity [W] | 6383.79600 |
| 247 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 6 | Design Size Gross Rated Sensible Heat Ratio | 0.69808 |
| 248 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 5 | Design Size Rated Air Flow Rate [m3/s] | 0.25708 |
| 249 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 5 | Design Size Gross Rated Heating Capacity [W] | 6383.79600 |
| 250 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 5 | Design Size Resistive Defrost Heater Capacity [W] | 6383.79600 |
| 251 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 5 | User-Specified Resistive Defrost Heater Capacity [W] | 2000.00000 |
| 252 | Coil:Heating:Electric | ELEC HTG COIL 7 | Design Size Nominal Capacity [W] | 6383.79600 |
| 253 | Controller:OutdoorAir | OUTDOOR AIR CONTROLLER 3 | Maximum Outdoor Air Flow Rate [m3/s] | 0.19270 |
| 254 | Controller:OutdoorAir | OUTDOOR AIR CONTROLLER 3 | Minimum Outdoor Air Flow Rate [m3/s] | 2.35974E-002 |
| 255 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 3 | Design Size Supply Air Flow Rate [m3/s] | 0.19270 |
| 256 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 3 | Design Size Heating Supply Air Flow Rate [m3/s] | 0.19270 |
| 257 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 3 | Design Size Cooling Supply Air Flow Rate [m3/s] | 0.19270 |
| 258 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 3 | Design Size No Load Supply Air Flow Rate [m3/s] | 0.19270 |
| 259 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 3 | Design Size Nominal Cooling Capacity [W] | 4785.28906 |
| 260 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 3 | Design Size Nominal Heating Capacity [W] | 4785.28906 |
| 261 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 3 | Design Size Maximum Supply Air Temperature [C] | 16.70000 |
| 262 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 3 | User-Specified Maximum Supply Air Temperature [C] | 80.00000 |
| 263 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 3 | Design Size Supplemental Heating Coil Nominal Capacity [W] | 4785.28906 |
| 264 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 3 | User-Specified Supplemental Heating Coil Nominal Capacity [W] | 4785.28906 |
| 265 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 3 | Fraction of Supply Air Flow That Goes Through the Controlling Zone | 1.00000 |
| 266 | Fan:OnOff | FAN ON OFF 8 | Design Size Maximum Flow Rate [m3/s] | 0.19270 |
| 267 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 7 | Design Size Rated Air Flow Rate [m3/s] | 0.19270 |
| 268 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 7 | Design Size Gross Rated Total Cooling Capacity [W] | 4785.28906 |
| 269 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 7 | Design Size Gross Rated Sensible Heat Ratio | 0.69808 |
| 270 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 6 | Design Size Rated Air Flow Rate [m3/s] | 0.19270 |
| 271 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 6 | Design Size Gross Rated Heating Capacity [W] | 4785.28906 |
| 272 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 6 | Design Size Resistive Defrost Heater Capacity [W] | 4785.28906 |
| 273 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 6 | User-Specified Resistive Defrost Heater Capacity [W] | 2000.00000 |
| 274 | Coil:Heating:Electric | ELEC HTG COIL 8 | Design Size Nominal Capacity [W] | 4785.28906 |
| 275 | Controller:OutdoorAir | OUTDOOR AIR CONTROLLER 4 | Maximum Outdoor Air Flow Rate [m3/s] | 0.32470 |
| 276 | Controller:OutdoorAir | OUTDOOR AIR CONTROLLER 4 | Minimum Outdoor Air Flow Rate [m3/s] | 2.35974E-002 |
| 277 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 4 | Design Size Supply Air Flow Rate [m3/s] | 0.32470 |
| 278 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 4 | Design Size Heating Supply Air Flow Rate [m3/s] | 0.32470 |
| 279 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 4 | Design Size Cooling Supply Air Flow Rate [m3/s] | 0.32470 |
| 280 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 4 | Design Size No Load Supply Air Flow Rate [m3/s] | 0.32470 |
| 281 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 4 | Design Size Nominal Cooling Capacity [W] | 8063.07030 |
| 282 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 4 | Design Size Nominal Heating Capacity [W] | 8063.07030 |
| 283 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 4 | Design Size Maximum Supply Air Temperature [C] | 16.70000 |
| 284 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 4 | User-Specified Maximum Supply Air Temperature [C] | 80.00000 |
