Program Version:EnergyPlus, Version 9.1.0-08d2e308bb, YMD=2019.07.16 16:11
Tabular Output Report in Format: HTML
Building: Building 1
Environment: RUN PERIOD 1 ** Philadelphia International Ap PA USA TMY3 WMO#=724080
Simulation Timestamp: 2019-07-16 16:11:39
Report: Annual Building Utility Performance Summary
For: Entire Facility
Timestamp: 2019-07-16 16:11:39
Values gathered over 8760.00 hours| Total Energy [GJ] | Energy Per Total Building Area [MJ/m2] | Energy Per Conditioned Building Area [MJ/m2] | |
| Total Site Energy | 155.30 | 174.56 | 371.45 |
| Net Site Energy | 155.30 | 174.56 | 371.45 |
| Total Source Energy | 336.92 | 378.71 | 805.87 |
| Net Source Energy | 336.92 | 378.71 | 805.87 |
| Site=>Source Conversion Factor | |
| Electricity | 3.167 |
| Natural Gas | 1.084 |
| District Cooling | 1.056 |
| District Heating | 3.613 |
| Steam | 0.300 |
| Gasoline | 1.050 |
| Diesel | 1.050 |
| Coal | 1.050 |
| Fuel Oil #1 | 1.050 |
| Fuel Oil #2 | 1.050 |
| Propane | 1.050 |
| Other Fuel 1 | 1.000 |
| Other Fuel 2 | 1.000 |
| Area [m2] | |
| Total Building Area | 889.66 |
| Net Conditioned Building Area | 418.08 |
| Unconditioned Building Area | 471.58 |
| Electricity [GJ] | Natural Gas [GJ] | Additional Fuel [GJ] | District Cooling [GJ] | District Heating [GJ] | Water [m3] | |
| Heating | 0.25 | 0.00 | 72.14 | 0.00 | 0.00 | 0.00 |
| Cooling | 10.68 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 12.25 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 2.83 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 32.16 | 1.05 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 4.63 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 19.31 | 0.00 | 0.00 | 0.00 | 0.00 | 197.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total End Uses | 82.11 | 1.05 | 72.14 | 0.00 | 0.00 | 197.00 |
| Subcategory | Electricity [GJ] | Natural Gas [GJ] | Additional Fuel [GJ] | District Cooling [GJ] | District Heating [GJ] | Water [m3] | |
| Heating | General | 0.25 | 0.00 | 72.14 | 0.00 | 0.00 | 0.00 |
| Cooling | General | 10.68 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | res lighting garage garage space | 0.23 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| res lighting interior living space | 5.24 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res lighting interior living space|story 2 | 6.78 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Exterior Lighting | res lighting exterior | 2.83 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | res extra refrig | 0.88 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| res freezer | 1.15 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res cd electric | 0.22 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res ceil fan | 0.93 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res cw | 0.01 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res dw | 0.73 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res hot tub heater electric | 0.25 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res hot tub pump | 0.31 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res mv_1 bath fan | 0.06 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res mv_1 house fan | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res mv_1 range fan | 0.04 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res misc plug loads | 22.17 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res pool heater electric | 0.05 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res pool pump | 0.86 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res range electric | 2.52 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res refrig | 1.73 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res well pump | 0.26 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res gas fireplace | 0.00 | 0.29 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res gas grill | 0.00 | 0.13 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res gas lighting | 0.00 | 0.03 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res hot tub heater gas | 0.00 | 0.13 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res pool heater gas | 0.00 | 0.47 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Exterior Equipment | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | res ac clg supply fan | 2.84 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| res fur propane htg supply fan | 1.79 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Pumps | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | res wh | 19.31 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| res shower | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 110.44 | |
| res sink | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 73.57 | |
| res bath | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 7.19 | |
| General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res cw | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.24 | |
| res dw | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 5.56 | |
| Refrigeration | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Electricity Intensity [MJ/m2] | Natural Gas Intensity [MJ/m2] | Additional Fuel Intensity [MJ/m2] | District Cooling Intensity [MJ/m2] | District Heating Intensity [MJ/m2] | Water Intensity [m3/m2] | |
| Lighting | 36.06 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| HVAC | 83.41 | 0.00 | 172.54 | 0.00 | 0.00 | 0.47 |
| Other | 76.92 | 2.51 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total | 196.39 | 2.51 | 172.54 | 0.00 | 0.00 | 0.47 |
| Electricity Intensity [MJ/m2] | Natural Gas Intensity [MJ/m2] | Additional Fuel Intensity [MJ/m2] | District Cooling Intensity [MJ/m2] | District Heating Intensity [MJ/m2] | Water Intensity [m3/m2] | |
| Lighting | 16.95 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| HVAC | 39.20 | 0.00 | 81.08 | 0.00 | 0.00 | 0.22 |
| Other | 36.15 | 1.18 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total | 92.29 | 1.18 | 81.08 | 0.00 | 0.00 | 0.22 |
| Electricity [GJ] | Percent Electricity [%] | |
| Fuel-Fired Power Generation | 0.000 | 0.00 |
| High Temperature Geothermal* | 0.000 | 0.00 |
| Photovoltaic Power | 0.000 | 0.00 |
| Wind Power | 0.000 | 0.00 |
| Power Conversion | 0.000 | 0.00 |
| Net Decrease in On-Site Storage | 0.000 | 0.00 |
| Total On-Site Electric Sources | 0.000 | 0.00 |
| Electricity Coming From Utility | 82.109 | 100.00 |
| Surplus Electricity Going To Utility | 0.000 | 0.00 |
| Net Electricity From Utility | 82.109 | 100.00 |
| Total On-Site and Utility Electric Sources | 82.109 | 100.00 |
| Total Electricity End Uses | 82.109 | 100.00 |
| Heat [GJ] | Percent Heat [%] | |
| Water-Side Heat Recovery | 0.00 | |
| Air to Air Heat Recovery for Cooling | 0.00 | |
| Air to Air Heat Recovery for Heating | 0.00 | |
| High-Temperature Geothermal* | 0.00 | |
| Solar Water Thermal | 0.00 | |
| Solar Air Thermal | 0.00 | |
| Total On-Site Thermal Sources | 0.00 |
| Water [m3] | Percent Water [%] | |
| Rainwater Collection | 0.00 | 0.00 |
| Condensate Collection | 0.00 | 0.00 |
| Groundwater Well | 0.00 | 0.00 |
| Total On Site Water Sources | 0.00 | 0.00 |
| - | - | - |
| Initial Storage | 0.00 | 0.00 |
| Final Storage | 0.00 | 0.00 |
| Change in Storage | 0.00 | 0.00 |
| - | - | - |
| Water Supplied by Utility | 197.00 | 100.00 |
| - | - | - |
| Total On Site, Change in Storage, and Utility Water Sources | 197.00 | 100.00 |
| Total Water End Uses | 197.00 | 100.00 |
| Degrees [deltaC] | |
| Tolerance for Zone Heating Setpoint Not Met Time | 0.20 |
| Tolerance for Zone Cooling Setpoint Not Met Time | 0.20 |
| Facility [Hours] | |
| Time Setpoint Not Met During Occupied Heating | 0.00 |
| Time Setpoint Not Met During Occupied Cooling | 8.00 |
| Time Not Comfortable Based on Simple ASHRAE 55-2004 | 4374.83 |
Table of Contents
TopBUILDING ENERGY PERFORMANCE - ELECTRICITY
| Meter |BUILDING ENERGY PERFORMANCE - NATURAL GAS
| Meter |BUILDING ENERGY PERFORMANCE - ELECTRICITY PEAK DEMAND
| Meter |BUILDING ENERGY PERFORMANCE - NATURAL GAS PEAK DEMAND
| Meter |Life-Cycle Cost Report
| Entire Facility |Report: Input Verification and Results Summary
For: Entire Facility
Timestamp: 2019-07-16 16:11:39
General| Value | |
| Program Version and Build | EnergyPlus, Version 9.1.0-08d2e308bb, YMD=2019.07.16 16:11 |
| RunPeriod | RUN PERIOD 1 |
| Weather File | Philadelphia International Ap PA USA TMY3 WMO#=724080 |
| Latitude [deg] | 39.87 |
| Longitude [deg] | -75.2 |
| Elevation [m] | 2.00 |
| Time Zone | -5.0 |
| North Axis Angle [deg] | 270.00 |
| Rotation for Appendix G [deg] | 0.00 |
| Hours Simulated [hrs] | 8760.00 |
| Total | North (315 to 45 deg) | East (45 to 135 deg) | South (135 to 225 deg) | West (225 to 315 deg) | |
| Gross Wall Area [m2] | 486.09 | 102.27 | 130.75 | 111.18 | 141.90 |
| Above Ground Wall Area [m2] | 365.70 | 84.91 | 101.29 | 84.91 | 94.60 |
| Window Opening Area [m2] | 42.47 | 7.88 | 11.18 | 9.22 | 14.19 |
| Gross Window-Wall Ratio [%] | 8.74 | 7.71 | 8.55 | 8.29 | 10.00 |
| Above Ground Window-Wall Ratio [%] | 11.61 | 9.28 | 11.03 | 10.86 | 15.00 |
| Total | North (315 to 45 deg) | East (45 to 135 deg) | South (135 to 225 deg) | West (225 to 315 deg) | |
| Gross Wall Area [m2] | 285.38 | 52.55 | 76.76 | 61.47 | 94.60 |
| Above Ground Wall Area [m2] | 285.38 | 52.55 | 76.76 | 61.47 | 94.60 |
| Window Opening Area [m2] | 42.47 | 7.88 | 11.18 | 9.22 | 14.19 |
| Gross Window-Wall Ratio [%] | 14.88 | 15.00 | 14.56 | 15.00 | 15.00 |
| Above Ground Window-Wall Ratio [%] | 14.88 | 15.00 | 14.56 | 15.00 | 15.00 |
| Total | |
| Gross Roof Area [m2] | 263.62 |
| Skylight Area [m2] | 0.00 |
| Skylight-Roof Ratio [%] | 0.00 |
| Area [m2] | Conditioned (Y/N) | Part of Total Floor Area (Y/N) | Volume [m3] | Multipliers | Above Ground Gross Wall Area [m2] | Underground Gross Wall Area [m2] | Window Glass Area [m2] | Opening Area [m2] | Lighting [W/m2] | People [m2 per person] | Plug and Process [W/m2] | |
| GARAGE ZONE | 53.51 | No | Yes | 130.48 | 1.00 | 44.59 | 0.00 | 0.00 | 0.00 | 0.3661 | 1.5788 | |
| LIVING ZONE | 418.06 | Yes | Yes | 1019.41 | 1.00 | 285.38 | 0.00 | 42.47 | 42.47 | 2.4028 | 129.43 | 533.9531 |
| RES DS RES AC ASYS RET AIR ZONE | 0.01 | Yes | Yes | 0.25 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.0000 | 0.0000 | |
| RES DS RES FUR PROPANE ASYS RET AIR ZONE | 0.01 | Yes | Yes | 0.25 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.0000 | 0.0000 | |
| UNFINISHED ATTIC ZONE | 235.79 | No | Yes | 10.00 | 1.00 | 35.72 | 0.00 | 0.00 | 0.00 | 0.0000 | 0.0000 | |
| UNFINISHED BASEMENT ZONE | 182.28 | No | Yes | 444.46 | 1.00 | 0.00 | 120.39 | 0.00 | 0.00 | 0.0000 | 0.0000 | |
| Total | 889.66 | 1604.85 | 365.70 | 120.39 | 42.47 | 42.47 | 1.1512 | 275.44 | 251.0071 | |||
| Conditioned Total | 418.08 | 1019.91 | 285.38 | 0.00 | 42.47 | 42.47 | 2.4027 | 129.44 | 533.9276 | |||
| Unconditioned Total | 471.58 | 584.95 | 80.31 | 120.39 | 0.00 | 0.00 | 0.0415 | 0.1791 | ||||
| Not Part of Total | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
Report: Demand End Use Components Summary
For: Entire Facility
Timestamp: 2019-07-16 16:11:39
End Uses| Electricity [W] | Natural Gas [W] | Propane [W] | District Cooling [W] | Steam [W] | Water [m3/s] | |
| Time of Peak | 24-JUL-19:00 | 01-FEB-10:09 | 23-JAN-01:00 | - | - | 06-JAN-16:10 |
| Heating | 0.00 | 0.00 | 16276.23 | 0.00 | 0.00 | 0.00 |
| Cooling | 1758.36 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 598.88 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 138.22 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 8242.99 | 67.79 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 475.06 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total End Uses | 11213.52 | 67.79 | 16276.23 | 0.00 | 0.00 | 0.00 |
| Subcategory | Electricity [W] | Natural Gas [W] | Propane [W] | District Cooling [W] | Steam [W] | Water [m3/s] | |
| Heating | General | 0.00 | 0.00 | 16276.23 | 0.00 | 0.00 | 0.00 |
| Cooling | General | 1758.36 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | res lighting garage garage space | 11.46 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| res lighting interior living space | 256.12 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res lighting interior living space|story 2 | 331.31 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Exterior Lighting | res lighting exterior | 138.22 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | res extra refrig | 34.33 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| res freezer | 45.08 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res cd electric | 6969.72 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res ceil fan | 41.26 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res cw | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res dw | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res hot tub heater electric | 11.30 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res hot tub pump | 13.71 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res mv_1 bath fan | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res mv_1 house fan | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res mv_1 range fan | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res misc plug loads | 983.38 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res pool heater electric | 0.13 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res pool pump | 2.32 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res range electric | 60.02 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res refrig | 67.67 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res well pump | 14.06 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res gas fireplace | 0.00 | 8.34 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res gas grill | 0.00 | 4.77 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res gas lighting | 0.00 | 0.99 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res hot tub heater gas | 0.00 | 1.41 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res pool heater gas | 0.00 | 52.28 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Exterior Equipment | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | res ac clg supply fan | 475.06 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| res fur propane htg supply fan | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Pumps | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | res wh | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| res shower | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res sink | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res bath | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res cw | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| res dw | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Refrigeration | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
Report: Source Energy End Use Components Summary
For: Entire Facility
Timestamp: 2019-07-16 16:11:39
Values gathered over 8760.00 hours| Source Electricity [GJ] | Source Natural Gas [GJ] | Source Additional Fuel [GJ] | Source District Cooling [GJ] | Source District Heating [GJ] | |
| Heating | 0.80 | 0.00 | 75.74 | 0.00 | 0.00 |
| Cooling | 33.81 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 38.80 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 8.95 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 101.85 | 1.14 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 14.67 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 61.16 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total Source Energy End Use Components | 260.04 | 1.14 | 75.74 | 0.00 | 0.00 |
