SNMPv2 Template for Cyberpower’s remote management card ver.305 (205) used in OR and PR-series UPSes. Tested on firmware version 1.3.0. Created by Taurus (https://github.com/RusTaurus) MIBs used: CPS-MIB (v2.9) https://www.cyberpowersystems.com/products/software/mib-files/
This is Zabbix SNMPv2 Template for Cyberpower’s remote management card ver.305(205) used in OR- and PR-series UPSes.
Tested on Zabbix 4.0 and 4.4, PR3000ELCDRT2U, OR1500ELCDRM1U with RMCARD305 (firmware version 1.3.0).
Here you can find latest firmware and MIB versions of RMCARD305.
Enhancements in v2 version of this template:
MIBs used: CPS-MIB (v2.9)
Sergey Romanov
| Name | Description | Default | Type |
|---|---|---|---|
| {$SNMP_COMMUNITY} |
-
 | public |
Text macro |
There are no template links in this template.
| Name | Description | Type | Key and additional info |
|---|---|---|---|
| Output Current Discovery |
Discovery because CPS-MIB::upsAdvanceOutputCurrent returns 0 (zero) on OR-series UPSes.
 | SNMP agent |
Output.current.discovery
Update: 30s
 |
| Configuration Discovery #1 |
Discovery because CPS-MIB::upsAdvanceConfigColdStart returns NULL on OR-series UPSes.
 | SNMP agent |
config.discovery.1
Update: 30s
 |
| Configuration Discovery #3 |
Discovery because CPS-MIB::upsAdvanceConfigReturnDelay returns NULL on OR-series UPSes.
 | SNMP agent |
config.discovery.3
Update: 30s
 |
| Battery Age Recommendation Discovery |
Discovery because CPS-MIB::upsBaseBatteryAgeRecommand returns 0 (zero) on OR-series UPSes.
 | SNMP agent |
BatteryAge.discovery
Update: 30s
 |
| Temperature Discovery |
Discovery because CPS-MIB::upsAdvanceBatteryTemperature returns 0 (zero) on OR-series UPSes.
 | SNMP agent |
Temperature.discovery
Update: 30s
 |
| Configuration Discovery #2 |
Discovery because CPS-MIB::upsAdvanceConfigRechargedCapacity returns NULL on OR-series UPSes.
 | SNMP agent |
config.discovery.2
Update: 30s
 |
| Configuration Discovery #5 |
Discovery because CPS-MIB::upsAdvanceConfigSleepDelay returns NULL on OR-series UPSes.
 | SNMP agent |
config.discovery.5
Update: 30s
 |
| Configuration Discovery #4 |
Discovery because CPS-MIB::upsAdvanceConfigShutoffDelay returns NULL on OR-series UPSes.
 | SNMP agent |
config.discovery.4
Update: 30s
 |
| Name | Description | Type | Key and additional info |
|---|---|---|---|
| Firmware Version |
CPS-MIB::upsAdvanceIdentFirmwareRevision - the UPS firmware revision
 | SNMP agent |
ups.info.FirmwareVersion
Update: 1h
 |
| Replace Indicator |
CPS-MIB::upsAdvanceBatteryReplaceIndicator - this value indicates if UPS batteries need to be replaced
 | SNMP agent |
battery.ReplaceIndicator
Update: 1h
 |
| Serial Number |
CPS-MIB::upsAdvanceIdentAgentSerialNumber - a string identifying the serial number of the Agent
 | SNMP agent |
rmcard.SerialNumber
Update: 1h
 |
| Load (watts) |
CPS-MIB::upsAdvanceOutputPower - the total output active power of the UPS system in W
 | SNMP agent |
output.LoadW
Update: 30s
 |
| System - Enter Sleep Mode After All Clients Shutdown |
CPS-MIB::upsAdvanceConfigSleepAfterAllClientShut - if this option is enabled, UPS will enter sleep mode after utility power failed and remaining MSDT+2 minutes.More information about MSDT please reference to help page of UPS - > PowerPanel List.
 | SNMP agent |
config.sleepMode
Update: 30m
 |
| Voltage |
CPS-MIB::upsAdvanceOutputVoltage - the UPS output voltage in Volts
 | SNMP agent |
output.Voltage
Update: 30s
 |
| Name |
CPS-MIB::upsBaseIdentName - the UPS identified name could be set by the administrator
 | SNMP agent |
ups.info.Name
Update: 1h
 |
| Remaining Runtime |
CPS-MIB::upsAdvanceBatteryRunTimeRemaining - the UPS battery remaining run time
 | SNMP agent |
battery.RemainingRuntime
Update: 30s
 |
| System - Audible Alarm |
CPS-MIB::upsAdvanceConfigAlarm - this value is set to handle audible alarms when power failure.
 | SNMP agent |
config.audibleAlarm
Update: 30m
 |
| Load Power |
CPS-MIB::upsAdvanceIdentLoadPower - the power rating (Watts) of the UPS
 | SNMP agent |
ups.info.LoadPower
Update: 1h
 |
| Frequency |
CPS-MIB::upsAdvanceOutputFrequency - the UPS output frequency in Hz
 | SNMP agent |
output.Frequency
Update: 30s
 |
| Model |
CPS-MIB::upsBaseIdentModel - the UPS model name
 | SNMP agent |
ups.info.Model
Update: 1h
 |
| Frequency |
CPS-MIB::upsAdvanceInputFrequency - the input line frequency in Hz
 | SNMP agent |
input.Frequency
Update: 30s
 |
| Status |
CPS-MIB::upsBaseOutputStatus - the UPS output status
 | SNMP agent |
output.Status
Update: 15s
 |
| Output Voltage |
CPS-MIB::upsAdvanceConfigOutputVoltage - the standard UPS output voltage in Volts. The possible values are 100, 110, 120, 127, 208, 220, 230, and 240. If a value other than a possible value is set, it will not be accepted.
 | SNMP agent |
config.outputVoltage
Update: 30m
 |
| Battery Low Threshold |
CPS-MIB::upsAdvanceConfigLowBatteryThreshold - when the UPS supplies battery power and the remaining capacity is lower than this threshold, the UPS will sound an alarm. The value expressed in percentage.
 | SNMP agent |
config.batteryLow
Update: 30m
 |
| Capacity |
CPS-MIB::upsAdvanceBatteryCapacity - the battery capacity expressed in percentage
 | SNMP agent |
battery.Capacity
Update: 30s
 |
| Power Rating |
CPS-MIB::upsAdvanceIdentPowerRating - the Volt-Amp rating of the UPS
 | SNMP agent |
ups.info.PowerRating
Update: 1h
 |
| Status |
CPS-MIB::upsBaseBatteryStatus - the UPS battery status. A batteryLow(3) value means the battery will be exhausted soon under the current load. The amount of low battery run time can be configured by the upsAdvanceConfigLowBatteryRunTime.
 | SNMP agent |
battery.Status
Update: 15s
 |
| Voltage Rating |
CPS-MIB::upsAdvanceBatteryVoltageRating - the DC voltage rating of the battery set
 | SNMP agent |
battery.VoltageRating
Update: 1h
 |
| System - Over Discharge Protection |
CPS-MIB::upsAdvanceConfigDeepDischargeProtection - when the UPS is on Battery Mode with 0% load and the status remains for the time configured, the RMCARD will enforce the UPS to Sleep Mode and the output will be turned off. The possible values are 0, 20, 40, and 60 minutes. If a value other than a possible value is set, it will not be accepted.
 | SNMP agent |
config.dischargeProtection
Update: 30m
 |
| Time on Battery |
CPS-MIB::upsBaseBatteryTimeOnBattery - the UPS wasted battery time since the UPS has transfered to backup mode
 | SNMP agent |
battery.TimeOnBattery
Update: 30s
 |
| Voltage |
CPS-MIB::upsAdvanceInputLineVoltage - the input line voltage in Volts
 | SNMP agent |
input.Voltage
Update: 30s
 |
| Status |
CPS-MIB::upsAdvanceInputStatus - display the present status of the utility power supplied to the UPS
 | SNMP agent |
input.Status
Update: 15s
 |
| Load |
CPS-MIB::upsAdvanceOutputLoad - the UPS output load expressed in percentage
 | SNMP agent |
output.Load
Update: 30s
 |
| Firmware Revision |
CPS-MIB::upsAdvanceIdentAgentFirmwareRevision - the SNMP agent firmware revision
 | SNMP agent |
rmcard.FirmwareRevision
Update: 1h
 |
| Last Fail Cause |
CPS-MIB::upsAdvanceInputLineFailCause - The reason of UPS power failure. This value is set to: - noTransfer(1), if UPS is in utility mode. - highLineVoltage(2), if UPS switch to battery mode by reason of input voltage over the high transfer vloltage. - brownout(3), if UPS switch to battery mode by reason of input voltage under the low transfer vloltage. - selfTest(4), if the UPS was commanded to do a self test.
 | SNMP agent |
input.FailCause
Update: 1h
 |
| Current |
CPS-MIB::upsAdvanceOutputCurrent - the UPS output current in Amps
 | SNMP agent |
output.current.[{#SNMPINDEX}]
Update: 1m

