Program Version:EnergyPlus, Version 9.1.0-fafb9d5652, YMD=2020.03.25 14:42
Tabular Output Report in Format: HTML
Building: Restaurant 10
Environment: RUN PERIOD 1 ** Buffalo Niagara Intl Ap NY USA TMY3 WMO#=725280
Simulation Timestamp: 2020-03-25 14:42:09
Report: Annual Building Utility Performance Summary
For: Entire Facility
Timestamp: 2020-03-25 14:42:09
Values gathered over 8760.00 hours| Total Energy [GJ] | Energy Per Total Building Area [MJ/m2] | Energy Per Conditioned Building Area [MJ/m2] | |
| Total Site Energy | 51377.66 | 4404.23 | 4404.23 |
| Net Site Energy | 51377.66 | 4404.23 | 4404.23 |
| Total Source Energy | 97379.33 | 8347.62 | 8347.62 |
| Net Source Energy | 97379.33 | 8347.62 | 8347.62 |
| Site=>Source Conversion Factor | |
| Electricity | 3.167 |
| Natural Gas | 1.084 |
| District Cooling | 1.056 |
| District Heating | 3.613 |
| Steam | 0.300 |
| Gasoline | 1.050 |
| Diesel | 1.050 |
| Coal | 1.050 |
| Fuel Oil #1 | 1.050 |
| Fuel Oil #2 | 1.050 |
| Propane | 1.050 |
| Other Fuel 1 | 1.000 |
| Other Fuel 2 | 1.000 |
| Area [m2] | |
| Total Building Area | 11665.53 |
| Net Conditioned Building Area | 11665.53 |
| Unconditioned Building Area | 0.00 |
| Electricity [GJ] | Natural Gas [GJ] | Additional Fuel [GJ] | District Cooling [GJ] | District Heating [GJ] | Water [m3] | |
| Heating | 0.00 | 5860.82 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | 3544.14 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 1962.18 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 713.69 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 10222.40 | 10723.85 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 1843.72 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 10.34 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 1715.99 | 14780.53 | 0.00 | 0.00 | 0.00 | 31561.28 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total End Uses | 20012.46 | 31365.20 | 0.00 | 0.00 | 0.00 | 31561.28 |
| Subcategory | Electricity [GJ] | Natural Gas [GJ] | Additional Fuel [GJ] | District Cooling [GJ] | District Heating [GJ] | Water [m3] | |
| Heating | General | 0.00 | 5860.82 | 0.00 | 0.00 | 0.00 | 0.00 |
| Boiler Parasitic | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Cooling | General | 3544.14 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | General | 1962.18 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | Building Facades | 9.57 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Main Entries | 13.38 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Other Doors | 13.38 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Parking Areas and Drives | 677.36 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Interior Equipment | Elevators | 691.10 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| General | 9531.31 | 10723.85 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Exterior Equipment | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | General | 1843.72 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | General | 10.34 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | Booster | 1715.99 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| General | 0.00 | 14780.53 | 0.00 | 0.00 | 0.00 | 31561.28 | |
| Refrigeration | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Electricity Intensity [MJ/m2] | Natural Gas Intensity [MJ/m2] | Additional Fuel Intensity [MJ/m2] | District Cooling Intensity [MJ/m2] | District Heating Intensity [MJ/m2] | Water Intensity [m3/m2] | |
| Lighting | 229.38 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| HVAC | 609.85 | 1769.43 | 0.00 | 0.00 | 0.00 | 2.71 |
| Other | 876.29 | 919.28 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total | 1715.52 | 2688.71 | 0.00 | 0.00 | 0.00 | 2.71 |
| Electricity Intensity [MJ/m2] | Natural Gas Intensity [MJ/m2] | Additional Fuel Intensity [MJ/m2] | District Cooling Intensity [MJ/m2] | District Heating Intensity [MJ/m2] | Water Intensity [m3/m2] | |
| Lighting | 229.38 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| HVAC | 609.85 | 1769.43 | 0.00 | 0.00 | 0.00 | 2.71 |
| Other | 876.29 | 919.28 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total | 1715.52 | 2688.71 | 0.00 | 0.00 | 0.00 | 2.71 |
| Electricity [GJ] | Percent Electricity [%] | |
| Fuel-Fired Power Generation | 0.000 | 0.00 |
| High Temperature Geothermal* | 0.000 | 0.00 |
| Photovoltaic Power | 0.000 | 0.00 |
| Wind Power | 0.000 | 0.00 |
| Power Conversion | 0.000 | 0.00 |
| Net Decrease in On-Site Storage | 0.000 | 0.00 |
| Total On-Site Electric Sources | 0.000 | 0.00 |
| Electricity Coming From Utility | 20012.456 | 100.00 |
| Surplus Electricity Going To Utility | 0.000 | 0.00 |
| Net Electricity From Utility | 20012.456 | 100.00 |
| Total On-Site and Utility Electric Sources | 20012.456 | 100.00 |
| Total Electricity End Uses | 20012.456 | 100.00 |
| Heat [GJ] | Percent Heat [%] | |
| Water-Side Heat Recovery | 0.00 | |
| Air to Air Heat Recovery for Cooling | 0.00 | |
| Air to Air Heat Recovery for Heating | 0.00 | |
| High-Temperature Geothermal* | 0.00 | |
| Solar Water Thermal | 0.00 | |
| Solar Air Thermal | 0.00 | |
| Total On-Site Thermal Sources | 0.00 |
| Water [m3] | Percent Water [%] | |
| Rainwater Collection | 0.00 | 0.00 |
| Condensate Collection | 0.00 | 0.00 |
| Groundwater Well | 0.00 | 0.00 |
| Total On Site Water Sources | 0.00 | 0.00 |
| - | - | - |
| Initial Storage | 0.00 | 0.00 |
| Final Storage | 0.00 | 0.00 |
| Change in Storage | 0.00 | 0.00 |
| - | - | - |
| Water Supplied by Utility | 31561.28 | 100.00 |
| - | - | - |
| Total On Site, Change in Storage, and Utility Water Sources | 31561.28 | 100.00 |
| Total Water End Uses | 31561.28 | 100.00 |
| Degrees [deltaC] | |
| Tolerance for Zone Heating Setpoint Not Met Time | 0.56 |
| Tolerance for Zone Cooling Setpoint Not Met Time | 0.56 |
| Facility [Hours] | |
| Time Setpoint Not Met During Occupied Heating | 0.00 |
| Time Setpoint Not Met During Occupied Cooling | 0.00 |
| Time Not Comfortable Based on Simple ASHRAE 55-2004 | 555.00 |
Table of Contents
TopBUILDING ENERGY PERFORMANCE - ELECTRICITY
| Meter |BUILDING ENERGY PERFORMANCE - NATURAL GAS
| Meter |BUILDING ENERGY PERFORMANCE - ELECTRICITY PEAK DEMAND
| Meter |BUILDING ENERGY PERFORMANCE - NATURAL GAS PEAK DEMAND
| Meter |Life-Cycle Cost Report
| Entire Facility |Report: Input Verification and Results Summary
For: Entire Facility
Timestamp: 2020-03-25 14:42:09
General| Value | |
| Program Version and Build | EnergyPlus, Version 9.1.0-fafb9d5652, YMD=2020.03.25 14:42 |
| RunPeriod | RUN PERIOD 1 |
| Weather File | Buffalo Niagara Intl Ap NY USA TMY3 WMO#=725280 |
| Latitude [deg] | 42.93 |
| Longitude [deg] | -78.7 |
| Elevation [m] | 215.00 |
| Time Zone | -5.0 |
| North Axis Angle [deg] | 0.00 |
| Rotation for Appendix G [deg] | 0.00 |
| Hours Simulated [hrs] | 8760.00 |
| Total | North (315 to 45 deg) | East (45 to 135 deg) | South (135 to 225 deg) | West (225 to 315 deg) | |
| Gross Wall Area [m2] | 3012.62 | 250.88 | 1255.42 | 250.89 | 1255.42 |
| Above Ground Wall Area [m2] | 3012.62 | 250.88 | 1255.42 | 250.89 | 1255.42 |
| Window Opening Area [m2] | 903.79 | 75.27 | 376.63 | 75.27 | 376.63 |
| Gross Window-Wall Ratio [%] | 30.00 | 30.00 | 30.00 | 30.00 | 30.00 |
| Above Ground Window-Wall Ratio [%] | 30.00 | 30.00 | 30.00 | 30.00 | 30.00 |
| Total | North (315 to 45 deg) | East (45 to 135 deg) | South (135 to 225 deg) | West (225 to 315 deg) | |
| Gross Wall Area [m2] | 3012.62 | 250.88 | 1255.42 | 250.89 | 1255.42 |
| Above Ground Wall Area [m2] | 3012.62 | 250.88 | 1255.42 | 250.89 | 1255.42 |
| Window Opening Area [m2] | 903.79 | 75.27 | 376.63 | 75.27 | 376.63 |
| Gross Window-Wall Ratio [%] | 30.00 | 30.00 | 30.00 | 30.00 | 30.00 |
| Above Ground Window-Wall Ratio [%] | 30.00 | 30.00 | 30.00 | 30.00 | 30.00 |
| Total | |
| Gross Roof Area [m2] | 3888.51 |
| Skylight Area [m2] | 0.00 |
| Skylight-Roof Ratio [%] | 0.00 |
| Area [m2] | Conditioned (Y/N) | Part of Total Floor Area (Y/N) | Volume [m3] | Multipliers | Above Ground Gross Wall Area [m2] | Underground Gross Wall Area [m2] | Window Glass Area [m2] | Opening Area [m2] | Lighting [W/m2] | People [m2 per person] | Plug and Process [W/m2] | |
| BUILDING STORY 1 THERMALZONE | 3888.51 | Yes | Yes | 11665.53 | 1.00 | 1004.21 | 0.00 | 301.26 | 301.26 | 9.5799 | 1.33 | 64.9279 |
| BUILDING STORY 2 THERMALZONE | 3888.51 | Yes | Yes | 11665.53 | 1.00 | 1004.21 | 0.00 | 301.26 | 301.26 | 9.5799 | 1.33 | 64.9279 |
| BUILDING STORY 3 THERMALZONE | 3888.51 | Yes | Yes | 11665.53 | 1.00 | 1004.21 | 0.00 | 301.26 | 301.26 | 12.3988 | 5.53 | 911.0297 |
| Total | 11665.53 | 34996.58 | 3012.62 | 0.00 | 903.79 | 903.79 | 10.5195 | 1.78 | 346.9618 | |||
| Conditioned Total | 11665.53 | 34996.58 | 3012.62 | 0.00 | 903.79 | 903.79 | 10.5195 | 1.78 | 346.9618 | |||
| Unconditioned Total | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | ||||||
| Not Part of Total | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
Report: Demand End Use Components Summary
For: Entire Facility
Timestamp: 2020-03-25 14:42:09
End Uses| Electricity [W] | Natural Gas [W] | Propane [W] | District Cooling [W] | Steam [W] | Water [m3/s] | |
| Time of Peak | 27-JUN-10:00 | 06-FEB-10:00 | - | - | - | 15-JAN-07:00 |
| Heating | 0.00 | 1288175.05 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | 528348.07 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 89524.82 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 586855.65 | 537194.43 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 81041.69 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 3.11 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 80826.51 | 655643.20 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total End Uses | 1366599.85 | 2481012.69 | 0.00 | 0.00 | 0.00 | 0.00 |
| Subcategory | Electricity [W] | Natural Gas [W] | Propane [W] | District Cooling [W] | Steam [W] | Water [m3/s] | |
| Heating | General | 0.00 | 1288175.05 | 0.00 | 0.00 | 0.00 | 0.00 |
| Boiler Parasitic | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Cooling | General | 528348.07 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | General | 89524.82 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | Building Facades | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Main Entries | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Other Doors | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Parking Areas and Drives | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Interior Equipment | Elevators | 54308.61 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| General | 532547.04 | 537194.43 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Exterior Equipment | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | General | 81041.69 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | General | 3.11 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | Booster | 80826.51 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| General | 0.00 | 655643.20 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Refrigeration | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
Report: Source Energy End Use Components Summary
For: Entire Facility
Timestamp: 2020-03-25 14:42:09