| 285 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 4 | Design Size Supplemental Heating Coil Nominal Capacity [W] | 8063.07030 |
| 286 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 4 | User-Specified Supplemental Heating Coil Nominal Capacity [W] | 8063.07030 |
| 287 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 4 | Fraction of Supply Air Flow That Goes Through the Controlling Zone | 1.00000 |
| 288 | Fan:OnOff | FAN ON OFF 9 | Design Size Maximum Flow Rate [m3/s] | 0.32470 |
| 289 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 8 | Design Size Rated Air Flow Rate [m3/s] | 0.32470 |
| 290 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 8 | Design Size Gross Rated Total Cooling Capacity [W] | 8063.07030 |
| 291 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 8 | Design Size Gross Rated Sensible Heat Ratio | 0.69808 |
| 292 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 7 | Design Size Rated Air Flow Rate [m3/s] | 0.32470 |
| 293 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 7 | Design Size Gross Rated Heating Capacity [W] | 8063.07030 |
| 294 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 7 | Design Size Resistive Defrost Heater Capacity [W] | 8063.07030 |
| 295 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 7 | User-Specified Resistive Defrost Heater Capacity [W] | 2000.00000 |
| 296 | Coil:Heating:Electric | ELEC HTG COIL 9 | Design Size Nominal Capacity [W] | 8063.07030 |
| 297 | Controller:OutdoorAir | OUTDOOR AIR CONTROLLER 5 | Maximum Outdoor Air Flow Rate [m3/s] | 0.37210 |
| 298 | Controller:OutdoorAir | OUTDOOR AIR CONTROLLER 5 | Minimum Outdoor Air Flow Rate [m3/s] | 2.35974E-002 |
| 299 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 5 | Design Size Supply Air Flow Rate [m3/s] | 0.37210 |
| 300 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 5 | Design Size Heating Supply Air Flow Rate [m3/s] | 0.37210 |
| 301 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 5 | Design Size Cooling Supply Air Flow Rate [m3/s] | 0.37210 |
| 302 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 5 | Design Size No Load Supply Air Flow Rate [m3/s] | 0.37210 |
| 303 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 5 | Design Size Nominal Cooling Capacity [W] | 9240.04799 |
| 304 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 5 | Design Size Nominal Heating Capacity [W] | 9240.04799 |
| 305 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 5 | Design Size Maximum Supply Air Temperature [C] | 16.70000 |
| 306 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 5 | User-Specified Maximum Supply Air Temperature [C] | 80.00000 |
| 307 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 5 | Design Size Supplemental Heating Coil Nominal Capacity [W] | 9240.04799 |
| 308 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 5 | User-Specified Supplemental Heating Coil Nominal Capacity [W] | 9240.04799 |
| 309 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 5 | Fraction of Supply Air Flow That Goes Through the Controlling Zone | 1.00000 |
| 310 | Fan:OnOff | FAN ON OFF 10 | Design Size Maximum Flow Rate [m3/s] | 0.37210 |
| 311 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 9 | Design Size Rated Air Flow Rate [m3/s] | 0.37210 |
| 312 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 9 | Design Size Gross Rated Total Cooling Capacity [W] | 9240.04799 |
| 313 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 9 | Design Size Gross Rated Sensible Heat Ratio | 0.69808 |
| 314 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 8 | Design Size Rated Air Flow Rate [m3/s] | 0.37210 |
| 315 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 8 | Design Size Gross Rated Heating Capacity [W] | 9240.04799 |
| 316 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 8 | Design Size Resistive Defrost Heater Capacity [W] | 9240.04799 |
| 317 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 8 | User-Specified Resistive Defrost Heater Capacity [W] | 2000.00000 |
| 318 | Coil:Heating:Electric | ELEC HTG COIL 10 | Design Size Nominal Capacity [W] | 9240.04799 |
| 319 | Controller:OutdoorAir | OUTDOOR AIR CONTROLLER 6 | Maximum Outdoor Air Flow Rate [m3/s] | 0.42390 |
| 320 | Controller:OutdoorAir | OUTDOOR AIR CONTROLLER 6 | Minimum Outdoor Air Flow Rate [m3/s] | 2.35974E-002 |
| 321 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 6 | Design Size Supply Air Flow Rate [m3/s] | 0.42390 |
| 322 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 6 | Design Size Heating Supply Air Flow Rate [m3/s] | 0.42390 |
| 323 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 6 | Design Size Cooling Supply Air Flow Rate [m3/s] | 0.42390 |