| Source Electricity [MJ/m2] | Source Natural Gas [MJ/m2] | Source Additional Fuel [MJ/m2] | Source District Cooling [MJ/m2] | Source District Heating [MJ/m2] | |
| Heating | 1.92 | 0.00 | 181.17 | 0.00 | 0.00 |
| Cooling | 80.88 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 92.80 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 21.42 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 243.60 | 2.72 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 35.09 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 146.28 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total Source Energy End Use Components | 621.98 | 2.72 | 181.17 | 0.00 | 0.00 |
| Source Electricity [MJ/m2] | Source Natural Gas [MJ/m2] | Source Additional Fuel [MJ/m2] | Source District Cooling [MJ/m2] | Source District Heating [MJ/m2] | |
| Heating | 1.92 | 0.00 | 181.17 | 0.00 | 0.00 |
| Cooling | 80.88 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 92.80 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 21.42 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 243.60 | 2.72 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 35.09 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 146.28 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total Source Energy End Use Components | 621.98 | 2.72 | 181.17 | 0.00 | 0.00 |
Report: Component Sizing Summary
For: Entire Facility
Timestamp: 2019-07-16 16:11:39
AirTerminal:SingleDuct:ConstantVolume:NoReheat| Design Size Maximum Air Flow Rate [m3/s] | User-Specified Maximum Air Flow Rate [m3/s] | |
| RES AC LIVING ZONE DIRECT AIR | 0.669882 | 0.685900 |
| RES FUR PROPANE LIVING ZONE DIRECT AIR | 0.669882 | 0.685900 |
| Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | Sum of Air Terminal Maximum Flow Rates [m3/s] | Adjusted Heating Design Air Flow Rate [m3/s] | Adjusted Cooling Design Air Flow Rate [m3/s] | Adjusted Main Design Air Flow Rate [m3/s] | User Heating Air Flow Ratio [] | Calculated Heating Air Flow Ratio [] | |
| RES AC ASYS | 0.000000 | 0.000000 | 0.685900 | 0.669882 | 0.379114 | 0.685900 | 0.300000 | 0.976647 |
| RES FUR PROPANE ASYS | 0.000000 | 0.000000 | 0.685900 | 0.669882 | 0.379114 | 0.685900 | 0.300000 | 0.976647 |
| User-Specified Supply Air Flow Rate [m3/s] | User-Specified Cooling Supply Air Flow Rate [m3/s] | User-Specified No Load Supply Air Flow Rate [m3/s] | Design Size Nominal Cooling Capacity [W] | User-Specified Nominal Cooling Capacity [W] | Design Size Supply Air Flow Rate [m3/s] | User-Specified Heating Supply Air Flow Rate [m3/s] | Design Size Nominal Heating Capacity [W] | User-Specified Nominal Heating Capacity [W] | Design Size Maximum Supply Air Temperature [C] | User-Specified Maximum Supply Air Temperature [C] | |
| RES AC UNITARY SYSTEM | 0.685900 | 0.685900 | 0.000000 | 28046.44 | 10242.85 | ||||||
| RES FUR PROPANE UNITARY SYSTEM | 0.506895 | 0.000000 | 0.685900 | 0.506895 | 15393.30 | 17309.11 | 16.70 | 48.89 |
| User-Specified Maximum Flow Rate [m3/s] | |
| RES AC CLG SUPPLY FAN | 0.685904 |
| RES FUR PROPANE HTG SUPPLY FAN | 0.685904 |
| Design Size Rated Air Flow Rate [m3/s] | User-Specified Rated Air Flow Rate [m3/s] | Design Size Gross Rated Total Cooling Capacity [W] | User-Specified Gross Rated Total Cooling Capacity [W] | User-Specified Gross Rated Sensible Heat Ratio | |
| RES AC COOLING COIL | 0.685900 | 0.530713 | 17925.72 | 10242.85 | 0.740403 |
| Design Size Nominal Capacity [W] | User-Specified Nominal Capacity [W] | |
| RES FUR PROPANE HEATING COIL | 15393.30 | 17309.11 |
| Use Side Design Flow Rate [m3/s] | |
| RES WH | 0.002181 |
Report: Surface Shadowing Summary
For: Entire Facility
Timestamp: 2019-07-16 16:11:39
Surfaces (Walls, Roofs, etc) that may be Shadowed by Other Surfaces| Possible Shadow Receivers | |
| SURFACE 25 - RES EAVES | Mir-RES NEIGHBORS LEFT | Mir-RES NEIGHBORS RIGHT | |
| Mir-SURFACE 25 - RES EAVES | SURFACE 39 - RES EAVES 1 | Mir-SURFACE 40 - RES EAVES 1 | Mir-SURFACE 43 - RES EAVES | Mir-SURFACE 43 - RES EAVES 2 | Mir-RES NEIGHBORS LEFT | Mir-RES NEIGHBORS RIGHT | SURFACE 26 | SURFACE 39 | |
| SURFACE 25 - RES EAVES 1 | Mir-RES NEIGHBORS LEFT | Mir-RES NEIGHBORS RIGHT | |
| Mir-SURFACE 25 - RES EAVES 1 | Mir-SURFACE 39 - RES EAVES 1 | SURFACE 40 - RES EAVES 1 | Mir-SURFACE 43 - RES EAVES | Mir-SURFACE 43 - RES EAVES 2 | Mir-RES NEIGHBORS LEFT | Mir-RES NEIGHBORS RIGHT | SURFACE 27 | SURFACE 40 | |
| SURFACE 25 - RES EAVES 2 | Mir-RES NEIGHBORS LEFT | Mir-RES NEIGHBORS RIGHT | |
| Mir-SURFACE 25 - RES EAVES 2 | SURFACE 39 - RES EAVES | Mir-SURFACE 39 - RES EAVES | SURFACE 39 - RES EAVES 1 | Mir-SURFACE 39 - RES EAVES 1 | Mir-SURFACE 40 - RES EAVES | Mir-SURFACE 40 - RES EAVES 1 | Mir-SURFACE 43 - RES EAVES | Mir-SURFACE 43 - RES EAVES 1 | Mir-SURFACE 43 - RES EAVES 2 | Mir-RES NEIGHBORS LEFT | Mir-RES NEIGHBORS RIGHT | SURFACE 39 | |
| SURFACE 39 - RES EAVES | Mir-SURFACE 25 - RES EAVES | Mir-SURFACE 25 - RES EAVES 2 | SURFACE 43 - RES EAVES | Mir-SURFACE 43 - RES EAVES | SURFACE 43 - RES EAVES 1 | Mir-SURFACE 43 - RES EAVES 1 | Mir-RES NEIGHBORS LEFT | SURFACE 43 | |
| Mir-SURFACE 39 - RES EAVES | Mir-SURFACE 25 - RES EAVES 1 | Mir-SURFACE 25 - RES EAVES 2 | Mir-SURFACE 40 - RES EAVES | Mir-SURFACE 40 - RES EAVES 1 | SURFACE 43 - RES EAVES 1 | Mir-SURFACE 43 - RES EAVES 1 | SURFACE 43 - RES EAVES 2 | Mir-SURFACE 43 - RES EAVES 2 | Mir-RES NEIGHBORS RIGHT | SURFACE 43 | |
| SURFACE 39 - RES EAVES 1 | Mir-SURFACE 25 - RES EAVES | SURFACE 43 - RES EAVES | Mir-RES NEIGHBORS LEFT | SURFACE 43 | |
| Mir-SURFACE 39 - RES EAVES 1 | Mir-SURFACE 25 - RES EAVES 1 | Mir-SURFACE 40 - RES EAVES 1 | SURFACE 43 - RES EAVES 2 | Mir-RES NEIGHBORS RIGHT | SURFACE 42 | SURFACE 43 | |
| SURFACE 40 - RES EAVES | Mir-SURFACE 25 - RES EAVES 1 | SURFACE 43 - RES EAVES 2 | Mir-SURFACE 43 - RES EAVES 2 | Mir-RES NEIGHBORS RIGHT | SURFACE 27 | SURFACE 43 | |
| Mir-SURFACE 40 - RES EAVES | Mir-SURFACE 25 - RES EAVES | Mir-SURFACE 25 - RES EAVES 2 | Mir-SURFACE 39 - RES EAVES | Mir-SURFACE 39 - RES EAVES 1 | SURFACE 43 - RES EAVES | Mir-SURFACE 43 - RES EAVES | SURFACE 43 - RES EAVES 1 | Mir-SURFACE 43 - RES EAVES 1 | Mir-RES NEIGHBORS LEFT | Mir-RES NEIGHBORS RIGHT | SURFACE 27 | SURFACE 43 | |
| SURFACE 40 - RES EAVES 1 | Mir-SURFACE 25 - RES EAVES 1 | SURFACE 43 - RES EAVES 2 | Mir-RES NEIGHBORS RIGHT | SURFACE 43 | |
| Mir-SURFACE 40 - RES EAVES 1 | Mir-SURFACE 25 - RES EAVES | Mir-SURFACE 39 - RES EAVES 1 | SURFACE 43 - RES EAVES | Mir-RES NEIGHBORS LEFT | Mir-RES NEIGHBORS RIGHT | SURFACE 42 | SURFACE 43 | |
| SURFACE 43 - RES EAVES | SURFACE 39 - RES EAVES 1 | Mir-SURFACE 40 - RES EAVES 1 | Mir-RES NEIGHBORS LEFT | Mir-RES NEIGHBORS RIGHT | SURFACE 39 | |
| Mir-SURFACE 43 - RES EAVES | Mir-SURFACE 25 - RES EAVES | Mir-SURFACE 25 - RES EAVES 1 | Mir-RES NEIGHBORS LEFT | Mir-RES NEIGHBORS RIGHT | SURFACE 26 | |
| SURFACE 43 - RES EAVES 1 | SURFACE 39 - RES EAVES | Mir-SURFACE 39 - RES EAVES | SURFACE 39 - RES EAVES 1 | Mir-SURFACE 39 - RES EAVES 1 | Mir-SURFACE 40 - RES EAVES | Mir-SURFACE 40 - RES EAVES 1 | Mir-RES NEIGHBORS LEFT | Mir-RES NEIGHBORS RIGHT | SURFACE 39 | |
| Mir-SURFACE 43 - RES EAVES 1 | Mir-SURFACE 25 - RES EAVES | Mir-SURFACE 25 - RES EAVES 1 | Mir-SURFACE 25 - RES EAVES 2 | SURFACE 39 - RES EAVES | Mir-SURFACE 39 - RES EAVES | Mir-SURFACE 40 - RES EAVES | Mir-RES NEIGHBORS LEFT | Mir-RES NEIGHBORS RIGHT | |
| SURFACE 43 - RES EAVES 2 | Mir-SURFACE 39 - RES EAVES 1 | SURFACE 40 - RES EAVES 1 | Mir-RES NEIGHBORS LEFT | Mir-RES NEIGHBORS RIGHT | SURFACE 40 | |
| Mir-SURFACE 43 - RES EAVES 2 | Mir-SURFACE 25 - RES EAVES | Mir-SURFACE 25 - RES EAVES 1 | Mir-RES NEIGHBORS LEFT | Mir-RES NEIGHBORS RIGHT | SURFACE 27 | |
| Mir-RES NEIGHBORS LEFT | SURFACE 25 - RES EAVES | Mir-SURFACE 25 - RES EAVES | SURFACE 25 - RES EAVES 1 | Mir-SURFACE 25 - RES EAVES 1 | SURFACE 25 - RES EAVES 2 | Mir-SURFACE 25 - RES EAVES 2 | SURFACE 39 - RES EAVES | SURFACE 39 - RES EAVES 1 | Mir-SURFACE 40 - RES EAVES | Mir-SURFACE 40 - RES EAVES 1 | SURFACE 43 - RES EAVES | Mir-SURFACE 43 - RES EAVES | SURFACE 43 - RES EAVES 1 | Mir-SURFACE 43 - RES EAVES 1 | SURFACE 43 - RES EAVES 2 | Mir-SURFACE 43 - RES EAVES 2 | Mir-RES NEIGHBORS RIGHT | SURFACE 36 | SURFACE 13 | SURFACE 16 | SURFACE 20 | SURFACE 21 | SURFACE 44 | SURFACE 45 | SURFACE 8 | SURFACE 26 | SURFACE 25 | SURFACE 39 | SURFACE 43 | |
| Mir-RES NEIGHBORS RIGHT | SURFACE 25 - RES EAVES | Mir-SURFACE 25 - RES EAVES | SURFACE 25 - RES EAVES 1 | Mir-SURFACE 25 - RES EAVES 1 | SURFACE 25 - RES EAVES 2 | Mir-SURFACE 25 - RES EAVES 2 | Mir-SURFACE 39 - RES EAVES | Mir-SURFACE 39 - RES EAVES 1 | SURFACE 40 - RES EAVES | Mir-SURFACE 40 - RES EAVES | SURFACE 40 - RES EAVES 1 | Mir-SURFACE 40 - RES EAVES 1 | SURFACE 43 - RES EAVES | Mir-SURFACE 43 - RES EAVES | SURFACE 43 - RES EAVES 1 | Mir-SURFACE 43 - RES EAVES 1 | SURFACE 43 - RES EAVES 2 | Mir-SURFACE 43 - RES EAVES 2 | Mir-RES NEIGHBORS LEFT | SURFACE 4 | SURFACE 10 | SURFACE 13 | SURFACE 18 | SURFACE 21 | SURFACE 44 | SURFACE 45 | SURFACE 27 | SURFACE 25 | SURFACE 40 | SURFACE 43 | |
| SURFACE 36 | Mir-SURFACE 25 - RES EAVES | Mir-SURFACE 25 - RES EAVES 2 | Mir-SURFACE 39 - RES EAVES | Mir-SURFACE 43 - RES EAVES | Mir-SURFACE 43 - RES EAVES 1 | Mir-RES NEIGHBORS LEFT | SURFACE 13 | SURFACE 21 | SURFACE 44 | SURFACE 45 | |
| SURFACE 4 | Mir-SURFACE 25 - RES EAVES 1 | Mir-SURFACE 40 - RES EAVES | Mir-SURFACE 43 - RES EAVES 2 | Mir-RES NEIGHBORS RIGHT | |
| SURFACE 5 | Mir-SURFACE 39 - RES EAVES 1 | Mir-SURFACE 40 - RES EAVES 1 | |
| SURFACE 10 | Mir-SURFACE 25 - RES EAVES 1 | Mir-SURFACE 40 - RES EAVES | Mir-SURFACE 43 - RES EAVES 2 | Mir-RES NEIGHBORS RIGHT | |
| SURFACE 13 | SURFACE 39 - RES EAVES | Mir-SURFACE 39 - RES EAVES | SURFACE 39 - RES EAVES 1 | Mir-SURFACE 39 - RES EAVES 1 | Mir-SURFACE 40 - RES EAVES | Mir-SURFACE 40 - RES EAVES 1 | Mir-SURFACE 43 - RES EAVES 1 | Mir-RES NEIGHBORS LEFT | Mir-RES NEIGHBORS RIGHT | SURFACE 36 | SURFACE 20 | SURFACE 39 | |
| SURFACE 16 | Mir-SURFACE 25 - RES EAVES | Mir-SURFACE 43 - RES EAVES | Mir-RES NEIGHBORS LEFT | |
| SURFACE 17 | Mir-SURFACE 25 - RES EAVES 2 | |
| SURFACE 18 | Mir-SURFACE 25 - RES EAVES 1 | Mir-SURFACE 40 - RES EAVES | SURFACE 43 - RES EAVES 2 | Mir-SURFACE 43 - RES EAVES 2 | Mir-RES NEIGHBORS RIGHT | |
| SURFACE 19 | Mir-SURFACE 39 - RES EAVES 1 | Mir-SURFACE 40 - RES EAVES 1 | |
| SURFACE 20 | Mir-SURFACE 25 - RES EAVES | Mir-SURFACE 25 - RES EAVES 2 | Mir-SURFACE 39 - RES EAVES | SURFACE 43 - RES EAVES | Mir-SURFACE 43 - RES EAVES | SURFACE 43 - RES EAVES 1 | Mir-SURFACE 43 - RES EAVES 1 | Mir-RES NEIGHBORS LEFT | SURFACE 21 | SURFACE 43 | |
| SURFACE 21 | SURFACE 39 - RES EAVES | Mir-SURFACE 39 - RES EAVES | SURFACE 39 - RES EAVES 1 | Mir-SURFACE 39 - RES EAVES 1 | Mir-SURFACE 40 - RES EAVES | Mir-SURFACE 40 - RES EAVES 1 | Mir-SURFACE 43 - RES EAVES 1 | Mir-RES NEIGHBORS LEFT | Mir-RES NEIGHBORS RIGHT | SURFACE 20 | SURFACE 39 | |
| SURFACE 44 | SURFACE 39 - RES EAVES | SURFACE 39 - RES EAVES 1 | Mir-SURFACE 40 - RES EAVES | Mir-SURFACE 40 - RES EAVES 1 | Mir-SURFACE 43 - RES EAVES 1 | Mir-RES NEIGHBORS LEFT | Mir-RES NEIGHBORS RIGHT | SURFACE 36 | SURFACE 20 | SURFACE 39 | |
| SURFACE 45 | SURFACE 39 - RES EAVES | SURFACE 39 - RES EAVES 1 | Mir-SURFACE 40 - RES EAVES | Mir-SURFACE 40 - RES EAVES 1 | Mir-SURFACE 43 - RES EAVES 1 | Mir-RES NEIGHBORS LEFT | Mir-RES NEIGHBORS RIGHT | SURFACE 36 | SURFACE 20 | SURFACE 39 | |
| SURFACE 8 | Mir-SURFACE 25 - RES EAVES | Mir-SURFACE 43 - RES EAVES | Mir-RES NEIGHBORS LEFT | |
| SURFACE 9 | Mir-SURFACE 25 - RES EAVES 2 | |
| SURFACE 26 | Mir-SURFACE 25 - RES EAVES | Mir-SURFACE 43 - RES EAVES | Mir-RES NEIGHBORS LEFT | |
| SURFACE 27 | Mir-SURFACE 25 - RES EAVES 1 | SURFACE 40 - RES EAVES | Mir-SURFACE 40 - RES EAVES | Mir-SURFACE 43 - RES EAVES 2 | Mir-RES NEIGHBORS RIGHT | |
| SURFACE 42 | Mir-SURFACE 39 - RES EAVES 1 | Mir-SURFACE 40 - RES EAVES 1 | |
| SURFACE 25 | Mir-RES NEIGHBORS LEFT | Mir-RES NEIGHBORS RIGHT | |
| SURFACE 39 | Mir-SURFACE 25 - RES EAVES | SURFACE 43 - RES EAVES | Mir-RES NEIGHBORS LEFT | SURFACE 43 | |
| SURFACE 40 | Mir-SURFACE 25 - RES EAVES 1 | SURFACE 43 - RES EAVES 2 | Mir-RES NEIGHBORS RIGHT | SURFACE 43 | |
| SURFACE 43 | SURFACE 39 - RES EAVES 1 | Mir-SURFACE 39 - RES EAVES 1 | SURFACE 40 - RES EAVES 1 | Mir-SURFACE 40 - RES EAVES 1 | Mir-RES NEIGHBORS LEFT | Mir-RES NEIGHBORS RIGHT | SURFACE 39 | SURFACE 40 | |
| Possible Shadow Receivers | |
| SURFACE 10 | SURFACE 10 - WINDOW 1 | SURFACE 10 - WINDOW 2 | SURFACE 10 - WINDOW 3 | |
| SURFACE 13 | SURFACE 13 - WINDOW 1 | SURFACE 13 - WINDOW 2 | SURFACE 13 - WINDOW 3 | SURFACE 13 - WINDOW 4 | |
| SURFACE 16 | SURFACE 16 - WINDOW 1 | SURFACE 16 - WINDOW 2 | SURFACE 16 - WINDOW 3 | SURFACE 16 - WINDOW 4 | |
| SURFACE 17 | SURFACE 17 - WINDOW 1 | SURFACE 17 - WINDOW 2 | SURFACE 17 - WINDOW 3 | SURFACE 17 - WINDOW 4 | SURFACE 17 - WINDOW 5 | SURFACE 17 - WINDOW 6 | SURFACE 17 - WINDOW 7 | |
| SURFACE 18 | SURFACE 18 - WINDOW 1 | SURFACE 18 - WINDOW 2 | SURFACE 18 - WINDOW 3 | SURFACE 18 - WINDOW 4 | SURFACE 18 - WINDOW 5 | |
| SURFACE 19 | SURFACE 19 - WINDOW 1 | SURFACE 19 - WINDOW 2 | SURFACE 19 - WINDOW 3 | |
| SURFACE 20 | SURFACE 20 - WINDOW 1 | SURFACE 20 - WINDOW 2 | |
| SURFACE 21 | SURFACE 21 - WINDOW 1 | SURFACE 21 - WINDOW 2 | SURFACE 21 - WINDOW 3 | SURFACE 21 - WINDOW 4 | |
| SURFACE 44 | UNIT 1 - SURFACE 13 - DOOR | |
| SURFACE 8 | SURFACE 8 - WINDOW 1 | SURFACE 8 - WINDOW 2 | SURFACE 8 - WINDOW 3 | SURFACE 8 - WINDOW 4 | |
| SURFACE 9 | SURFACE 9 - WINDOW 1 | SURFACE 9 - WINDOW 2 | SURFACE 9 - WINDOW 3 | SURFACE 9 - WINDOW 4 | SURFACE 9 - WINDOW 5 | SURFACE 9 - WINDOW 6 | SURFACE 9 - WINDOW 7 | |
Report: Adaptive Comfort Summary
For: Entire Facility
Timestamp: 2019-07-16 16:11:39
Time Not Meeting the Adaptive Comfort Models during Occupied Hours| ASHRAE55 90% Acceptability Limits [Hours] | ASHRAE55 80% Acceptability Limits [Hours] | CEN15251 Category I Acceptability Limits [Hours] | CEN15251 Category II Acceptability Limits [Hours] | CEN15251 Category III Acceptability Limits [Hours] |
Report: Initialization Summary
For: Entire Facility
Timestamp: 2019-07-16 16:11:39
Version| Version ID | |
| 1 | 9.1 |
| #TimeSteps | Minutes per TimeStep {minutes} | |
| 1 | 6 | 10 |
| Minimum System TimeStep {minutes} | Max HVAC Iterations | Minimum Plant Iterations | Maximum Plant Iterations | |
| 1 | 1 | 20 | 2 | 8 |
| Do Zone Sizing | Do System Sizing | Do Plant Sizing | Do Design Days | Do Weather Simulation | Do HVAC Sizing Simulation | |
| 1 | Yes | Yes | Yes | Yes | Yes | No |
| Tolerance for Time Heating Setpoint Not Met | Tolerance for Zone Cooling Setpoint Not Met Time | |
| 1 | 0.200 | 0.200 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | 18.00 | 18.00 | 18.00 | 18.00 | 18.00 | 18.00 | 18.00 | 18.00 | 18.00 | 18.00 | 18.00 | 18.00 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | 1.62 | 0.54 | 2.47 | 5.49 | 13.39 | 19.49 | 23.60 | 24.85 | 22.72 | 17.98 | 11.66 | 5.79 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | 12.75 | 12.75 | 12.75 | 12.75 | 12.75 | 12.75 | 12.75 | 12.75 | 12.75 | 12.75 | 12.75 | 12.75 |
| Jan{dimensionless} | Feb{dimensionless} | Mar{dimensionless} | Apr{dimensionless} | May{dimensionless} | Jun{dimensionless} | Jul{dimensionless} | Aug{dimensionless} | Sep{dimensionless} | Oct{dimensionless} | Nov{dimensionless} | Dec{dimensionless} | |