LLD
 |
| System - Cold Start |
CPS-MIB::upsAdvanceConfigColdStart - set the ability of the UPS can start in the absence of input power. When this option is enabled the UPS can be turned on without having input power.
 | SNMP agent |
config.coldStart.[{#SNMPINDEX}]
Update: 30m

LLD
 |
| Power Restore - Returned Delay |
CPS-MIB::upsAdvanceConfigReturnDelay - the delay time the UPS will turn on after power recovery. The value is also used in a ‘reboot’ or ‘wake up’ sequence. The possible values are 0 to 600 seconds. If a value other than a supported value is set, the value will not be accepted.
 | SNMP agent |
config.returnedDelay.[{#SNMPINDEX}]
Update: 30m

LLD
 |
| Age Recommendation |
CPS-MIB::upsBaseBatteryAgeRecommand - Recommended battery life in months
 | SNMP agent |
battery.ageRecommend.[{#SNMPINDEX}]
Update: 1h

LLD
 |
| Last Replace Date |
CPS-MIB::upsBaseBatteryLastReplaceDate - the UPS batteries last replaced date in mm/dd/yyyy format. This value is originally set when manufactured. If batteries replaced, administrator should reset this value.
 | SNMP agent |
battery.lastReplaceDate.[{#SNMPINDEX}]
Update: 1h

LLD
 |
| Temperature |
CPS-MIB::upsAdvanceBatteryTemperature - the UPS battery temperature expressed in Celsius
 | SNMP agent |
ups.info.Temperature.[{#SNMPINDEX}]
Update: 1m

LLD
 |
| Power Restore - Recharged Capacity |
CPS-MIB::upsAdvanceConfigRechargedCapacity - when the utility power restores, the UPS will start to recharge until the specified battery capacity in percentage is met before restoring output power. The possible values are 0, 15, 30, 45, 60, 75, and 90. If a value other than a possible value is set, it will not be accepted.
 | SNMP agent |
config.rechargedCapacity.[{#SNMPINDEX}]
Update: 30m

LLD
 |
| Timers - Sleep Delay |
CPS-MIB::upsAdvanceConfigSleepDelay - the delay time the UPS will enter sleep mode after receiving a sleep command. The possible values are between 60 to 5940 seconds. If a value other than a supported value is set, the value will not be accepted.
 | SNMP agent |
config.sleepDelay.[{#SNMPINDEX}]
Update: 30m

LLD
 |
| Timers - ShutOff Delay |
CPS-MIB::upsAdvanceConfigShutoffDelay - the delay time the UPS will remain on after receiving a turn off command. The possible values are between 60 to 5940 seconds. If a value other than a supported value is set, the value will not be accepted.
 | SNMP agent |
config.shutoffDelay.[{#SNMPINDEX}]
Update: 30m