Values gathered over 8760.00 hours| Source Electricity [GJ] | Source Natural Gas [GJ] | Source Additional Fuel [GJ] | Source District Cooling [GJ] | Source District Heating [GJ] | |
| Heating | 0.00 | 6353.13 | 0.00 | 0.00 | 0.00 |
| Cooling | 11224.28 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 6214.22 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 2260.26 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 32374.35 | 11624.65 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 5839.05 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 32.74 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 5434.54 | 16022.09 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total Source Energy End Use Components | 63379.45 | 33999.88 | 0.00 | 0.00 | 0.00 |
| Source Electricity [MJ/m2] | Source Natural Gas [MJ/m2] | Source Additional Fuel [MJ/m2] | Source District Cooling [MJ/m2] | Source District Heating [MJ/m2] | |
| Heating | 0.00 | 544.61 | 0.00 | 0.00 | 0.00 |
| Cooling | 962.18 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 532.70 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 193.76 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 2775.22 | 996.50 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 500.54 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 2.81 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 465.86 | 1373.46 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total Source Energy End Use Components | 5433.06 | 2914.56 | 0.00 | 0.00 | 0.00 |
| Source Electricity [MJ/m2] | Source Natural Gas [MJ/m2] | Source Additional Fuel [MJ/m2] | Source District Cooling [MJ/m2] | Source District Heating [MJ/m2] | |
| Heating | 0.00 | 544.61 | 0.00 | 0.00 | 0.00 |
| Cooling | 962.18 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 532.70 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 193.76 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 2775.22 | 996.50 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 500.54 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 2.81 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 465.86 | 1373.46 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total Source Energy End Use Components | 5433.06 | 2914.56 | 0.00 | 0.00 | 0.00 |
Report: Component Sizing Summary
For: Entire Facility
Timestamp: 2020-03-25 14:42:09
AirTerminal:SingleDuct:VAV:Reheat| Design Size Maximum Air Flow Rate [m3/s] | Design Size Constant Minimum Air Flow Fraction | User-Specified Constant Minimum Air Flow Fraction | Design Size Minimum Air Flow Rate [m3/s] | Design Size Maximum Flow Fraction during Reheat [] | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | Design Size Maximum Reheat Water Flow Rate [m3/s] | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | |
| BUILDING STORY 1 THERMALZONE VAV TERMINAL | 29.31 | 0.101088 | 0.700000 | 20.52 | 0.700000 | 0.005277 | 0.005336 | 20.52 | 12.78 | 0.008000 |
| BUILDING STORY 2 THERMALZONE VAV TERMINAL | 33.64 | 0.088088 | 0.700000 | 23.55 | 0.700000 | 0.006055 | 0.006281 | 23.55 | 12.78 | 0.008000 |
| BUILDING STORY 3 THERMALZONE VAV TERMINAL | 38.22 | 0.077523 | 0.700000 | 26.76 | 0.700000 | 0.006881 | 0.007314 | 26.76 | 12.78 | 0.008000 |
| Design Size Rated Capacity [W] | Design Size Maximum Water Flow Rate [m3/s] | Design Size U-Factor Times Area Value [W/K] | |
| BUILDING STORY 1 THERMALZONE REHEAT COIL | 243940.06 | 0.005336 | 4329.25 |
| BUILDING STORY 2 THERMALZONE REHEAT COIL | 287148.75 | 0.006281 | 5113.66 |
| BUILDING STORY 3 THERMALZONE REHEAT COIL | 334401.84 | 0.007314 | 5975.61 |
| 1 ZONE PVAV MAIN HTG COIL | 301624.11 | 0.006597 | 3962.86 |
| 1 ZONE PVAV 1 MAIN HTG COIL | 346138.08 | 0.007571 | 4547.70 |
| 1 ZONE PVAV 2 MAIN HTG COIL | 167637.73 | 0.003667 | 2496.62 |
| Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | Sum of Air Terminal Maximum Flow Rates [m3/s] | Adjusted Heating Design Air Flow Rate [m3/s] | Adjusted Cooling Design Air Flow Rate [m3/s] | Adjusted Main Design Air Flow Rate [m3/s] | User Heating Air Flow Ratio [] | Calculated Heating Air Flow Ratio [] | Design Supply Air Flow Rate [m3/s] | |
| 1 ZONE PVAV | 20.52 | 20.52 | 29.31 | 20.52 | 29.31 | 29.31 | 0.300000 | 0.700000 | 29.31 |
| 1 ZONE PVAV 1 | 23.55 | 23.55 | 33.64 | 23.55 | 33.64 | 33.64 | 0.300000 | 0.700000 | 33.64 |
| 1 ZONE PVAV 2 | 26.76 | 26.76 | 38.22 | 26.76 | 38.22 | 38.22 | 0.300000 | 0.700000 | 38.22 |
| Maximum Outdoor Air Flow Rate [m3/s] | Minimum Outdoor Air Flow Rate [m3/s] | |
| CONTROLLER OUTDOOR AIR 1 | 29.31 | |
| CONTROLLER OUTDOOR AIR 2 | 33.64 | |
| CONTROLLER OUTDOOR AIR 3 | 38.22 | 6.05 |
| Design Size High Speed Rated Air Flow Rate [m3/s] | Design Size High Speed Gross Rated Total Cooling Capacity [W] | Design Size High Speed Rated Sensible Heat Ratio | Design Size Low Speed Rated Air Flow Rate [m3/s] | Design Size Low Speed Gross Rated Total Cooling Capacity [W] | User-Specified Low Speed Gross Rated Sensible Heat Ratio | |
| 1 ZONE PVAV 2SPD DX CLG COIL 2214KBTU/HR 9.5EER | 29.31 | 727874.55 | 0.698083 | 9.77 | 242600.59 | 0.690000 |
| 1 ZONE PVAV 1 2SPD DX CLG COIL 2625KBTU/HR 9.5EER | 33.64 | 835294.97 | 0.698083 | 11.21 | 278403.81 | 0.690000 |
| 1 ZONE PVAV 2 2SPD DX CLG COIL 2996KBTU/HR 9.5EER | 38.22 | 949135.58 | 0.698083 | 12.74 | 316346.89 | 0.690000 |
| Design Size Maximum Flow Rate [m3/s] | |
| 1 ZONE PVAV FAN | 29.31 |
| 1 ZONE PVAV 1 FAN | 33.64 |
| 1 ZONE PVAV 2 FAN | 38.22 |
| Maximum Actuated Flow [m3/s] | |
| 1 ZONE PVAV MAIN HTG COIL CONTROLLER | 0.006597 |
| 1 ZONE PVAV 1 MAIN HTG COIL CONTROLLER | 0.007571 |
| 1 ZONE PVAV 2 MAIN HTG COIL CONTROLLER | 0.003667 |
| Maximum Loop Flow Rate [m3/s] | Plant Loop Volume [m3] | |
| FULLSERVICERESTAURANT KITCHEN - 90.1-2013 SERVICE WATER BOOSTER LOOP | 0.001916 | 0.229909 |
| FULLSERVICERESTAURANT KITCHEN - 90.1-2013 SERVICE WATER LOOP | 0.014050 | 1.69 |
| HOT WATER LOOP | 0.036766 | 4.41 |
| Design Flow Rate [m3/s] | Design Power Consumption [W] | |
| BOOSTER WATER LOOP PUMP | 0.001916 | |
| FULLSERVICERESTAURANT KITCHEN - 90.1-2013 SERVICE WATER LOOP WATER MAINS PRESSURE DRIVEN | 0.014050 | 0.000026 |
| HOT WATER LOOP PUMP | 0.036766 | 9148.82 |
| Loop Supply Side Design Fluid Flow Rate [m3/s] | Loop Demand Side Design Fluid Flow Rate [m3/s] | Heat Exchanger U-Factor Times Area Value [W/C] | Loop-to-loop Temperature Difference Used to Size Heat Exchanger U-Factor Times Area Value [C] | |
| HX FOR BOOSTER WATER HEATING | 0.001916 | 0.001916 | 2334.78 | 17.22 |
| Use Side Design Flow Rate [m3/s] | |
| 6.0GAL ELECTRICITY BOOSTER WATER HEATER - 367KBTU/HR 1.0 THERM EFF | 0.001916 |
| 1913GAL NATURALGAS WATER HEATER - 1913KBTU/HR 0.802 THERM EFF | 0.014050 |
| Design Size Design Fluid Flow Rate [m3/s] | |
| MAINS WATER MAKEUP FOR SWH BOOSTER | 0.010857 |
| Design Size Nominal Capacity [W] | Design Size Design Water Flow Rate [m3/s] | |
| BOILER 5353KBTU/HR 0.8 THERMAL EFF | 1680890.57 | 0.036766 |
Report: Surface Shadowing Summary
For: Entire Facility
Timestamp: 2020-03-25 14:42:09
Surfaces (Walls, Roofs, etc) that may be Shadowed by Other Surfaces| Possible Shadow Receivers | |
| Mir-SHADING SURFACE 1 | Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 4 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 6 | Mir-SHADING SURFACE 10 | Mir-SHADING SURFACE 11 | Mir-SHADING SURFACE 12 | Mir-SHADING SURFACE 8 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 14 | Mir-SHADING SURFACE 15 | Mir-SHADING SURFACE 16 | Mir-SHADING SURFACE 17 | Mir-SHADING SURFACE 18 | Mir-SHADING SURFACE 20 | Mir-SHADING SURFACE 21 | Mir-SHADING SURFACE 22 | Mir-SHADING SURFACE 23 | Mir-SHADING SURFACE 24 | Mir-SHADING SURFACE 26 | Mir-SHADING SURFACE 27 | Mir-SHADING SURFACE 28 | Mir-SHADING SURFACE 29 | Mir-SHADING SURFACE 30 | |
| Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 4 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 6 | Mir-SHADING SURFACE 10 | Mir-SHADING SURFACE 11 | Mir-SHADING SURFACE 12 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 15 | Mir-SHADING SURFACE 16 | Mir-SHADING SURFACE 17 | Mir-SHADING SURFACE 18 | Mir-SHADING SURFACE 21 | Mir-SHADING SURFACE 22 | Mir-SHADING SURFACE 23 | Mir-SHADING SURFACE 24 | Mir-SHADING SURFACE 27 | Mir-SHADING SURFACE 28 | Mir-SHADING SURFACE 29 | Mir-SHADING SURFACE 30 | |
| Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 4 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 6 | Mir-SHADING SURFACE 10 | Mir-SHADING SURFACE 11 | Mir-SHADING SURFACE 12 | Mir-SHADING SURFACE 8 | Mir-SHADING SURFACE 14 | Mir-SHADING SURFACE 16 | Mir-SHADING SURFACE 17 | Mir-SHADING SURFACE 18 | Mir-SHADING SURFACE 20 | Mir-SHADING SURFACE 22 | Mir-SHADING SURFACE 23 | Mir-SHADING SURFACE 24 | Mir-SHADING SURFACE 26 | Mir-SHADING SURFACE 28 | Mir-SHADING SURFACE 29 | Mir-SHADING SURFACE 30 | |
| Mir-SHADING SURFACE 4 | Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 6 | Mir-SHADING SURFACE 11 | Mir-SHADING SURFACE 12 | Mir-SHADING SURFACE 8 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 14 | Mir-SHADING SURFACE 15 | Mir-SHADING SURFACE 17 | Mir-SHADING SURFACE 18 | Mir-SHADING SURFACE 20 | Mir-SHADING SURFACE 21 | Mir-SHADING SURFACE 23 | Mir-SHADING SURFACE 24 | Mir-SHADING SURFACE 26 | Mir-SHADING SURFACE 27 | Mir-SHADING SURFACE 29 | Mir-SHADING SURFACE 30 | |
| Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 4 | Mir-SHADING SURFACE 6 | Mir-SHADING SURFACE 10 | Mir-SHADING SURFACE 12 | Mir-SHADING SURFACE 8 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 14 | Mir-SHADING SURFACE 15 | Mir-SHADING SURFACE 16 | Mir-SHADING SURFACE 18 | Mir-SHADING SURFACE 20 | Mir-SHADING SURFACE 21 | Mir-SHADING SURFACE 22 | Mir-SHADING SURFACE 24 | Mir-SHADING SURFACE 26 | Mir-SHADING SURFACE 27 | Mir-SHADING SURFACE 28 | Mir-SHADING SURFACE 30 | |
| Mir-SHADING SURFACE 10 | Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 6 | Mir-SHADING SURFACE 11 | Mir-SHADING SURFACE 12 | Mir-SHADING SURFACE 8 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 14 | Mir-SHADING SURFACE 15 | Mir-SHADING SURFACE 17 | Mir-SHADING SURFACE 18 | Mir-SHADING SURFACE 20 | Mir-SHADING SURFACE 21 | Mir-SHADING SURFACE 23 | Mir-SHADING SURFACE 24 | Mir-SHADING SURFACE 26 | Mir-SHADING SURFACE 27 | Mir-SHADING SURFACE 29 | Mir-SHADING SURFACE 30 | |
| Mir-SHADING SURFACE 11 | Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 4 | Mir-SHADING SURFACE 6 | Mir-SHADING SURFACE 10 | Mir-SHADING SURFACE 12 | Mir-SHADING SURFACE 8 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 14 | Mir-SHADING SURFACE 15 | Mir-SHADING SURFACE 16 | Mir-SHADING SURFACE 18 | Mir-SHADING SURFACE 20 | Mir-SHADING SURFACE 21 | Mir-SHADING SURFACE 22 | Mir-SHADING SURFACE 24 | Mir-SHADING SURFACE 26 | Mir-SHADING SURFACE 27 | Mir-SHADING SURFACE 28 | Mir-SHADING SURFACE 30 | |
| SHADING SURFACE 12 | Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 4 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 6 | |
| Mir-SHADING SURFACE 12 | Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 4 | Mir-SHADING SURFACE 5 | |