| 1 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 |
| Normal | Daylighting {dimensionless} | |
| 1 | 1.000 | 1.000 |
| Jan{dimensionless} | Feb{dimensionless} | Mar{dimensionless} | Apr{dimensionless} | May{dimensionless} | Jun{dimensionless} | Jul{dimensionless} | Aug{dimensionless} | Sep{dimensionless} | Oct{dimensionless} | Nov{dimensionless} | Dec{dimensionless} | |
| 1 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 |
| Jan{dimensionless} | Feb{dimensionless} | Mar{dimensionless} | Apr{dimensionless} | May{dimensionless} | Jun{dimensionless} | Jul{dimensionless} | Aug{dimensionless} | Sep{dimensionless} | Oct{dimensionless} | Nov{dimensionless} | Dec{dimensionless} | |
| 1 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 |
| Wind Sensor Height Above Ground {m} | Wind Speed Profile Exponent {} | Wind Speed Profile Boundary Layer Thickness {m} | Air Temperature Sensor Height Above Ground {m} | Wind Speed Modifier Coefficient-Internal | Temperature Modifier Coefficient-Internal | |
| 1 | 10.000 | 0.140 | 270.000 | 1.500 | 1.586 | 9.750E-003 |
| Location Name | Latitude {N+/S- Deg} | Longitude {E+/W- Deg} | Time Zone Number {GMT+/-} | Elevation {m} | Standard Pressure at Elevation {Pa} | Standard RhoAir at Elevation | |
| 1 | Philadelphia International Ap PA USA TMY3 WMO#=724080 | 39.87 | -75.23 | -5.00 | 2.00 | 101301 | 1.2040 |
| Calculation Method{} | Water Mains Temperature Schedule Name{} | Annual Average Outdoor Air Temperature{C} | Maximum Difference In Monthly Average Outdoor Air Temperatures{deltaC} | Fixed Default Water Mains Temperature{C} | |
| 1 | Correlation | NA | 12.75 | 26.92 | NA |
| Building Name | North Axis {deg} | Terrain | Loads Convergence Tolerance Value | Temperature Convergence Tolerance Value | Solar Distribution | Maximum Number of Warmup Days | Minimum Number of Warmup Days | |
| 1 | Building 1 | 270.000 | Suburbs | 4.00000E-002 | 0.40000 | FullExterior | 25 | 6 |
| Algorithm {Simple TARP CeilingDiffuser AdaptiveConvectionAlgorithm} |
|
| 1 | TARP |
| Algorithm {SimpleCombined TARP MoWitt DOE-2 AdaptiveConvectionAlgorithm} |
|
| 1 | DOE-2 |
| Value {Anisotropic} | |
| 1 | Anisotropic |
| Value {ThirdOrderBackwardDifference AnalyticalSolution EulerMethod} |
|
| 1 | ThirdOrderBackwardDifference |
| Simulation {Yes/No} | Carbon Dioxide Concentration | |
| 1 | No | N/A |
| Simulation {Yes/No} | Generic Contaminant Concentration | |
| 1 | No | N/A |
| Enforce Mass Balance |
Adjust Zone Mixing |
Adjust Zone Infiltration {AddInfiltration AdjustInfiltration None} |
Infiltration Zones {MixingSourceZonesOnly AllZones} |
|
| 1 | No | N/A | N/A | N/A |
| Value {RegulaFalsi Bisection BisectionThenRegulaFalsi RegulaFalsiThenBisection} |
|
| 1 | RegulaFalsi |
| Wind Speed Profile Exponent {} | Wind Speed Profile Boundary Layer Thickness {m} | Air Temperature Gradient Coefficient {K/m} | |
| 1 | 0.220 | 370.000 | 6.500000E-003 |
| Starting Corner | Vertex Input Direction | Coordinate System | Daylight Reference Point Coordinate System | Rectangular (Simple) Surface Coordinate System | |
| 1 | UpperLeftCorner | Counterclockwise | RelativeCoordinateSystem | RelativeCoordinateSystem | RelativeToZoneOrigin |
| Sensible Heat Capacity Multiplier | Moisture Capacity Multiplier | Carbon Dioxide Capacity Multiplier | Generic Contaminant Capacity Multiplier | |
| 1 | 1.000 | 1.000 | 1.000 | 1.000 |
| Value {CTF - ConductionTransferFunction EMPD - MoisturePenetrationDepthConductionTransferFunction CondFD - ConductionFiniteDifference HAMT - CombinedHeatAndMoistureFiniteElement} - Description |
Inside Surface Max Temperature Limit{C} |
Surface Convection Coefficient Lower Limit {W/m2-K} |
Surface Convection Coefficient Upper Limit {W/m2-K} |
|
| 1 | CTF - ConductionTransferFunction | 200 | 0.10 | 1000.0 |
| 2 | KivaFoundation - TwoDimensionalFiniteDifference | 200 | 0.10 | 1000.0 |
| Number of Fixed Detached Shades | Number of Building Detached Shades | Number of Attached Shades | |
| 1 | 0 | 24 | 0 |
| Number of Zones | Number of Zone Surfaces | Number of SubSurfaces | |
| 1 | 6 | 105 | 44 |
| Zone Name | North Axis {deg} | Origin X-Coordinate {m} | Origin Y-Coordinate {m} | Origin Z-Coordinate {m} | Centroid X-Coordinate {m} | Centroid Y-Coordinate {m} | Centroid Z-Coordinate {m} | Type | Zone Multiplier | Zone List Multiplier | Minimum X {m} | Maximum X {m} | Minimum Y {m} | Maximum Y {m} | Minimum Z {m} | Maximum Z {m} | Ceiling Height {m} | Volume {m3} | Zone Inside Convection Algorithm {Simple-Detailed-CeilingDiffuser-TrombeWall} | Zone Outside Convection Algorithm {Simple-Detailed-Tarp-MoWitt-DOE-2-BLAST} | Floor Area {m2} | Exterior Gross Wall Area {m2} | Exterior Net Wall Area {m2} | Exterior Window Area {m2} | Number of Surfaces | Number of SubSurfaces | Number of Shading SubSurfaces | Part of Total Building Area | |
| 1 | GARAGE ZONE | 0.0 | 0.00 | 0.00 | 0.00 | -2.89E-015 | 15.74 | 1.22 | 1 | 1 | 1 | -3.66 | 3.66 | 12.08 | 19.40 | 0.00 | 2.44 | 2.44 | 130.48 | TARP | DOE-2 | 53.51 | 44.59 | 44.59 | 0.00 | 7 | 0 | 0 | Yes |
| 2 | LIVING ZONE | 0.0 | 0.00 | 0.00 | 0.00 | -4.48 | 10.56 | 2.63 | 1 | 1 | 1 | -10.78 | 3.66 | -1.98E-015 | 19.40 | 0.00 | 4.88 | 4.56 | 1019.41 | TARP | DOE-2 | 418.06 | 285.38 | 241.05 | 42.47 | 18 | 44 | 0 | Yes |
| 3 | RES DS RES AC ASYS RET AIR ZONE | 0.0 | 0.00 | 0.00 | 0.00 | -74.05 | 5.00E-002 | 0.50 | 1 | 1 | 1 | -74.10 | -74.00 | -1.36E-014 | 1.00E-001 | 0.00 | 1.00 | 1.00 | 0.25 | TARP | DOE-2 | 1.00E-002 | 0.00 | 0.00 | 0.00 | 6 | 0 | 0 | Yes |
| 4 | RES DS RES FUR PROPANE ASYS RET AIR ZONE | 0.0 | 0.00 | 0.00 | 0.00 | -74.05 | 5.00E-002 | 0.50 | 1 | 1 | 1 | -74.10 | -74.00 | -1.36E-014 | 1.00E-001 | 0.00 | 1.00 | 1.00 | 0.25 | TARP | DOE-2 | 1.00E-002 | 0.00 | 0.00 | 0.00 | 6 | 0 | 0 | Yes |
| 5 | UNFINISHED ATTIC ZONE | 0.0 | 0.00 | 0.00 | 0.00 | -4.41 | 10.85 | 5.69 | 1 | 1 | 1 | -10.78 | 3.66 | -1.98E-015 | 19.40 | 4.88 | 7.88 | 1.58 | 10.00 | TARP | DOE-2 | 235.79 | 35.72 | 35.72 | 0.00 | 9 | 0 | 0 | Yes |
| 6 | UNFINISHED BASEMENT ZONE | 0.0 | 0.00 | 0.00 | -2.44 | -5.10 | 10.14 | -1.22 | 1 | 1 | 1 | -10.78 | 0.00 | -1.98E-015 | 19.40 | -2.44 | 0.00 | 2.44 | 444.46 | TARP | DOE-2 | 182.28 | 0.00 | 0.00 | 0.00 | 8 | 0 | 0 | Yes |
| Zone Name | Floor Area {m2} | # Occupants | Area per Occupant {m2/person} | Occupant per Area {person/m2} | Interior Lighting {W/m2} | Electric Load {W/m2} | Gas Load {W/m2} | Other Load {W/m2} | Hot Water Eq {W/m2} | Steam Equipment {W/m2} | Sum Loads per Area {W/m2} | Outdoor Controlled Baseboard Heat | |
| 1 | GARAGE ZONE | 53.51 | 0.0 | N/A | 0.000 | 0.366 | 1.579 | 0.000 | 0.000 | 0.000 | 0.000 | 1.945 | No |
| 2 | LIVING ZONE | 418.06 | 3.2 | 129.431 | 7.726E-003 | 2.403 | 448.943 | 0.260 | 84.749 | 0.000 | 0.000 | 536.356 | No |
| 3 | RES DS RES AC ASYS RET AIR ZONE | 1.00E-002 | 0.0 | N/A | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | No |
| 4 | RES DS RES FUR PROPANE ASYS RET AIR ZONE | 1.00E-002 | 0.0 | N/A | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | No |
| 5 | UNFINISHED ATTIC ZONE | 235.79 | 0.0 | N/A | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | No |
| 6 | UNFINISHED BASEMENT ZONE | 182.28 | 0.0 | N/A | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | No |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Number of People {} | People/Floor Area {person/m2} | Floor Area per person {m2/person} | Fraction Radiant | Fraction Convected | Sensible Fraction Calculation | Activity level | ASHRAE 55 Warnings | Carbon Dioxide Generation Rate | Nominal Minimum Number of People | Nominal Maximum Number of People | |
| 1 | RES OCCUPANTS|LIVING SPACE | RES OCCUPANTS SCHEDULE | LIVING ZONE | 418.06 | 3.2 | 1.4 | 3.369E-003 | 296.861 | 0.320 | 0.680 | 0.573 | SCHEDULE RULESET 1 | No | 0.0000 | 0 | 1 |
| 2 | RES OCCUPANTS|LIVING SPACE|STORY 2 | RES OCCUPANTS SCHEDULE | LIVING ZONE | 418.06 | 3.2 | 1.8 | 4.358E-003 | 229.488 | 0.320 | 0.680 | 0.573 | SCHEDULE RULESET 1 | No | 0.0000 | 0 | 2 |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Lighting Level {W} | Lights/Floor Area {W/m2} | Lights per person {W/person} | Fraction Return Air | Fraction Radiant | Fraction Short Wave | Fraction Convected | Fraction Replaceable | End-Use Category | Nominal Minimum Lighting Level {W} | Nominal Maximum Lighting Level {W} | |
| 1 | RES LIGHTING GARAGE GARAGE SPACE | RES LIGHTING GARAGE | GARAGE ZONE | 53.51 | 0.0 | 19.591 | 0.366 | N/A | 0.000 | 0.600 | 0.200 | 0.200 | 1.000 | res lighting garage garage space | 0.000 | 19.591 |
| 2 | RES LIGHTING INTERIOR LIVING SPACE | RES LIGHTING INTERIOR | LIVING ZONE | 418.06 | 3.2 | 437.981 | 1.048 | 135.598 | 0.000 | 0.600 | 0.200 | 0.200 | 1.000 | res lighting interior living space | 0.000 | 437.981 |
| 3 | RES LIGHTING INTERIOR LIVING SPACE|STORY 2 | RES LIGHTING INTERIOR | LIVING ZONE | 418.06 | 3.2 | 566.563 | 1.355 | 175.406 | 0.000 | 0.600 | 0.200 | 0.200 | 1.000 | res lighting interior living space|story 2 | 0.000 | 566.563 |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Equipment Level {W} | Equipment/Floor Area {W/m2} | Equipment per person {W/person} | Fraction Latent | Fraction Radiant | Fraction Lost | Fraction Convected | End-Use SubCategory | Nominal Minimum Equipment Level {W} | Nominal Maximum Equipment Level {W} | |
| 1 | RES EXTRA REFRIG | RES EXTRA REFRIG SCHEDULE | GARAGE ZONE | 53.51 | 0.0 | 36.525 | 0.683 | N/A | 0.000 | 0.000 | 0.000 | 1.000 | res extra refrig | 0.000 | 36.525 |
| 2 | RES FREEZER | RES FREEZER SCHEDULE | GARAGE ZONE | 53.51 | 0.0 | 47.957 | 0.896 | N/A | 0.000 | 0.000 | 0.000 | 1.000 | res freezer | 0.000 | 47.957 |
| 3 | RES CD ELECTRIC | RES CD ELECTRIC SCHEDULE | LIVING ZONE | 418.06 | 3.2 | 167566.421 | 400.816 | 51878.149 | 5.000E-002 | 9.000E-002 | 0.800 | 6.000E-002 | res cd electric | 0.000 | 6969.724 |
| 4 | RES CEIL FAN BENCHMARK|LIVING SPACE | RES CEIL FAN BENCHMARK|LIVING SPACE SCHEDULE | LIVING ZONE | 418.06 | 3.2 | 27.544 | 6.589E-002 | 8.528 | 0.000 | 0.558 | 7.000E-002 | 0.372 | res ceil fan | 0.000 | 27.544 |
| 5 | RES CEIL FAN BENCHMARK|LIVING SPACE|STORY 2 | RES CEIL FAN BENCHMARK|LIVING SPACE SCHEDULE | LIVING ZONE | 418.06 | 3.2 | 35.631 | 8.523E-002 | 11.031 | 0.000 | 0.558 | 7.000E-002 | 0.372 | res ceil fan | 0.000 | 35.631 |
| 6 | RES CEIL FAN NON BENCHMARK EQUIP | RES CEIL FAN MASTER | LIVING ZONE | 418.06 | 3.2 | 0.000 | 0.000 | 0.000 | 0.000 | 0.558 | 7.000E-002 | 0.372 | General | 0.000 | 0.000 |
| 7 | RES CW | RES CW SCHEDULE | LIVING ZONE | 418.06 | 3.2 | 7433.168 | 17.780 | 2301.291 | 0.000 | 0.480 | 0.200 | 0.320 | res cw | 0.000 | 309.174 |
| 8 | RES DW | RES DW SCHEDULE | LIVING ZONE | 418.06 | 3.2 | 10547.935 | 25.230 | 3265.614 | 0.150 | 0.360 | 0.250 | 0.240 | res dw | 0.000 | 1352.085 |
| 9 | RES HOT TUB HEATER ELECTRIC | RES HOT TUB HEATER ELECTRIC SCHEDULE | LIVING ZONE | 418.06 | 3.2 | 27.971 | 6.691E-002 | 8.660 | 0.000 | 0.000 | 1.000 | 0.000 | res hot tub heater electric | 0.000 | 27.971 |
| 10 | RES HOT TUB PUMP | RES HOT TUB HEATER ELECTRIC SCHEDULE | LIVING ZONE | 418.06 | 3.2 | 33.939 | 8.118E-002 | 10.508 | 0.000 | 0.000 | 1.000 | 0.000 | res hot tub pump | 0.000 | 33.939 |
| 11 | RES INFIL_1 BATH FAN | ALWAYS ON DISCRETE | LIVING ZONE | 418.06 | 3.2 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 | 0.000 | res mv_1 bath fan | 0.000 | 0.000 |
| 12 | RES INFIL_1 HOUSE FAN | ALWAYS ON DISCRETE | LIVING ZONE | 418.06 | 3.2 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 | 0.000 | res mv_1 house fan | 0.000 | 0.000 |
| 13 | RES INFIL_1 RANGE FAN | ALWAYS ON DISCRETE | LIVING ZONE | 418.06 | 3.2 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 | 0.000 | res mv_1 range fan | 0.000 | 0.000 |
| 14 | RES MISC PLUG LOADS|LIVING SPACE | RES MISC PLUG LOADS SCHEDULE | LIVING ZONE | 418.06 | 3.2 | 656.449 | 1.570 | 203.235 | 2.100E-002 | 0.558 | 4.900E-002 | 0.372 | res misc plug loads | 0.000 | 656.449 |
| 15 | RES MISC PLUG LOADS|LIVING SPACE|STORY 2 | RES MISC PLUG LOADS SCHEDULE | LIVING ZONE | 418.06 | 3.2 | 849.168 | 2.031 | 262.900 | 2.100E-002 | 0.558 | 4.900E-002 | 0.372 | res misc plug loads | 0.000 | 849.168 |
| 16 | RES POOL HEATER ELECTRIC | RES POOL HEATER ELECTRIC SCHEDULE | LIVING ZONE | 418.06 | 3.2 | 5.280 | 1.263E-002 | 1.635 | 0.000 | 0.000 | 1.000 | 0.000 | res pool heater electric | 0.000 | 5.280 |
| 17 | RES POOL PUMP | RES POOL HEATER ELECTRIC SCHEDULE | LIVING ZONE | 418.06 | 3.2 | 96.855 | 0.232 | 29.986 | 0.000 | 0.000 | 1.000 | 0.000 | res pool pump | 0.000 | 96.855 |
| 18 | RES RANGE ELECTRIC | RES RANGE ELECTRIC|FALSE SCHEDULE | LIVING ZONE | 418.06 | 3.2 | 314.948 | 0.753 | 97.507 | 0.300 | 0.240 | 0.300 | 0.160 | res range electric | 0.000 | 314.948 |
| 19 | RES REFRIG | RES REFRIG SCHEDULE | LIVING ZONE | 418.06 | 3.2 | 71.988 | 0.172 | 22.287 | 0.000 | 0.000 | 0.000 | 1.000 | res refrig | 0.000 | 71.988 |
| 20 | RES WELL PUMP | RES WELL PUMP SCHEDULE | LIVING ZONE | 418.06 | 3.2 | 19.626 | 4.695E-002 | 6.076 | 0.000 | 0.000 | 1.000 | 0.000 | res well pump | 0.000 | 19.626 |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Equipment Level {W} | Equipment/Floor Area {W/m2} | Equipment per person {W/person} | Fraction Latent | Fraction Radiant | Fraction Lost | Fraction Convected | End-Use SubCategory | Nominal Minimum Equipment Level {W} | Nominal Maximum Equipment Level {W} | |
| 1 | RES GAS FIREPLACE | RES GAS FIREPLACE SCHEDULE | LIVING ZONE | 418.06 | 3.2 | 21.739 | 5.200E-002 | 6.730 | 0.000 | 0.000 | 0.000 | 1.000 | res gas fireplace | 0.000 | 21.739 |
| 2 | RES GAS GRILL | RES GAS GRILL SCHEDULE | LIVING ZONE | 418.06 | 3.2 | 17.438 | 4.171E-002 | 5.399 | 0.000 | 0.000 | 0.000 | 1.000 | res gas grill | 0.000 | 17.438 |
| 3 | RES GAS LIGHTING | RES GAS LIGHTING SCHEDULE | LIVING ZONE | 418.06 | 3.2 | 2.582 | 6.175E-003 | 0.799 | 0.000 | 0.000 | 0.000 | 1.000 | res gas lighting | 0.000 | 2.582 |
| 4 | RES HOT TUB HEATER GAS | RES HOT TUB HEATER ELECTRIC SCHEDULE | LIVING ZONE | 418.06 | 3.2 | 14.812 | 3.543E-002 | 4.586 | 0.000 | 0.000 | 1.000 | 0.000 | res hot tub heater gas | 0.000 | 14.812 |
| 5 | RES POOL HEATER GAS | RES POOL HEATER ELECTRIC SCHEDULE | LIVING ZONE | 418.06 | 3.2 | 52.280 | 0.125 | 16.186 | 0.000 | 0.000 | 1.000 | 0.000 | res pool heater gas | 0.000 | 52.280 |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Equipment Level {W} | Equipment/Floor Area {W/m2} | Equipment per person {W/person} | Fraction Latent | Fraction Radiant | Fraction Lost | Fraction Convected | Nominal Minimum Equipment Level {W} | Nominal Maximum Equipment Level {W} | |
| 1 | RES BATH | RES BATH SCHEDULE | LIVING ZONE | 418.06 | 3.2 | 14516.325 | 34.723 | 4494.218 | 0.000 | 0.000 | 0.000 | 1.000 | 0.000 | 3473.756 |
| 2 | RES DS RES AC ASYS SUPDCNTOLVEQ | ALWAYS ON DISCRETE | LIVING ZONE | 418.06 | 3.2 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 | 0.000 | 0.000 |
| 3 | RES DS RES AC ASYS SUPLATLKTOLVEQ | ALWAYS ON DISCRETE | LIVING ZONE | 418.06 | 3.2 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 | 0.000 | 0.000 |
| 4 | RES DS RES AC ASYS SUPSLKTOLVEQ | ALWAYS ON DISCRETE | LIVING ZONE | 418.06 | 3.2 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 | 0.000 | 0.000 |
| 5 | RES DS RES FUR PROPANE ASYS SUPDCNTOLVEQ | ALWAYS ON DISCRETE | LIVING ZONE | 418.06 | 3.2 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 | 0.000 | 0.000 |
| 6 | RES DS RES FUR PROPANE ASYS SUPLATLKTOLVEQ | ALWAYS ON DISCRETE | LIVING ZONE | 418.06 | 3.2 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 | 0.000 | 0.000 |