LLD
 |
There are no triggers in this template.
SNMPv2 Template for Cyberpower’s remote management card ver.305 (205) used in OR and PR-series UPSes. Tested on firmware version 1.3.0. Created by Taurus (https://github.com/RusTaurus) MIBs used: CPS-MIB (v2.9) https://www.cyberpowersystems.com/products/software/mib-files/
This is Zabbix SNMPv2 Template for Cyberpower’s remote management card ver.305(205) used in OR- and PR-series UPSes.
Tested on Zabbix 4.0 and 4.4, PR3000ELCDRT2U, OR1500ELCDRM1U with RMCARD305 (firmware version 1.3.0).
Here you can find latest firmware and MIB versions of RMCARD305.
Enhancements in v2 version of this template:
MIBs used: CPS-MIB (v2.9)
Sergey Romanov
| Name | Description | Default | Type |
|---|---|---|---|
| {$SNMP_COMMUNITY} |
-
 | public |
Text macro |
There are no template links in this template.
| Name | Description | Type | Key and additional info |
|---|---|---|---|
| Output Current Discovery |
Discovery because CPS-MIB::upsAdvanceOutputCurrent returns 0 (zero) on OR-series UPSes.
 | SNMP agent |
Output.current.discovery
Update: 30s
 |
| Configuration Discovery #3 |
Discovery because CPS-MIB::upsAdvanceConfigReturnDelay returns NULL on OR-series UPSes.
 | SNMP agent |
config.discovery.3
Update: 30s
 |
| Configuration Discovery #2 |
Discovery because CPS-MIB::upsAdvanceConfigRechargedCapacity returns NULL on OR-series UPSes.
 | SNMP agent |
config.discovery.2
Update: 30s
 |
| Configuration Discovery #4 |
Discovery because CPS-MIB::upsAdvanceConfigShutoffDelay returns NULL on OR-series UPSes.
 | SNMP agent |
config.discovery.4
Update: 30s
 |
| Temperature Discovery |
Discovery because CPS-MIB::upsAdvanceBatteryTemperature returns 0 (zero) on OR-series UPSes.
 | SNMP agent |
Temperature.discovery
Update: 30s
 |
| Battery Age Recommendation Discovery |
Discovery because CPS-MIB::upsBaseBatteryAgeRecommand returns 0 (zero) on OR-series UPSes.
 | SNMP agent |
BatteryAge.discovery
Update: 30s
 |
| Configuration Discovery #5 |
Discovery because CPS-MIB::upsAdvanceConfigSleepDelay returns NULL on OR-series UPSes.
 | SNMP agent |
config.discovery.5
Update: 30s
 |
| Configuration Discovery #1 |
Discovery because CPS-MIB::upsAdvanceConfigColdStart returns NULL on OR-series UPSes.
 | SNMP agent |
config.discovery.1
Update: 30s
 |
| Name | Description | Type | Key and additional info |
|---|---|---|---|
| Replace Indicator |
CPS-MIB::upsAdvanceBatteryReplaceIndicator - this value indicates if UPS batteries need to be replaced
 | SNMP agent |
battery.ReplaceIndicator
Update: 1h
 |
| Voltage |
CPS-MIB::upsAdvanceOutputVoltage - the UPS output voltage in Volts
 | SNMP agent |
output.Voltage
Update: 30s
 |
| Battery Low Threshold |
CPS-MIB::upsAdvanceConfigLowBatteryThreshold - when the UPS supplies battery power and the remaining capacity is lower than this threshold, the UPS will sound an alarm. The value expressed in percentage.
 | SNMP agent |
config.batteryLow
Update: 30m
 |
| Power Rating |
CPS-MIB::upsAdvanceIdentPowerRating - the Volt-Amp rating of the UPS
 | SNMP agent |
ups.info.PowerRating
Update: 1h
 |
| Firmware Revision |
CPS-MIB::upsAdvanceIdentAgentFirmwareRevision - the SNMP agent firmware revision
 | SNMP agent |
rmcard.FirmwareRevision
Update: 1h
 |
| Status |
CPS-MIB::upsBaseBatteryStatus - the UPS battery status. A batteryLow(3) value means the battery will be exhausted soon under the current load. The amount of low battery run time can be configured by the upsAdvanceConfigLowBatteryRunTime.
 | SNMP agent |
battery.Status
Update: 15s
 |
| System - Over Discharge Protection |
CPS-MIB::upsAdvanceConfigDeepDischargeProtection - when the UPS is on Battery Mode with 0% load and the status remains for the time configured, the RMCARD will enforce the UPS to Sleep Mode and the output will be turned off. The possible values are 0, 20, 40, and 60 minutes. If a value other than a possible value is set, it will not be accepted.
 | SNMP agent |
config.dischargeProtection
Update: 30m
 |
| Last Fail Cause |
CPS-MIB::upsAdvanceInputLineFailCause - The reason of UPS power failure. This value is set to: - noTransfer(1), if UPS is in utility mode. - highLineVoltage(2), if UPS switch to battery mode by reason of input voltage over the high transfer vloltage. - brownout(3), if UPS switch to battery mode by reason of input voltage under the low transfer vloltage. - selfTest(4), if the UPS was commanded to do a self test.
 | SNMP agent |
input.FailCause
Update: 1h
 |
| Time on Battery |
CPS-MIB::upsBaseBatteryTimeOnBattery - the UPS wasted battery time since the UPS has transfered to backup mode
 | SNMP agent |
battery.TimeOnBattery
Update: 30s
 |
| System - Enter Sleep Mode After All Clients Shutdown |
CPS-MIB::upsAdvanceConfigSleepAfterAllClientShut - if this option is enabled, UPS will enter sleep mode after utility power failed and remaining MSDT+2 minutes.More information about MSDT please reference to help page of UPS - > PowerPanel List.
 | SNMP agent |
config.sleepMode
Update: 30m
 |
| Load Power |
CPS-MIB::upsAdvanceIdentLoadPower - the power rating (Watts) of the UPS
 | SNMP agent |
ups.info.LoadPower
Update: 1h
 |
| System - Audible Alarm |
CPS-MIB::upsAdvanceConfigAlarm - this value is set to handle audible alarms when power failure.
 | SNMP agent |
config.audibleAlarm
Update: 30m
 |
| Frequency |
CPS-MIB::upsAdvanceOutputFrequency - the UPS output frequency in Hz
 | SNMP agent |
output.Frequency
Update: 30s
 |
| Frequency |
CPS-MIB::upsAdvanceInputFrequency - the input line frequency in Hz
 | SNMP agent |
input.Frequency
Update: 30s
 |
| Voltage Rating |
CPS-MIB::upsAdvanceBatteryVoltageRating - the DC voltage rating of the battery set
 | SNMP agent |
battery.VoltageRating
Update: 1h
 |
| Status |
CPS-MIB::upsAdvanceInputStatus - display the present status of the utility power supplied to the UPS
 | SNMP agent |
input.Status
Update: 15s
 |
| Output Voltage |
CPS-MIB::upsAdvanceConfigOutputVoltage - the standard UPS output voltage in Volts. The possible values are 100, 110, 120, 127, 208, 220, 230, and 240. If a value other than a possible value is set, it will not be accepted.
 | SNMP agent |
config.outputVoltage
Update: 30m
 |
| Remaining Runtime |
CPS-MIB::upsAdvanceBatteryRunTimeRemaining - the UPS battery remaining run time
 | SNMP agent |
battery.RemainingRuntime
Update: 30s
 |
| Name |
CPS-MIB::upsBaseIdentName - the UPS identified name could be set by the administrator
 | SNMP agent |
ups.info.Name
Update: 1h
 |
| Serial Number |
CPS-MIB::upsAdvanceIdentAgentSerialNumber - a string identifying the serial number of the Agent
 | SNMP agent |
rmcard.SerialNumber
Update: 1h
 |
| Status |
CPS-MIB::upsBaseOutputStatus - the UPS output status
 | SNMP agent |
output.Status
Update: 15s
 |
| Load |
CPS-MIB::upsAdvanceOutputLoad - the UPS output load expressed in percentage
 | SNMP agent |
output.Load
Update: 30s
 |
| Firmware Version |
CPS-MIB::upsAdvanceIdentFirmwareRevision - the UPS firmware revision
 | SNMP agent |
ups.info.FirmwareVersion
Update: 1h
 |
| Capacity |
CPS-MIB::upsAdvanceBatteryCapacity - the battery capacity expressed in percentage
 | SNMP agent |
battery.Capacity
Update: 30s
 |
| Model |
CPS-MIB::upsBaseIdentModel - the UPS model name
 | SNMP agent |
ups.info.Model
Update: 1h
 |
| Voltage |
CPS-MIB::upsAdvanceInputLineVoltage - the input line voltage in Volts
 | SNMP agent |
input.Voltage
Update: 30s
 |
| Load (watts) |
CPS-MIB::upsAdvanceOutputPower - the total output active power of the UPS system in W
 | SNMP agent |
output.LoadW
Update: 30s
 |
| Current |
CPS-MIB::upsAdvanceOutputCurrent - the UPS output current in Amps
 | SNMP agent |
output.current.[{#SNMPINDEX}]
Update: 1m