| Mir-SHADING SURFACE 7 | Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 4 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 6 | Mir-SHADING SURFACE 10 | Mir-SHADING SURFACE 11 | Mir-SHADING SURFACE 12 | Mir-SHADING SURFACE 8 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 14 | Mir-SHADING SURFACE 15 | Mir-SHADING SURFACE 16 | Mir-SHADING SURFACE 17 | Mir-SHADING SURFACE 18 | Mir-SHADING SURFACE 20 | Mir-SHADING SURFACE 21 | Mir-SHADING SURFACE 22 | Mir-SHADING SURFACE 23 | Mir-SHADING SURFACE 24 | Mir-SHADING SURFACE 26 | Mir-SHADING SURFACE 27 | Mir-SHADING SURFACE 28 | Mir-SHADING SURFACE 29 | Mir-SHADING SURFACE 30 | |
| Mir-SHADING SURFACE 8 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 4 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 6 | Mir-SHADING SURFACE 10 | Mir-SHADING SURFACE 11 | Mir-SHADING SURFACE 12 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 15 | Mir-SHADING SURFACE 16 | Mir-SHADING SURFACE 17 | Mir-SHADING SURFACE 18 | Mir-SHADING SURFACE 21 | Mir-SHADING SURFACE 22 | Mir-SHADING SURFACE 23 | Mir-SHADING SURFACE 24 | Mir-SHADING SURFACE 27 | Mir-SHADING SURFACE 28 | Mir-SHADING SURFACE 29 | Mir-SHADING SURFACE 30 | |
| Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 4 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 6 | Mir-SHADING SURFACE 10 | Mir-SHADING SURFACE 11 | Mir-SHADING SURFACE 12 | Mir-SHADING SURFACE 8 | Mir-SHADING SURFACE 14 | Mir-SHADING SURFACE 16 | Mir-SHADING SURFACE 17 | Mir-SHADING SURFACE 18 | Mir-SHADING SURFACE 20 | Mir-SHADING SURFACE 22 | Mir-SHADING SURFACE 23 | Mir-SHADING SURFACE 24 | Mir-SHADING SURFACE 26 | Mir-SHADING SURFACE 28 | Mir-SHADING SURFACE 29 | Mir-SHADING SURFACE 30 | |
| Mir-SHADING SURFACE 13 | Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 4 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 6 | Mir-SHADING SURFACE 10 | Mir-SHADING SURFACE 11 | Mir-SHADING SURFACE 12 | Mir-SHADING SURFACE 8 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 14 | Mir-SHADING SURFACE 15 | Mir-SHADING SURFACE 16 | Mir-SHADING SURFACE 17 | Mir-SHADING SURFACE 18 | Mir-SHADING SURFACE 20 | Mir-SHADING SURFACE 21 | Mir-SHADING SURFACE 22 | Mir-SHADING SURFACE 23 | Mir-SHADING SURFACE 24 | Mir-SHADING SURFACE 26 | Mir-SHADING SURFACE 27 | Mir-SHADING SURFACE 28 | Mir-SHADING SURFACE 29 | Mir-SHADING SURFACE 30 | |
| Mir-SHADING SURFACE 14 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 4 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 6 | Mir-SHADING SURFACE 10 | Mir-SHADING SURFACE 11 | Mir-SHADING SURFACE 12 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 15 | Mir-SHADING SURFACE 16 | Mir-SHADING SURFACE 17 | Mir-SHADING SURFACE 18 | Mir-SHADING SURFACE 21 | Mir-SHADING SURFACE 22 | Mir-SHADING SURFACE 23 | Mir-SHADING SURFACE 24 | Mir-SHADING SURFACE 27 | Mir-SHADING SURFACE 28 | Mir-SHADING SURFACE 29 | Mir-SHADING SURFACE 30 | |
| Mir-SHADING SURFACE 15 | Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 4 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 6 | Mir-SHADING SURFACE 10 | Mir-SHADING SURFACE 11 | Mir-SHADING SURFACE 12 | Mir-SHADING SURFACE 8 | Mir-SHADING SURFACE 14 | Mir-SHADING SURFACE 16 | Mir-SHADING SURFACE 17 | Mir-SHADING SURFACE 18 | Mir-SHADING SURFACE 20 | Mir-SHADING SURFACE 22 | Mir-SHADING SURFACE 23 | Mir-SHADING SURFACE 24 | Mir-SHADING SURFACE 26 | Mir-SHADING SURFACE 28 | Mir-SHADING SURFACE 29 | Mir-SHADING SURFACE 30 | |
| Mir-SHADING SURFACE 16 | Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 6 | Mir-SHADING SURFACE 11 | Mir-SHADING SURFACE 12 | Mir-SHADING SURFACE 8 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 14 | Mir-SHADING SURFACE 15 | Mir-SHADING SURFACE 17 | Mir-SHADING SURFACE 18 | Mir-SHADING SURFACE 20 | Mir-SHADING SURFACE 21 | Mir-SHADING SURFACE 23 | Mir-SHADING SURFACE 24 | Mir-SHADING SURFACE 26 | Mir-SHADING SURFACE 27 | Mir-SHADING SURFACE 29 | Mir-SHADING SURFACE 30 | |
| Mir-SHADING SURFACE 17 | Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 4 | Mir-SHADING SURFACE 6 | Mir-SHADING SURFACE 10 | Mir-SHADING SURFACE 12 | Mir-SHADING SURFACE 8 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 14 | Mir-SHADING SURFACE 15 | Mir-SHADING SURFACE 16 | Mir-SHADING SURFACE 18 | Mir-SHADING SURFACE 20 | Mir-SHADING SURFACE 21 | Mir-SHADING SURFACE 22 | Mir-SHADING SURFACE 24 | Mir-SHADING SURFACE 26 | Mir-SHADING SURFACE 27 | Mir-SHADING SURFACE 28 | Mir-SHADING SURFACE 30 | |
| SHADING SURFACE 18 | Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 4 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 6 | Mir-SHADING SURFACE 10 | Mir-SHADING SURFACE 11 | Mir-SHADING SURFACE 12 | Mir-SHADING SURFACE 8 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 26 | Mir-SHADING SURFACE 27 | Mir-SHADING SURFACE 28 | Mir-SHADING SURFACE 29 | Mir-SHADING SURFACE 30 | |
| Mir-SHADING SURFACE 18 | Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 4 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 10 | Mir-SHADING SURFACE 11 | Mir-SHADING SURFACE 8 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 26 | Mir-SHADING SURFACE 27 | Mir-SHADING SURFACE 28 | Mir-SHADING SURFACE 29 | |
| Mir-SHADING SURFACE 19 | Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 4 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 6 | Mir-SHADING SURFACE 10 | Mir-SHADING SURFACE 11 | Mir-SHADING SURFACE 12 | Mir-SHADING SURFACE 8 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 14 | Mir-SHADING SURFACE 15 | Mir-SHADING SURFACE 16 | Mir-SHADING SURFACE 17 | Mir-SHADING SURFACE 18 | Mir-SHADING SURFACE 20 | Mir-SHADING SURFACE 21 | Mir-SHADING SURFACE 22 | Mir-SHADING SURFACE 23 | Mir-SHADING SURFACE 24 | Mir-SHADING SURFACE 26 | Mir-SHADING SURFACE 27 | Mir-SHADING SURFACE 28 | Mir-SHADING SURFACE 29 | Mir-SHADING SURFACE 30 | |
| Mir-SHADING SURFACE 20 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 4 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 6 | Mir-SHADING SURFACE 10 | Mir-SHADING SURFACE 11 | Mir-SHADING SURFACE 12 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 15 | Mir-SHADING SURFACE 16 | Mir-SHADING SURFACE 17 | Mir-SHADING SURFACE 18 | Mir-SHADING SURFACE 21 | Mir-SHADING SURFACE 22 | Mir-SHADING SURFACE 23 | Mir-SHADING SURFACE 24 | Mir-SHADING SURFACE 27 | Mir-SHADING SURFACE 28 | Mir-SHADING SURFACE 29 | Mir-SHADING SURFACE 30 | |
| Mir-SHADING SURFACE 21 | Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 4 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 6 | Mir-SHADING SURFACE 10 | Mir-SHADING SURFACE 11 | Mir-SHADING SURFACE 12 | Mir-SHADING SURFACE 8 | Mir-SHADING SURFACE 14 | Mir-SHADING SURFACE 16 | Mir-SHADING SURFACE 17 | Mir-SHADING SURFACE 18 | Mir-SHADING SURFACE 20 | Mir-SHADING SURFACE 22 | Mir-SHADING SURFACE 23 | Mir-SHADING SURFACE 24 | Mir-SHADING SURFACE 26 | Mir-SHADING SURFACE 28 | Mir-SHADING SURFACE 29 | Mir-SHADING SURFACE 30 | |
| Mir-SHADING SURFACE 22 | Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 6 | Mir-SHADING SURFACE 11 | Mir-SHADING SURFACE 12 | Mir-SHADING SURFACE 8 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 14 | Mir-SHADING SURFACE 15 | Mir-SHADING SURFACE 17 | Mir-SHADING SURFACE 18 | Mir-SHADING SURFACE 20 | Mir-SHADING SURFACE 21 | Mir-SHADING SURFACE 23 | Mir-SHADING SURFACE 24 | Mir-SHADING SURFACE 26 | Mir-SHADING SURFACE 27 | Mir-SHADING SURFACE 29 | Mir-SHADING SURFACE 30 | |
| Mir-SHADING SURFACE 23 | Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 4 | Mir-SHADING SURFACE 6 | Mir-SHADING SURFACE 10 | Mir-SHADING SURFACE 12 | Mir-SHADING SURFACE 8 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 14 | Mir-SHADING SURFACE 15 | Mir-SHADING SURFACE 16 | Mir-SHADING SURFACE 18 | Mir-SHADING SURFACE 20 | Mir-SHADING SURFACE 21 | Mir-SHADING SURFACE 22 | Mir-SHADING SURFACE 24 | Mir-SHADING SURFACE 26 | Mir-SHADING SURFACE 27 | Mir-SHADING SURFACE 28 | Mir-SHADING SURFACE 30 | |
| SHADING SURFACE 24 | Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 4 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 6 | Mir-SHADING SURFACE 10 | Mir-SHADING SURFACE 11 | Mir-SHADING SURFACE 12 | Mir-SHADING SURFACE 8 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 26 | Mir-SHADING SURFACE 27 | Mir-SHADING SURFACE 28 | Mir-SHADING SURFACE 29 | Mir-SHADING SURFACE 30 | |
| Mir-SHADING SURFACE 24 | Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 4 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 10 | Mir-SHADING SURFACE 11 | Mir-SHADING SURFACE 8 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 26 | Mir-SHADING SURFACE 27 | Mir-SHADING SURFACE 28 | Mir-SHADING SURFACE 29 | |
| Mir-SHADING SURFACE 25 | Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 4 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 6 | Mir-SHADING SURFACE 10 | Mir-SHADING SURFACE 11 | Mir-SHADING SURFACE 12 | Mir-SHADING SURFACE 8 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 14 | Mir-SHADING SURFACE 15 | Mir-SHADING SURFACE 16 | Mir-SHADING SURFACE 17 | Mir-SHADING SURFACE 18 | Mir-SHADING SURFACE 20 | Mir-SHADING SURFACE 21 | Mir-SHADING SURFACE 22 | Mir-SHADING SURFACE 23 | Mir-SHADING SURFACE 24 | Mir-SHADING SURFACE 26 | Mir-SHADING SURFACE 27 | Mir-SHADING SURFACE 28 | Mir-SHADING SURFACE 29 | Mir-SHADING SURFACE 30 | |
| Mir-SHADING SURFACE 26 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 4 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 6 | Mir-SHADING SURFACE 10 | Mir-SHADING SURFACE 11 | Mir-SHADING SURFACE 12 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 15 | Mir-SHADING SURFACE 16 | Mir-SHADING SURFACE 17 | Mir-SHADING SURFACE 18 | Mir-SHADING SURFACE 21 | Mir-SHADING SURFACE 22 | Mir-SHADING SURFACE 23 | Mir-SHADING SURFACE 24 | Mir-SHADING SURFACE 27 | Mir-SHADING SURFACE 28 | Mir-SHADING SURFACE 29 | Mir-SHADING SURFACE 30 | |
| Mir-SHADING SURFACE 27 | Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 4 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 6 | Mir-SHADING SURFACE 10 | Mir-SHADING SURFACE 11 | Mir-SHADING SURFACE 12 | Mir-SHADING SURFACE 8 | Mir-SHADING SURFACE 14 | Mir-SHADING SURFACE 16 | Mir-SHADING SURFACE 17 | Mir-SHADING SURFACE 18 | Mir-SHADING SURFACE 20 | Mir-SHADING SURFACE 22 | Mir-SHADING SURFACE 23 | Mir-SHADING SURFACE 24 | Mir-SHADING SURFACE 26 | Mir-SHADING SURFACE 28 | Mir-SHADING SURFACE 29 | Mir-SHADING SURFACE 30 | |
| Mir-SHADING SURFACE 28 | Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 6 | Mir-SHADING SURFACE 11 | Mir-SHADING SURFACE 12 | Mir-SHADING SURFACE 8 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 14 | Mir-SHADING SURFACE 15 | Mir-SHADING SURFACE 17 | Mir-SHADING SURFACE 18 | Mir-SHADING SURFACE 20 | Mir-SHADING SURFACE 21 | Mir-SHADING SURFACE 23 | Mir-SHADING SURFACE 24 | Mir-SHADING SURFACE 26 | Mir-SHADING SURFACE 27 | Mir-SHADING SURFACE 29 | Mir-SHADING SURFACE 30 | |
| Mir-SHADING SURFACE 29 | Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 4 | Mir-SHADING SURFACE 6 | Mir-SHADING SURFACE 10 | Mir-SHADING SURFACE 12 | Mir-SHADING SURFACE 8 | Mir-SHADING SURFACE 9 | Mir-SHADING SURFACE 14 | Mir-SHADING SURFACE 15 | Mir-SHADING SURFACE 16 | Mir-SHADING SURFACE 18 | Mir-SHADING SURFACE 20 | Mir-SHADING SURFACE 21 | Mir-SHADING SURFACE 22 | Mir-SHADING SURFACE 24 | Mir-SHADING SURFACE 26 | Mir-SHADING SURFACE 27 | Mir-SHADING SURFACE 28 | Mir-SHADING SURFACE 30 | |
| SHADING SURFACE 30 | Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 4 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 6 | |
| Mir-SHADING SURFACE 30 | Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 4 | Mir-SHADING SURFACE 5 | |