| 324 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 6 | Design Size No Load Supply Air Flow Rate [m3/s] | 0.42390 |
| 325 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 6 | Design Size Nominal Cooling Capacity [W] | 10526.43700 |
| 326 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 6 | Design Size Nominal Heating Capacity [W] | 10526.43700 |
| 327 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 6 | Design Size Maximum Supply Air Temperature [C] | 16.70000 |
| 328 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 6 | User-Specified Maximum Supply Air Temperature [C] | 80.00000 |
| 329 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 6 | Design Size Supplemental Heating Coil Nominal Capacity [W] | 10526.43700 |
| 330 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 6 | User-Specified Supplemental Heating Coil Nominal Capacity [W] | 10526.43700 |
| 331 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 6 | Fraction of Supply Air Flow That Goes Through the Controlling Zone | 1.00000 |
| 332 | Fan:OnOff | FAN ON OFF 11 | Design Size Maximum Flow Rate [m3/s] | 0.42390 |
| 333 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 10 | Design Size Rated Air Flow Rate [m3/s] | 0.42390 |
| 334 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 10 | Design Size Gross Rated Total Cooling Capacity [W] | 10526.43700 |
| 335 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 10 | Design Size Gross Rated Sensible Heat Ratio | 0.69808 |
| 336 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 9 | Design Size Rated Air Flow Rate [m3/s] | 0.42390 |
| 337 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 9 | Design Size Gross Rated Heating Capacity [W] | 10526.43700 |
| 338 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 9 | Design Size Resistive Defrost Heater Capacity [W] | 10526.43700 |
| 339 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 9 | User-Specified Resistive Defrost Heater Capacity [W] | 2000.00000 |
| 340 | Coil:Heating:Electric | ELEC HTG COIL 11 | Design Size Nominal Capacity [W] | 10526.43700 |
| 341 | Controller:OutdoorAir | OUTDOOR AIR CONTROLLER 7 | Maximum Outdoor Air Flow Rate [m3/s] | 0.37116 |
| 342 | Controller:OutdoorAir | OUTDOOR AIR CONTROLLER 7 | Minimum Outdoor Air Flow Rate [m3/s] | 2.35974E-002 |
| 343 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 7 | Design Size Supply Air Flow Rate [m3/s] | 0.37116 |
| 344 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 7 | Design Size Heating Supply Air Flow Rate [m3/s] | 0.37116 |
| 345 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 7 | Design Size Cooling Supply Air Flow Rate [m3/s] | 0.37116 |
| 346 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 7 | Design Size No Load Supply Air Flow Rate [m3/s] | 0.37116 |
| 347 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 7 | Design Size Nominal Cooling Capacity [W] | 9216.66405 |
| 348 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 7 | Design Size Nominal Heating Capacity [W] | 9216.66405 |
| 349 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 7 | Design Size Maximum Supply Air Temperature [C] | 16.70000 |
| 350 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 7 | User-Specified Maximum Supply Air Temperature [C] | 80.00000 |
| 351 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 7 | Design Size Supplemental Heating Coil Nominal Capacity [W] | 9216.66405 |
| 352 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 7 | User-Specified Supplemental Heating Coil Nominal Capacity [W] | 9216.66405 |
| 353 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 7 | Fraction of Supply Air Flow That Goes Through the Controlling Zone | 1.00000 |
| 354 | Fan:OnOff | FAN ON OFF 12 | Design Size Maximum Flow Rate [m3/s] | 0.37116 |
| 355 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 11 | Design Size Rated Air Flow Rate [m3/s] | 0.37116 |
| 356 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 11 | Design Size Gross Rated Total Cooling Capacity [W] | 9216.66405 |
| 357 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 11 | Design Size Gross Rated Sensible Heat Ratio | 0.69808 |
| 358 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 10 | Design Size Rated Air Flow Rate [m3/s] | 0.37116 |
| 359 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 10 | Design Size Gross Rated Heating Capacity [W] | 9216.66405 |
| 360 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 10 | Design Size Resistive Defrost Heater Capacity [W] | 9216.66405 |