LLD
 |
| Power Restore - Returned Delay |
CPS-MIB::upsAdvanceConfigReturnDelay - the delay time the UPS will turn on after power recovery. The value is also used in a ‘reboot’ or ‘wake up’ sequence. The possible values are 0 to 600 seconds. If a value other than a supported value is set, the value will not be accepted.
 | SNMP agent |
config.returnedDelay.[{#SNMPINDEX}]
Update: 30m

LLD
 |
| Power Restore - Recharged Capacity |
CPS-MIB::upsAdvanceConfigRechargedCapacity - when the utility power restores, the UPS will start to recharge until the specified battery capacity in percentage is met before restoring output power. The possible values are 0, 15, 30, 45, 60, 75, and 90. If a value other than a possible value is set, it will not be accepted.
 | SNMP agent |
config.rechargedCapacity.[{#SNMPINDEX}]
Update: 30m

LLD
 |
| Timers - ShutOff Delay |
CPS-MIB::upsAdvanceConfigShutoffDelay - the delay time the UPS will remain on after receiving a turn off command. The possible values are between 60 to 5940 seconds. If a value other than a supported value is set, the value will not be accepted.
 | SNMP agent |
config.shutoffDelay.[{#SNMPINDEX}]
Update: 30m

LLD
 |
| Temperature |
CPS-MIB::upsAdvanceBatteryTemperature - the UPS battery temperature expressed in Celsius
 | SNMP agent |
ups.info.Temperature.[{#SNMPINDEX}]
Update: 1m

LLD
 |
| Age Recommendation |
CPS-MIB::upsBaseBatteryAgeRecommand - Recommended battery life in months
 | SNMP agent |
battery.ageRecommend.[{#SNMPINDEX}]
Update: 1h

LLD
 |
| Last Replace Date |
CPS-MIB::upsBaseBatteryLastReplaceDate - the UPS batteries last replaced date in mm/dd/yyyy format. This value is originally set when manufactured. If batteries replaced, administrator should reset this value.
 | SNMP agent |
battery.lastReplaceDate.[{#SNMPINDEX}]
Update: 1h

LLD
 |
| Timers - Sleep Delay |
CPS-MIB::upsAdvanceConfigSleepDelay - the delay time the UPS will enter sleep mode after receiving a sleep command. The possible values are between 60 to 5940 seconds. If a value other than a supported value is set, the value will not be accepted.
 | SNMP agent |
config.sleepDelay.[{#SNMPINDEX}]
Update: 30m

LLD
 |
| System - Cold Start |
CPS-MIB::upsAdvanceConfigColdStart - set the ability of the UPS can start in the absence of input power. When this option is enabled the UPS can be turned on without having input power.
 | SNMP agent |
config.coldStart.[{#SNMPINDEX}]
Update: 30m