| SURFACE 18 | Mir-SHADING SURFACE 2 | Mir-SHADING SURFACE 3 | Mir-SHADING SURFACE 4 | Mir-SHADING SURFACE 5 | Mir-SHADING SURFACE 6 | |
| Possible Shadow Receivers | |
| SURFACE 2 | SUB SURFACE 1 | |
| SURFACE 3 | SUB SURFACE 2 | |
| SURFACE 4 | SUB SURFACE 3 | |
| SURFACE 5 | SUB SURFACE 4 | |
| SURFACE 10 | SUB SURFACE 7 | |
| SURFACE 11 | SUB SURFACE 8 | |
| SURFACE 8 | SUB SURFACE 5 | |
| SURFACE 9 | SUB SURFACE 6 | |
| SURFACE 14 | SUB SURFACE 9 | |
| SURFACE 15 | SUB SURFACE 10 | |
| SURFACE 16 | SUB SURFACE 11 | |
| SURFACE 17 | SUB SURFACE 12 | |
Report: Adaptive Comfort Summary
For: Entire Facility
Timestamp: 2020-03-25 14:42:09
Time Not Meeting the Adaptive Comfort Models during Occupied Hours| ASHRAE55 90% Acceptability Limits [Hours] | ASHRAE55 80% Acceptability Limits [Hours] | CEN15251 Category I Acceptability Limits [Hours] | CEN15251 Category II Acceptability Limits [Hours] | CEN15251 Category III Acceptability Limits [Hours] |
Report: Initialization Summary
For: Entire Facility
Timestamp: 2020-03-25 14:42:09
Version| Version ID | |
| 1 | 9.1 |
| #TimeSteps | Minutes per TimeStep {minutes} | |
| 1 | 1 | 60 |
| Minimum System TimeStep {minutes} | Max HVAC Iterations | Minimum Plant Iterations | Maximum Plant Iterations | |
| 1 | 1 | 20 | 2 | 8 |
| Do Zone Sizing | Do System Sizing | Do Plant Sizing | Do Design Days | Do Weather Simulation | Do HVAC Sizing Simulation | |
| 1 | Yes | Yes | Yes | No | Yes | No |
| Tolerance for Time Heating Setpoint Not Met | Tolerance for Zone Cooling Setpoint Not Met Time | |
| 1 | 0.556 | 0.556 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | 20.26 | 20.16 | 20.19 | 20.28 | 20.39 | 22.70 | 23.12 | 23.23 | 23.27 | 20.97 | 20.62 | 20.41 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | -2.87 | -0.64 | 3.71 | 7.83 | 15.62 | 19.72 | 20.85 | 18.77 | 13.96 | 7.98 | 2.08 | -1.81 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 |
| Jan{dimensionless} | Feb{dimensionless} | Mar{dimensionless} | Apr{dimensionless} | May{dimensionless} | Jun{dimensionless} | Jul{dimensionless} | Aug{dimensionless} | Sep{dimensionless} | Oct{dimensionless} | Nov{dimensionless} | Dec{dimensionless} | |
| 1 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 |
| Normal | Daylighting {dimensionless} | |
| 1 | 1.000 | 1.000 |
| Jan{dimensionless} | Feb{dimensionless} | Mar{dimensionless} | Apr{dimensionless} | May{dimensionless} | Jun{dimensionless} | Jul{dimensionless} | Aug{dimensionless} | Sep{dimensionless} | Oct{dimensionless} | Nov{dimensionless} | Dec{dimensionless} | |
| 1 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 |
| Jan{dimensionless} | Feb{dimensionless} | Mar{dimensionless} | Apr{dimensionless} | May{dimensionless} | Jun{dimensionless} | Jul{dimensionless} | Aug{dimensionless} | Sep{dimensionless} | Oct{dimensionless} | Nov{dimensionless} | Dec{dimensionless} | |
| 1 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 |
| Wind Sensor Height Above Ground {m} | Wind Speed Profile Exponent {} | Wind Speed Profile Boundary Layer Thickness {m} | Air Temperature Sensor Height Above Ground {m} | Wind Speed Modifier Coefficient-Internal | Temperature Modifier Coefficient-Internal | |
| 1 | 10.000 | 0.140 | 270.000 | 1.500 | 1.586 | 9.750E-003 |
| Location Name | Latitude {N+/S- Deg} | Longitude {E+/W- Deg} | Time Zone Number {GMT+/-} | Elevation {m} | Standard Pressure at Elevation {Pa} | Standard RhoAir at Elevation | |
| 1 | Buffalo Niagara Intl Ap NY USA TMY3 WMO#=725280 | 42.93 | -78.73 | -5.00 | 215.00 | 98769 | 1.1739 |
| Calculation Method{} | Water Mains Temperature Schedule Name{} | Annual Average Outdoor Air Temperature{C} | Maximum Difference In Monthly Average Outdoor Air Temperatures{deltaC} | Fixed Default Water Mains Temperature{C} | |
| 1 | Correlation | NA | 8.97 | 26.20 | NA |
| Building Name | North Axis {deg} | Terrain | Loads Convergence Tolerance Value | Temperature Convergence Tolerance Value | Solar Distribution | Maximum Number of Warmup Days | Minimum Number of Warmup Days | |
| 1 | Restaurant 10 | 0.000 | City | 4.00000E-002 | 0.40000 | FullExterior | 25 | 6 |
| Algorithm {Simple TARP CeilingDiffuser AdaptiveConvectionAlgorithm} |
|
| 1 | TARP |
| Algorithm {SimpleCombined TARP MoWitt DOE-2 AdaptiveConvectionAlgorithm} |
|
| 1 | DOE-2 |
| Value {Anisotropic} | |
| 1 | Anisotropic |
| Value {ThirdOrderBackwardDifference AnalyticalSolution EulerMethod} |
|
| 1 | ThirdOrderBackwardDifference |
| Simulation {Yes/No} | Carbon Dioxide Concentration | |
| 1 | No | N/A |
| Simulation {Yes/No} | Generic Contaminant Concentration | |
| 1 | No | N/A |
| Enforce Mass Balance |
Adjust Zone Mixing |
Adjust Zone Infiltration {AddInfiltration AdjustInfiltration None} |
Infiltration Zones {MixingSourceZonesOnly AllZones} |
|
| 1 | No | N/A | N/A | N/A |
| Value {RegulaFalsi Bisection BisectionThenRegulaFalsi RegulaFalsiThenBisection} |
|
| 1 | RegulaFalsi |
| Wind Speed Profile Exponent {} | Wind Speed Profile Boundary Layer Thickness {m} | Air Temperature Gradient Coefficient {K/m} | |
| 1 | 0.330 | 460.000 | 6.500000E-003 |
| Starting Corner | Vertex Input Direction | Coordinate System | Daylight Reference Point Coordinate System | Rectangular (Simple) Surface Coordinate System | |
| 1 | UpperLeftCorner | Counterclockwise | RelativeCoordinateSystem | RelativeCoordinateSystem | RelativeToZoneOrigin |
| Value {CTF - ConductionTransferFunction EMPD - MoisturePenetrationDepthConductionTransferFunction CondFD - ConductionFiniteDifference HAMT - CombinedHeatAndMoistureFiniteElement} - Description |
Inside Surface Max Temperature Limit{C} |
Surface Convection Coefficient Lower Limit {W/m2-K} |
Surface Convection Coefficient Upper Limit {W/m2-K} |
|
| 1 | CTF - ConductionTransferFunction | 200 | 0.10 | 1000.0 |
| Number of Fixed Detached Shades | Number of Building Detached Shades | Number of Attached Shades | |
| 1 | 0 | 60 | 0 |
| Number of Zones | Number of Zone Surfaces | Number of SubSurfaces | |
| 1 | 3 | 63 | 12 |
| Zone Name | North Axis {deg} | Origin X-Coordinate {m} | Origin Y-Coordinate {m} | Origin Z-Coordinate {m} | Centroid X-Coordinate {m} | Centroid Y-Coordinate {m} | Centroid Z-Coordinate {m} | Type | Zone Multiplier | Zone List Multiplier | Minimum X {m} | Maximum X {m} | Minimum Y {m} | Maximum Y {m} | Minimum Z {m} | Maximum Z {m} | Ceiling Height {m} | Volume {m3} | Zone Inside Convection Algorithm {Simple-Detailed-CeilingDiffuser-TrombeWall} | Zone Outside Convection Algorithm {Simple-Detailed-Tarp-MoWitt-DOE-2-BLAST} | Floor Area {m2} | Exterior Gross Wall Area {m2} | Exterior Net Wall Area {m2} | Exterior Window Area {m2} | Number of Surfaces | Number of SubSurfaces | Number of Shading SubSurfaces | Part of Total Building Area | |
| 1 | BUILDING STORY 1 THERMALZONE | 0.0 | 0.00 | 0.00 | 0.00 | 35.10 | 70.57 | 1.50 | 1 | 1 | 1 | -9.00E-012 | 70.19 | 1.38E-004 | 141.15 | 0.00 | 3.00 | 3.00 | 11665.53 | TARP | DOE-2 | 3888.51 | 1004.21 | 702.95 | 301.26 | 6 | 4 | 0 | Yes |
| 2 | BUILDING STORY 2 THERMALZONE | 0.0 | 0.00 | 0.00 | 0.00 | 35.10 | 70.57 | 4.50 | 1 | 1 | 1 | -9.00E-012 | 70.19 | 1.38E-004 | 141.15 | 3.00 | 6.00 | 3.00 | 11665.53 | TARP | DOE-2 | 3888.51 | 1004.21 | 702.95 | 301.26 | 6 | 4 | 0 | Yes |
| 3 | BUILDING STORY 3 THERMALZONE | 0.0 | 0.00 | 0.00 | 0.00 | 35.10 | 70.57 | 7.50 | 1 | 1 | 1 | -9.00E-012 | 70.19 | 1.38E-004 | 141.15 | 6.00 | 9.00 | 3.00 | 11665.53 | TARP | DOE-2 | 3888.51 | 1004.21 | 702.95 | 301.26 | 6 | 4 | 0 | Yes |
| Zone Name | Floor Area {m2} | # Occupants | Area per Occupant {m2/person} | Occupant per Area {person/m2} | Interior Lighting {W/m2} | Electric Load {W/m2} | Gas Load {W/m2} | Other Load {W/m2} | Hot Water Eq {W/m2} | Steam Equipment {W/m2} | Sum Loads per Area {W/m2} | Outdoor Controlled Baseboard Heat | |
| 1 | BUILDING STORY 1 THERMALZONE | 3888.51 | 2929.9 | 1.327 | 0.753 | 9.580 | 64.928 | 0.000 | 0.000 | 0.000 | 0.000 | 74.508 | No |
| 2 | BUILDING STORY 2 THERMALZONE | 3888.51 | 2929.9 | 1.327 | 0.753 | 9.580 | 64.928 | 0.000 | 0.000 | 0.000 | 0.000 | 74.508 | No |
| 3 | BUILDING STORY 3 THERMALZONE | 3888.51 | 703.3 | 5.529 | 0.181 | 12.399 | 379.687 | 531.343 | 0.000 | 0.000 | 0.000 | 923.429 | No |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Number of People {} | People/Floor Area {person/m2} | Floor Area per person {m2/person} | Fraction Radiant | Fraction Convected | Sensible Fraction Calculation | Activity level | ASHRAE 55 Warnings | Carbon Dioxide Generation Rate | Nominal Minimum Number of People | Nominal Maximum Number of People | MRT Calculation Type | Work Efficiency | Clothing Insulation Calculation Method | Clothing Insulation Calculation Method Schedule | Clothing | Air Velocity | Fanger Calculation | Pierce Calculation | KSU Calculation | |
| 1 | BUILDING STORY 3 THERMALZONE FULLSERVICERESTAURANT DINING PEOPLE 1 | RESTAURANTSITDOWN BLDG_OCC_SCH | BUILDING STORY 3 THERMALZONE | 3888.51 | 703.3 | 532.1 | 0.137 | 7.308 | 0.300 | 0.700 | AutoCalculate | RESTAURANTSITDOWN ACTIVITY_SCH | Yes | 3.8200E-008 | 0 | 532 | Zone Averaged | WORK EFFICIENCY SCHEDULE | Clothing Insulation Schedule | N/A | CLOTHING SCHEDULE | AIR VELOCITY SCHEDULE | Yes | No | No |
| 2 | BUILDING STORY 3 THERMALZONE FULLSERVICERESTAURANT KITCHEN PEOPLE 1 | RESTAURANTSITDOWN BLDG_OCC_SCH | BUILDING STORY 3 THERMALZONE | 3888.51 | 703.3 | 171.3 | 4.405E-002 | 22.704 | 0.300 | 0.700 | AutoCalculate | RESTAURANTSITDOWN ACTIVITY_SCH | Yes | 3.8200E-008 | 0 | 171 | Zone Averaged | WORK EFFICIENCY SCHEDULE | Clothing Insulation Schedule | N/A | CLOTHING SCHEDULE | AIR VELOCITY SCHEDULE | Yes | No | No |
| 3 | BUILDING STORY 2 THERMALZONE FULLSERVICERESTAURANT DINING PEOPLE 2 | RESTAURANTSITDOWN BLDG_OCC_SCH | BUILDING STORY 2 THERMALZONE | 3888.51 | 2929.9 | 2929.9 | 0.753 | 1.327 | 0.300 | 0.700 | AutoCalculate | RESTAURANTSITDOWN ACTIVITY_SCH | Yes | 3.8200E-008 | 0 | 2930 | Zone Averaged | WORK EFFICIENCY SCHEDULE | Clothing Insulation Schedule | N/A | CLOTHING SCHEDULE | AIR VELOCITY SCHEDULE | Yes | No | No |
| 4 | BUILDING STORY 1 THERMALZONE FULLSERVICERESTAURANT DINING PEOPLE 3 | RESTAURANTSITDOWN BLDG_OCC_SCH | BUILDING STORY 1 THERMALZONE | 3888.51 | 2929.9 | 2929.9 | 0.753 | 1.327 | 0.300 | 0.700 | AutoCalculate | RESTAURANTSITDOWN ACTIVITY_SCH | Yes | 3.8200E-008 | 0 | 2930 | Zone Averaged | WORK EFFICIENCY SCHEDULE | Clothing Insulation Schedule | N/A | CLOTHING SCHEDULE | AIR VELOCITY SCHEDULE | Yes | No | No |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Lighting Level {W} | Lights/Floor Area {W/m2} | Lights per person {W/person} | Fraction Return Air | Fraction Radiant | Fraction Short Wave | Fraction Convected | Fraction Replaceable | End-Use Category | Nominal Minimum Lighting Level {W} | Nominal Maximum Lighting Level {W} | |
| 1 | BUILDING STORY 3 THERMALZONE FULLSERVICERESTAURANT DINING LIGHTS 1 | RESTAURANTSITDOWN BLDG_LIGHT_DINING_SCH_2013 | BUILDING STORY 3 THERMALZONE | 3888.51 | 703.3 | 6764.862 | 1.740 | 9.618 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 6764.862 |
| 2 | BUILDING STORY 3 THERMALZONE FULLSERVICERESTAURANT KITCHEN LIGHTS 1 | RESTAURANTSITDOWN BLDG_LIGHT_KITCHEN_SCH_2010_2013 | BUILDING STORY 3 THERMALZONE | 3888.51 | 703.3 | 41448.050 | 10.659 | 58.930 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 41448.050 |