| 7 | RES DS RES FUR PROPANE ASYS SUPSLKTOLVEQ | ALWAYS ON DISCRETE | LIVING ZONE | 418.06 | 3.2 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 | 0.000 | 0.000 |
| 8 | RES HOT WATER DISTRIBUTION | RES HOT WATER DISTRIBUTION SCHEDULE | LIVING ZONE | 418.06 | 3.2 | 80.785 | 0.193 | 25.011 | 0.000 | 0.000 | 0.000 | 1.000 | 0.000 | 80.785 |
| 9 | RES SHOWER | RES SHOWER SCHEDULE | LIVING ZONE | 418.06 | 3.2 | 16671.804 | 39.879 | 5161.549 | 0.487 | 0.000 | 0.000 | 0.513 | 0.000 | 10223.167 |
| 10 | RES SINK | RES SINK SCHEDULE | LIVING ZONE | 418.06 | 3.2 | 4161.720 | 9.955 | 1288.458 | 0.312 | 0.000 | 0.000 | 0.688 | 0.000 | 1066.207 |
| 11 | RES DS RES AC ASYS RETDCNTOPLEQ | ALWAYS ON DISCRETE | RES DS RES AC ASYS RET AIR ZONE | 1.00E-002 | 0.0 | 0.000 | 0.000 | N/A | 0.000 | 0.000 | 0.000 | 1.000 | 0.000 | 0.000 |
| 12 | RES DS RES AC ASYS RETLATLKEQ | ALWAYS ON DISCRETE | RES DS RES AC ASYS RET AIR ZONE | 1.00E-002 | 0.0 | 0.000 | 0.000 | N/A | 0.000 | 0.000 | 0.000 | 1.000 | 0.000 | 0.000 |
| 13 | RES DS RES AC ASYS RETSLKEQ | ALWAYS ON DISCRETE | RES DS RES AC ASYS RET AIR ZONE | 1.00E-002 | 0.0 | 0.000 | 0.000 | N/A | 0.000 | 0.000 | 0.000 | 1.000 | 0.000 | 0.000 |
| 14 | RES DS RES FUR PROPANE ASYS RETDCNTOPLEQ | ALWAYS ON DISCRETE | RES DS RES FUR PROPANE ASYS RET AIR ZONE | 1.00E-002 | 0.0 | 0.000 | 0.000 | N/A | 0.000 | 0.000 | 0.000 | 1.000 | 0.000 | 0.000 |
| 15 | RES DS RES FUR PROPANE ASYS RETLATLKEQ | ALWAYS ON DISCRETE | RES DS RES FUR PROPANE ASYS RET AIR ZONE | 1.00E-002 | 0.0 | 0.000 | 0.000 | N/A | 0.000 | 0.000 | 0.000 | 1.000 | 0.000 | 0.000 |
| 16 | RES DS RES FUR PROPANE ASYS RETSLKEQ | ALWAYS ON DISCRETE | RES DS RES FUR PROPANE ASYS RET AIR ZONE | 1.00E-002 | 0.0 | 0.000 | 0.000 | N/A | 0.000 | 0.000 | 0.000 | 1.000 | 0.000 | 0.000 |
| 17 | RES DS RES AC ASYS RETDCNTOAHEQUIP | ALWAYS ON DISCRETE | UNFINISHED BASEMENT ZONE | 182.28 | 0.0 | 0.000 | 0.000 | N/A | 0.000 | 0.000 | 0.000 | 1.000 | 0.000 | 0.000 |
| 18 | RES DS RES AC ASYS SUPDCNTOAHEQ | ALWAYS ON DISCRETE | UNFINISHED BASEMENT ZONE | 182.28 | 0.0 | 0.000 | 0.000 | N/A | 0.000 | 0.000 | 0.000 | 1.000 | 0.000 | 0.000 |
| 19 | RES DS RES AC ASYS SUPLATLKTOAHEQ | ALWAYS ON DISCRETE | UNFINISHED BASEMENT ZONE | 182.28 | 0.0 | 0.000 | 0.000 | N/A | 0.000 | 0.000 | 0.000 | 1.000 | 0.000 | 0.000 |
| 20 | RES DS RES AC ASYS SUPSLKTOAHEQ | ALWAYS ON DISCRETE | UNFINISHED BASEMENT ZONE | 182.28 | 0.0 | 0.000 | 0.000 | N/A | 0.000 | 0.000 | 0.000 | 1.000 | 0.000 | 0.000 |
| 21 | RES DS RES FUR PROPANE ASYS RETDCNTOAHEQUIP | ALWAYS ON DISCRETE | UNFINISHED BASEMENT ZONE | 182.28 | 0.0 | 0.000 | 0.000 | N/A | 0.000 | 0.000 | 0.000 | 1.000 | 0.000 | 0.000 |
| 22 | RES DS RES FUR PROPANE ASYS SUPDCNTOAHEQ | ALWAYS ON DISCRETE | UNFINISHED BASEMENT ZONE | 182.28 | 0.0 | 0.000 | 0.000 | N/A | 0.000 | 0.000 | 0.000 | 1.000 | 0.000 | 0.000 |
| 23 | RES DS RES FUR PROPANE ASYS SUPLATLKTOAHEQ | ALWAYS ON DISCRETE | UNFINISHED BASEMENT ZONE | 182.28 | 0.0 | 0.000 | 0.000 | N/A | 0.000 | 0.000 | 0.000 | 1.000 | 0.000 | 0.000 |
| 24 | RES DS RES FUR PROPANE ASYS SUPSLKTOAHEQ | ALWAYS ON DISCRETE | UNFINISHED BASEMENT ZONE | 182.28 | 0.0 | 0.000 | 0.000 | N/A | 0.000 | 0.000 | 0.000 | 1.000 | 0.000 | 0.000 |
| Calculation Method | Value {days} | Allowable Number Figures in Shadow Overlap {} | Polygon Clipping Algorithm | Sky Diffuse Modeling Algorithm | External Shading Calculation Method | Output External Shading Calculation Results | Disable Self-Shading Within Shading Zone Groups | Disable Self-Shading From Shading Zone Groups to Other Zones | |
| 1 | AverageOverDaysInFrequency | 20 | 15000 | SutherlandHodgman | SimpleSkyDiffuseModeling | InternalCalculation | No | No | No |
| Type | Name | Volume {m3} | Maximum Capacity {W} | Standard Rated Recovery Efficiency | Standard Rated Energy Factor | |
| 1 | WaterHeater:Mixed | RES WH | 0.2248 | 1318.8 | 0.196 | 1.1217 |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Design Volume Flow Rate {m3/s} | Volume Flow Rate/Floor Area {m3/s-m2} | Volume Flow Rate/Exterior Surface Area {m3/s-m2} | ACH - Air Changes per Hour | Equation A - Constant Term Coefficient {} | Equation B - Temperature Term Coefficient {1/C} | Equation C - Velocity Term Coefficient {s/m} | Equation D - Velocity Squared Term Coefficient {s2/m2} | |
| 1 | RES INFIL_1 FLOW | ALWAYS ON DISCRETE | LIVING ZONE | 418.06 | 3.2 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 | 0.000 | 0.000 | 0.000 |
| 2 | RES NV_1 FLOW | ALWAYS ON DISCRETE | LIVING ZONE | 418.06 | 3.2 | 0.000 | 0.000 | 0.000 | 0.000 | 1.000 | 0.000 | 0.000 | 0.000 |
| 3 | RES INFIL|UNFINISHED BASEMENT SPACE | ALWAYS ON DISCRETE | UNFINISHED BASEMENT ZONE | 182.28 | 0.0 | 1.235E-002 | 6.773E-005 | N/A | 0.100 | 1.000 | 0.000 | 0.000 | 0.000 |
| 4 | RES INFIL|GARAGE SPACE | ALWAYS ON DISCRETE | GARAGE ZONE | 53.51 | 0.0 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| 5 | RES INFIL|GARAGE ATTIC SPACE | ALWAYS ON DISCRETE | UNFINISHED ATTIC ZONE | 235.79 | 0.0 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| 6 | RES INFIL|UNFINISHED ATTIC SPACE | ALWAYS ON DISCRETE | UNFINISHED ATTIC ZONE | 235.79 | 0.0 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Design Volume Flow Rate {m3/s} | Volume Flow Rate/Floor Area {m3/s-m2} | Volume Flow Rate/person Area {m3/s-person} | ACH - Air Changes per Hour | From/Source Zone | Delta Temperature {C} | |
| 1 | RES DS RES AC ASYS AHTOLIVMIX | ALWAYS ON CONTINUOUS | LIVING ZONE | 418.06 | 3.2 | 0.000 | 0.000 | 0.000 | 0.000 | UNFINISHED BASEMENT ZONE | 0.00 |
| 2 | RES DS RES FUR PROPANE ASYS AHTOLIVMIX | ALWAYS ON CONTINUOUS | LIVING ZONE | 418.06 | 3.2 | 0.000 | 0.000 | 0.000 | 0.000 | UNFINISHED BASEMENT ZONE | 0.00 |
| 3 | RES DS RES AC ASYS LIVTOAHMIX | ALWAYS ON CONTINUOUS | UNFINISHED BASEMENT ZONE | 182.28 | 0.0 | 0.000 | 0.000 | N/A | 0.000 | LIVING ZONE | 0.00 |
| 4 | RES DS RES FUR PROPANE ASYS LIVTOAHMIX | ALWAYS ON CONTINUOUS | UNFINISHED BASEMENT ZONE | 182.28 | 0.0 | 0.000 | 0.000 | N/A | 0.000 | LIVING ZONE | 0.00 |
| Simple | |
| 1 | Simple |
| Zone Name | Mixing/Mundt/UCSDDV/UCSDCV/UCSDUFI/UCSDUFE/User Defined | |
| 1 | GARAGE ZONE | Mixing/Well-Stirred |
| 2 | LIVING ZONE | Mixing/Well-Stirred |
| 3 | RES DS RES AC ASYS RET AIR ZONE | Mixing/Well-Stirred |
| 4 | RES DS RES FUR PROPANE ASYS RET AIR ZONE | Mixing/Well-Stirred |
| 5 | UNFINISHED ATTIC ZONE | Mixing/Well-Stirred |
| 6 | UNFINISHED BASEMENT ZONE | Mixing/Well-Stirred |
| No Multizone or Distribution/Multizone with Distribution/Multizone without Distribution/Multizone with Distribution only during Fan Operation | |
| 1 | NoMultizoneOrDistribution |
| Value | |
| 1 | 6 |
| Sizing Factor ID | Value | |
| 1 | Global | 1.2500 |
| 2 | Zone LIVING ZONE | 1.2500 |
| Sizing Factor ID | Value | |
| 1 | Global | 1.1500 |
| 2 | Zone LIVING ZONE | 1.1500 |
| Zone Name | Load Type | Calc Des Load {W} | User Des Load {W} | Calc Des Air Flow Rate {m3/s} | User Des Air Flow Rate {m3/s} | Design Day Name | Date/Time of Peak | Temperature at Peak {C} | Humidity Ratio at Peak {kgWater/kgDryAir} | Floor Area {m2} | # Occupants | Calc Outdoor Air Flow Rate {m3/s} | Calc DOAS Heat Addition Rate {W} | |
| 1 | LIVING ZONE | Cooling | 4005.18454 | 4605.96223 | 0.32966 | 0.37911 | ANN CLG 1% CONDNS DB=>MWB | 7/21 16:10:00 | 31.91067 | 1.46440E-002 | 418.06368 | 3.23000 | 0.00000 | 0.00000 |
| 2 | LIVING ZONE | Heating | 12431.12583 | 15538.90729 | 0.53591 | 0.66988 | ANN HTG 99% CONDNS DB | 1/21 24:00:00 | -8.40000 | 1.84320E-003 | 418.06368 | 3.23000 | 0.00000 | 0.00000 |
| System Name | Load Type | Peak Load Kind | User Design Capacity | Calc Des Air Flow Rate [m3/s] | User Des Air Flow Rate [m3/s] | Design Day Name | Date/Time of Peak | |
| 1 | RES AC ASYS | Cooling | Sensible | 8765.68 | 0.37911 | 0.37911 | ANN CLG 1% CONDNS DB=>MWB | 7/21 00:00:00 |
| 2 | RES AC ASYS | Heating | Sensible | 20342.84 | 0.66988 | 0.66988 | ANN HTG 99% CONDNS DB | 1/21 24:00:00 |
| 3 | RES FUR PROPANE ASYS | Cooling | Sensible | 8765.68 | 0.37911 | 0.37911 | ANN CLG 1% CONDNS DB=>MWB | 7/21 00:00:00 |
| 4 | RES FUR PROPANE ASYS | Heating | Sensible | 20342.84 | 0.66988 | 0.66988 | ANN HTG 99% CONDNS DB | 1/21 24:00:00 |
| Component Type | Component Name | Input Field Description | Value | |
| 1 | AirTerminal:SingleDuct:ConstantVolume:NoReheat | RES AC LIVING ZONE DIRECT AIR | Design Size Maximum Air Flow Rate [m3/s] | 0.66988 |
| 2 | AirTerminal:SingleDuct:ConstantVolume:NoReheat | RES AC LIVING ZONE DIRECT AIR | User-Specified Maximum Air Flow Rate [m3/s] | 0.68590 |
| 3 | AirTerminal:SingleDuct:ConstantVolume:NoReheat | RES FUR PROPANE LIVING ZONE DIRECT AIR | Design Size Maximum Air Flow Rate [m3/s] | 0.66988 |
| 4 | AirTerminal:SingleDuct:ConstantVolume:NoReheat | RES FUR PROPANE LIVING ZONE DIRECT AIR | User-Specified Maximum Air Flow Rate [m3/s] | 0.68590 |
| 5 | AirLoopHVAC | RES AC ASYS | Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | 0.00000 |
| 6 | AirLoopHVAC | RES AC ASYS | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | 0.00000 |
| 7 | AirLoopHVAC | RES AC ASYS | Sum of Air Terminal Maximum Flow Rates [m3/s] | 0.68590 |
| 8 | AirLoopHVAC | RES AC ASYS | Adjusted Heating Design Air Flow Rate [m3/s] | 0.66988 |
| 9 | AirLoopHVAC | RES AC ASYS | Adjusted Cooling Design Air Flow Rate [m3/s] | 0.37911 |
| 10 | AirLoopHVAC | RES AC ASYS | Adjusted Main Design Air Flow Rate [m3/s] | 0.68590 |
| 11 | AirLoopHVAC | RES AC ASYS | User Heating Air Flow Ratio [] | 0.30000 |
| 12 | AirLoopHVAC | RES AC ASYS | Calculated Heating Air Flow Ratio [] | 0.97665 |
| 13 | AirLoopHVAC | RES FUR PROPANE ASYS | Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | 0.00000 |
| 14 | AirLoopHVAC | RES FUR PROPANE ASYS | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | 0.00000 |
| 15 | AirLoopHVAC | RES FUR PROPANE ASYS | Sum of Air Terminal Maximum Flow Rates [m3/s] | 0.68590 |
| 16 | AirLoopHVAC | RES FUR PROPANE ASYS | Adjusted Heating Design Air Flow Rate [m3/s] | 0.66988 |
| 17 | AirLoopHVAC | RES FUR PROPANE ASYS | Adjusted Cooling Design Air Flow Rate [m3/s] | 0.37911 |
| 18 | AirLoopHVAC | RES FUR PROPANE ASYS | Adjusted Main Design Air Flow Rate [m3/s] | 0.68590 |
| 19 | AirLoopHVAC | RES FUR PROPANE ASYS | User Heating Air Flow Ratio [] | 0.30000 |
| 20 | AirLoopHVAC | RES FUR PROPANE ASYS | Calculated Heating Air Flow Ratio [] | 0.97665 |
| 21 | AirLoopHVAC:UnitarySystem | RES AC UNITARY SYSTEM | User-Specified Supply Air Flow Rate [m3/s] | 0.68590 |
| 22 | AirLoopHVAC:UnitarySystem | RES AC UNITARY SYSTEM | User-Specified Cooling Supply Air Flow Rate [m3/s] | 0.68590 |
| 23 | AirLoopHVAC:UnitarySystem | RES AC UNITARY SYSTEM | User-Specified No Load Supply Air Flow Rate [m3/s] | 0.00000 |
| 24 | AirLoopHVAC:UnitarySystem | RES AC UNITARY SYSTEM | Design Size Nominal Cooling Capacity [W] | 28046.43503 |
| 25 | AirLoopHVAC:UnitarySystem | RES AC UNITARY SYSTEM | User-Specified Nominal Cooling Capacity [W] | 10242.84575 |
| 26 | Fan:OnOff | RES AC CLG SUPPLY FAN | User-Specified Maximum Flow Rate [m3/s] | 0.68590 |
| 27 | Coil:Cooling:DX:SingleSpeed | RES AC COOLING COIL | Design Size Rated Air Flow Rate [m3/s] | 0.68590 |
| 28 | Coil:Cooling:DX:SingleSpeed | RES AC COOLING COIL | User-Specified Rated Air Flow Rate [m3/s] | 0.53071 |
| 29 | Coil:Cooling:DX:SingleSpeed | RES AC COOLING COIL | Design Size Gross Rated Total Cooling Capacity [W] | 17925.71707 |
| 30 | Coil:Cooling:DX:SingleSpeed | RES AC COOLING COIL | User-Specified Gross Rated Total Cooling Capacity [W] | 10242.84575 |
| 31 | Coil:Cooling:DX:SingleSpeed | RES AC COOLING COIL | User-Specified Gross Rated Sensible Heat Ratio | 0.74040 |
| 32 | AirLoopHVAC:UnitarySystem | RES FUR PROPANE UNITARY SYSTEM | Design Size Supply Air Flow Rate [m3/s] | 0.68590 |
| 33 | AirLoopHVAC:UnitarySystem | RES FUR PROPANE UNITARY SYSTEM | User-Specified Supply Air Flow Rate [m3/s] | 0.50690 |
| 34 | AirLoopHVAC:UnitarySystem | RES FUR PROPANE UNITARY SYSTEM | User-Specified Heating Supply Air Flow Rate [m3/s] | 0.50690 |
| 35 | AirLoopHVAC:UnitarySystem | RES FUR PROPANE UNITARY SYSTEM | User-Specified No Load Supply Air Flow Rate [m3/s] | 0.00000 |
| 36 | AirLoopHVAC:UnitarySystem | RES FUR PROPANE UNITARY SYSTEM | Design Size Nominal Heating Capacity [W] | 15393.30110 |
| 37 | AirLoopHVAC:UnitarySystem | RES FUR PROPANE UNITARY SYSTEM | User-Specified Nominal Heating Capacity [W] | 17309.11027 |
| 38 | AirLoopHVAC:UnitarySystem | RES FUR PROPANE UNITARY SYSTEM | Design Size Maximum Supply Air Temperature [C] | 16.70000 |
| 39 | AirLoopHVAC:UnitarySystem | RES FUR PROPANE UNITARY SYSTEM | User-Specified Maximum Supply Air Temperature [C] | 48.88889 |
| 40 | Fan:OnOff | RES FUR PROPANE HTG SUPPLY FAN | User-Specified Maximum Flow Rate [m3/s] | 0.68590 |
| 41 | Coil:Heating:Fuel | RES FUR PROPANE HEATING COIL | Design Size Nominal Capacity [W] | 15393.30110 |
| 42 | Coil:Heating:Fuel | RES FUR PROPANE HEATING COIL | User-Specified Nominal Capacity [W] | 17309.11027 |
| 43 | WaterHeater:Mixed | RES WH | Use Side Design Flow Rate [m3/s] | 2.18108E-003 |
| Component Type | Component Name | Standard Rating (Net) Cooling Capacity {W} | Standard Rated Net COP {W/W} | EER {Btu/W-h} | SEER {Btu/W-h} | IEER {Btu/W-h} | |
| 1 | Coil:Cooling:DX:SingleSpeed | RES AC COOLING COIL | 9768.7 | 2.60 | 8.87 | 9.84 | 9.96 |
| Environment Name | Environment Type | Start Date | End Date | Start DayOfWeek | Duration {#days} | Source:Start DayOfWeek | Use Daylight Saving | Use Holidays | Apply Weekend Holiday Rule | Use Rain Values | Use Snow Values | |
| 1 | ANN CLG 1% CONDNS DB=>MWB | SizingPeriod:DesignDay | 07/21 | 07/21 | SummerDesignDay | 1 | N/A | N/A | N/A | N/A | N/A | N/A |
| 2 | ANN HTG 99% CONDNS DB | SizingPeriod:DesignDay | 01/21 | 01/21 | WinterDesignDay | 1 | N/A | N/A | N/A | N/A | N/A | N/A |
| 3 | RUN PERIOD 1 | WeatherFileRunPeriod | 01/01/2009 | 12/31/2009 | Thursday | 365 | Use RunPeriod Specified Day | No | No | No | Yes | Yes |
| Daylight Saving Indicator | Source | Start Date | End Date | |
| 1 | No | SizingPeriod:DesignDay | ||
| 2 | No | SizingPeriod:DesignDay | ||
| 3 | Yes | InputFile | 04/07 | 10/26 |
| NumberofWarmupDays | |
| 1 | 6 |
| 2 | 6 |
| 3 | 6 |
| Max Dry-Bulb Temp {C} | Temp Range {dC} | Temp Range Ind Type | Hum Ind Value at Max Temp | Hum Ind Type | Pressure {Pa} | Wind Direction {deg CW from N} | Wind Speed {m/s} | Clearness | Rain | Snow | |
| 1 | 32.60 | 9.40 | DefaultMultipliers | 101301 | 0 | 5.0 | 0.00 | No | No | ||
| 2 | -8.40 | 0.00 | DefaultMultipliers | 101301 | 0 | 11.6 | 0.00 | No | No |
| DayOfYear | ASHRAE A Coeff | ASHRAE B Coeff | ASHRAE C Coeff | Solar Constant-Annual Variation | Eq of Time {minutes} | Solar Declination Angle {deg} | Solar Model | |
| 1 | 202 | 1084.4 | 0.2082 | 0.1365 | 1.0 | -6.23 | 20.6 | ASHRAEClearSky |
| 2 | 21 | 1229.0 | 0.1415 | 5.7310E-002 | 1.0 | -11.15 | -20.1 | ASHRAEClearSky |
| Style | Unit Conversion | |
| 1 | HTML | None |
| Zone Name | Environment Type/Name | Average Warmup Temperature Difference {deltaC} | Std Dev Warmup Temperature Difference {deltaC} | Max Temperature Pass/Fail Convergence | Min Temperature Pass/Fail Convergence | Average Warmup Load Difference {W} | Std Dev Warmup Load Difference {W} | Heating Load Pass/Fail Convergence | Cooling Load Pass/Fail Convergence | |
| 1 | GARAGE ZONE | SizingPeriod: ANN CLG 1% CONDNS DB=>MWB | 2.1692582158E-002 | 1.3134193479E-002 | Pass | Pass | 0.0000000000 | 0.0000000000 | Pass | Pass |