LLD
 |
There are no triggers in this template.
SNMPv2 Template for Cyberpower’s remote management card ver.305 (205) used in OR and PR-series UPSes. Tested on firmware version 1.3.0. Created by Taurus (https://github.com/RusTaurus) MIBs used: CPS-MIB (v2.9) https://www.cyberpowersystems.com/products/software/mib-files/
This is Zabbix SNMPv2 Template for Cyberpower’s remote management card ver.305(205) used in OR- and PR-series UPSes.
Tested on Zabbix 4.0 and 4.4, PR3000ELCDRT2U, OR1500ELCDRM1U with RMCARD305 (firmware version 1.3.0).
Here you can find latest firmware and MIB versions of RMCARD305.
Enhancements in v2 version of this template:
MIBs used: CPS-MIB (v2.9)
Sergey Romanov
| Name | Description | Default | Type |
|---|---|---|---|
| {$SNMP_COMMUNITY} |
-
 | public |
Text macro |
There are no template links in this template.
| Name | Description | Type | Key and additional info |
|---|---|---|---|
| Output Current Discovery |
Discovery because CPS-MIB::upsAdvanceOutputCurrent returns 0 (zero) on OR-series UPSes.
 | SNMP agent |
Output.current.discovery
Update: 30s
 |
| Configuration Discovery #3 |
Discovery because CPS-MIB::upsAdvanceConfigReturnDelay returns NULL on OR-series UPSes.
 | SNMP agent |
config.discovery.3
Update: 30s
 |
| Configuration Discovery #2 |
Discovery because CPS-MIB::upsAdvanceConfigRechargedCapacity returns NULL on OR-series UPSes.
 | SNMP agent |
config.discovery.2
Update: 30s
 |
| Configuration Discovery #4 |
Discovery because CPS-MIB::upsAdvanceConfigShutoffDelay returns NULL on OR-series UPSes.
 | SNMP agent |
config.discovery.4
Update: 30s
 |
| Temperature Discovery |
Discovery because CPS-MIB::upsAdvanceBatteryTemperature returns 0 (zero) on OR-series UPSes.
 | SNMP agent |
Temperature.discovery
Update: 30s
 |
| Battery Age Recommendation Discovery |
Discovery because CPS-MIB::upsBaseBatteryAgeRecommand returns 0 (zero) on OR-series UPSes.
 | SNMP agent |
BatteryAge.discovery
Update: 30s
 |
| Configuration Discovery #5 |
Discovery because CPS-MIB::upsAdvanceConfigSleepDelay returns NULL on OR-series UPSes.
 | SNMP agent |
config.discovery.5
Update: 30s
 |
| Configuration Discovery #1 |
Discovery because CPS-MIB::upsAdvanceConfigColdStart returns NULL on OR-series UPSes.
 | SNMP agent |
config.discovery.1
Update: 30s
 |
| Name | Description | Type | Key and additional info |
|---|---|---|---|
| Replace Indicator |
CPS-MIB::upsAdvanceBatteryReplaceIndicator - this value indicates if UPS batteries need to be replaced
 | SNMP agent |
battery.ReplaceIndicator
Update: 1h
 |
| Voltage |
CPS-MIB::upsAdvanceOutputVoltage - the UPS output voltage in Volts
 | SNMP agent |
output.Voltage
Update: 30s
 |
| Battery Low Threshold |
CPS-MIB::upsAdvanceConfigLowBatteryThreshold - when the UPS supplies battery power and the remaining capacity is lower than this threshold, the UPS will sound an alarm. The value expressed in percentage.
 | SNMP agent |
config.batteryLow
Update: 30m
 |
| Power Rating |
CPS-MIB::upsAdvanceIdentPowerRating - the Volt-Amp rating of the UPS
 | SNMP agent |
ups.info.PowerRating
Update: 1h
 |
| Firmware Revision |
CPS-MIB::upsAdvanceIdentAgentFirmwareRevision - the SNMP agent firmware revision
 | SNMP agent |
rmcard.FirmwareRevision
Update: 1h
 |
| Status |
CPS-MIB::upsBaseBatteryStatus - the UPS battery status. A batteryLow(3) value means the battery will be exhausted soon under the current load. The amount of low battery run time can be configured by the upsAdvanceConfigLowBatteryRunTime.
 | SNMP agent |
battery.Status
Update: 15s
 |
| System - Over Discharge Protection |
CPS-MIB::upsAdvanceConfigDeepDischargeProtection - when the UPS is on Battery Mode with 0% load and the status remains for the time configured, the RMCARD will enforce the UPS to Sleep Mode and the output will be turned off. The possible values are 0, 20, 40, and 60 minutes. If a value other than a possible value is set, it will not be accepted.
 | SNMP agent |
config.dischargeProtection
Update: 30m
 |
| Last Fail Cause |
CPS-MIB::upsAdvanceInputLineFailCause - The reason of UPS power failure. This value is set to: - noTransfer(1), if UPS is in utility mode. - highLineVoltage(2), if UPS switch to battery mode by reason of input voltage over the high transfer vloltage. - brownout(3), if UPS switch to battery mode by reason of input voltage under the low transfer vloltage. - selfTest(4), if the UPS was commanded to do a self test.
 | SNMP agent |
input.FailCause
Update: 1h
 |
| Time on Battery |
CPS-MIB::upsBaseBatteryTimeOnBattery - the UPS wasted battery time since the UPS has transfered to backup mode
 | SNMP agent |
battery.TimeOnBattery
Update: 30s
 |
| System - Enter Sleep Mode After All Clients Shutdown |
CPS-MIB::upsAdvanceConfigSleepAfterAllClientShut - if this option is enabled, UPS will enter sleep mode after utility power failed and remaining MSDT+2 minutes.More information about MSDT please reference to help page of UPS - > PowerPanel List.
 | SNMP agent |
config.sleepMode
Update: 30m
 |
| Load Power |
CPS-MIB::upsAdvanceIdentLoadPower - the power rating (Watts) of the UPS
 | SNMP agent |
ups.info.LoadPower
Update: 1h
 |
| System - Audible Alarm |
CPS-MIB::upsAdvanceConfigAlarm - this value is set to handle audible alarms when power failure.
 | SNMP agent |
config.audibleAlarm
Update: 30m
 |
| Frequency |
CPS-MIB::upsAdvanceOutputFrequency - the UPS output frequency in Hz
 | SNMP agent |
output.Frequency
Update: 30s
 |
| Frequency |
CPS-MIB::upsAdvanceInputFrequency - the input line frequency in Hz
 | SNMP agent |
input.Frequency
Update: 30s
 |
| Voltage Rating |
CPS-MIB::upsAdvanceBatteryVoltageRating - the DC voltage rating of the battery set
 | SNMP agent |
battery.VoltageRating
Update: 1h
 |
| Status |
CPS-MIB::upsAdvanceInputStatus - display the present status of the utility power supplied to the UPS
 | SNMP agent |
input.Status
Update: 15s
 |
| Output Voltage |
CPS-MIB::upsAdvanceConfigOutputVoltage - the standard UPS output voltage in Volts. The possible values are 100, 110, 120, 127, 208, 220, 230, and 240. If a value other than a possible value is set, it will not be accepted.
 | SNMP agent |
config.outputVoltage
Update: 30m
 |
| Remaining Runtime |
CPS-MIB::upsAdvanceBatteryRunTimeRemaining - the UPS battery remaining run time
 | SNMP agent |
battery.RemainingRuntime
Update: 30s
 |
| Name |
CPS-MIB::upsBaseIdentName - the UPS identified name could be set by the administrator
 | SNMP agent |
ups.info.Name
Update: 1h
 |
| Serial Number |
CPS-MIB::upsAdvanceIdentAgentSerialNumber - a string identifying the serial number of the Agent
 | SNMP agent |
rmcard.SerialNumber
Update: 1h
 |
| Status |
CPS-MIB::upsBaseOutputStatus - the UPS output status
 | SNMP agent |
output.Status
Update: 15s
 |
| Load |
CPS-MIB::upsAdvanceOutputLoad - the UPS output load expressed in percentage
 | SNMP agent |
output.Load
Update: 30s
 |
| Firmware Version |
CPS-MIB::upsAdvanceIdentFirmwareRevision - the UPS firmware revision
 | SNMP agent |
ups.info.FirmwareVersion
Update: 1h
 |
| Capacity |
CPS-MIB::upsAdvanceBatteryCapacity - the battery capacity expressed in percentage
 | SNMP agent |
battery.Capacity
Update: 30s
 |
| Model |
CPS-MIB::upsBaseIdentModel - the UPS model name
 | SNMP agent |
ups.info.Model
Update: 1h
 |
| Voltage |
CPS-MIB::upsAdvanceInputLineVoltage - the input line voltage in Volts
 | SNMP agent |
input.Voltage
Update: 30s
 |
| Load (watts) |
CPS-MIB::upsAdvanceOutputPower - the total output active power of the UPS system in W
 | SNMP agent |
output.LoadW
Update: 30s
 |
| Current |
CPS-MIB::upsAdvanceOutputCurrent - the UPS output current in Amps
 | SNMP agent |
output.current.[{#SNMPINDEX}]
Update: 1m