| 3 | BUILDING STORY 2 THERMALZONE FULLSERVICERESTAURANT DINING LIGHTS 2 | RESTAURANTSITDOWN BLDG_LIGHT_DINING_SCH_2013 | BUILDING STORY 2 THERMALZONE | 3888.51 | 2929.9 | 37251.445 | 9.580 | 12.714 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 37251.445 |
| 4 | BUILDING STORY 1 THERMALZONE FULLSERVICERESTAURANT DINING LIGHTS 3 | RESTAURANTSITDOWN BLDG_LIGHT_DINING_SCH_2013 | BUILDING STORY 1 THERMALZONE | 3888.51 | 2929.9 | 37251.445 | 9.580 | 12.714 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 37251.445 |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Equipment Level {W} | Equipment/Floor Area {W/m2} | Equipment per person {W/person} | Fraction Latent | Fraction Radiant | Fraction Lost | Fraction Convected | End-Use SubCategory | Nominal Minimum Equipment Level {W} | Nominal Maximum Equipment Level {W} | |
| 1 | BUILDING STORY 3 THERMALZONE 9 ELEVATOR FANS | ELEVATOR SCHEDULE 3 | BUILDING STORY 3 THERMALZONE | 3888.51 | 703.3 | 278.476 | 7.162E-002 | 0.396 | 0.000 | 0.500 | 0.000 | 0.500 | Elevators | 0.000 | 278.476 |
| 2 | BUILDING STORY 3 THERMALZONE 9 ELEVATOR LIFT MOTORS | ELEVATOR SCHEDULE 1 | BUILDING STORY 3 THERMALZONE | 3888.51 | 703.3 | 144421.007 | 37.140 | 205.336 | 0.000 | 0.000 | 1.000 | 0.000 | Elevators | 0.000 | 144421.007 |
| 3 | BUILDING STORY 3 THERMALZONE 9 ELEVATOR LIGHTS | ELEVATOR SCHEDULE 2 | BUILDING STORY 3 THERMALZONE | 3888.51 | 703.3 | 290.988 | 7.483E-002 | 0.414 | 0.000 | 0.500 | 0.000 | 0.500 | Elevators | 0.000 | 290.988 |
| 4 | BUILDING STORY 3 THERMALZONE FULLSERVICERESTAURANT DINING ELEC EQUIP 1 | RESTAURANTSITDOWN BLDG_EQUIP_SCH | BUILDING STORY 3 THERMALZONE | 3888.51 | 703.3 | 45849.045 | 11.791 | 65.188 | 0.250 | 0.300 | 0.000 | 0.450 | General | 0.000 | 13296.223 |
| 5 | BUILDING STORY 3 THERMALZONE FULLSERVICERESTAURANT KITCHEN ELEC EQUIP 1 | RESTAURANTSITDOWN BLDG_EQUIP_SCH | BUILDING STORY 3 THERMALZONE | 3888.51 | 703.3 | 1285574.643 | 330.609 | 1827.812 | 0.250 | 0.300 | 0.200 | 0.250 | General | 0.000 | 372816.646 |
| 6 | BUILDING STORY 2 THERMALZONE FULLSERVICERESTAURANT DINING ELEC EQUIP 2 | RESTAURANTSITDOWN BLDG_EQUIP_SCH | BUILDING STORY 2 THERMALZONE | 3888.51 | 2929.9 | 252472.712 | 64.928 | 86.171 | 0.250 | 0.300 | 0.000 | 0.450 | General | 0.000 | 73217.087 |
| 7 | BUILDING STORY 1 THERMALZONE FULLSERVICERESTAURANT DINING ELEC EQUIP 3 | RESTAURANTSITDOWN BLDG_EQUIP_SCH | BUILDING STORY 1 THERMALZONE | 3888.51 | 2929.9 | 252472.712 | 64.928 | 86.171 | 0.250 | 0.300 | 0.000 | 0.450 | General | 0.000 | 73217.087 |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Equipment Level {W} | Equipment/Floor Area {W/m2} | Equipment per person {W/person} | Fraction Latent | Fraction Radiant | Fraction Lost | Fraction Convected | End-Use SubCategory | Nominal Minimum Equipment Level {W} | Nominal Maximum Equipment Level {W} | |
| 1 | BUILDING STORY 3 THERMALZONE FULLSERVICERESTAURANT KITCHEN GAS EQUIP 1 | RESTAURANTSITDOWN REST_GAS_EQUIP_SCH | BUILDING STORY 3 THERMALZONE | 3888.51 | 703.3 | 2066132.438 | 531.343 | 2937.598 | 0.100 | 0.200 | 0.700 | 0.000 | General | 0.000 | 599178.407 |
| Calculation Method | Value {days} | Allowable Number Figures in Shadow Overlap {} | Polygon Clipping Algorithm | Sky Diffuse Modeling Algorithm | External Shading Calculation Method | Output External Shading Calculation Results | Disable Self-Shading Within Shading Zone Groups | Disable Self-Shading From Shading Zone Groups to Other Zones | |
| 1 | AverageOverDaysInFrequency | 20 | 15000 | SutherlandHodgman | SimpleSkyDiffuseModeling | InternalCalculation | No | No | No |
| Zone Name | Number of Exterior Windows | Number of Exterior Windows in Adjacent Zones | |
| 1 | BUILDING STORY 1 THERMALZONE | 4 | 0 |
| 2 | BUILDING STORY 2 THERMALZONE | 4 | 0 |
| 3 | BUILDING STORY 3 THERMALZONE | 4 | 0 |
| Zone Name | Number of Adjacent Zones with Windows | Adjacent Zone Names - 1st 100 (max) | |
| 1 | BUILDING STORY 1 THERMALZONE | 0 | |
| 2 | BUILDING STORY 2 THERMALZONE | 0 | |
| 3 | BUILDING STORY 3 THERMALZONE | 0 |
| Type | Name | Volume {m3} | Maximum Capacity {W} | Standard Rated Recovery Efficiency | Standard Rated Energy Factor | |
| 1 | WaterHeater:Mixed | 6.0GAL ELECTRICITY BOOSTER WATER HEATER - 367KBTU/HR 1.0 THERM EFF | 2.2712E-002 | 107653.1 | 38.034 | 0.9175 |
| 2 | WaterHeater:Mixed | 1913GAL NATURALGAS WATER HEATER - 1913KBTU/HR 0.802 THERM EFF | 7.2421 | 560693.6 | 9.686E-002 | 0.2910 |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Design Volume Flow Rate {m3/s} | Volume Flow Rate/Floor Area {m3/s-m2} | Volume Flow Rate/Exterior Surface Area {m3/s-m2} | ACH - Air Changes per Hour | Equation A - Constant Term Coefficient {} | Equation B - Temperature Term Coefficient {1/C} | Equation C - Velocity Term Coefficient {s/m} | Equation D - Velocity Squared Term Coefficient {s2/m2} | |
| 1 | BUILDING STORY 3 THERMALZONE FULLSERVICERESTAURANT DINING A - STORY GROUND INFILTRATION | ALWAYS ON DISCRETE | BUILDING STORY 3 THERMALZONE | 3888.51 | 703.3 | 7.545E-002 | 1.940E-005 | 1.542E-005 | 2.328E-002 | 0.000 | 0.000 | 0.224 | 0.000 |
| 2 | BUILDING STORY 3 THERMALZONE FULLSERVICERESTAURANT DINING A END_B - STORY GROUND INFILTRATION | ALWAYS ON DISCRETE | BUILDING STORY 3 THERMALZONE | 3888.51 | 703.3 | 0.102 | 2.627E-005 | 2.087E-005 | 3.152E-002 | 0.000 | 0.000 | 0.224 | 0.000 |
| 3 | BUILDING STORY 3 THERMALZONE FULLSERVICERESTAURANT DINING B END_B - STORY GROUND INFILTRATION | ALWAYS ON DISCRETE | BUILDING STORY 3 THERMALZONE | 3888.51 | 703.3 | 0.595 | 1.529E-004 | 1.215E-004 | 0.183 | 0.000 | 0.000 | 0.224 | 0.000 |
| 4 | BUILDING STORY 3 THERMALZONE FULLSERVICERESTAURANT DINING C - STORY GROUND INFILTRATION | ALWAYS ON DISCRETE | BUILDING STORY 3 THERMALZONE | 3888.51 | 703.3 | 7.545E-002 | 1.940E-005 | 1.542E-005 | 2.328E-002 | 0.000 | 0.000 | 0.224 | 0.000 |
| 5 | BUILDING STORY 3 THERMALZONE FULLSERVICERESTAURANT DINING C END_B - STORY GROUND INFILTRATION | ALWAYS ON DISCRETE | BUILDING STORY 3 THERMALZONE | 3888.51 | 703.3 | 0.102 | 2.627E-005 | 2.087E-005 | 3.152E-002 | 0.000 | 0.000 | 0.224 | 0.000 |
| 6 | BUILDING STORY 3 THERMALZONE FULLSERVICERESTAURANT KITCHEN A - STORY GROUND INFILTRATION | ALWAYS ON DISCRETE | BUILDING STORY 3 THERMALZONE | 3888.51 | 703.3 | 0.519 | 1.335E-004 | 1.061E-004 | 0.160 | 0.000 | 0.000 | 0.224 | 0.000 |
| 7 | BUILDING STORY 3 THERMALZONE FULLSERVICERESTAURANT KITCHEN A END_A - STORY GROUND INFILTRATION | ALWAYS ON DISCRETE | BUILDING STORY 3 THERMALZONE | 3888.51 | 703.3 | 0.102 | 2.627E-005 | 2.087E-005 | 3.152E-002 | 0.000 | 0.000 | 0.224 | 0.000 |
| 8 | BUILDING STORY 3 THERMALZONE FULLSERVICERESTAURANT KITCHEN B END_A - STORY GROUND INFILTRATION | ALWAYS ON DISCRETE | BUILDING STORY 3 THERMALZONE | 3888.51 | 703.3 | 0.595 | 1.529E-004 | 1.215E-004 | 0.183 | 0.000 | 0.000 | 0.224 | 0.000 |
| 9 | BUILDING STORY 3 THERMALZONE FULLSERVICERESTAURANT KITCHEN C - STORY GROUND INFILTRATION | ALWAYS ON DISCRETE | BUILDING STORY 3 THERMALZONE | 3888.51 | 703.3 | 0.519 | 1.335E-004 | 1.061E-004 | 0.160 | 0.000 | 0.000 | 0.224 | 0.000 |
| 10 | BUILDING STORY 3 THERMALZONE FULLSERVICERESTAURANT KITCHEN C END_A - STORY GROUND INFILTRATION | ALWAYS ON DISCRETE | BUILDING STORY 3 THERMALZONE | 3888.51 | 703.3 | 0.102 | 2.627E-005 | 2.087E-005 | 3.152E-002 | 0.000 | 0.000 | 0.224 | 0.000 |
| 11 | BUILDING STORY 2 THERMALZONE FULLSERVICERESTAURANT DINING A - STORY MID INFILTRATION | ALWAYS ON DISCRETE | BUILDING STORY 2 THERMALZONE | 3888.51 | 2929.9 | 0.122 | 3.138E-005 | 1.215E-004 | 3.766E-002 | 0.000 | 0.000 | 0.224 | 0.000 |
| 12 | BUILDING STORY 2 THERMALZONE FULLSERVICERESTAURANT DINING A END_A - STORY MID INFILTRATION | ALWAYS ON DISCRETE | BUILDING STORY 2 THERMALZONE | 3888.51 | 2929.9 | 2.096E-002 | 5.391E-006 | 2.087E-005 | 6.469E-003 | 0.000 | 0.000 | 0.224 | 0.000 |
| 13 | BUILDING STORY 2 THERMALZONE FULLSERVICERESTAURANT DINING A END_B - STORY MID INFILTRATION | ALWAYS ON DISCRETE | BUILDING STORY 2 THERMALZONE | 3888.51 | 2929.9 | 2.096E-002 | 5.391E-006 | 2.087E-005 | 6.469E-003 | 0.000 | 0.000 | 0.224 | 0.000 |
| 14 | BUILDING STORY 2 THERMALZONE FULLSERVICERESTAURANT DINING B END_A - STORY MID INFILTRATION | ALWAYS ON DISCRETE | BUILDING STORY 2 THERMALZONE | 3888.51 | 2929.9 | 0.122 | 3.138E-005 | 1.215E-004 | 3.766E-002 | 0.000 | 0.000 | 0.224 | 0.000 |
| 15 | BUILDING STORY 2 THERMALZONE FULLSERVICERESTAURANT DINING B END_B - STORY MID INFILTRATION | ALWAYS ON DISCRETE | BUILDING STORY 2 THERMALZONE | 3888.51 | 2929.9 | 0.122 | 3.138E-005 | 1.215E-004 | 3.766E-002 | 0.000 | 0.000 | 0.224 | 0.000 |
| 16 | BUILDING STORY 2 THERMALZONE FULLSERVICERESTAURANT DINING C - STORY MID INFILTRATION | ALWAYS ON DISCRETE | BUILDING STORY 2 THERMALZONE | 3888.51 | 2929.9 | 0.122 | 3.138E-005 | 1.215E-004 | 3.766E-002 | 0.000 | 0.000 | 0.224 | 0.000 |
| 17 | BUILDING STORY 2 THERMALZONE FULLSERVICERESTAURANT DINING C END_A - STORY MID INFILTRATION | ALWAYS ON DISCRETE | BUILDING STORY 2 THERMALZONE | 3888.51 | 2929.9 | 2.096E-002 | 5.391E-006 | 2.087E-005 | 6.469E-003 | 0.000 | 0.000 | 0.224 | 0.000 |
| 18 | BUILDING STORY 2 THERMALZONE FULLSERVICERESTAURANT DINING C END_B - STORY MID INFILTRATION | ALWAYS ON DISCRETE | BUILDING STORY 2 THERMALZONE | 3888.51 | 2929.9 | 2.096E-002 | 5.391E-006 | 2.087E-005 | 6.469E-003 | 0.000 | 0.000 | 0.224 | 0.000 |
| 19 | BUILDING STORY 1 THERMALZONE FULLSERVICERESTAURANT DINING A - STORY TOP INFILTRATION | ALWAYS ON DISCRETE | BUILDING STORY 1 THERMALZONE | 3888.51 | 2929.9 | 1.995E-002 | 5.131E-006 | 1.987E-005 | 6.157E-003 | 0.000 | 0.000 | 0.224 | 0.000 |
| 20 | BUILDING STORY 1 THERMALZONE FULLSERVICERESTAURANT DINING A END_A - STORY TOP INFILTRATION | ALWAYS ON DISCRETE | BUILDING STORY 1 THERMALZONE | 3888.51 | 2929.9 | 3.428E-003 | 8.815E-007 | 3.413E-006 | 1.058E-003 | 0.000 | 0.000 | 0.224 | 0.000 |
| 21 | BUILDING STORY 1 THERMALZONE FULLSERVICERESTAURANT DINING A END_B - STORY TOP INFILTRATION | ALWAYS ON DISCRETE | BUILDING STORY 1 THERMALZONE | 3888.51 | 2929.9 | 3.428E-003 | 8.815E-007 | 3.413E-006 | 1.058E-003 | 0.000 | 0.000 | 0.224 | 0.000 |
| 22 | BUILDING STORY 1 THERMALZONE FULLSERVICERESTAURANT DINING B END_A - STORY TOP INFILTRATION | ALWAYS ON DISCRETE | BUILDING STORY 1 THERMALZONE | 3888.51 | 2929.9 | 1.995E-002 | 5.131E-006 | 1.987E-005 | 6.157E-003 | 0.000 | 0.000 | 0.224 | 0.000 |
| 23 | BUILDING STORY 1 THERMALZONE FULLSERVICERESTAURANT DINING B END_B - STORY TOP INFILTRATION | ALWAYS ON DISCRETE | BUILDING STORY 1 THERMALZONE | 3888.51 | 2929.9 | 1.995E-002 | 5.131E-006 | 1.987E-005 | 6.157E-003 | 0.000 | 0.000 | 0.224 | 0.000 |
| 24 | BUILDING STORY 1 THERMALZONE FULLSERVICERESTAURANT DINING C - STORY TOP INFILTRATION | ALWAYS ON DISCRETE | BUILDING STORY 1 THERMALZONE | 3888.51 | 2929.9 | 1.995E-002 | 5.131E-006 | 1.987E-005 | 6.157E-003 | 0.000 | 0.000 | 0.224 | 0.000 |
| 25 | BUILDING STORY 1 THERMALZONE FULLSERVICERESTAURANT DINING C END_A - STORY TOP INFILTRATION | ALWAYS ON DISCRETE | BUILDING STORY 1 THERMALZONE | 3888.51 | 2929.9 | 3.428E-003 | 8.815E-007 | 3.413E-006 | 1.058E-003 | 0.000 | 0.000 | 0.224 | 0.000 |
| 26 | BUILDING STORY 1 THERMALZONE FULLSERVICERESTAURANT DINING C END_B - STORY TOP INFILTRATION | ALWAYS ON DISCRETE | BUILDING STORY 1 THERMALZONE | 3888.51 | 2929.9 | 3.428E-003 | 8.815E-007 | 3.413E-006 | 1.058E-003 | 0.000 | 0.000 | 0.224 | 0.000 |