| 2 | LIVING ZONE | SizingPeriod: ANN CLG 1% CONDNS DB=>MWB | 9.6162247111E-006 | 6.3705123697E-006 | Pass | Pass | 1.1435293045E-002 | 5.6677242008E-003 | Pass | Pass |
| 3 | RES DS RES AC ASYS RET AIR ZONE | SizingPeriod: ANN CLG 1% CONDNS DB=>MWB | 1.8336827739E-003 | 1.6806483527E-003 | Pass | Pass | 1.0953717388E-002 | 6.1835868838E-003 | Pass | Pass |
| 4 | RES DS RES FUR PROPANE ASYS RET AIR ZONE | SizingPeriod: ANN CLG 1% CONDNS DB=>MWB | 0.0000000000 | 0.0000000000 | Pass | Pass | 0.0000000000 | 0.0000000000 | Pass | Pass |
| 5 | UNFINISHED ATTIC ZONE | SizingPeriod: ANN CLG 1% CONDNS DB=>MWB | 0.1156308028 | 6.3274778204E-002 | Pass | Pass | 0.0000000000 | 0.0000000000 | Pass | Pass |
| 6 | UNFINISHED BASEMENT ZONE | SizingPeriod: ANN CLG 1% CONDNS DB=>MWB | 1.2815194292E-002 | 1.3447556053E-002 | Pass | Pass | 0.0000000000 | 0.0000000000 | Pass | Pass |
| 7 | GARAGE ZONE | SizingPeriod: ANN HTG 99% CONDNS DB | 4.4170401232E-002 | 4.5108551520E-002 | Pass | Pass | 0.0000000000 | 0.0000000000 | Pass | Pass |
| 8 | LIVING ZONE | SizingPeriod: ANN HTG 99% CONDNS DB | 9.2025152930E-014 | 7.7595058044E-014 | Pass | Pass | 8.7590811348E-005 | 2.7358708051E-004 | Pass | Pass |
| 9 | RES DS RES AC ASYS RET AIR ZONE | SizingPeriod: ANN HTG 99% CONDNS DB | 4.9343245539E-017 | 4.1577357721E-016 | Pass | Pass | 0.0000000000 | 0.0000000000 | Pass | Pass |
| 10 | RES DS RES FUR PROPANE ASYS RET AIR ZONE | SizingPeriod: ANN HTG 99% CONDNS DB | 4.0408684135E-004 | 7.3875462645E-004 | Pass | Pass | 9.4086245595E-004 | 1.6671734093E-003 | Pass | Pass |
| 11 | UNFINISHED ATTIC ZONE | SizingPeriod: ANN HTG 99% CONDNS DB | 2.8693096396E-006 | 1.9027356279E-006 | Pass | Pass | 0.0000000000 | 0.0000000000 | Pass | Pass |
| 12 | UNFINISHED BASEMENT ZONE | SizingPeriod: ANN HTG 99% CONDNS DB | 2.3738334642E-003 | 5.3114443824E-003 | Pass | Pass | 0.0000000000 | 0.0000000000 | Pass | Pass |
| 13 | GARAGE ZONE | RunPeriod: RUN PERIOD 1 | 3.1744894724E-002 | 2.1455307912E-002 | Pass | Pass | 0.0000000000 | 0.0000000000 | Pass | Pass |
| 14 | LIVING ZONE | RunPeriod: RUN PERIOD 1 | 4.9301558843E-007 | 3.0037965019E-006 | Pass | Pass | 7.3846742484E-002 | 0.4804617338 | Pass | Pass |
| 15 | RES DS RES AC ASYS RET AIR ZONE | RunPeriod: RUN PERIOD 1 | 1.4802973662E-015 | 1.8488908177E-015 | Pass | Pass | 0.0000000000 | 0.0000000000 | Pass | Pass |
| 16 | RES DS RES FUR PROPANE ASYS RET AIR ZONE | RunPeriod: RUN PERIOD 1 | 3.7724206638E-003 | 4.5869110379E-003 | Pass | Pass | 0.3382240571 | 1.7117151522 | Pass | Pass |
| 17 | UNFINISHED ATTIC ZONE | RunPeriod: RUN PERIOD 1 | 0.1276861481 | 9.5062471009E-002 | Pass | Pass | 0.0000000000 | 0.0000000000 | Pass | Pass |
| 18 | UNFINISHED BASEMENT ZONE | RunPeriod: RUN PERIOD 1 | 2.9960989750E-002 | 4.7808602675E-002 | Pass | Pass | 0.0000000000 | 0.0000000000 | Pass | Pass |
Report: Annual Heat Emissions Summary
For: Entire Facility
Timestamp: 2019-07-16 16:11:39
Heat Emission by Components| Envelope Convection | Zone Exfiltration | Zone Exhaust Air | HVAC Relief Air | HVAC Reject Heat | Total | |
| Heat Emissions [GJ] | 463.23 | 75.90 | 0.00 | 0.00 | 62.20 | 601.34 |
Report: Climatic Data Summary
For: Entire Facility
Timestamp: 2019-07-16 16:11:39
SizingPeriod:DesignDay| Maximum Dry Bulb [C] | Daily Temperature Range [deltaC] | Humidity Value | Humidity Type | Wind Speed [m/s] | Wind Direction | |
| ANN CLG 1% CONDNS DB=>MWB | 32.60 | 9.40 | 23.60 | Wetbulb [C] | 5.00 | 0.00 |
| ANN HTG 99% CONDNS DB | -8.40 | 0.00 | -8.40 | Wetbulb [C] | 11.60 | 0.00 |
| Value | |
| None |
Report: Envelope Summary
For: Entire Facility
Timestamp: 2019-07-16 16:11:39
Opaque Exterior| Construction | Reflectance | U-Factor with Film [W/m2-K] | U-Factor no Film [W/m2-K] | Gross Area [m2] | Net Area [m2] | Azimuth [deg] | Tilt [deg] | Cardinal Direction | |
| SURFACE 36 | WALLEXTUNINSUNFIN | 0.70 | 1.689 | 2.261 | 8.92 | 8.92 | 180.00 | 90.00 | S |
| SURFACE 4 | WALLEXTUNINSUNFIN | 0.70 | 1.689 | 2.261 | 17.84 | 17.84 | 0.00 | 90.00 | N |
| SURFACE 5 | WALLEXTUNINSUNFIN | 0.70 | 1.689 | 2.261 | 17.84 | 17.84 | 90.00 | 90.00 | E |
| SURFACE 1 | FLOORFNDGRNDUNFINSLAB | 0.30 | 3.340 | 17.747 | 53.51 | 53.51 | 90.00 | 180.00 | |
| SURFACE 10 | WALLEXTINSFIN | 0.70 | 0.356 | 0.376 | 17.36 | 14.75 | 0.00 | 90.00 | N |
| SURFACE 13 | WALLEXTINSFIN | 0.70 | 0.356 | 0.376 | 26.90 | 22.85 | 90.00 | 90.00 | E |
| SURFACE 16 | WALLEXTINSFIN | 0.70 | 0.356 | 0.376 | 26.28 | 22.34 | 180.00 | 90.00 | S |
| SURFACE 17 | WALLEXTINSFIN | 0.70 | 0.356 | 0.376 | 47.30 | 40.20 | 270.00 | 90.00 | W |
| SURFACE 18 | WALLEXTINSFIN | 0.70 | 0.356 | 0.376 | 35.20 | 29.92 | 0.00 | 90.00 | N |
| SURFACE 19 | WALLEXTINSFIN | 0.70 | 0.356 | 0.376 | 17.84 | 15.15 | 90.00 | 90.00 | E |
| SURFACE 20 | WALLEXTINSFIN | 0.70 | 0.356 | 0.376 | 8.92 | 7.58 | 180.00 | 90.00 | S |
| SURFACE 21 | WALLEXTINSFIN | 0.70 | 0.356 | 0.376 | 29.46 | 25.02 | 90.00 | 90.00 | E |
| SURFACE 44 | WALLEXTINSFIN | 0.70 | 0.356 | 0.376 | 2.25 | 0.39 | 90.00 | 90.00 | E |
| SURFACE 45 | WALLEXTINSFIN | 0.70 | 0.356 | 0.376 | 0.31 | 0.31 | 90.00 | 90.00 | E |
| SURFACE 8 | WALLEXTINSFIN | 0.70 | 0.356 | 0.376 | 26.28 | 22.34 | 180.00 | 90.00 | S |
| SURFACE 9 | WALLEXTINSFIN | 0.70 | 0.356 | 0.376 | 47.30 | 40.20 | 270.00 | 90.00 | W |
| SURFACE 26 | WALLEXTUNINSUNFIN | 0.70 | 1.689 | 2.261 | 14.52 | 14.52 | 180.00 | 90.00 | S |
| SURFACE 27 | WALLEXTUNINSUNFIN | 0.70 | 1.689 | 2.261 | 14.52 | 14.52 | 0.00 | 90.00 | N |
| SURFACE 42 | WALLEXTUNINSUNFIN | 0.70 | 1.689 | 2.261 | 6.69 | 6.69 | 90.00 | 90.00 | E |
| SURFACE 25 | ROOFUNFININSEXT | 0.15 | 2.605 | 4.057 | 116.85 | 116.85 | 270.00 | 26.57 | |
| SURFACE 39 | ROOFUNFININSEXT | 0.15 | 2.605 | 4.057 | 22.44 | 22.44 | 180.00 | 26.57 | |
| SURFACE 40 | ROOFUNFININSEXT | 0.15 | 2.605 | 4.057 | 22.44 | 22.44 | 0.00 | 26.57 | |
| SURFACE 43 | ROOFUNFININSEXT | 0.15 | 2.605 | 4.057 | 101.90 | 101.90 | 90.00 | 26.57 | |
| SURFACE 29 | WALLFNDGRNDUNFINB | 0.30 | 2.547 | 5.210 | 26.28 | 26.28 | 180.00 | 90.00 | S |
| SURFACE 30 | WALLFNDGRNDUNFINB | 0.30 | 2.547 | 5.210 | 47.30 | 47.30 | 270.00 | 90.00 | W |
| SURFACE 31 | WALLFNDGRNDUNFINB | 0.30 | 2.547 | 5.210 | 17.36 | 17.36 | 0.00 | 90.00 | N |
| SURFACE 34 | WALLFNDGRNDUNFINB | 0.30 | 2.547 | 5.210 | 29.46 | 29.46 | 90.00 | 90.00 | E |
| SURFACE 28 | FLOORFNDGRNDUNFINB | 0.30 | 3.340 | 17.747 | 182.28 | 182.28 | 90.00 | 180.00 |
| Construction | Glass Area [m2] | Frame Area [m2] | Divider Area [m2] | Area of One Opening [m2] | Area of Multiplied Openings [m2] | Glass U-Factor [W/m2-K] | Glass SHGC | Glass Visible Transmittance | Frame Conductance [W/m2-K] | Divider Conductance [W/m2-K] | Shade Control | Parent Surface | Azimuth [deg] | Tilt [deg] | Cardinal Direction | |
| SURFACE 10 - WINDOW 1 | WINDOWCONSTRUCTION | 0.87 | 0.00 | 0.00 | 0.87 | 0.87 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 10 | 0.00 | 90.00 | N | ||
| SURFACE 10 - WINDOW 2 | WINDOWCONSTRUCTION | 0.87 | 0.00 | 0.00 | 0.87 | 0.87 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 10 | 0.00 | 90.00 | N | ||
| SURFACE 10 - WINDOW 3 | WINDOWCONSTRUCTION | 0.87 | 0.00 | 0.00 | 0.87 | 0.87 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 10 | 0.00 | 90.00 | N | ||
| SURFACE 13 - WINDOW 1 | WINDOWCONSTRUCTION | 1.01 | 0.00 | 0.00 | 1.01 | 1.01 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 13 | 90.00 | 90.00 | E | ||
| SURFACE 13 - WINDOW 2 | WINDOWCONSTRUCTION | 1.01 | 0.00 | 0.00 | 1.01 | 1.01 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 13 | 90.00 | 90.00 | E | ||
| SURFACE 13 - WINDOW 3 | WINDOWCONSTRUCTION | 1.01 | 0.00 | 0.00 | 1.01 | 1.01 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 13 | 90.00 | 90.00 | E | ||
| SURFACE 13 - WINDOW 4 | WINDOWCONSTRUCTION | 1.01 | 0.00 | 0.00 | 1.01 | 1.01 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 13 | 90.00 | 90.00 | E | ||
| SURFACE 16 - WINDOW 1 | WINDOWCONSTRUCTION | 0.99 | 0.00 | 0.00 | 0.99 | 0.99 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 16 | 180.00 | 90.00 | S | ||
| SURFACE 16 - WINDOW 2 | WINDOWCONSTRUCTION | 0.99 | 0.00 | 0.00 | 0.99 | 0.99 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 16 | 180.00 | 90.00 | S | ||
| SURFACE 16 - WINDOW 3 | WINDOWCONSTRUCTION | 0.99 | 0.00 | 0.00 | 0.99 | 0.99 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 16 | 180.00 | 90.00 | S | ||
| SURFACE 16 - WINDOW 4 | WINDOWCONSTRUCTION | 0.99 | 0.00 | 0.00 | 0.99 | 0.99 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 16 | 180.00 | 90.00 | S | ||
| SURFACE 17 - WINDOW 1 | WINDOWCONSTRUCTION | 1.01 | 0.00 | 0.00 | 1.01 | 1.01 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 17 | 270.00 | 90.00 | W | ||
| SURFACE 17 - WINDOW 2 | WINDOWCONSTRUCTION | 1.01 | 0.00 | 0.00 | 1.01 | 1.01 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 17 | 270.00 | 90.00 | W | ||
| SURFACE 17 - WINDOW 3 | WINDOWCONSTRUCTION | 1.01 | 0.00 | 0.00 | 1.01 | 1.01 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 17 | 270.00 | 90.00 | W | ||
| SURFACE 17 - WINDOW 4 | WINDOWCONSTRUCTION | 1.01 | 0.00 | 0.00 | 1.01 | 1.01 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 17 | 270.00 | 90.00 | W | ||
| SURFACE 17 - WINDOW 5 | WINDOWCONSTRUCTION | 1.01 | 0.00 | 0.00 | 1.01 | 1.01 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 17 | 270.00 | 90.00 | W | ||
| SURFACE 17 - WINDOW 6 | WINDOWCONSTRUCTION | 1.01 | 0.00 | 0.00 | 1.01 | 1.01 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 17 | 270.00 | 90.00 | W | ||
| SURFACE 17 - WINDOW 7 | WINDOWCONSTRUCTION | 1.01 | 0.00 | 0.00 | 1.01 | 1.01 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 17 | 270.00 | 90.00 | W | ||
| SURFACE 18 - WINDOW 1 | WINDOWCONSTRUCTION | 1.06 | 0.00 | 0.00 | 1.06 | 1.06 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 18 | 0.00 | 90.00 | N | ||
| SURFACE 18 - WINDOW 2 | WINDOWCONSTRUCTION | 1.06 | 0.00 | 0.00 | 1.06 | 1.06 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 18 | 0.00 | 90.00 | N | ||
| SURFACE 18 - WINDOW 3 | WINDOWCONSTRUCTION | 1.06 | 0.00 | 0.00 | 1.06 | 1.06 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 18 | 0.00 | 90.00 | N | ||
| SURFACE 18 - WINDOW 4 | WINDOWCONSTRUCTION | 1.06 | 0.00 | 0.00 | 1.06 | 1.06 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 18 | 0.00 | 90.00 | N | ||
| SURFACE 18 - WINDOW 5 | WINDOWCONSTRUCTION | 1.06 | 0.00 | 0.00 | 1.06 | 1.06 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 18 | 0.00 | 90.00 | N | ||
| SURFACE 19 - WINDOW 1 | WINDOWCONSTRUCTION | 0.90 | 0.00 | 0.00 | 0.90 | 0.90 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 19 | 90.00 | 90.00 | E | ||
| SURFACE 19 - WINDOW 2 | WINDOWCONSTRUCTION | 0.90 | 0.00 | 0.00 | 0.90 | 0.90 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 19 | 90.00 | 90.00 | E | ||
| SURFACE 19 - WINDOW 3 | WINDOWCONSTRUCTION | 0.90 | 0.00 | 0.00 | 0.90 | 0.90 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 19 | 90.00 | 90.00 | E | ||
| SURFACE 20 - WINDOW 1 | WINDOWCONSTRUCTION | 0.67 | 0.00 | 0.00 | 0.67 | 0.67 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 20 | 180.00 | 90.00 | S | ||
| SURFACE 20 - WINDOW 2 | WINDOWCONSTRUCTION | 0.67 | 0.00 | 0.00 | 0.67 | 0.67 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 20 | 180.00 | 90.00 | S | ||
| SURFACE 21 - WINDOW 1 | WINDOWCONSTRUCTION | 1.11 | 0.00 | 0.00 | 1.11 | 1.11 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 21 | 90.00 | 90.00 | E | ||
| SURFACE 21 - WINDOW 2 | WINDOWCONSTRUCTION | 1.11 | 0.00 | 0.00 | 1.11 | 1.11 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 21 | 90.00 | 90.00 | E | ||
| SURFACE 21 - WINDOW 3 | WINDOWCONSTRUCTION | 1.11 | 0.00 | 0.00 | 1.11 | 1.11 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 21 | 90.00 | 90.00 | E | ||
| SURFACE 21 - WINDOW 4 | WINDOWCONSTRUCTION | 1.11 | 0.00 | 0.00 | 1.11 | 1.11 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 21 | 90.00 | 90.00 | E | ||
| SURFACE 8 - WINDOW 1 | WINDOWCONSTRUCTION | 0.99 | 0.00 | 0.00 | 0.99 | 0.99 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 8 | 180.00 | 90.00 | S | ||
| SURFACE 8 - WINDOW 2 | WINDOWCONSTRUCTION | 0.99 | 0.00 | 0.00 | 0.99 | 0.99 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 8 | 180.00 | 90.00 | S | ||
| SURFACE 8 - WINDOW 3 | WINDOWCONSTRUCTION | 0.99 | 0.00 | 0.00 | 0.99 | 0.99 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 8 | 180.00 | 90.00 | S | ||
| SURFACE 8 - WINDOW 4 | WINDOWCONSTRUCTION | 0.99 | 0.00 | 0.00 | 0.99 | 0.99 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 8 | 180.00 | 90.00 | S | ||
| SURFACE 9 - WINDOW 1 | WINDOWCONSTRUCTION | 1.01 | 0.00 | 0.00 | 1.01 | 1.01 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 9 | 270.00 | 90.00 | W | ||
| SURFACE 9 - WINDOW 2 | WINDOWCONSTRUCTION | 1.01 | 0.00 | 0.00 | 1.01 | 1.01 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 9 | 270.00 | 90.00 | W | ||
| SURFACE 9 - WINDOW 3 | WINDOWCONSTRUCTION | 1.01 | 0.00 | 0.00 | 1.01 | 1.01 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 9 | 270.00 | 90.00 | W | ||
| SURFACE 9 - WINDOW 4 | WINDOWCONSTRUCTION | 1.01 | 0.00 | 0.00 | 1.01 | 1.01 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 9 | 270.00 | 90.00 | W | ||
| SURFACE 9 - WINDOW 5 | WINDOWCONSTRUCTION | 1.01 | 0.00 | 0.00 | 1.01 | 1.01 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 9 | 270.00 | 90.00 | W | ||
| SURFACE 9 - WINDOW 6 | WINDOWCONSTRUCTION | 1.01 | 0.00 | 0.00 | 1.01 | 1.01 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 9 | 270.00 | 90.00 | W | ||
| SURFACE 9 - WINDOW 7 | WINDOWCONSTRUCTION | 1.01 | 0.00 | 0.00 | 1.01 | 1.01 | 2.102 | 0.212 | 0.122 | Yes | SURFACE 9 | 270.00 | 90.00 | W | ||
| Total or Average | 42.47 | 2.102 | 0.212 | 0.122 | ||||||||||||
| North Total or Average | 7.88 | 2.102 | 0.212 | 0.122 | ||||||||||||
| Non-North Total or Average | 34.59 | 2.102 | 0.212 | 0.122 |
| Construction | Area of One Opening [m2] | Area of Openings [m2] | Glass U-Factor [W/m2-K] | Glass SHGC | Glass Visible Transmittance | Parent Surface | |
| Total or Average | 0.00 | - | - | - |
| Construction | U-Factor with Film [W/m2-K] | U-Factor no Film [W/m2-K] | Gross Area [m2] | Parent Surface | |
| UNIT 1 - SURFACE 13 - DOOR | DOOR | 1.142 | 1.377 | 1.86 | SURFACE 44 |
Report: Shading Summary
For: Entire Facility
Timestamp: 2019-07-16 16:11:39
Sunlit Fraction| March 21 9am | March 21 noon | March 21 3pm | June 21 9am | June 21 noon | June 21 3pm | December 21 9am | December 21 noon | December 21 3pm | |
| SURFACE 10 - WINDOW 1 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| SURFACE 10 - WINDOW 2 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| SURFACE 10 - WINDOW 3 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| SURFACE 13 - WINDOW 1 | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 0.00 |
| SURFACE 13 - WINDOW 2 | 1.00 | 1.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 1.00 | 0.00 |
| SURFACE 13 - WINDOW 3 | 1.00 | 1.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 |
| SURFACE 13 - WINDOW 4 | 1.00 | 1.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 |
| SURFACE 16 - WINDOW 1 | 1.00 | 1.00 | 1.00 | 0.00 | 1.00 | 0.00 | 0.00 | 0.00 | 1.00 |
| SURFACE 16 - WINDOW 2 | 1.00 | 1.00 | 1.00 | 0.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.07 |
| SURFACE 16 - WINDOW 3 | 1.00 | 1.00 | 1.00 | 0.00 | 1.00 | 0.61 | 0.00 | 0.00 | 0.00 |
| SURFACE 16 - WINDOW 4 | 1.00 | 1.00 | 1.00 | 0.00 | 0.96 | 0.95 | 0.00 | 0.00 | 0.00 |