| 361 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 10 | User-Specified Resistive Defrost Heater Capacity [W] | 2000.00000 |
| 362 | Coil:Heating:Electric | ELEC HTG COIL 12 | Design Size Nominal Capacity [W] | 9216.66405 |
| 363 | Controller:OutdoorAir | OUTDOOR AIR CONTROLLER 8 | Maximum Outdoor Air Flow Rate [m3/s] | 0.32470 |
| 364 | Controller:OutdoorAir | OUTDOOR AIR CONTROLLER 8 | Minimum Outdoor Air Flow Rate [m3/s] | 2.35974E-002 |
| 365 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 8 | Design Size Supply Air Flow Rate [m3/s] | 0.32470 |
| 366 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 8 | Design Size Heating Supply Air Flow Rate [m3/s] | 0.32470 |
| 367 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 8 | Design Size Cooling Supply Air Flow Rate [m3/s] | 0.32470 |
| 368 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 8 | Design Size No Load Supply Air Flow Rate [m3/s] | 0.32470 |
| 369 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 8 | Design Size Nominal Cooling Capacity [W] | 8063.07030 |
| 370 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 8 | Design Size Nominal Heating Capacity [W] | 8063.07030 |
| 371 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 8 | Design Size Maximum Supply Air Temperature [C] | 16.70000 |
| 372 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 8 | User-Specified Maximum Supply Air Temperature [C] | 80.00000 |
| 373 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 8 | Design Size Supplemental Heating Coil Nominal Capacity [W] | 8063.07030 |
| 374 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 8 | User-Specified Supplemental Heating Coil Nominal Capacity [W] | 8063.07030 |
| 375 | AirLoopHVAC:UnitarySystem | UNITARY - DX HEAT PUMP - CYCLING - ELEC REHEAT 8 | Fraction of Supply Air Flow That Goes Through the Controlling Zone | 1.00000 |
| 376 | Fan:OnOff | FAN ON OFF 13 | Design Size Maximum Flow Rate [m3/s] | 0.32470 |
| 377 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 12 | Design Size Rated Air Flow Rate [m3/s] | 0.32470 |
| 378 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 12 | Design Size Gross Rated Total Cooling Capacity [W] | 8063.07030 |
| 379 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 12 | Design Size Gross Rated Sensible Heat Ratio | 0.69808 |
| 380 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 11 | Design Size Rated Air Flow Rate [m3/s] | 0.32470 |
| 381 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 11 | Design Size Gross Rated Heating Capacity [W] | 8063.07030 |
| 382 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 11 | Design Size Resistive Defrost Heater Capacity [W] | 8063.07030 |
| 383 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 11 | User-Specified Resistive Defrost Heater Capacity [W] | 2000.00000 |
| 384 | Coil:Heating:Electric | ELEC HTG COIL 13 | Design Size Nominal Capacity [W] | 8063.07030 |
| Component Type | Component Name | Standard Rating (Net) Cooling Capacity {W} | Standard Rated Net COP {W/W} | EER {Btu/W-h} | SEER {Btu/W-h} | IEER {Btu/W-h} | |
| 1 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 4 | 4707.3 | 3.07 | 10.47 | 10.41 | 10.78 |
| 2 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 13 | 9332.4 | 3.07 | 10.47 | 10.41 | 10.78 |
| 3 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 14 | 10893.9 | 3.07 | 10.47 | 10.41 | 10.78 |
| 4 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 15 | 9462.4 | 3.07 | 10.47 | 10.41 | 10.78 |
| 5 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 5 | 7806.9 | 3.07 | 10.47 | 10.41 | 10.78 |
| 6 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 6 | 6181.0 | 3.07 | 10.47 | 10.41 | 10.78 |
| 7 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 7 | 4633.3 | 3.07 | 10.47 | 10.41 | 10.78 |
| 8 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 8 | 7806.9 | 3.07 | 10.47 | 10.41 | 10.78 |
| 9 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 9 | 8946.5 | 3.07 | 10.47 | 10.41 | 10.78 |
| 10 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 10 | 10192.0 | 3.07 | 10.47 | 10.41 | 10.78 |
| 11 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 11 | 8923.9 | 3.07 | 10.47 | 10.41 | 10.78 |
| 12 | Coil:Cooling:DX:SingleSpeed | 1 SPD DX CLG COIL 12 | 7806.9 | 3.07 | 10.47 | 10.41 | 10.78 |
| Component Type | Component Name | High Temperature Heating (net) Rating Capacity {W} | Low Temperature Heating (net) Rating Capacity {W} | HSPF {Btu/W-h} | Region Number | |
| 1 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 3 | 5019.1 | 2761.8 | 6.53 | 4 |
| 2 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 12 | 9950.5 | 5475.3 | 6.54 | 4 |