| Simple | |
| 1 | Simple |
| Zone Name | Mixing/Mundt/UCSDDV/UCSDCV/UCSDUFI/UCSDUFE/User Defined | |
| 1 | BUILDING STORY 1 THERMALZONE | Mixing/Well-Stirred |
| 2 | BUILDING STORY 2 THERMALZONE | Mixing/Well-Stirred |
| 3 | BUILDING STORY 3 THERMALZONE | Mixing/Well-Stirred |
| No Multizone or Distribution/Multizone with Distribution/Multizone without Distribution/Multizone with Distribution only during Fan Operation | |
| 1 | NoMultizoneOrDistribution |
| Sensible Heat Capacity Multiplier | Moisture Capacity Multiplier | Carbon Dioxide Capacity Multiplier | Generic Contaminant Capacity Multiplier | |
| 1 | 1.000 | 1.000 | 1.000 | 1.000 |
| Value | |
| 1 | 1 |
| Sizing Factor ID | Value | |
| 1 | Global | 1.2500 |
| 2 | Zone BUILDING STORY 1 THERMALZONE | 1.2500 |
| 3 | Zone BUILDING STORY 2 THERMALZONE | 1.2500 |
| 4 | Zone BUILDING STORY 3 THERMALZONE | 1.2500 |
| Sizing Factor ID | Value | |
| 1 | Global | 1.1500 |
| 2 | Zone BUILDING STORY 1 THERMALZONE | 1.1500 |
| 3 | Zone BUILDING STORY 2 THERMALZONE | 1.1500 |
| 4 | Zone BUILDING STORY 3 THERMALZONE | 1.1500 |
| Zone Name | Load Type | Calc Des Load {W} | User Des Load {W} | Calc Des Air Flow Rate {m3/s} | User Des Air Flow Rate {m3/s} | Design Day Name | Date/Time of Peak | Temperature at Peak {C} | Humidity Ratio at Peak {kgWater/kgDryAir} | Floor Area {m2} | # Occupants | Calc Outdoor Air Flow Rate {m3/s} | Calc DOAS Heat Addition Rate {W} | |
| 1 | BUILDING STORY 1 THERMALZONE | Cooling |<PHONE_NUMBER>5 |<PHONE_NUMBER>7 | 25.48827 | 29.31151 | BUFFALO NIAGARA INTL AP ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 09:00:00 | 25.18500 | 1.33455E-002 | 3888.50837 | 2929.88890 | 13.92630 | 0.00000 |
| 2 | BUILDING STORY 1 THERMALZONE | Heating | 33660.19805 | 42075.24756 | 0.96961 | 13.92630 | BUFFALO NIAGARA INTL AP ANN HTG 99.6% CONDNS DB 1 | 1/21 24:00:00 | -16.30000 | 9.24091E-004 | 3888.50837 | 2929.88890 | 13.92630 | 0.00000 |
| 3 | BUILDING STORY 2 THERMALZONE | Cooling |<PHONE_NUMBER>8 |<PHONE_NUMBER>7 | 29.24985 | 33.63733 | BUFFALO NIAGARA INTL AP ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 09:00:00 | 25.18500 | 1.33455E-002 | 3888.50837 | 2929.88890 | 13.92630 | 0.00000 |
| 4 | BUILDING STORY 2 THERMALZONE | Heating | 44772.78740 | 55965.98424 | 1.28961 | 13.92630 | BUFFALO NIAGARA INTL AP ANN HTG 99.6% CONDNS DB 1 | 1/21 24:00:00 | -16.30000 | 9.24091E-004 | 3888.50837 | 2929.88890 | 13.92630 | 0.00000 |
| 5 | BUILDING STORY 3 THERMALZONE | Cooling |<PHONE_NUMBER>7 |<PHONE_NUMBER>0 | 33.23625 | 38.22169 | BUFFALO NIAGARA INTL AP ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 07:00:00 | 21.83700 | 1.33455E-002 | 3888.50837 | 703.34076 | 6.04520 | 0.00000 |
| 6 | BUILDING STORY 3 THERMALZONE | Heating |<PHONE_NUMBER>5 |<PHONE_NUMBER>4 | 2.93825 | 6.04520 | BUFFALO NIAGARA INTL AP ANN HTG 99.6% CONDNS DB 1 | 1/21 24:00:00 | -16.30000 | 9.24091E-004 | 3888.50837 | 703.34076 | 6.04520 | 0.00000 |
| System Name | Load Type | Peak Load Kind | User Design Capacity | Calc Des Air Flow Rate [m3/s] | User Des Air Flow Rate [m3/s] | Design Day Name | Date/Time of Peak | |
| 1 | 1 ZONE PVAV | Cooling | Sensible | 463642.74 | 29.31151 | 29.31151 | BUFFALO NIAGARA INTL AP ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 00:00:00 |
| 2 | 1 ZONE PVAV | Heating | Sensible | 477685.98 | 13.92630 | 13.92630 | BUFFALO NIAGARA INTL AP ANN HTG 99.6% CONDNS DB 1 | 1/21 01:00:00 |
| 3 | 1 ZONE PVAV 1 | Cooling | Sensible | 517208.04 | 33.63733 | 33.63733 | BUFFALO NIAGARA INTL AP ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 00:00:00 |
| 4 | 1 ZONE PVAV 1 | Heating | Sensible | 477685.98 | 13.92630 | 13.92630 | BUFFALO NIAGARA INTL AP ANN HTG 99.6% CONDNS DB 1 | 1/21 01:00:00 |
| 5 | 1 ZONE PVAV 2 | Cooling | Sensible | 581766.58 | 38.22169 | 38.22169 | BUFFALO NIAGARA INTL AP ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 00:00:00 |
| 6 | 1 ZONE PVAV 2 | Heating | Sensible | 207356.37 | 6.04520 | 6.04520 | BUFFALO NIAGARA INTL AP ANN HTG 99.6% CONDNS DB 1 | 1/21 01:00:00 |
| Component Type | Component Name | Input Field Description | Value | |
| 1 | AirTerminal:SingleDuct:VAV:Reheat | BUILDING STORY 1 THERMALZONE VAV TERMINAL | Design Size Maximum Air Flow Rate [m3/s] | 29.31151 |
| 2 | AirTerminal:SingleDuct:VAV:Reheat | BUILDING STORY 1 THERMALZONE VAV TERMINAL | Design Size Constant Minimum Air Flow Fraction | 0.10109 |
| 3 | AirTerminal:SingleDuct:VAV:Reheat | BUILDING STORY 1 THERMALZONE VAV TERMINAL | User-Specified Constant Minimum Air Flow Fraction | 0.70000 |
| 4 | AirTerminal:SingleDuct:VAV:Reheat | BUILDING STORY 1 THERMALZONE VAV TERMINAL | Design Size Minimum Air Flow Rate [m3/s] | 20.51806 |
| 5 | AirTerminal:SingleDuct:VAV:Reheat | BUILDING STORY 1 THERMALZONE VAV TERMINAL | Design Size Maximum Flow Fraction during Reheat [] | 0.70000 |
| 6 | AirTerminal:SingleDuct:VAV:Reheat | BUILDING STORY 1 THERMALZONE VAV TERMINAL | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 5.27659E-003 |
| 7 | AirTerminal:SingleDuct:VAV:Reheat | BUILDING STORY 1 THERMALZONE VAV TERMINAL | Design Size Maximum Reheat Water Flow Rate [m3/s] | 5.33566E-003 |
| 8 | AirTerminal:SingleDuct:VAV:Reheat | BUILDING STORY 1 THERMALZONE VAV TERMINAL | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | 20.51806 |
| 9 | AirTerminal:SingleDuct:VAV:Reheat | BUILDING STORY 1 THERMALZONE VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | 12.77778 |
| 10 | AirTerminal:SingleDuct:VAV:Reheat | BUILDING STORY 1 THERMALZONE VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | 8.00000E-003 |
| 11 | Coil:Heating:Water | BUILDING STORY 1 THERMALZONE REHEAT COIL | Design Size Rated Capacity [W] |<PHONE_NUMBER>2 |
| 12 | Coil:Heating:Water | BUILDING STORY 1 THERMALZONE REHEAT COIL | Design Size Maximum Water Flow Rate [m3/s] | 5.33566E-003 |
| 13 | Coil:Heating:Water | BUILDING STORY 1 THERMALZONE REHEAT COIL | Design Size U-Factor Times Area Value [W/K] | 4329.24821 |
| 14 | AirTerminal:SingleDuct:VAV:Reheat | BUILDING STORY 2 THERMALZONE VAV TERMINAL | Design Size Maximum Air Flow Rate [m3/s] | 33.63733 |
| 15 | AirTerminal:SingleDuct:VAV:Reheat | BUILDING STORY 2 THERMALZONE VAV TERMINAL | Design Size Constant Minimum Air Flow Fraction | 8.80880E-002 |
| 16 | AirTerminal:SingleDuct:VAV:Reheat | BUILDING STORY 2 THERMALZONE VAV TERMINAL | User-Specified Constant Minimum Air Flow Fraction | 0.70000 |
| 17 | AirTerminal:SingleDuct:VAV:Reheat | BUILDING STORY 2 THERMALZONE VAV TERMINAL | Design Size Minimum Air Flow Rate [m3/s] | 23.54613 |
| 18 | AirTerminal:SingleDuct:VAV:Reheat | BUILDING STORY 2 THERMALZONE VAV TERMINAL | Design Size Maximum Flow Fraction during Reheat [] | 0.70000 |
| 19 | AirTerminal:SingleDuct:VAV:Reheat | BUILDING STORY 2 THERMALZONE VAV TERMINAL | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 6.05531E-003 |
| 20 | AirTerminal:SingleDuct:VAV:Reheat | BUILDING STORY 2 THERMALZONE VAV TERMINAL | Design Size Maximum Reheat Water Flow Rate [m3/s] | 6.28076E-003 |
| 21 | AirTerminal:SingleDuct:VAV:Reheat | BUILDING STORY 2 THERMALZONE VAV TERMINAL | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | 23.54613 |
| 22 | AirTerminal:SingleDuct:VAV:Reheat | BUILDING STORY 2 THERMALZONE VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | 12.77778 |
| 23 | AirTerminal:SingleDuct:VAV:Reheat | BUILDING STORY 2 THERMALZONE VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | 8.00000E-003 |
| 24 | Coil:Heating:Water | BUILDING STORY 2 THERMALZONE REHEAT COIL | Design Size Rated Capacity [W] |<PHONE_NUMBER>5 |
| 25 | Coil:Heating:Water | BUILDING STORY 2 THERMALZONE REHEAT COIL | Design Size Maximum Water Flow Rate [m3/s] | 6.28076E-003 |
| 26 | Coil:Heating:Water | BUILDING STORY 2 THERMALZONE REHEAT COIL | Design Size U-Factor Times Area Value [W/K] | 5113.65684 |
| 27 | AirTerminal:SingleDuct:VAV:Reheat | BUILDING STORY 3 THERMALZONE VAV TERMINAL | Design Size Maximum Air Flow Rate [m3/s] | 38.22169 |
| 28 | AirTerminal:SingleDuct:VAV:Reheat | BUILDING STORY 3 THERMALZONE VAV TERMINAL | Design Size Constant Minimum Air Flow Fraction | 7.75226E-002 |
| 29 | AirTerminal:SingleDuct:VAV:Reheat | BUILDING STORY 3 THERMALZONE VAV TERMINAL | User-Specified Constant Minimum Air Flow Fraction | 0.70000 |
| 30 | AirTerminal:SingleDuct:VAV:Reheat | BUILDING STORY 3 THERMALZONE VAV TERMINAL | Design Size Minimum Air Flow Rate [m3/s] | 26.75518 |
| 31 | AirTerminal:SingleDuct:VAV:Reheat | BUILDING STORY 3 THERMALZONE VAV TERMINAL | Design Size Maximum Flow Fraction during Reheat [] | 0.70000 |
| 32 | AirTerminal:SingleDuct:VAV:Reheat | BUILDING STORY 3 THERMALZONE VAV TERMINAL | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 6.88058E-003 |
| 33 | AirTerminal:SingleDuct:VAV:Reheat | BUILDING STORY 3 THERMALZONE VAV TERMINAL | Design Size Maximum Reheat Water Flow Rate [m3/s] | 7.31432E-003 |
| 34 | AirTerminal:SingleDuct:VAV:Reheat | BUILDING STORY 3 THERMALZONE VAV TERMINAL | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | 26.75518 |
| 35 | AirTerminal:SingleDuct:VAV:Reheat | BUILDING STORY 3 THERMALZONE VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | 12.77778 |
| 36 | AirTerminal:SingleDuct:VAV:Reheat | BUILDING STORY 3 THERMALZONE VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | 8.00000E-003 |
| 37 | Coil:Heating:Water | BUILDING STORY 3 THERMALZONE REHEAT COIL | Design Size Rated Capacity [W] |<PHONE_NUMBER>9 |
| 38 | Coil:Heating:Water | BUILDING STORY 3 THERMALZONE REHEAT COIL | Design Size Maximum Water Flow Rate [m3/s] | 7.31432E-003 |
| 39 | Coil:Heating:Water | BUILDING STORY 3 THERMALZONE REHEAT COIL | Design Size U-Factor Times Area Value [W/K] | 5975.60505 |
| 40 | AirLoopHVAC | 1 ZONE PVAV | Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | 20.51806 |
| 41 | AirLoopHVAC | 1 ZONE PVAV | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | 20.51806 |
| 42 | AirLoopHVAC | 1 ZONE PVAV | Sum of Air Terminal Maximum Flow Rates [m3/s] | 29.31151 |
| 43 | AirLoopHVAC | 1 ZONE PVAV | Adjusted Heating Design Air Flow Rate [m3/s] | 20.51806 |
| 44 | AirLoopHVAC | 1 ZONE PVAV | Adjusted Cooling Design Air Flow Rate [m3/s] | 29.31151 |
| 45 | AirLoopHVAC | 1 ZONE PVAV | Adjusted Main Design Air Flow Rate [m3/s] | 29.31151 |
| 46 | AirLoopHVAC | 1 ZONE PVAV | User Heating Air Flow Ratio [] | 0.30000 |
| 47 | AirLoopHVAC | 1 ZONE PVAV | Calculated Heating Air Flow Ratio [] | 0.70000 |
| 48 | AirLoopHVAC | 1 ZONE PVAV 1 | Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | 23.54613 |
| 49 | AirLoopHVAC | 1 ZONE PVAV 1 | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | 23.54613 |
| 50 | AirLoopHVAC | 1 ZONE PVAV 1 | Sum of Air Terminal Maximum Flow Rates [m3/s] | 33.63733 |
| 51 | AirLoopHVAC | 1 ZONE PVAV 1 | Adjusted Heating Design Air Flow Rate [m3/s] | 23.54613 |
| 52 | AirLoopHVAC | 1 ZONE PVAV 1 | Adjusted Cooling Design Air Flow Rate [m3/s] | 33.63733 |
| 53 | AirLoopHVAC | 1 ZONE PVAV 1 | Adjusted Main Design Air Flow Rate [m3/s] | 33.63733 |
| 54 | AirLoopHVAC | 1 ZONE PVAV 1 | User Heating Air Flow Ratio [] | 0.30000 |
| 55 | AirLoopHVAC | 1 ZONE PVAV 1 | Calculated Heating Air Flow Ratio [] | 0.70000 |
| 56 | AirLoopHVAC | 1 ZONE PVAV 2 | Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | 26.75518 |