| SURFACE 17 - WINDOW 1 | 0.00 | 0.00 | 0.77 | 0.00 | 0.00 | 0.55 | 0.00 | 0.00 | 1.00 |
| SURFACE 17 - WINDOW 2 | 0.00 | 0.00 | 0.77 | 0.00 | 0.00 | 0.55 | 0.00 | 0.00 | 1.00 |
| SURFACE 17 - WINDOW 3 | 0.00 | 0.00 | 0.77 | 0.00 | 0.00 | 0.55 | 0.00 | 0.00 | 1.00 |
| SURFACE 17 - WINDOW 4 | 0.00 | 0.00 | 0.77 | 0.00 | 0.00 | 0.55 | 0.00 | 0.00 | 1.00 |
| SURFACE 17 - WINDOW 5 | 0.00 | 0.00 | 0.77 | 0.00 | 0.00 | 0.55 | 0.00 | 0.00 | 1.00 |
| SURFACE 17 - WINDOW 6 | 0.00 | 0.00 | 0.77 | 0.00 | 0.00 | 0.55 | 0.00 | 0.00 | 1.00 |
| SURFACE 17 - WINDOW 7 | 0.00 | 0.00 | 0.77 | 0.00 | 0.00 | 0.55 | 0.00 | 0.00 | 1.00 |
| SURFACE 18 - WINDOW 1 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| SURFACE 18 - WINDOW 2 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| SURFACE 18 - WINDOW 3 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| SURFACE 18 - WINDOW 4 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| SURFACE 18 - WINDOW 5 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| SURFACE 19 - WINDOW 1 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.63 | 0.00 |
| SURFACE 19 - WINDOW 2 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.22 | 0.00 |
| SURFACE 19 - WINDOW 3 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 |
| SURFACE 20 - WINDOW 1 | 0.70 | 0.65 | 0.38 | 0.00 | 0.00 | 0.00 | 1.00 | 1.00 | 0.29 |
| SURFACE 20 - WINDOW 2 | 0.70 | 0.65 | 0.66 | 0.13 | 0.00 | 0.00 | 1.00 | 1.00 | 0.55 |
| SURFACE 21 - WINDOW 1 | 0.98 | 0.00 | 0.00 | 0.75 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 |
| SURFACE 21 - WINDOW 2 | 0.98 | 0.00 | 0.00 | 0.75 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 |
| SURFACE 21 - WINDOW 3 | 0.98 | 0.00 | 0.00 | 0.75 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 |
| SURFACE 21 - WINDOW 4 | 0.98 | 0.00 | 0.00 | 0.75 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 |
| SURFACE 8 - WINDOW 1 | 0.00 | 0.00 | 1.00 | 0.00 | 1.00 | 1.00 | 0.00 | 0.00 | 1.00 |
| SURFACE 8 - WINDOW 2 | 0.00 | 0.00 | 1.00 | 0.00 | 1.00 | 1.00 | 0.00 | 0.00 | 0.07 |
| SURFACE 8 - WINDOW 3 | 1.00 | 0.00 | 0.00 | 0.19 | 1.00 | 1.00 | 0.00 | 0.00 | 0.00 |
| SURFACE 8 - WINDOW 4 | 1.00 | 0.00 | 0.00 | 0.88 | 1.00 | 1.00 | 0.00 | 0.00 | 0.00 |
| SURFACE 9 - WINDOW 1 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 |
| SURFACE 9 - WINDOW 2 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 |
| SURFACE 9 - WINDOW 3 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 |
| SURFACE 9 - WINDOW 4 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 |
| SURFACE 9 - WINDOW 5 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 |
| SURFACE 9 - WINDOW 6 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 |
| SURFACE 9 - WINDOW 7 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 |
| Name | Type | Shaded Construction | Control | Glare Control | |
| SURFACE 10 - WINDOW 1 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 10 - WINDOW 2 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 10 - WINDOW 3 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 13 - WINDOW 1 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 13 - WINDOW 2 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 13 - WINDOW 3 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 13 - WINDOW 4 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 16 - WINDOW 1 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 16 - WINDOW 2 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 16 - WINDOW 3 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 16 - WINDOW 4 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 17 - WINDOW 1 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 17 - WINDOW 2 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 17 - WINDOW 3 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 17 - WINDOW 4 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 17 - WINDOW 5 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 17 - WINDOW 6 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 17 - WINDOW 7 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 18 - WINDOW 1 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 18 - WINDOW 2 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 18 - WINDOW 3 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 18 - WINDOW 4 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 18 - WINDOW 5 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 19 - WINDOW 1 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 19 - WINDOW 2 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 19 - WINDOW 3 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 20 - WINDOW 1 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 20 - WINDOW 2 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 21 - WINDOW 1 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 21 - WINDOW 2 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 21 - WINDOW 3 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 21 - WINDOW 4 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 8 - WINDOW 1 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 8 - WINDOW 2 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 8 - WINDOW 3 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 8 - WINDOW 4 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 9 - WINDOW 1 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 9 - WINDOW 2 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 9 - WINDOW 3 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 9 - WINDOW 4 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 9 - WINDOW 5 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 9 - WINDOW 6 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No | |
| SURFACE 9 - WINDOW 7 | WINDOWSHADINGCONTROL | Interior Shade | OnIfScheduleAllows | No |
Report: Lighting Summary
For: Entire Facility
Timestamp: 2019-07-16 16:11:39
Interior Lighting| Zone | Lighting Power Density [W/m2] | Zone Area [m2] | Total Power [W] | End Use Subcategory | Schedule Name | Scheduled Hours/Week [hr] | Hours/Week > 1% [hr] | Full Load Hours/Week [hr] | Return Air Fraction | Conditioned (Y/N) | Consumption [GJ] | |
| RES LIGHTING GARAGE GARAGE SPACE | GARAGE ZONE | 0.3661 | 53.51 | 19.59 | res lighting garage garage space | RES LIGHTING GARAGE | 63.72 | 168.00 | 63.72 | 0.0000 | N | 0.23 |
| RES LIGHTING INTERIOR LIVING SPACE | LIVING ZONE | 1.0476 | 418.06 | 437.98 | res lighting interior living space | RES LIGHTING INTERIOR | 63.72 | 168.00 | 63.72 | 0.0000 | Y | 5.24 |
| RES LIGHTING INTERIOR LIVING SPACE|STORY 2 | LIVING ZONE | 1.3552 | 418.06 | 566.56 | res lighting interior living space|story 2 | RES LIGHTING INTERIOR | 63.72 | 168.00 | 63.72 | 0.0000 | Y | 6.78 |
| Interior Lighting Total | 1.1512 | 889.64 | 1024.14 | 12.25 |
| Zone | Control Name | Daylighting Method | Control Type | Fraction Controlled | Lighting Installed in Zone [W] | Lighting Controlled [W] | |
| None |
| Total Watts | Astronomical Clock/Schedule | Schedule Name | Scheduled Hours/Week [hr] | Hours/Week > 1% [hr] | Full Load Hours/Week [hr] | Consumption [GJ] | |
| RES LIGHTING EXTERIOR | 236.37 | Schedule | RES LIGHTING EXTERIOR | 63.72 | 168.00 | 63.72 | 2.83 |
| Exterior Lighting Total | 236.37 | 2.83 |
Report: Equipment Summary
For: Entire Facility
Timestamp: 2019-07-16 16:11:39
Central Plant| Type | Nominal Capacity [W] | Nominal Efficiency [W/W] | IPLV in SI Units [W/W] | IPLV in IP Units [Btu/W-h] | |
| None |
| Type | Design Coil Load [W] | Nominal Total Capacity [W] | Nominal Sensible Capacity [W] | Nominal Latent Capacity [W] | Nominal Sensible Heat Ratio | Nominal Efficiency [W/W] | Nominal Coil UA Value [W/C] | Nominal Coil Surface Area [m2] | |
| RES AC COOLING COIL | Coil:Cooling:DX:SingleSpeed | 10242.85 | 7583.83 | 2659.02 | 0.74 | 3.07 |
| DX Cooling Coil Type | Standard Rated Net Cooling Capacity [W] | Standard Rated Net COP [W/W] | EER [Btu/W-h] | SEER [Btu/W-h] | IEER [Btu/W-h] | |
| RES AC COOLING COIL | 9768.7 | 2.60 | 8.87 | 9.84 | 9.96 |
| DX Cooling Coil Type | Rated Net Cooling Capacity Test A [W] | Rated Electric Power Test A [W] | Rated Net Cooling Capacity Test B [W] | Rated Electric Power Test B [W] | Rated Net Cooling Capacity Test C [W] | Rated Electric Power Test C [W] | Rated Net Cooling Capacity Test D [W] | Rated Electric Power Test D [W] | |
| RES AC COOLING COIL | Coil:Cooling:DX:SingleSpeed |
| DX Heating Coil Type | High Temperature Heating (net) Rating Capacity [W] | Low Temperature Heating (net) Rating Capacity [W] | HSPF [Btu/W-h] | Region Number | |
| None |
| Type | Design Coil Load [W] | Nominal Total Capacity [W] | Nominal Efficiency [W/W] | |
| RES FUR PROPANE HEATING COIL | Coil:Heating:Fuel | 17309.11 | 0.80 |
| Type | Total Efficiency [W/W] | Delta Pressure [pa] | Max Air Flow Rate [m3/s] | Rated Electric Power [W] | Rated Power Per Max Air Flow Rate [W-s/m3] | Motor Heat In Air Fraction | Fan Energy Index | End Use Subcategory | Design Day Name for Fan Sizing Peak | Date/Time for Fan Sizing Peak | |
| RES AC CLG SUPPLY FAN | Fan:OnOff | 0.75 | 794.58 | 0.69 | 726.67 | 1059.44 | 1.00 | 1.90 | res ac clg supply fan | ||
| RES FUR PROPANE HTG SUPPLY FAN | Fan:OnOff | 0.75 | 794.58 | 0.69 | 726.67 | 1059.44 | 1.00 | 1.90 | res fur propane htg supply fan |
| Type | Control | Head [pa] | Water Flow [m3/s] | Electric Power [W] | Power Per Water Flow Rate [W-s/m3] | Motor Efficiency [W/W] | End Use Subcategory | |
| PUMP VARIABLE SPEED 1 | Pump:VariableSpeed | Intermittent | 1.00 | 0.010000 | 0.00 | 0.00 | 1.00 | General |
| Type | Storage Volume [m3] | Input [W] | Thermal Efficiency [W/W] | Recovery Efficiency [W/W] | Energy Factor | |
| RES WH | WaterHeater:Mixed | 0.22 | 1318.82 | 1.00 | 0.20 | 1.12 |
Report: HVAC Sizing Summary
For: Entire Facility
Timestamp: 2019-07-16 16:11:39
Zone Sensible Cooling| Calculated Design Load [W] | User Design Load [W] | User Design Load per Area [W/m2] | Calculated Design Air Flow [m3/s] | User Design Air Flow [m3/s] | Design Day Name | Date/Time Of Peak {TIMESTAMP} | Thermostat Setpoint Temperature at Peak Load [C] | Indoor Temperature at Peak Load [C] | Indoor Humidity Ratio at Peak Load [kgWater/kgAir] | Outdoor Temperature at Peak Load [C] | Outdoor Humidity Ratio at Peak Load [kgWater/kgAir] | Minimum Outdoor Air Flow Rate [m3/s] | Heat Gain Rate from DOAS [W] | |
| LIVING ZONE | 4005.18 | 4605.96 | 11.02 | 0.330 | 0.379 | ANN CLG 1% CONDNS DB=>MWB | 7/21 16:10:00 | 23.89 | 23.89 | 0.01035 | 31.91 | 0.01464 | 0.000 | 0.00 |
| Calculated Design Load [W] | User Design Load [W] | User Design Load per Area [W/m2] | Calculated Design Air Flow [m3/s] | User Design Air Flow [m3/s] | Design Day Name | Date/Time Of Peak {TIMESTAMP} | Thermostat Setpoint Temperature at Peak Load [C] | Indoor Temperature at Peak Load [C] | Indoor Humidity Ratio at Peak Load [kgWater/kgAir] | Outdoor Temperature at Peak Load [C] | Outdoor Humidity Ratio at Peak Load [kgWater/kgAir] | Minimum Outdoor Air Flow Rate [m3/s] | Heat Gain Rate from DOAS [W] | |
| LIVING ZONE | 12431.13 | 15538.91 | 37.17 | 0.536 | 0.670 | ANN HTG 99% CONDNS DB | 1/21 24:00:00 | 21.11 | 21.11 | 0.00669 | -8.40 | 0.00184 | 0.000 | 0.00 |
| Calculated cooling [m3/s] | User cooling [m3/s] | Calculated heating [m3/s] | User heating [m3/s] | Adjusted cooling [m3/s] | Adjusted heating [m3/s] | Adjusted main [m3/s] | Calculated Heating Air Flow Ratio [] | User Heating Air Flow Ratio [] | |
| RES AC ASYS | 0.38 | 0.38 | 0.67 | 0.67 | 0.3791 | 0.6699 | 0.6859 | 0.9766 | 0.3000 |
| RES FUR PROPANE ASYS | 0.38 | 0.38 | 0.67 | 0.67 | 0.3791 | 0.6699 | 0.6859 | 0.9766 | 0.3000 |
| Previous Design Volume Flow Rate [m3/s] | Algorithm Volume Flow Rate [m3/s] | Coincident Design Volume Flow Rate [m3/s] | Coincident Size Adjusted | Peak Sizing Period Name | Peak Day into Period {TIMESTAMP}[day] | Peak Hour Of Day {TIMESTAMP}[hr] | Peak Step Start Minute {TIMESTAMP}[min] | |
| None |
| Coil Type | HVAC Type | HVAC Name | Coil Final Gross Total Capacity [W] | Coil Final Gross Sensible Capacity [W] | Coil Final Reference Air Volume Flow Rate [m3/s] | Coil Final Reference Plant Fluid Volume Flow Rate [m3/s] | Coil U-value Times Area Value [W/K] | Design Day Name at Sensible Ideal Loads Peak | Date/Time at Sensible Ideal Loads Peak | Design Day Name at Air Flow Ideal Loads Peak | Date/Time at Air Flow Ideal Loads Peak | Coil Total Capacity at Ideal Loads Peak [W] | Coil Sensible Capacity at Ideal Loads Peak [W] | Coil Air Volume Flow Rate at Ideal Loads Peak [m3/s] | Coil Entering Air Drybulb at Ideal Loads Peak [C] | Coil Entering Air Wetbulb at Ideal Loads Peak [C] | Coil Entering Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Coil Leaving Air Drybulb at Ideal Loads Peak [C] | Coil Leaving Air Wetbulb at Ideal Loads Peak [C] | Coil Leaving Air Humidity Ratio at Ideal Loads Peak [C] | Outdoor Air Drybulb at Ideal Loads Peak [C] | Outdoor Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Outdoor Air Wetbulb at Ideal Loads Peak [C] | Outdoor Air Flow Percentage at Ideal Loads Peak [%] | Zone Air Drybulb at Ideal Loads Peak [C] | Zone Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Zone Air Relative Humidity at Ideal Loads Peak [%] | Zone Sensible Heat Gain at Ideal Loads Peak [W] | Zone Latent Heat Gain at Ideal Loads Peak [W] | Coil Total Capacity at Rating Conditions [W] | Coil Sensible Capacity at Rating Conditions [W] | |
| RES AC COOLING COIL | Coil:Cooling:DX:SingleSpeed | AirLoopHVAC | RES AC ASYS | 10242.846 | 7583.829 | 0.530713 | -999.0 | -999.000 | ANN CLG 1% CONDNS DB=>MWB | 7/21 15:10:00 | ANN CLG 1% CONDNS DB=>MWB | 7/21 16:10:00 | 8460.97 | 4894.75 | 0.530713 | 32.76 | 23.64 | 0.01464395 | 12.80 | 12.10 | 0.00850000 | 31.91 | 0.01464395 | 23.41 | 0.0000 | 23.89 | 0.01034797 | 55.9146 | 4605.96 | 0.00 | 10179.11 | 7589.07 |
| RES FUR PROPANE HEATING COIL | Coil:Heating:Fuel | AirLoopHVAC | RES FUR PROPANE ASYS | 17309.110 | 17309.110 | -999.0 | -999.0 | -999.000 | ANN HTG 99% CONDNS DB | 1/21 24:00:00 | ANN HTG 99% CONDNS DB | 1/21 24:00:00 | 17309.11 | 15620.83 | 0.506895 | -8.40 | -8.40 | 0.00184320 | 16.70 | 13.18 | 0.00800000 | -8.40 | 0.00184320 | -8.40 | 0.0000 | 21.11 | 0.00669148 | 43.0601 | 15538.91 | 0.00 | -999.00 | -999.00 |
Report: Coil Sizing Details
For: Entire Facility
Timestamp: 2019-07-16 16:11:39