LLD
 |
| Power Restore - Returned Delay |
CPS-MIB::upsAdvanceConfigReturnDelay - the delay time the UPS will turn on after power recovery. The value is also used in a ‘reboot’ or ‘wake up’ sequence. The possible values are 0 to 600 seconds. If a value other than a supported value is set, the value will not be accepted.
 | SNMP agent |
config.returnedDelay.[{#SNMPINDEX}]
Update: 30m

LLD
 |
| Power Restore - Recharged Capacity |
CPS-MIB::upsAdvanceConfigRechargedCapacity - when the utility power restores, the UPS will start to recharge until the specified battery capacity in percentage is met before restoring output power. The possible values are 0, 15, 30, 45, 60, 75, and 90. If a value other than a possible value is set, it will not be accepted.
 | SNMP agent |
config.rechargedCapacity.[{#SNMPINDEX}]
Update: 30m

LLD
 |
| Timers - ShutOff Delay |
CPS-MIB::upsAdvanceConfigShutoffDelay - the delay time the UPS will remain on after receiving a turn off command. The possible values are between 60 to 5940 seconds. If a value other than a supported value is set, the value will not be accepted.
 | SNMP agent |
config.shutoffDelay.[{#SNMPINDEX}]
Update: 30m

LLD
 |
| Temperature |
CPS-MIB::upsAdvanceBatteryTemperature - the UPS battery temperature expressed in Celsius
 | SNMP agent |
ups.info.Temperature.[{#SNMPINDEX}]
Update: 1m

LLD
 |
| Age Recommendation |
CPS-MIB::upsBaseBatteryAgeRecommand - Recommended battery life in months
 | SNMP agent |
battery.ageRecommend.[{#SNMPINDEX}]
Update: 1h

LLD
 |
| Last Replace Date |
CPS-MIB::upsBaseBatteryLastReplaceDate - the UPS batteries last replaced date in mm/dd/yyyy format. This value is originally set when manufactured. If batteries replaced, administrator should reset this value.
 | SNMP agent |
battery.lastReplaceDate.[{#SNMPINDEX}]
Update: 1h

LLD
 |
| Timers - Sleep Delay |
CPS-MIB::upsAdvanceConfigSleepDelay - the delay time the UPS will enter sleep mode after receiving a sleep command. The possible values are between 60 to 5940 seconds. If a value other than a supported value is set, the value will not be accepted.
 | SNMP agent |
config.sleepDelay.[{#SNMPINDEX}]
Update: 30m

LLD
 |
| System - Cold Start |
CPS-MIB::upsAdvanceConfigColdStart - set the ability of the UPS can start in the absence of input power. When this option is enabled the UPS can be turned on without having input power.
 | SNMP agent |
config.coldStart.[{#SNMPINDEX}]
Update: 30m

LLD
 |
There are no triggers in this template.