| 57 | AirLoopHVAC | 1 ZONE PVAV 2 | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | 26.75518 |
| 58 | AirLoopHVAC | 1 ZONE PVAV 2 | Sum of Air Terminal Maximum Flow Rates [m3/s] | 38.22169 |
| 59 | AirLoopHVAC | 1 ZONE PVAV 2 | Adjusted Heating Design Air Flow Rate [m3/s] | 26.75518 |
| 60 | AirLoopHVAC | 1 ZONE PVAV 2 | Adjusted Cooling Design Air Flow Rate [m3/s] | 38.22169 |
| 61 | AirLoopHVAC | 1 ZONE PVAV 2 | Adjusted Main Design Air Flow Rate [m3/s] | 38.22169 |
| 62 | AirLoopHVAC | 1 ZONE PVAV 2 | User Heating Air Flow Ratio [] | 0.30000 |
| 63 | AirLoopHVAC | 1 ZONE PVAV 2 | Calculated Heating Air Flow Ratio [] | 0.70000 |
| 64 | AirLoopHVAC | 1 ZONE PVAV | Design Supply Air Flow Rate [m3/s] | 29.31151 |
| 65 | AirLoopHVAC | 1 ZONE PVAV 1 | Design Supply Air Flow Rate [m3/s] | 33.63733 |
| 66 | AirLoopHVAC | 1 ZONE PVAV 2 | Design Supply Air Flow Rate [m3/s] | 38.22169 |
| 67 | Controller:OutdoorAir | CONTROLLER OUTDOOR AIR 1 | Maximum Outdoor Air Flow Rate [m3/s] | 29.31151 |
| 68 | Coil:Cooling:DX:TwoSpeed | 1 ZONE PVAV 2SPD DX CLG COIL 2214KBTU/HR 9.5EER | Design Size High Speed Rated Air Flow Rate [m3/s] | 29.31151 |
| 69 | Coil:Cooling:DX:TwoSpeed | 1 ZONE PVAV 2SPD DX CLG COIL 2214KBTU/HR 9.5EER | Design Size High Speed Gross Rated Total Cooling Capacity [W] |<PHONE_NUMBER>8 |
| 70 | Coil:Cooling:DX:TwoSpeed | 1 ZONE PVAV 2SPD DX CLG COIL 2214KBTU/HR 9.5EER | Design Size High Speed Rated Sensible Heat Ratio | 0.69808 |
| 71 | Coil:Cooling:DX:TwoSpeed | 1 ZONE PVAV 2SPD DX CLG COIL 2214KBTU/HR 9.5EER | Design Size Low Speed Rated Air Flow Rate [m3/s] | 9.76953 |
| 72 | Coil:Cooling:DX:TwoSpeed | 1 ZONE PVAV 2SPD DX CLG COIL 2214KBTU/HR 9.5EER | Design Size Low Speed Gross Rated Total Cooling Capacity [W] |<PHONE_NUMBER>1 |
| 73 | Coil:Cooling:DX:TwoSpeed | 1 ZONE PVAV 2SPD DX CLG COIL 2214KBTU/HR 9.5EER | User-Specified Low Speed Gross Rated Sensible Heat Ratio | 0.69000 |
| 74 | Coil:Heating:Water | 1 ZONE PVAV MAIN HTG COIL | Design Size Rated Capacity [W] |<PHONE_NUMBER>8 |
| 75 | Coil:Heating:Water | 1 ZONE PVAV MAIN HTG COIL | Design Size Maximum Water Flow Rate [m3/s] | 6.59738E-003 |
| 76 | Coil:Heating:Water | 1 ZONE PVAV MAIN HTG COIL | Design Size U-Factor Times Area Value [W/K] | 3962.85863 |
| 77 | Fan:VariableVolume | 1 ZONE PVAV FAN | Design Size Maximum Flow Rate [m3/s] | 29.31151 |
| 78 | Controller:WaterCoil | 1 ZONE PVAV MAIN HTG COIL CONTROLLER | Maximum Actuated Flow [m3/s] | 6.59738E-003 |
| 79 | Controller:OutdoorAir | CONTROLLER OUTDOOR AIR 2 | Maximum Outdoor Air Flow Rate [m3/s] | 33.63733 |
| 80 | Coil:Cooling:DX:TwoSpeed | 1 ZONE PVAV 1 2SPD DX CLG COIL 2625KBTU/HR 9.5EER | Design Size High Speed Rated Air Flow Rate [m3/s] | 33.63733 |
| 81 | Coil:Cooling:DX:TwoSpeed | 1 ZONE PVAV 1 2SPD DX CLG COIL 2625KBTU/HR 9.5EER | Design Size High Speed Gross Rated Total Cooling Capacity [W] |<PHONE_NUMBER>3 |
| 82 | Coil:Cooling:DX:TwoSpeed | 1 ZONE PVAV 1 2SPD DX CLG COIL 2625KBTU/HR 9.5EER | Design Size High Speed Rated Sensible Heat Ratio | 0.69808 |
| 83 | Coil:Cooling:DX:TwoSpeed | 1 ZONE PVAV 1 2SPD DX CLG COIL 2625KBTU/HR 9.5EER | Design Size Low Speed Rated Air Flow Rate [m3/s] | 11.21132 |
| 84 | Coil:Cooling:DX:TwoSpeed | 1 ZONE PVAV 1 2SPD DX CLG COIL 2625KBTU/HR 9.5EER | Design Size Low Speed Gross Rated Total Cooling Capacity [W] |<PHONE_NUMBER>5 |
| 85 | Coil:Cooling:DX:TwoSpeed | 1 ZONE PVAV 1 2SPD DX CLG COIL 2625KBTU/HR 9.5EER | User-Specified Low Speed Gross Rated Sensible Heat Ratio | 0.69000 |
| 86 | Coil:Heating:Water | 1 ZONE PVAV 1 MAIN HTG COIL | Design Size Rated Capacity [W] |<PHONE_NUMBER>6 |
| 87 | Coil:Heating:Water | 1 ZONE PVAV 1 MAIN HTG COIL | Design Size Maximum Water Flow Rate [m3/s] | 7.57102E-003 |
| 88 | Coil:Heating:Water | 1 ZONE PVAV 1 MAIN HTG COIL | Design Size U-Factor Times Area Value [W/K] | 4547.70106 |
| 89 | Fan:VariableVolume | 1 ZONE PVAV 1 FAN | Design Size Maximum Flow Rate [m3/s] | 33.63733 |
| 90 | Controller:WaterCoil | 1 ZONE PVAV 1 MAIN HTG COIL CONTROLLER | Maximum Actuated Flow [m3/s] | 7.57102E-003 |
| 91 | Controller:OutdoorAir | CONTROLLER OUTDOOR AIR 3 | Maximum Outdoor Air Flow Rate [m3/s] | 38.22169 |
| 92 | Controller:OutdoorAir | CONTROLLER OUTDOOR AIR 3 | Minimum Outdoor Air Flow Rate [m3/s] | 6.04520 |
| 93 | Coil:Cooling:DX:TwoSpeed | 1 ZONE PVAV 2 2SPD DX CLG COIL 2996KBTU/HR 9.5EER | Design Size High Speed Rated Air Flow Rate [m3/s] | 38.22169 |
| 94 | Coil:Cooling:DX:TwoSpeed | 1 ZONE PVAV 2 2SPD DX CLG COIL 2996KBTU/HR 9.5EER | Design Size High Speed Gross Rated Total Cooling Capacity [W] |<PHONE_NUMBER>4 |
| 95 | Coil:Cooling:DX:TwoSpeed | 1 ZONE PVAV 2 2SPD DX CLG COIL 2996KBTU/HR 9.5EER | Design Size High Speed Rated Sensible Heat Ratio | 0.69808 |
| 96 | Coil:Cooling:DX:TwoSpeed | 1 ZONE PVAV 2 2SPD DX CLG COIL 2996KBTU/HR 9.5EER | Design Size Low Speed Rated Air Flow Rate [m3/s] | 12.73929 |
| 97 | Coil:Cooling:DX:TwoSpeed | 1 ZONE PVAV 2 2SPD DX CLG COIL 2996KBTU/HR 9.5EER | Design Size Low Speed Gross Rated Total Cooling Capacity [W] |<PHONE_NUMBER>3 |
| 98 | Coil:Cooling:DX:TwoSpeed | 1 ZONE PVAV 2 2SPD DX CLG COIL 2996KBTU/HR 9.5EER | User-Specified Low Speed Gross Rated Sensible Heat Ratio | 0.69000 |
| 99 | Coil:Heating:Water | 1 ZONE PVAV 2 MAIN HTG COIL | Design Size Rated Capacity [W] |<PHONE_NUMBER>3 |
| 100 | Coil:Heating:Water | 1 ZONE PVAV 2 MAIN HTG COIL | Design Size Maximum Water Flow Rate [m3/s] | 3.66671E-003 |
| 101 | Coil:Heating:Water | 1 ZONE PVAV 2 MAIN HTG COIL | Design Size U-Factor Times Area Value [W/K] | 2496.62058 |
| 102 | Fan:VariableVolume | 1 ZONE PVAV 2 FAN | Design Size Maximum Flow Rate [m3/s] | 38.22169 |
| 103 | Controller:WaterCoil | 1 ZONE PVAV 2 MAIN HTG COIL CONTROLLER | Maximum Actuated Flow [m3/s] | 3.66671E-003 |
| 104 | PlantLoop | FULLSERVICERESTAURANT KITCHEN - 90.1-2013 SERVICE WATER BOOSTER LOOP | Maximum Loop Flow Rate [m3/s] | 1.91591E-003 |
| 105 | PlantLoop | FULLSERVICERESTAURANT KITCHEN - 90.1-2013 SERVICE WATER BOOSTER LOOP | Plant Loop Volume [m3] | 0.22991 |
| 106 | Pump:VariableSpeed | BOOSTER WATER LOOP PUMP | Design Flow Rate [m3/s] | 1.91591E-003 |
| 107 | HeatExchanger:FluidToFluid | HX FOR BOOSTER WATER HEATING | Loop Supply Side Design Fluid Flow Rate [m3/s] | 1.91591E-003 |
| 108 | HeatExchanger:FluidToFluid | HX FOR BOOSTER WATER HEATING | Loop Demand Side Design Fluid Flow Rate [m3/s] | 1.91591E-003 |
| 109 | HeatExchanger:FluidToFluid | HX FOR BOOSTER WATER HEATING | Heat Exchanger U-Factor Times Area Value [W/C] | 2334.77868 |
| 110 | HeatExchanger:FluidToFluid | HX FOR BOOSTER WATER HEATING | Loop-to-loop Temperature Difference Used to Size Heat Exchanger U-Factor Times Area Value [C] | 17.22222 |
| 111 | WaterHeater:Mixed | 6.0GAL ELECTRICITY BOOSTER WATER HEATER - 367KBTU/HR 1.0 THERM EFF | Use Side Design Flow Rate [m3/s] | 1.91591E-003 |
| 112 | PlantComponent:TemperatureSource | MAINS WATER MAKEUP FOR SWH BOOSTER | Design Size Design Fluid Flow Rate [m3/s] | 1.08568E-002 |
| 113 | PlantLoop | FULLSERVICERESTAURANT KITCHEN - 90.1-2013 SERVICE WATER LOOP | Maximum Loop Flow Rate [m3/s] | 1.40500E-002 |
| 114 | PlantLoop | FULLSERVICERESTAURANT KITCHEN - 90.1-2013 SERVICE WATER LOOP | Plant Loop Volume [m3] | 1.68600 |
| 115 | Pump:VariableSpeed | FULLSERVICERESTAURANT KITCHEN - 90.1-2013 SERVICE WATER LOOP WATER MAINS PRESSURE DRIVEN | Design Flow Rate [m3/s] | 1.40500E-002 |
| 116 | Pump:VariableSpeed | FULLSERVICERESTAURANT KITCHEN - 90.1-2013 SERVICE WATER LOOP WATER MAINS PRESSURE DRIVEN | Design Power Consumption [W] | 2.57325E-005 |
| 117 | WaterHeater:Mixed | 1913GAL NATURALGAS WATER HEATER - 1913KBTU/HR 0.802 THERM EFF | Use Side Design Flow Rate [m3/s] | 1.40500E-002 |
| 118 | PlantLoop | HOT WATER LOOP | Maximum Loop Flow Rate [m3/s] | 3.67659E-002 |
| 119 | PlantLoop | HOT WATER LOOP | Plant Loop Volume [m3] | 4.41190 |
| 120 | Pump:VariableSpeed | HOT WATER LOOP PUMP | Design Flow Rate [m3/s] | 3.67659E-002 |
| 121 | Pump:VariableSpeed | HOT WATER LOOP PUMP | Design Power Consumption [W] | 9148.81683 |
| 122 | Boiler:HotWater | BOILER 5353KBTU/HR 0.8 THERMAL EFF | Design Size Nominal Capacity [W] | 1680890.56984 |
| 123 | Boiler:HotWater | BOILER 5353KBTU/HR 0.8 THERMAL EFF | Design Size Design Water Flow Rate [m3/s] | 3.67659E-002 |
| Component Type | Name | Nominal Total Capacity {W} | |
| 1 | Coil:Heating:Water | BUILDING STORY 1 THERMALZONE REHEAT COIL | 230576.31 |
| 2 | Coil:Heating:Water | BUILDING STORY 2 THERMALZONE REHEAT COIL | 271412.41 |
| 3 | Coil:Heating:Water | BUILDING STORY 3 THERMALZONE REHEAT COIL | 316069.64 |
| 4 | Coil:Heating:Water | 1 ZONE PVAV MAIN HTG COIL | 201369.05 |
| 5 | Coil:Heating:Water | 1 ZONE PVAV 1 MAIN HTG COIL | 231087.29 |
| 6 | Coil:Heating:Water | 1 ZONE PVAV 2 MAIN HTG COIL | 134665.52 |
| DX Coil Type | DX Coil Name | Fan Type | Fan Name | Standard Net Cooling Capacity {W} | Standard Net Cooling Capacity {Btu/h} | IEER {Btu/W-h} | COP 100% Capacity {W/W} | COP 75% Capacity {W/W} | COP 50% Capacity {W/W} | COP 25% Capacity {W/W} | EER 100% Capacity {Btu/W-h} | EER 75% Capacity {Btu/W-h} | EER 50% Capacity {Btu/W-h} | EER 25% Capacity {Btu/W-h} | Supply Air Flow 100% {kg/s} | Supply Air Flow 75% {kg/s} | Supply Air Flow 50% {kg/s} | Supply Air Flow 25% {kg/s} | |
| 1 | Coil:Cooling:DX:TwoSpeed | 1 ZONE PVAV 2SPD DX CLG COIL 2214KBTU/HR 9.5EER | N/A | N/A | 704017.29 | 2402206.71 | 10.82 | 2.89 | 3.13 | 3.24 | 3.30 | 9.87 | 10.67 | 11.06 | 11.26 | 33.0472 | 26.2379 | 18.2881 | 8.1846 |
| 2 | Coil:Cooling:DX:TwoSpeed | 1 ZONE PVAV 1 2SPD DX CLG COIL 2625KBTU/HR 9.5EER | N/A | N/A | 807916.83 | 2756726.65 | 10.82 | 2.89 | 3.13 | 3.24 | 3.30 | 9.87 | 10.67 | 11.06 | 11.26 | 37.9243 | 30.1101 | 20.9870 | 9.3925 |
| 3 | Coil:Cooling:DX:TwoSpeed | 1 ZONE PVAV 2 2SPD DX CLG COIL 2996KBTU/HR 9.5EER | N/A | N/A | 918026.13 | 3132435.18 | 10.82 | 2.89 | 3.13 | 3.24 | 3.30 | 9.87 | 10.67 | 11.06 | 11.26 | 43.0930 | 34.2138 | 23.8473 | 10.6726 |
| Environment Name | Environment Type | Start Date | End Date | Start DayOfWeek | Duration {#days} | Source:Start DayOfWeek | Use Daylight Saving | Use Holidays | Apply Weekend Holiday Rule | Use Rain Values | Use Snow Values | |
| 1 | RUN PERIOD 1 | WeatherFileRunPeriod | 01/01/2019 | 12/31/2019 | Tuesday | 365 | Use RunPeriod Specified Day | No | No | No | Yes | Yes |
| Daylight Saving Indicator | Source | Start Date | End Date | |
| 1 | Yes | InputFile | 03/10 | 11/03 |
| NumberofWarmupDays | |
| 1 | 6 |
| Style | Unit Conversion | |
| 1 | HTML | None |
| Zone Name | Environment Type/Name | Average Warmup Temperature Difference {deltaC} | Std Dev Warmup Temperature Difference {deltaC} | Max Temperature Pass/Fail Convergence | Min Temperature Pass/Fail Convergence | Average Warmup Load Difference {W} | Std Dev Warmup Load Difference {W} | Heating Load Pass/Fail Convergence | Cooling Load Pass/Fail Convergence | |
| 1 | BUILDING STORY 1 THERMALZONE | RunPeriod: RUN PERIOD 1 | 0.2098066170 | 0.4256891876 | Pass | Pass | 0.1909056469 | 0.2601322733 | Pass | Pass |
| 2 | BUILDING STORY 2 THERMALZONE | RunPeriod: RUN PERIOD 1 | 0.2355895987 | 0.5426906495 | Pass | Pass | 0.1776059541 | 0.2374441218 | Pass | Pass |
| 3 | BUILDING STORY 3 THERMALZONE | RunPeriod: RUN PERIOD 1 | 0.7454436827 | 1.2665131493 | Pass | Pass | 6.6839008162E-002 | 0.1899964903 | Pass | Pass |