Coils| Coil Type | Coil Location | HVAC Type | HVAC Name | Zone Name(s) | System Sizing Method Concurrence | System Sizing Method Capacity | System Sizing Method Air Flow | Autosized Coil Capacity? | Autosized Coil Airflow? | Autosized Coil Water Flow? | OA Pretreated prior to coil inlet? | Coil Final Gross Total Capacity [W] | Coil Final Gross Sensible Capacity [W] | Coil Final Reference Air Volume Flow Rate [m3/s] | Coil Final Reference Plant Fluid Volume Flow Rate [m3/s] | Coil U-value Times Area Value [W/K] | Terminal Unit Reheat Coil Multiplier | DX Coil Capacity Increase Ratio from Too Low Flow/Capacity Ratio | DX Coil Capacity Decrease Ratio from Too High Flow/Capacity Ratio | Moist Air Heat Capacity [J/kg-K] | Dry Air Heat Capacity [J/kg-K] | Standard Air Density Adjusted for Elevation [kg/m3] | Supply Fan Name for Coil | Supply Fan Type for Coil | Supply Fan Maximum Air Volume Flow Rate [m3/s] | Supply Fan Maximum Air Mass Flow Rate [kg/s] | Plant Name for Coil | Plant Fluid Specific Heat Capacity [J/kg-K] | Plant Fluid Density [kg/m3] | Plant Maximum Fluid Mass Flow Rate [kg/s] | Plant Design Fluid Return Temperature [C] | Plant Design Fluid Supply Temperature [C] | Plant Design Fluid Temperature Difference [deltaC] | Plant Design Capacity [W] | Coil Capacity Percentage of Plant Design Capacity [%] | Coil Fluid Flow Rate Percentage of Plant Design Flow Rate [%] | Design Day Name at Sensible Ideal Loads Peak | Date/Time at Sensible Ideal Loads Peak | Design Day Name at Total Ideal Loads Peak | Date/Time at Total Ideal Loads Peak | Design Day Name at Air Flow Ideal Loads Peak | Date/Time at Air Flow Ideal Loads Peak | Coil Total Capacity at Ideal Loads Peak [W] | Coil Sensible Capacity at Ideal Loads Peak [W] | Coil Off-Rating Capacity Modifier at Ideal Loads Peak [ ] | Coil Air Mass Flow Rate at Ideal Loads Peak [kg/s] | Coil Air Volume Flow Rate at Ideal Loads Peak [m3/s] | Coil Entering Air Drybulb at Ideal Loads Peak [C] | Coil Entering Air Wetbulb at Ideal Loads Peak [C] | Coil Entering Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Coil Entering Air Enthalpy at Ideal Loads Peak [J/KG-K] | Coil Leaving Air Drybulb at Ideal Loads Peak [C] | Coil Leaving Air Wetbulb at Ideal Loads Peak [C] | Coil Leaving Air Humidity Ratio at Ideal Loads Peak [C] | Coil Leaving Air Enthalpy at Ideal Loads Peak [J/KG-K] | Coil Plant Fluid Mass Flow Rate at Ideal Loads Peak [kg/s] | Coil Entering Plant Fluid Temperature at Ideal Loads Peak [C] | Coil Leaving Plant Fluid Temperature at Ideal Loads Peak [C] | Coil Plant Fluid Temperature Difference at Ideal Loads Peak [deltaC] | Supply Fan Air Heat Gain at Ideal Loads Peak [W] | Coil and Fan Net Total Capacity at Ideal Loads Peak [W] | Outdoor Air Drybulb at Ideal Loads Peak [C] | Outdoor Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Outdoor Air Wetbulb at Ideal Loads Peak [C] | Outdoor Air Volume Flow Rate at Ideal Loads Peak [m3/s] | Outdoor Air Flow Percentage at Ideal Loads Peak [%] | System Return Air Drybulb at Ideal Loads Peak [C] | System Return Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Zone Air Drybulb at Ideal Loads Peak [C] | Zone Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Zone Air Relative Humidity at Ideal Loads Peak [%] | Zone Sensible Heat Gain at Ideal Loads Peak [W] | Zone Latent Heat Gain at Ideal Loads Peak [W] | Coil Total Capacity at Rating Conditions [W] | Coil Sensible Capacity at Rating Conditions [W] | Coil Air Mass Flow Rate at Rating Conditions [kg/s] | Coil Entering Air Drybulb at Rating Conditions [C] | Coil Entering Air Wetbulb at Rating Conditions [C] | Coil Entering Air Humidity Ratio at Rating Conditions [KGWATER/KGDRYAIR] | Coil Entering Air Enthalpy at Rating Conditions [J/KG-K] | Coil Leaving Air Drybulb at Rating Conditions [C] | Coil Leaving Air Wetbulb at Rating Conditions [C] | Coil Leaving Air Humidity Ratio at Rating Conditions [KGWATER/KGDRYAIR] | Coil Leaving Air Enthalpy at Rating Conditions [J/KG-K] | |
| RES AC COOLING COIL | Coil:Cooling:DX:SingleSpeed | AirLoop | AirLoopHVAC | RES AC ASYS | LIVING ZONE | Non-Coincident | CoolingDesignCapacity | N/A | No | No | unknown | No | 10242.846 | 7583.829 | 0.530713 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1032.0624 | 1004.8586 | 1.2040 | RES AC CLG SUPPLY FAN | Fan:OnOff | 0.685904 | 0.82584484 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | ANN CLG 1% CONDNS DB=>MWB | 7/21 15:10:00 | ANN CLG 1% CONDNS DB=>MWB | 7/21 15:30:00 | ANN CLG 1% CONDNS DB=>MWB | 7/21 16:10:00 | 8460.97 | 4894.75 | 1.2106 | 0.63899098 | 0.530713 | 32.76 | 23.64 | 0.01464395 | 70437.4 | 12.80 | 12.10 | 0.00850000 | 34322.2 | -999.0 | -999.00 | -999.00 | -999.00 | 562.259 | 7898.71 | 31.91 | 0.01464395 | 23.41 | 0.00000000 | 0.0000 | 23.89 | 0.01034797 | 23.89 | 0.01034797 | 55.9146 | 4605.96 | 0.00 | 10179.11 | 7589.07 | 0.61369237 | 26.67 | 19.44 | 0.01117891 | 55307.7 | 14.57 | 13.80 | 0.00952417 | 38721.0 | |
| RES FUR PROPANE HEATING COIL | Coil:Heating:Fuel | AirLoop | AirLoopHVAC | RES FUR PROPANE ASYS | LIVING ZONE | Non-Coincident | HeatingDesignCapacity | N/A | No | No | unknown | No | 17309.110 | 17309.110 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.2040 | RES FUR PROPANE HTG SUPPLY FAN | Fan:OnOff | 0.685904 | 0.82584484 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | ANN HTG 99% CONDNS DB | 1/21 24:00:00 | unknown | unknown | ANN HTG 99% CONDNS DB | 1/21 24:00:00 | 17309.11 | 15620.83 | 1.0000 | 0.61031366 | 0.506895 | -8.40 | -8.40 | 0.00184320 | -3859.7 | 16.70 | 13.18 | 0.00800000 | 37036.7 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 17309.11 | -8.40 | 0.00184320 | -8.40 | 0.00000000 | 0.0000 | 21.11 | 0.00669148 | 21.11 | 0.00669148 | 43.0601 | 15538.91 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 |
Report: System Summary
For: Entire Facility
Timestamp: 2019-07-16 16:11:39
Economizer| High Limit Shutoff Control | Minimum Outdoor Air [m3/s] | Maximum Outdoor Air [m3/s] | Return Air Temp Limit | Return Air Enthalpy Limit | Outdoor Air Temperature Limit [C] | Outdoor Air Enthalpy Limit [C] | |
| None |
| Controller:MechanicalVentilation Name | Outdoor Air Per Person [m3/s-person] | Outdoor Air Per Area [m3/s-m2] | Outdoor Air Per Zone [m3/s] | Outdoor Air ACH [ach] | Outdoor Air Method | Outdoor Air Schedule Name | Air Distribution Effectiveness in Cooling Mode | Air Distribution Effectiveness in Heating Mode | Air Distribution Effectiveness Schedule Name | |
| None |
| Winter Clothes [hr] | Summer Clothes [hr] | Summer or Winter Clothes [hr] | |
| LIVING ZONE | 4375.00 | 8755.33 | 4374.83 |
| GARAGE ZONE | 0.00 | 0.00 | 0.00 |
| RES DS RES AC ASYS RET AIR ZONE | 0.00 | 0.00 | 0.00 |
| RES DS RES FUR PROPANE ASYS RET AIR ZONE | 0.00 | 0.00 | 0.00 |
| UNFINISHED ATTIC ZONE | 0.00 | 0.00 | 0.00 |
| UNFINISHED BASEMENT ZONE | 0.00 | 0.00 | 0.00 |
| Facility | 4375.00 | 8755.33 | 4374.83 |
| During Heating [hr] | During Cooling [hr] | During Occupied Heating [hr] | During Occupied Cooling [hr] | |
| LIVING ZONE | 0.00 | 8.00 | 0.00 | 8.00 |
| GARAGE ZONE | 0.00 | 0.00 | 0.00 | 0.00 |
| RES DS RES AC ASYS RET AIR ZONE | 0.00 | 0.00 | 0.00 | 0.00 |
| RES DS RES FUR PROPANE ASYS RET AIR ZONE | 0.00 | 0.00 | 0.00 | 0.00 |
| UNFINISHED ATTIC ZONE | 0.00 | 0.00 | 0.00 | 0.00 |
| UNFINISHED BASEMENT ZONE | 0.00 | 0.00 | 0.00 | 0.00 |
| Facility | 0.00 | 8.00 | 0.00 | 8.00 |
Report: Outdoor Air Summary
For: Entire Facility
Timestamp: 2019-07-16 16:11:39
Average Outdoor Air During Occupied Hours| Average Number of Occupants | Nominal Number of Occupants | Zone Volume [m3] | Mechanical Ventilation [ach] | Infiltration [ach] | AFN Infiltration [ach] | Simple Ventilation [ach] | |
| LIVING ZONE | 1.13 | 3.23 | 1019.41 | 0.000 | 0.256 | 0.000 | 0.000 |
| Average Number of Occupants | Nominal Number of Occupants | Zone Volume [m3] | Mechanical Ventilation [ach] | Infiltration [ach] | AFN Infiltration [ach] | Simple Ventilation [ach] | |
| LIVING ZONE | 1.13 | 3.23 | 1019.41 | 0.000 | 0.000 | 0.000 | 0.000 |
Report: Object Count Summary
For: Entire Facility
Timestamp: 2019-07-16 16:11:39
Surfaces by Class| Total | Outdoors | |
| Wall | 36 | 22 |
| Floor | 8 | 2 |
| Roof | 10 | 4 |
| Internal Mass | 7 | 0 |
| Building Detached Shading | 24 | 24 |
| Fixed Detached Shading | 0 | 0 |
| Window | 43 | 43 |
| Door | 1 | 1 |
| Glass Door | 0 | 0 |
| Shading | 0 | 0 |
| Overhang | 0 | 0 |
| Fin | 0 | 0 |
| Tubular Daylighting Device Dome | 0 | 0 |
| Tubular Daylighting Device Diffuser | 0 | 0 |
| Count | |
| HVAC Air Loops | 2 |
| Conditioned Zones | 3 |
| Unconditioned Zones | 3 |
| Supply Plenums | 0 |
| Return Plenums | 2 |
| Count | |
| IDF Objects | 0 |
| Defaulted Fields | 0 |
| Fields with Defaults | 0 |
| Autosized Fields | 0 |
| Autosizable Fields | 0 |
| Autocalculated Fields | 0 |
| Autocalculatable Fields | 0 |
Report: Energy Meters
For: Entire Facility
Timestamp: 2019-07-16 16:11:39
Annual and Peak Values - Electricity| Electricity Annual Value [GJ] | Electricity Minimum Value [W] | Timestamp of Minimum {TIMESTAMP} | Electricity Maximum Value [W] | Timestamp of Maximum {TIMESTAMP} | |
| Electricity:Facility | 82.11 | 695.77 | 01-JUL-03:30 | 11213.52 | 24-JUL-20:00 |
| Electricity:Building | 44.41 | 683.74 | 01-JUL-03:10 | 9707.83 | 06-FEB-21:00 |
| Electricity:Zone:GARAGE ZONE | 2.26 | 47.42 | 01-FEB-04:10 | 97.87 | 01-MAR-18:10 |
| InteriorLights:Electricity | 12.25 | 50.77 | 01-JAN-02:10 | 1024.14 | 01-DEC-18:10 |
| InteriorLights:Electricity:Zone:GARAGE ZONE | 0.23 | 0.97 | 01-JAN-02:10 | 19.59 | 01-DEC-18:10 |
| res lighting garage garage space:InteriorLights:Electricity | 0.23 | 0.97 | 01-JAN-02:10 | 19.59 | 01-DEC-18:10 |
| Electricity:Zone:LIVING ZONE | 42.15 | 621.92 | 01-JUL-03:10 | 9629.31 | 06-FEB-21:00 |
| InteriorLights:Electricity:Zone:LIVING ZONE | 12.02 | 49.80 | 01-JAN-02:10 | 1004.54 | 01-DEC-18:10 |
| res lighting interior living space:InteriorLights:Electricity | 5.24 | 21.71 | 01-JAN-02:10 | 437.98 | 01-DEC-18:10 |
| res lighting interior living space|story 2:InteriorLights:Electricity | 6.78 | 28.09 | 01-JAN-02:10 | 566.56 | 01-DEC-18:10 |
| InteriorEquipment:Electricity | 32.16 | 631.43 | 01-JUL-08:10 | 8765.81 | 06-FEB-21:00 |
| InteriorEquipment:Electricity:Zone:GARAGE ZONE | 2.03 | 46.34 | 01-FEB-04:10 | 84.48 | 01-JUN-17:10 |
| res extra refrig:InteriorEquipment:Electricity | 0.88 | 20.04 | 01-FEB-04:10 | 36.53 | 01-JUN-17:10 |
| res freezer:InteriorEquipment:Electricity | 1.15 | 26.31 | 01-FEB-04:10 | 47.96 | 01-JUN-17:10 |
| InteriorEquipment:Electricity:Zone:LIVING ZONE | 30.13 | 562.16 | 01-JUL-08:10 | 8705.31 | 06-FEB-21:00 |
| res cd electric:InteriorEquipment:Electricity | 0.22 | 0.00 | 01-JAN-00:10 | 6969.72 | 02-JAN-21:00 |
| res ceil fan:InteriorEquipment:Electricity | 0.93 | 13.37 | 01-JUL-08:10 | 63.17 | 01-FEB-20:10 |
| General:InteriorEquipment:Electricity | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| res cw:InteriorEquipment:Electricity | 0.01 | 0.00 | 01-JAN-00:10 | 309.17 | 02-JAN-20:00 |
| res dw:InteriorEquipment:Electricity | 0.73 | 0.00 | 01-JAN-00:10 | 1352.08 | 01-JAN-13:30 |
| res hot tub heater electric:InteriorEquipment:Electricity | 0.25 | 2.45 | 01-APR-11:10 | 27.97 | 01-JUN-15:10 |
| res hot tub pump:InteriorEquipment:Electricity | 0.31 | 2.97 | 01-APR-11:10 | 33.94 | 01-JUN-15:10 |
| res mv_1 bath fan:InteriorEquipment:Electricity | 0.06 | 0.00 | 01-JAN-00:10 | 45.01 | 01-JAN-21:20 |
| res mv_1 house fan:InteriorEquipment:Electricity | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| res mv_1 range fan:InteriorEquipment:Electricity | 0.04 | 0.00 | 01-JAN-00:10 | 30.00 | 01-JAN-12:20 |
| res misc plug loads:InteriorEquipment:Electricity | 22.17 | 318.56 | 01-JUL-08:10 | 1505.62 | 01-FEB-20:10 |
| res pool heater electric:InteriorEquipment:Electricity | 0.05 | 0.09 | 01-JUL-00:10 | 5.28 | 01-FEB-10:10 |
| res pool pump:InteriorEquipment:Electricity | 0.86 | 1.74 | 01-JUL-00:10 | 96.86 | 01-FEB-10:10 |
| res range electric:InteriorEquipment:Electricity | 2.52 | 6.81 | 01-JUN-01:10 | 314.95 | 01-JAN-17:10 |
| res refrig:InteriorEquipment:Electricity | 1.73 | 39.49 | 01-FEB-04:10 | 71.99 | 01-JUN-17:10 |
| res well pump:InteriorEquipment:Electricity | 0.26 | 2.60 | 01-JUL-02:10 | 19.63 | 01-FEB-21:10 |
| Electricity:Plant | 19.31 | 0.00 | 01-JAN-00:10 | 1318.82 | 01-JAN-05:30 |
| WaterSystems:Electricity | 19.31 | 0.00 | 01-JAN-00:10 | 1318.82 | 01-JAN-05:30 |
| res wh:WaterSystems:Electricity | 19.31 | 0.00 | 01-JAN-00:10 | 1318.82 | 01-JAN-05:30 |
| ElectricityPurchased:Facility | 82.11 | 695.77 | 01-JUL-03:30 | 11213.52 | 24-JUL-20:00 |
| ElectricityPurchased:Plant | 82.11 | 695.77 | 01-JUL-03:30 | 11213.52 | 24-JUL-20:00 |
| Cogeneration:ElectricityPurchased | 82.11 | 695.77 | 01-JUL-03:30 | 11213.52 | 24-JUL-20:00 |
| ElectricitySurplusSold:Facility | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| ElectricitySurplusSold:Plant | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| Cogeneration:ElectricitySurplusSold | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| ElectricityNet:Facility | 82.11 | 695.77 | 01-JUL-03:30 | 11213.52 | 24-JUL-20:00 |
| ElectricityNet:Plant | 82.11 | 695.77 | 01-JUL-03:30 | 11213.52 | 24-JUL-20:00 |
| Cogeneration:ElectricityNet | 82.11 | 695.77 | 01-JUL-03:30 | 11213.52 | 24-JUL-20:00 |
| Electricity:HVAC | 15.56 | 0.00 | 06-JAN-16:10 | 4185.99 | 07-JUL-15:00 |
| Fans:Electricity | 4.63 | 0.00 | 06-JAN-16:10 | 726.67 | 12-MAY-15:10 |
| res ac clg supply fan:Fans:Electricity | 2.84 | 0.00 | 01-JAN-00:10 | 726.67 | 12-MAY-15:10 |
| res fur propane htg supply fan:Fans:Electricity | 1.79 | 0.00 | 06-JAN-16:10 | 403.98 | 23-JAN-02:00 |
| Cooling:Electricity | 10.68 | 0.00 | 01-JAN-00:10 | 3459.32 | 07-JUL-15:00 |
| Heating:Electricity | 0.25 | 0.00 | 06-JAN-16:10 | 57.17 | 23-JAN-02:00 |
| ExteriorLights:Electricity | 2.83 | 11.72 | 01-JAN-02:10 | 236.37 | 01-DEC-18:10 |
| res lighting exterior:ExteriorLights:Electricity | 2.83 | 11.72 | 01-JAN-02:10 | 236.37 | 01-DEC-18:10 |
| Pumps:Electricity | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| General:Pumps:Electricity | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| Gas Annual Value [GJ] | Gas Minimum Value [W] | Timestamp of Minimum {TIMESTAMP} | Gas Maximum Value [W] | Timestamp of Maximum {TIMESTAMP} | |
| Gas:Facility | 1.05 | 7.84 | 01-NOV-03:10 | 67.79 | 01-FEB-10:10 |
| Gas:Building | 1.05 | 7.84 | 01-NOV-03:10 | 67.79 | 01-FEB-10:10 |
| Gas:Zone:LIVING ZONE | 1.05 | 7.84 | 01-NOV-03:10 | 67.79 | 01-FEB-10:10 |
| InteriorEquipment:Gas | 1.05 | 7.84 | 01-NOV-03:10 | 67.79 | 01-FEB-10:10 |
| InteriorEquipment:Gas:Zone:LIVING ZONE | 1.05 | 7.84 | 01-NOV-03:10 | 67.79 | 01-FEB-10:10 |
| res gas fireplace:InteriorEquipment:Gas | 0.29 | 2.88 | 01-JUL-02:10 | 21.74 | 01-FEB-21:10 |
| res gas grill:InteriorEquipment:Gas | 0.13 | 0.09 | 01-JUN-00:10 | 17.44 | 01-JAN-17:10 |
| res gas lighting:InteriorEquipment:Gas | 0.03 | 0.34 | 01-JUL-02:10 | 2.58 | 01-FEB-21:10 |
| res hot tub heater gas:InteriorEquipment:Gas | 0.13 | 1.30 | 01-APR-11:10 | 14.81 | 01-JUN-15:10 |
| res pool heater gas:InteriorEquipment:Gas | 0.47 | 0.94 | 01-JUL-00:10 | 52.28 | 01-FEB-10:10 |
| Cooling Annual Value [GJ] | Cooling Minimum Value [W] | Timestamp of Minimum {TIMESTAMP} | Cooling Maximum Value [W] | Timestamp of Maximum {TIMESTAMP} | |
| None |
| Annual Value [m3] | Minimum Value [m3/s] | Timestamp of Minimum {TIMESTAMP} | Maximum Value [m3/s] | Timestamp of Maximum {TIMESTAMP} | |
| Water:Facility | 197.00 | 0.00 | 01-JAN-00:10 | 0.00 | 17-FEB-16:10 |
| Water:Plant | 197.00 | 0.00 | 01-JAN-00:10 | 0.00 | 17-FEB-16:10 |
| WaterSystems:Water | 197.00 | 0.00 | 01-JAN-00:10 | 0.00 | 17-FEB-16:10 |
| res wh:WaterSystems:Water | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| MainsWater:Facility | 197.00 | 0.00 | 01-JAN-00:10 | 0.00 | 17-FEB-16:10 |
| MainsWater:Plant | 197.00 | 0.00 | 01-JAN-00:10 | 0.00 | 17-FEB-16:10 |
| WaterSystems:MainsWater | 197.00 | 0.00 | 01-JAN-00:10 | 0.00 | 17-FEB-16:10 |
| res wh:WaterSystems:MainsWater | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| res shower:WaterSystems:Water | 110.44 | 0.00 | 01-JAN-00:10 | 0.00 | 17-FEB-16:10 |
| res shower:WaterSystems:MainsWater | 110.44 | 0.00 | 01-JAN-00:10 | 0.00 | 17-FEB-16:10 |
| res sink:WaterSystems:Water | 73.57 | 0.00 | 01-JAN-00:10 | 0.00 | 29-MAR-18:10 |
| res sink:WaterSystems:MainsWater | 73.57 | 0.00 | 01-JAN-00:10 | 0.00 | 29-MAR-18:10 |
| res bath:WaterSystems:Water | 7.19 | 0.00 | 01-JAN-00:10 | 0.00 | 04-AUG-19:50 |
| res bath:WaterSystems:MainsWater | 7.19 | 0.00 | 01-JAN-00:10 | 0.00 | 04-AUG-19:50 |