Public Member Functions | |
| def | __init__ |
| def | classify |
| Classifies decomposed clusters in 2 categories: | |
| def | decompose |
| Converts the clusters given as input into "decomposed clusters",i.e. | |
| def | separate |
| Decomposes and separates all the clusters in clustering into pure or mixed clusters depending if their elements come from one or more source trajectories. |
Definition at line 59 of file comparator.py.
Definition at line 64 of file comparator.py.
| def pyproct.clustering.comparison.comparator.Separator.classify | ( | cls, | |
| decomposed_clusters | |||
| ) |
Classifies decomposed clusters in 2 categories:
| decomposed_clusters,: | A list of decomposed clusters. |
Definition at line 78 of file comparator.py.
| def pyproct.clustering.comparison.comparator.Separator.decompose | ( | cls, | |
| clusters, | |||
| traj_ranges | |||
| ) |
Converts the clusters given as input into "decomposed clusters",i.e.
a new data structure that divides the elements of the cluster according to its source trajectory. Example: cluster 1 has the following elements: [1, 3, 4, 7, 8, 12] and traj_ranges = {"traj_A":(0,6),"traj_B":(7,15) The resulting "decomposed cluster" will be: dc = {"traj_A":[1, 3, 4], "traj_B":[7, 8, 12]}
| clusters,: | A list containing cluster objects. |
| traj_ranges,: | A dictionary that contains the starting and ending frame of each trajectory (indexed by a trajectory id). The numbering is accumulative, so if we have 2 trajectories of 10 models each, first will start in 0 and end in 9 and second will start in 10 and end in 19. |
Definition at line 112 of file comparator.py.
| def pyproct.clustering.comparison.comparator.Separator.separate | ( | cls, | |
| clusters, | |||
| traj_ranges | |||
| ) |
Decomposes and separates all the clusters in clustering into pure or mixed clusters depending if their elements come from one or more source trajectories.
| clusters,: | A list containing cluster objects. |
| traj_ranges,: | A dictionary that contains the starting and ending frame of each trajectory (indexed by a trajectory id). The numbering is accumulative, so if we have 2 trajectories of 10 models each, first will start in 0 and end in 9 and second will start in 10 and end in 19. |
Definition at line 143 of file comparator.py.


Technologically, the private press is more advanced than the state press, but this advantage may be short-lived because the government is now three years into a major modernization program for its news organs.
Operating on shoestring budgets with skeleton staffs, many private newspapers and magazines lay out their publications themselves on personal computers equipped with outdated desktop publishing programs that are modified to work in both the Amharic and English languages. Using laser printers to prepare camera-ready page proofs, self-taught production staffs produce the most basic graphics. These publications would greatly benefit from access to more sophisticated technology and production training.
The independent press publishes products that vary in editorial quality and political analysis. English-language newspapers reflect the decline of English-language instruction in the educational system. And both Amharic- and English-language publications reflect the negligible editorial skills of the majority of practicing journalists.
Some newspapers, like the Addis Tribune and The Monitor, which have been accused in the past of treading too carefully to avoid the perception of criticizing the government, are now covering more local and political issues, as well as press freedom and human rights. However, the bulk of the criticism directed squarely at the government can be found in publications like Tobia and Urji, which are regarded as political opposition papers by the government and its supporters. There is some justification for the governments view: some independent publishers and journalists were partisans of Col. Mengistu; others of the late Emperor Haile Selassie; and others still of various ethnic insurgent groups. This, however, does not justify the states intolerance of the expression of opposing viewpoints.
English-language newspapers targeting the Addis-based international community have created a new segment of the market. 7 Days Update and Addis Digest excerpt major stories from both the state and private media, providing translations of articles from Amharic-language publications. Entrepreneur and The Sun are weekly newspapers that extensively cover business issues.
Reporter, an Amharic-language weekly, has also carved out a niche for itself, offering investigative reporting in the form of exposés of government corruption and mismanagement. Many of the best-selling independent Amharic-language publications plan to publish English-language editions in the near future.
| (c) 1996 Committee Protect Journalists | |Index |CPJ Website| |


About
Work
Contact
Software Developer
Ciara Morrissey
Here are some of my projects
Tribute Page
Form
Landing Page
Technical
Personal
Show all


Hit the slopes!
- We offer a wide range of skiing and snowboarding options for everyone from professionals to beginners
- High quality equipment is always available for rental
- Our skilled instructers offer lessons multiple times a day
Non-stop Entertainment
- Live music and shows are held every night
- Enjoy dancing in our ballroom or relax at our bar
- Kids can enjoy playing games and activites while parents go out for the night
- Don't forget to check out our ice skating rink


Welcome to my blog.
This website/blog will be updated throughout my time here at Dev Academy and serve as a landmark of my progress.


21-Apr-2017 | Milku
You probably think I'm going to talk about Sonic the Hedgehog, but you'd be wrong.
A couple of my humans took advantage of time off work and high school to go along to the local primary school and see a willow sculpture of a hedgehog being installed. One of the school girls had designed it and she was there helping some experts transform long sticks of willow into a beautiful hedgehog-like structure. My humans got involved too, weaving the willow into a body and they were responsible for the eyes. Maybe they'll do a hamster sculpture next. I must email the headteacher...
And then, surfing the internet, I found a new pop idol. After The Hamsters, of course. It’s Katy Perry. Did you know that her video for ‘Chained to the Rhythm’ features a hamster? The whole thing is a homage to all the YouTube videos showing people preparing gourmet food for hamsters and then clips of the hamsters scoffing the dainty morsels. Katy’s hamster isn’t the most photogenic possible and it’s so wasteful of the treats, dropping them on the floor and then ignoring them. Katy, next time you need a good looking hamster who will appreciate your culinary efforts, just call me.
It mightn't look like it, but I can appreciate gourmet food given half a chance.


You've decided to learn how to program. Congratulations! But there is still a long way to go. The next step is deciding what language best suits your goals. Take the quiz to find out your ideal path! Once you've taken this quiz, you can try my other version.
Cascading Style Sheets (CSS) is a style sheet language used for describing the presentation of a document written in a markup language. CSS is designed primarily to enable the separation of document content from document presentation, including aspects such as the layout, colors, and fonts. (Source:Wikipedia)
A web designer's job duties cover all aspects of creating a website. Upon meeting with clients and assessing their needs, web designers help create and maintain the product. Their duties include, but aren't limited to, the following: Writing and editing content. (Source: study.com)
C# (pronounced "C-sharp") is an object-oriented programming language from Microsoft that aims to combine the computing power of C++ with the programming ease of Visual Basic. C# is based on C++ and contains features similar to those of Java. (Source: Tech Target)
PHP is a server-side scripting language designed primarily for web development but also used as a general-purpose programming language. ... PHP originally stood for Personal Home Page, but it now stands for the recursive acronym PHP: Hypertext Preprocessor. (Source: Wikipedia)
Java is a general-purpose computer programming language that is concurrent, class-based, object-oriented, and specifically designed to have as few implementation dependencies as possible. (Source: Wikipedia)
Ruby is a dynamic, reflective, object-oriented, general-purpose programming language. It was designed and developed in the mid-1990s by Yukihiro "Matz" Matsumoto in Japan. According to its creator, Ruby was influenced by Perl, Smalltalk, Eiffel, Ada, and Lisp. (Source: Wikipedia)


PostgreSQL
i) to enable verification, pre-processing and storing of consistent data;
ii) to ensure availability of data, decoupling our web application from EpiCollect5;
iii)to reduce the risk of data loss;
iv) to improve performance;
v) to leverage DBMS capabilities and, in particular, the interface between Python and PostgreSQL.


--- layout: rustwasm title: web_sys::console assert description: web_sys::console_assert function keyword: web_sys::console::assert, console assert function ---
A false assertion prints message to the console without interrupting execution of subsequent code.
pub fn console_assert() {
web_sys::console::assert();
}
pub fn assert()


---
layout: page
id: news
hastitle: true
title: Fab Foundation News
hasdescription: true
description:
- paragraph: >-
Keep up with the activities, events and news around the Fab Foundation, our partners and the international Fab Lab community!
Have news to share with the network? Submit your news here!
hasjumplinks: true
jumplinks:
- link: Newsletters
url: news-newsletters
- link: Fab News
url: news-fabnews
background-img: news-bg-edited.jpg
---
{% include fixed/news-all.html texts=site.data.news.news-full-module %}


Rcmdr menu items to display mosaic and assoc plots Allows to visually restructure the underlying structables Developed after extended discussions with Rich Heiberger
| Version: | 1.0-7 |
| Depends: | ENmisc, vcd (≥ 1.2-11), Hmisc, Rcmdr |
| Published: | 2013-01-09 |
| Author: | Erich Neuwirth [aut, cre] |
| Maintainer: | Erich Neuwirth <erich.neuwirth at univie.ac.at> |
| License: | GPL-2 |
| NeedsCompilation: | no |
| CRAN checks: | RcmdrPlugin.mosaic results |
| Reference manual: | RcmdrPlugin.mosaic.pdf |
| Package source: | RcmdrPlugin.mosaic_1.0-7.tar.gz |
| Windows binaries: | r-devel: RcmdrPlugin.mosaic_1.0-7.zip, r-release: RcmdrPlugin.mosaic_1.0-7.zip, r-oldrel: RcmdrPlugin.mosaic_1.0-7.zip |
| OS X binaries: | r-release: RcmdrPlugin.mosaic_1.0-7.tgz, r-oldrel: RcmdrPlugin.mosaic_1.0-7.tgz |
| Old sources: | RcmdrPlugin.mosaic archive |
Please use the canonical form https://CRAN.R-project.org/package=RcmdrPlugin.mosaic to link to this page.


To view this page ensure that Adobe Flash Player version 10.2.0 or greater is installed.
This was one of the games made during
Manila Game Jam 2013!
You can view other games from the Philippines on the official site!
Instructions
- Avoid the mob of dancers by moving your mouse to a safe location.

- Collect D-O-N-N-A letters to shove these dancers away!
About
Celebrating the Golden Era of Donna Cruz's career, Donnafied: Kapag Tumibok ang Puso is "flash-mob simulator" where you have to dodge hordes of wannabe dancers as they dance to the beat. Game design is based on the song's lyrics.
Credits:
Watch the classic video of the song here:
Music used in the game: ( We do not own the music! )
Kapag Tumibok Ang Puso - by Donna Cruz


I am a recent engineering student seeking career opportunity. My goal is to become an influence of technology and expand my skills throughout different sectors of engineering. I am an individual who enjoys hands-on projects and software development.
GPA: 2.73
Other activities included:
Problem: Fill a gap in a manufacturing process
Solution: Develop and program a crane-like mechanism to transport product from one process to another
Role: Programming PLC and arduino components
Details
Collaborated with a start-up company to design and build a process that would make the company's manufacturing process easily flow. The mechanism included two potential use designs; one that included a PLC, stepper motor, photoelectric sensors and an alarm feature and the other which included an Arduino with stepper motor shield and used a relay to operate a claw.
Problem: Solve present and future agricultural problems
Solution: Utilize hydroponics, and passive techniques to research alternatives for crop farming.
Role: Lead a team each semester to complete research projects while under the supervision of the project coordinator.
Details
Projects ranged differently from each other each semester under Evergreen.
Problem: Surveillance system is needed to monitor crop growth inside a shipping container.
Solution: Create a robotic device to roam the shipping container via Wi-Fi on a web browser.
Role: Program robotic device using Arduino IDE.
Details
Use Arduino hardware and libraries to program robotic device. The device utilized two DC motors to move in both X and Y axis. The arduino utilized a Wi-Fi shield and motor shield. A web browser was made to control the device with user interactive buttons. The device had a live feed camera mounted to the top which the broadcast could be seen through the same web page.