| General:WaterSystems:Water | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| General:WaterSystems:MainsWater | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| res cw:WaterSystems:Water | 0.24 | 0.00 | 01-JAN-00:10 | 0.00 | 02-JAN-20:00 |
| res cw:WaterSystems:MainsWater | 0.24 | 0.00 | 01-JAN-00:10 | 0.00 | 02-JAN-20:00 |
| res dw:WaterSystems:Water | 5.56 | 0.00 | 01-JAN-00:10 | 0.00 | 26-MAR-13:30 |
| res dw:WaterSystems:MainsWater | 5.56 | 0.00 | 01-JAN-00:10 | 0.00 | 26-MAR-13:30 |
| Annual Value [kg] | Minimum Value [kg/s] | Timestamp of Minimum {TIMESTAMP} | Maximum Value [kg/s] | Timestamp of Maximum {TIMESTAMP} | |
| Carbon Equivalent:Facility | 0.00 | 0.000 | 01-JAN-00:10 | 0.000 | 01-JAN-00:10 |
| CarbonEquivalentEmissions:Carbon Equivalent | 0.00 | 0.000 | 01-JAN-00:10 | 0.000 | 01-JAN-00:10 |
| Annual Value [m3] | Minimum Value [m3/s] | Timestamp of Minimum {TIMESTAMP} | Maximum Value [m3/s] | Timestamp of Maximum {TIMESTAMP} | |
| None |
| Annual Value [L] | Minimum Value [L] | Timestamp of Minimum {TIMESTAMP} | Maximum Value [L] | Timestamp of Maximum {TIMESTAMP} | |
| None |
| Annual Value [GJ] | Minimum Value [W] | Timestamp of Minimum {TIMESTAMP} | Maximum Value [W] | Timestamp of Maximum {TIMESTAMP} | |
| PlantLoopHeatingDemand:Facility | 18.27 | 0.00 | 01-JAN-00:10 | 38129.09 | 06-FEB-06:10 |
| PlantLoopHeatingDemand:Plant | 18.27 | 0.00 | 01-JAN-00:10 | 38129.09 | 06-FEB-06:10 |
| WaterSystems:PlantLoopHeatingDemand | 18.27 | 0.00 | 01-JAN-00:10 | 38129.09 | 06-FEB-06:10 |
| res wh:WaterSystems:PlantLoopHeatingDemand | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| EnergyTransfer:Facility | 202.94 | 0.00 | 26-JAN-18:10 | 54765.38 | 23-JAN-06:10 |
| EnergyTransfer:Building | 89.86 | 0.00 | 06-JAN-16:10 | 13711.74 | 23-JAN-06:00 |
| EnergyTransfer:Zone:GARAGE ZONE | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| Heating:EnergyTransfer | 60.92 | 0.00 | 06-JAN-16:10 | 13562.49 | 23-JAN-02:00 |
| Heating:EnergyTransfer:Zone:GARAGE ZONE | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| Cooling:EnergyTransfer | 28.94 | 0.00 | 01-JAN-16:10 | 9230.38 | 15-SEP-15:10 |
| Cooling:EnergyTransfer:Zone:GARAGE ZONE | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| EnergyTransfer:Zone:LIVING ZONE | 88.42 | 0.00 | 06-JAN-16:10 | 13562.49 | 23-JAN-02:00 |
| Heating:EnergyTransfer:Zone:LIVING ZONE | 59.76 | 0.00 | 06-JAN-16:10 | 13562.49 | 23-JAN-02:00 |
| Cooling:EnergyTransfer:Zone:LIVING ZONE | 28.67 | 0.00 | 01-JAN-00:10 | 9230.38 | 15-SEP-15:10 |
| EnergyTransfer:Zone:RES DS RES AC ASYS RET AIR ZONE | 1.15 | 0.00 | 01-JAN-00:10 | 663.04 | 04-AUG-20:10 |
| Heating:EnergyTransfer:Zone:RES DS RES AC ASYS RET AIR ZONE | 1.15 | 0.00 | 01-JAN-00:10 | 663.04 | 04-AUG-20:10 |
| Cooling:EnergyTransfer:Zone:RES DS RES AC ASYS RET AIR ZONE | 0.00 | 0.00 | 01-JAN-00:10 | 14.86 | 17-SEP-07:50 |
| EnergyTransfer:Zone:RES DS RES FUR PROPANE ASYS RET AIR ZONE | 0.29 | 0.00 | 06-JAN-16:10 | 157.51 | 19-JAN-05:40 |
| Heating:EnergyTransfer:Zone:RES DS RES FUR PROPANE ASYS RET AIR ZONE | 0.02 | 0.00 | 01-JAN-00:10 | 35.70 | 27-JAN-16:30 |
| Cooling:EnergyTransfer:Zone:RES DS RES FUR PROPANE ASYS RET AIR ZONE | 0.28 | 0.00 | 01-JAN-16:10 | 157.51 | 19-JAN-05:40 |
| EnergyTransfer:Zone:UNFINISHED ATTIC ZONE | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| Heating:EnergyTransfer:Zone:UNFINISHED ATTIC ZONE | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| Cooling:EnergyTransfer:Zone:UNFINISHED ATTIC ZONE | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| EnergyTransfer:Zone:UNFINISHED BASEMENT ZONE | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| Heating:EnergyTransfer:Zone:UNFINISHED BASEMENT ZONE | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| Cooling:EnergyTransfer:Zone:UNFINISHED BASEMENT ZONE | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| EnergyTransfer:Plant | 18.27 | 0.00 | 01-JAN-00:10 | 38129.09 | 06-FEB-06:10 |
| WaterSystems:EnergyTransfer | 18.27 | 0.00 | 01-JAN-00:10 | 38129.09 | 06-FEB-06:10 |
| res shower:WaterSystems:EnergyTransfer | 8.93 | 0.00 | 01-JAN-00:10 | 38129.09 | 06-FEB-06:10 |
| res sink:WaterSystems:EnergyTransfer | 8.05 | 0.00 | 01-JAN-00:10 | 14221.52 | 08-FEB-18:10 |
| res bath:WaterSystems:EnergyTransfer | 0.53 | 0.00 | 01-JAN-00:10 | 17635.19 | 27-JAN-20:50 |
| General:WaterSystems:EnergyTransfer | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| res cw:WaterSystems:EnergyTransfer | 0.02 | 0.00 | 01-JAN-00:10 | 784.48 | 06-FEB-20:00 |
| res dw:WaterSystems:EnergyTransfer | 0.74 | 0.00 | 01-JAN-00:10 | 1678.86 | 09-FEB-06:00 |
| EnergyTransfer:HVAC | 94.81 | 0.00 | 06-JAN-16:10 | 13020.98 | 23-JAN-02:00 |
| CoolingCoils:EnergyTransfer | 37.10 | 0.00 | 01-JAN-00:10 | 11352.89 | 22-SEP-15:10 |
| HeatingCoils:EnergyTransfer | 57.71 | 0.00 | 06-JAN-16:10 | 13020.98 | 23-JAN-02:00 |
| Propane:Facility | 72.14 | 0.00 | 06-JAN-16:10 | 16276.23 | 23-JAN-02:00 |
| Propane:HVAC | 72.14 | 0.00 | 06-JAN-16:10 | 16276.23 | 23-JAN-02:00 |
| Heating:Propane | 72.14 | 0.00 | 06-JAN-16:10 | 16276.23 | 23-JAN-02:00 |
Report: Sensible Heat Gain Summary
For: Entire Facility
Timestamp: 2019-07-16 16:11:39
Annual Building Sensible Heat Gain Components| HVAC Zone Eq & Other Sensible Air Heating [GJ] | HVAC Zone Eq & Other Sensible Air Cooling [GJ] | HVAC Terminal Unit Sensible Air Heating [GJ] | HVAC Terminal Unit Sensible Air Cooling [GJ] | HVAC Input Heated Surface Heating [GJ] | HVAC Input Cooled Surface Cooling [GJ] | People Sensible Heat Addition [GJ] | Lights Sensible Heat Addition [GJ] | Equipment Sensible Heat Addition [GJ] | Window Heat Addition [GJ] | Interzone Air Transfer Heat Addition [GJ] | Infiltration Heat Addition [GJ] | Opaque Surface Conduction and Other Heat Addition [GJ] | Equipment Sensible Heat Removal [GJ] | Window Heat Removal [GJ] | Interzone Air Transfer Heat Removal [GJ] | Infiltration Heat Removal [GJ] | Opaque Surface Conduction and Other Heat Removal [GJ] | |
| LIVING ZONE | 0.000 | 0.000 | 59.755 | -28.667 | 0.000 | 0.000 | 4.519 | 12.016 | 25.839 | 12.108 | 0.066 | 1.178 | 0.000 | -3.826 | -17.011 | -0.267 | -26.572 | -39.138 |
| GARAGE ZONE | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.234 | 2.030 | 0.000 | 0.000 | 0.036 | 0.000 | 0.000 | 0.000 | 0.000 | -0.906 | -1.393 |
| RES DS RES AC ASYS RET AIR ZONE | 1.146 | -0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | -1.147 | 0.000 | 0.000 | 0.000 | -0.000 |
| RES DS RES FUR PROPANE ASYS RET AIR ZONE | 0.019 | -0.276 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.277 | 0.000 | 0.000 | 0.000 | 0.000 | -0.019 | 0.000 | 0.000 | 0.000 | -0.000 |
| UNFINISHED ATTIC ZONE | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 2.200 | 45.246 | 0.000 | 0.000 | 0.000 | -47.447 | -0.000 |
| UNFINISHED BASEMENT ZONE | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 13.357 | 0.000 | 0.000 | 0.588 | 0.000 | -8.160 | 0.000 | 0.000 | -4.600 | -1.184 |
| Total Facility | 1.165 | -0.276 | 59.755 | -28.667 | 0.000 | 0.000 | 4.519 | 12.251 | 41.503 | 12.108 | 0.066 | 4.002 | 45.247 | -13.152 | -17.011 | -0.267 | -79.525 | -41.716 |
| Time of Peak {TIMESTAMP} | HVAC Zone Eq & Other Sensible Air Heating [W] | HVAC Zone Eq & Other Sensible Air Cooling [W] | HVAC Terminal Unit Sensible Air Heating [W] | HVAC Terminal Unit Sensible Air Cooling [W] | HVAC Input Heated Surface Heating [W] | HVAC Input Cooled Surface Cooling [W] | People Sensible Heat Addition [W] | Lights Sensible Heat Addition [W] | Equipment Sensible Heat Addition [W] | Window Heat Addition [W] | Interzone Air Transfer Heat Addition [W] | Infiltration Heat Addition [W] | Opaque Surface Conduction and Other Heat Addition [W] | Equipment Sensible Heat Removal [W] | Window Heat Removal [W] | Interzone Air Transfer Heat Removal [W] | Infiltration Heat Removal [W] | Opaque Surface Conduction and Other Heat Removal [W] | |
| LIVING ZONE | 01-SEP-20:00 | 0.00 | -9290.92 | 0.00 | -0.00 | 0.00 | 0.00 | 187.46 | 806.52 | 7648.94 | 268.15 | 0.00 | 146.05 | 323.72 | 0.00 | -0.00 | -89.92 | 0.00 | 0.00 |
| GARAGE ZONE | - | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| RES DS RES AC ASYS RET AIR ZONE | 18-SEP-05:05 | 0.00 | -25.28 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 25.28 | 0.00 | -0.00 | 0.00 | 0.00 | 0.00 |
| RES DS RES FUR PROPANE ASYS RET AIR ZONE | 19-JAN-05:40 | 0.00 | -157.51 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 156.93 | 0.00 | 0.00 | 0.00 | 0.58 | 0.00 | -0.00 | 0.00 | 0.00 | 0.00 |
| UNFINISHED ATTIC ZONE | - | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| UNFINISHED BASEMENT ZONE | - | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total Facility | 01-SEP-20:00 | 0.00 | -8950.33 | 0.00 | 0.00 | 0.00 | 0.00 | 187.46 | 822.25 | 7728.35 | 268.15 | 0.00 | 242.27 | 3097.39 | -2462.92 | 0.00 | -89.92 | -842.70 | 0.00 |
| Time of Peak {TIMESTAMP} | HVAC Zone Eq & Other Sensible Air Heating [W] | HVAC Zone Eq & Other Sensible Air Cooling [W] | HVAC Terminal Unit Sensible Air Heating [W] | HVAC Terminal Unit Sensible Air Cooling [W] | HVAC Input Heated Surface Heating [W] | HVAC Input Cooled Surface Cooling [W] | People Sensible Heat Addition [W] | Lights Sensible Heat Addition [W] | Equipment Sensible Heat Addition [W] | Window Heat Addition [W] | Interzone Air Transfer Heat Addition [W] | Infiltration Heat Addition [W] | Opaque Surface Conduction and Other Heat Addition [W] | Equipment Sensible Heat Removal [W] | Window Heat Removal [W] | Interzone Air Transfer Heat Removal [W] | Infiltration Heat Removal [W] | Opaque Surface Conduction and Other Heat Removal [W] | |
| LIVING ZONE | 23-JAN-02:00 | 0.00 | 0.00 | 13562.12 | -0.00 | 0.00 | 0.00 | 208.29 | 74.70 | 0.00 | 0.00 | 34.28 | 0.00 | 0.00 | -2051.81 | -2647.49 | 0.00 | -5402.71 | -3777.39 |
| GARAGE ZONE | - | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| RES DS RES AC ASYS RET AIR ZONE | 07-JUL-15:10 | 718.30 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -505.02 | -0.00 | 0.00 | 0.00 | -213.27 |
| RES DS RES FUR PROPANE ASYS RET AIR ZONE | 27-JAN-16:25 | 57.91 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | 0.00 | 0.00 | -57.91 |
| UNFINISHED ATTIC ZONE | - | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| UNFINISHED BASEMENT ZONE | - | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total Facility | 23-JAN-02:00 | -141.69 | 0.00 | 13562.12 | 0.00 | 0.00 | 0.00 | 208.29 | 76.16 | 2899.10 | 0.00 | 34.28 | 0.00 | 0.00 | -2051.81 | -2647.49 | 0.00 | -6898.88 | -5040.08 |
Report: Standard 62.1 Summary
For: Entire Facility
Timestamp: 2019-07-16 16:11:39
System Ventilation Requirements for Cooling| Sum of Zone Primary Air Flow - Vpz-sum [m3/s] | System Population - Ps | Sum of Zone Population - Pz-sum | Occupant Diversity - D | Uncorrected Outdoor Air Intake Airflow - Vou [m3/s] | System Primary Airflow - Vps [m3/s] | Average Outdoor Air Fraction - Xs | System Ventilation Efficiency - Ev | Outdoor Air Intake Flow - Vot [m3/s] | Percent Outdoor Air - %OA | Environment Name of Peak System Population - Ps | Date and Time of Last Peak System Population - Ps | |
| RES AC ASYS | 0.6859 | 0.0000 | 3.2300 | 1.0000 | 0.0000 | 0.3791 | 0.0000 | 1.0000 | 0.0000 | 0.0000 | ||
| RES FUR PROPANE ASYS | 0.6859 | 0.0000 | 3.2300 | 1.0000 | 0.0000 | 0.3791 | 0.0000 | 1.0000 | 0.0000 | 0.0000 |
| Sum of Zone Primary Air Flow - Vpz-sum [m3/s] | System Population - Ps | Sum of Zone Population - Pz-sum | Occupant Diversity - D | Uncorrected Outdoor Air Intake Airflow - Vou [m3/s] | System Primary Airflow - Vps [m3/s] | Average Outdoor Air Fraction - Xs | System Ventilation Efficiency - Ev | Outdoor Air Intake Flow Vot [m3/s] | Percent Outdoor Air - %OA | Environment Name of Peak System Population - Ps | Date and Time of Last Peak System Population - Ps | |
| RES AC ASYS | 0.0000 | 0.0000 | 3.2300 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 | 0.0000 | |||
| RES FUR PROPANE ASYS | 0.0000 | 0.0000 | 3.2300 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 | 0.0000 |
| AirLoop Name | People Outdoor Air Rate - Rp [m3/s-person] | Zone Population - Pz | Area Outdoor Air Rate - Ra [m3/s-m2] | Zone Floor Area - Az [m2] | Breathing Zone Outdoor Airflow - Vbz [m3/s] | Cooling Zone Air Distribution Effectiveness - Ez-clg | Cooling Zone Outdoor Airflow - Voz-clg [m3/s] | Heating Zone Air Distribution Effectiveness - Ez-htg | Heating Zone Outdoor Airflow - Voz-htg [m3/s] | |
| LIVING ZONE | RES FUR PROPANE ASYS | 0.000000 | 3.2300 | 0.000000 | 418.06 | 0.0000 | 1.0000 | 0.0000 | 1.000 | 0.0000 |
| People Outdoor Air Rate - Rp [m3/s-person] | Sum of Zone Population - Pz-sum | Area Outdoor Air Rate - Ra [m3/s-m2] | Sum of Zone Floor Area - Az-sum [m2] | Breathing Zone Outdoor Airflow - Vbz [m3/s] | Cooling Zone Outdoor Airflow - Voz-clg [m3/s] | Heating Zone Outdoor Airflow - Voz-htg [m3/s] | |
| RES AC ASYS | 0.000000 | 3.23 | 0.000000 | 418.0637 | 0.0000 | 0.0000 | 0.0000 |
| RES FUR PROPANE ASYS | 0.000000 | 3.23 | 0.000000 | 418.0637 | 0.0000 | 0.0000 | 0.0000 |
| AirLoop Name | Box Type | Zone Primary Airflow - Vpz [m3/s] | Zone Discharge Airflow - Vdz [m3/s] | Minimum Zone Primary Airflow - Vpz-min [m3/s] | Zone Outdoor Airflow Cooling - Voz-clg [m3/s] | Primary Outdoor Air Fraction - Zpz | Primary Air Fraction - Ep | Secondary Recirculation Fraction- Er | Supply Air Fraction- Fa | Mixed Air Fraction - Fb | Outdoor Air Fraction - Fc | Zone Ventilation Efficiency - Evz | |
| LIVING ZONE | RES FUR PROPANE ASYS | AIRTERMINAL:SINGLEDUCT:CONSTANTVOLUME:NOREHEAT | 0.6859 | 0.6859 | 0.0000 | 0.0000 | 0.0000 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| Sum of Zone Primary Airflow - Vpz-sum [m3/s] | System Primary Airflow - Vps [m3/s] | Sum of Zone Discharge Airflow - Vdz-sum [m3/s] | Sum of Min Zone Primary Airflow - Vpz-min [m3/s] | Zone Outdoor Airflow Cooling - Voz-clg [m3/s] | Zone Ventilation Efficiency - Evz-min | |
| RES AC ASYS | 0.6859 | 0.3791 | 0.6859 | 0.0000 | 0.0000 | 1.0000 |
| RES FUR PROPANE ASYS | 0.6859 | 0.3791 | 0.6859 | 0.0000 | 0.0000 | 1.0000 |
| AirLoop Name | Box Type | Zone Primary Airflow - Vpz [m3/s] | Zone Discharge Airflow - Vdz [m3/s] | Minimum Zone Primary Airflow - Vpz-min [m3/s] | Zone Outdoor Airflow Heating - Voz-htg [m3/s] | Primary Outdoor Air Fraction - Zpz | Primary Air Fraction - Ep | Secondary Recirculation Fraction- Er | Supply Air Fraction- Fa | Mixed Air Fraction - Fb | Outdoor Air Fraction - Fc | Zone Ventilation Efficiency - Evz | |
| LIVING ZONE | RES FUR PROPANE ASYS | AIRTERMINAL:SINGLEDUCT:CONSTANTVOLUME:NOREHEAT | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| Sum of Zone Primary Airflow - Vpz-sum [m3/s] | System Primary Airflow - Vps [m3/s] | Sum of Zone Discharge Airflow - Vdz-sum [m3/s] | Sum of Min Zone Primary Airflow - Vpz-min [m3/s] | Zone Outdoor Airflow Heating - Voz-htg [m3/s] | Zone Ventilation Efficiency - Evz-min | |
| RES AC ASYS | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| RES FUR PROPANE ASYS | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
Report: LEED Summary
For: Entire Facility
Timestamp: 2019-07-16 16:11:39
Sec1.1A-General Information| Data | |
| Weather File | RUN PERIOD 1 ** Philadelphia International Ap PA USA TMY3 WMO#=724080 |
| Total gross floor area [m2] | 889.66 |
| Principal Heating Source | Additional Fuel |
| Space Area [m2] | Regularly Occupied Area [m2] | Unconditioned Area [m2] | Typical Hours/Week in Operation [hr/wk] | |
| LIVING ZONE | 418.06 | 418.06 | 0.00 | 168.00 |