Report: Annual Heat Emissions Summary
For: Entire Facility
Timestamp: 2020-03-25 14:42:09
Heat Emission by Components| Envelope Convection | Zone Exfiltration | Zone Exhaust Air | HVAC Relief Air | HVAC Reject Heat | Total | |
| Heat Emissions [GJ] | 2233.26 | 1234.11 | 0.00 | 12402.68 | 18674.19 | 34544.21 |
Report: Climatic Data Summary
For: Entire Facility
Timestamp: 2020-03-25 14:42:09
SizingPeriod:DesignDay| Maximum Dry Bulb [C] | Daily Temperature Range [deltaC] | Humidity Value | Humidity Type | Wind Speed [m/s] | Wind Direction | |
| BUFFALO NIAGARA INTL AP ANN CLG .4% CONDNS DB=>MWB 1 | 30.30 | 9.30 | 21.80 | Wetbulb [C] | 5.70 | 240.00 |
| BUFFALO NIAGARA INTL AP ANN CLG .4% CONDNS WB=>MDB 1 | 27.80 | 9.30 | 23.80 | Wetbulb [C] | 5.70 | 240.00 |
| BUFFALO NIAGARA INTL AP ANN HTG 99.6% CONDNS DB 1 | -16.30 | 0.00 | -16.30 | Wetbulb [C] | 5.10 | 270.00 |
| Value | |
| None |
Report: Envelope Summary
For: Entire Facility
Timestamp: 2020-03-25 14:42:09
Opaque Exterior| Construction | Reflectance | U-Factor with Film [W/m2-K] | U-Factor no Film [W/m2-K] | Gross Area [m2] | Net Area [m2] | Azimuth [deg] | Tilt [deg] | Cardinal Direction | |
| SURFACE 2 | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-20.41 | 0.30 | 0.278 | 0.290 | 83.63 | 58.54 | 161.87 | 90.00 | S |
| SURFACE 3 | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-20.41 | 0.30 | 0.278 | 0.290 | 418.47 | 292.93 | 251.74 | 90.00 | W |
| SURFACE 4 | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-20.41 | 0.30 | 0.278 | 0.290 | 83.63 | 58.54 | 341.87 | 90.00 | N |
| SURFACE 5 | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-20.41 | 0.30 | 0.278 | 0.290 | 418.47 | 292.93 | 71.74 | 90.00 | E |
| SURFACE 1 | TYPICAL INSULATED CARPETED 8IN SLAB FLOOR | 0.30 | 2.144 | 3.285 | 3888.51 | 3888.51 | 71.74 | 180.00 | |
| SURFACE 10 | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-20.41 | 0.30 | 0.278 | 0.290 | 83.63 | 58.54 | 341.87 | 90.00 | N |
| SURFACE 11 | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-20.41 | 0.30 | 0.278 | 0.290 | 418.47 | 292.93 | 71.74 | 90.00 | E |
| SURFACE 8 | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-20.41 | 0.30 | 0.278 | 0.290 | 83.63 | 58.54 | 161.87 | 90.00 | S |
| SURFACE 9 | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-20.41 | 0.30 | 0.278 | 0.290 | 418.47 | 292.93 | 251.74 | 90.00 | W |
| SURFACE 14 | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-20.41 | 0.30 | 0.278 | 0.290 | 83.63 | 58.54 | 161.87 | 90.00 | S |
| SURFACE 15 | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-20.41 | 0.30 | 0.278 | 0.290 | 418.47 | 292.93 | 251.74 | 90.00 | W |
| SURFACE 16 | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-20.41 | 0.30 | 0.278 | 0.290 | 83.63 | 58.54 | 341.87 | 90.00 | N |
| SURFACE 17 | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-20.41 | 0.30 | 0.278 | 0.290 | 418.47 | 292.93 | 71.74 | 90.00 | E |
| SURFACE 18 | TYPICAL WOOD JOIST ATTIC FLOOR R-47.62 | 0.30 | 0.120 | 0.122 | 3888.51 | 3888.51 | 251.74 | 0.00 |
| Construction | Glass Area [m2] | Frame Area [m2] | Divider Area [m2] | Area of One Opening [m2] | Area of Multiplied Openings [m2] | Glass U-Factor [W/m2-K] | Glass SHGC | Glass Visible Transmittance | Frame Conductance [W/m2-K] | Divider Conductance [W/m2-K] | Shade Control | Parent Surface | Azimuth [deg] | Tilt [deg] | Cardinal Direction | |
| SUB SURFACE 1 | U 0.48 SHGC 0.40 DBL REF-D CLR 6MM/13MM | 25.09 | 0.00 | 0.00 | 25.09 | 25.09 | 2.653 | 0.426 | 0.308 | No | SURFACE 2 | 161.87 | 90.00 | S | ||
| SUB SURFACE 2 | U 0.48 SHGC 0.40 DBL REF-D CLR 6MM/13MM | 125.54 | 0.00 | 0.00 | 125.54 | 125.54 | 2.653 | 0.426 | 0.308 | No | SURFACE 3 | 251.74 | 90.00 | W | ||
| SUB SURFACE 3 | U 0.48 SHGC 0.40 DBL REF-D CLR 6MM/13MM | 25.09 | 0.00 | 0.00 | 25.09 | 25.09 | 2.653 | 0.426 | 0.308 | No | SURFACE 4 | 341.87 | 90.00 | N | ||
| SUB SURFACE 4 | U 0.48 SHGC 0.40 DBL REF-D CLR 6MM/13MM | 125.54 | 0.00 | 0.00 | 125.54 | 125.54 | 2.653 | 0.426 | 0.308 | No | SURFACE 5 | 71.74 | 90.00 | E | ||
| SUB SURFACE 7 | U 0.48 SHGC 0.40 DBL REF-D CLR 6MM/13MM | 25.09 | 0.00 | 0.00 | 25.09 | 25.09 | 2.653 | 0.426 | 0.308 | No | SURFACE 10 | 341.87 | 90.00 | N | ||
| SUB SURFACE 8 | U 0.48 SHGC 0.40 DBL REF-D CLR 6MM/13MM | 125.54 | 0.00 | 0.00 | 125.54 | 125.54 | 2.653 | 0.426 | 0.308 | No | SURFACE 11 | 71.74 | 90.00 | E | ||
| SUB SURFACE 5 | U 0.48 SHGC 0.40 DBL REF-D CLR 6MM/13MM | 25.09 | 0.00 | 0.00 | 25.09 | 25.09 | 2.653 | 0.426 | 0.308 | No | SURFACE 8 | 161.87 | 90.00 | S | ||
| SUB SURFACE 6 | U 0.48 SHGC 0.40 DBL REF-D CLR 6MM/13MM | 125.54 | 0.00 | 0.00 | 125.54 | 125.54 | 2.653 | 0.426 | 0.308 | No | SURFACE 9 | 251.74 | 90.00 | W | ||
| SUB SURFACE 9 | U 0.48 SHGC 0.40 DBL REF-D CLR 6MM/13MM | 25.09 | 0.00 | 0.00 | 25.09 | 25.09 | 2.653 | 0.426 | 0.308 | No | SURFACE 14 | 161.87 | 90.00 | S | ||
| SUB SURFACE 10 | U 0.48 SHGC 0.40 DBL REF-D CLR 6MM/13MM | 125.54 | 0.00 | 0.00 | 125.54 | 125.54 | 2.653 | 0.426 | 0.308 | No | SURFACE 15 | 251.74 | 90.00 | W | ||
| SUB SURFACE 11 | U 0.48 SHGC 0.40 DBL REF-D CLR 6MM/13MM | 25.09 | 0.00 | 0.00 | 25.09 | 25.09 | 2.653 | 0.426 | 0.308 | No | SURFACE 16 | 341.87 | 90.00 | N | ||
| SUB SURFACE 12 | U 0.48 SHGC 0.40 DBL REF-D CLR 6MM/13MM | 125.54 | 0.00 | 0.00 | 125.54 | 125.54 | 2.653 | 0.426 | 0.308 | No | SURFACE 17 | 71.74 | 90.00 | E | ||
| Total or Average | 903.79 | 2.653 | 0.426 | 0.308 | ||||||||||||
| North Total or Average | 75.27 | 2.653 | 0.426 | 0.308 | ||||||||||||
| Non-North Total or Average | 828.52 | 2.653 | 0.426 | 0.308 |
| Construction | Area of One Opening [m2] | Area of Openings [m2] | Glass U-Factor [W/m2-K] | Glass SHGC | Glass Visible Transmittance | Parent Surface | |
| Total or Average | 0.00 | - | - | - |
| Construction | U-Factor with Film [W/m2-K] | U-Factor no Film [W/m2-K] | Gross Area [m2] | Parent Surface | |
| None |
Report: Shading Summary
For: Entire Facility
Timestamp: 2020-03-25 14:42:09
Sunlit Fraction| March 21 9am | March 21 noon | March 21 3pm | June 21 9am | June 21 noon | June 21 3pm | December 21 9am | December 21 noon | December 21 3pm | |
| None |
| Name | Type | Shaded Construction | Control | Glare Control | |
| None |
Report: Lighting Summary
For: Entire Facility
Timestamp: 2020-03-25 14:42:09
Interior Lighting| Zone | Lighting Power Density [W/m2] | Zone Area [m2] | Total Power [W] | End Use Subcategory | Schedule Name | Scheduled Hours/Week [hr] | Hours/Week > 1% [hr] | Full Load Hours/Week [hr] | Return Air Fraction | Conditioned (Y/N) | Consumption [GJ] | |
| BUILDING STORY 3 THERMALZONE FULLSERVICERESTAURANT DINING LIGHTS 1 | BUILDING STORY 3 THERMALZONE | 1.7397 | 3888.51 | 6764.86 | General | RESTAURANTSITDOWN BLDG_LIGHT_DINING_SCH_2013 | 91.84 | 167.98 | 91.83 | 0.0000 | Y | 116.61 |
| BUILDING STORY 3 THERMALZONE FULLSERVICERESTAURANT KITCHEN LIGHTS 1 | BUILDING STORY 3 THERMALZONE | 10.6591 | 3888.51 | 41448.05 | General | RESTAURANTSITDOWN BLDG_LIGHT_KITCHEN_SCH_2010_2013 | 81.02 | 167.98 | 81.01 | 0.0000 | Y | 630.33 |
| BUILDING STORY 2 THERMALZONE FULLSERVICERESTAURANT DINING LIGHTS 2 | BUILDING STORY 2 THERMALZONE | 9.5799 | 3888.51 | 37251.44 | General | RESTAURANTSITDOWN BLDG_LIGHT_DINING_SCH_2013 | 91.84 | 167.98 | 87.42 | 0.0000 | Y | 611.31 |
| BUILDING STORY 1 THERMALZONE FULLSERVICERESTAURANT DINING LIGHTS 3 | BUILDING STORY 1 THERMALZONE | 9.5799 | 3888.51 | 37251.44 | General | RESTAURANTSITDOWN BLDG_LIGHT_DINING_SCH_2013 | 91.84 | 167.98 | 86.36 | 0.0000 | Y | 603.87 |
| Interior Lighting Total | 7.8896 | 15554.03 | 122715.80 | 1962.12 |
| Zone | Control Name | Daylighting Method | Control Type | Fraction Controlled | Lighting Installed in Zone [W] | Lighting Controlled [W] | |
| BUILDING STORY 1 SPACE DAYLT SENSOR 1 | BUILDING STORY 1 THERMALZONE | BUILDING STORY 1 THERMALZONE DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.14 | 37251.44 | 5215.20 |
| BUILDING STORY 1 SPACE DAYLT SENSOR 2 | BUILDING STORY 1 THERMALZONE | BUILDING STORY 1 THERMALZONE DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.39 | 37251.44 | 14565.31 |
| BUILDING STORY 2 SPACE DAYLT SENSOR 1 | BUILDING STORY 2 THERMALZONE | BUILDING STORY 2 THERMALZONE DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.14 | 37251.44 | 5215.20 |
| BUILDING STORY 2 SPACE DAYLT SENSOR 2 | BUILDING STORY 2 THERMALZONE | BUILDING STORY 2 THERMALZONE DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.26 | 37251.44 | 9797.13 |
| BUILDING STORY 3 SPACE DAYLT SENSOR 1 | BUILDING STORY 3 THERMALZONE | BUILDING STORY 3 THERMALZONE DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.14 | 48212.91 | 6749.81 |
| BUILDING STORY 3 SPACE DAYLT SENSOR 2 | BUILDING STORY 3 THERMALZONE | BUILDING STORY 3 THERMALZONE DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.39 | 48212.91 | 18851.25 |
| Total Watts | Astronomical Clock/Schedule | Schedule Name | Scheduled Hours/Week [hr] | Hours/Week > 1% [hr] | Full Load Hours/Week [hr] | Consumption [GJ] | |
| BUILDING FACADES | 1227.83 | AstronomicalClock | - | 41.52 | 41.52 | 9.57 | |
| MAIN ENTRIES | 1005.05 | AstronomicalClock | - | 83.52 | 70.92 | 13.38 | |
| OTHER DOORS | 1005.05 | AstronomicalClock | - | 83.52 | 70.92 | 13.38 | |
| PARKING AREAS AND DRIVES | 50880.56 | AstronomicalClock | - | 83.52 | 70.92 | 677.36 | |
| Exterior Lighting Total | 54118.48 | 713.69 |
Report: Equipment Summary
For: Entire Facility
Timestamp: 2020-03-25 14:42:09
Central Plant| Type | Nominal Capacity [W] | Nominal Efficiency [W/W] | IPLV in SI Units [W/W] | IPLV in IP Units [Btu/W-h] | |
| HX FOR BOOSTER WATER HEATING | HeatExchanger:FluidToFluid | 138074.78 | |||
| BOILER 5353KBTU/HR 0.8 THERMAL EFF | Boiler:HotWater | 1680890.57 | 0.80 |
| Type | Design Coil Load [W] | Nominal Total Capacity [W] | Nominal Sensible Capacity [W] | Nominal Latent Capacity [W] | Nominal Sensible Heat Ratio | Nominal Efficiency [W/W] | Nominal Coil UA Value [W/C] | Nominal Coil Surface Area [m2] | |
| 1 ZONE PVAV 2SPD DX CLG COIL 2214KBTU/HR 9.5EER | Coil:Cooling:DX:TwoSpeed | 727874.55 | 508117.01 | 219757.54 | 0.70 | 3.30 | |||
| 1 ZONE PVAV 1 2SPD DX CLG COIL 2625KBTU/HR 9.5EER | Coil:Cooling:DX:TwoSpeed | 835294.97 | 583105.40 | 252189.57 | 0.70 | 3.30 | |||
| 1 ZONE PVAV 2 2SPD DX CLG COIL 2996KBTU/HR 9.5EER | Coil:Cooling:DX:TwoSpeed | 949135.58 | 662575.62 | 286559.96 | 0.70 | 3.30 |
| DX Cooling Coil Type | Standard Rated Net Cooling Capacity [W] | Standard Rated Net COP [W/W] | EER [Btu/W-h] | SEER [Btu/W-h] | IEER [Btu/W-h] | |
| 1 ZONE PVAV 2SPD DX CLG COIL 2214KBTU/HR 9.5EER | 704017.3 | 2.89 | 9.87 | N/A | 10.82 | |
| 1 ZONE PVAV 1 2SPD DX CLG COIL 2625KBTU/HR 9.5EER | 807916.8 | 2.89 | 9.87 | N/A | 10.82 | |
| 1 ZONE PVAV 2 2SPD DX CLG COIL 2996KBTU/HR 9.5EER | 918026.1 | 2.89 | 9.87 | N/A | 10.82 |
| DX Cooling Coil Type | Rated Net Cooling Capacity Test A [W] | Rated Electric Power Test A [W] | Rated Net Cooling Capacity Test B [W] | Rated Electric Power Test B [W] | Rated Net Cooling Capacity Test C [W] | Rated Electric Power Test C [W] | Rated Net Cooling Capacity Test D [W] | Rated Electric Power Test D [W] | |
| 1 ZONE PVAV 2SPD DX CLG COIL 2214KBTU/HR 9.5EER | Coil:Cooling:DX:TwoSpeed | ||||||||
| 1 ZONE PVAV 1 2SPD DX CLG COIL 2625KBTU/HR 9.5EER | Coil:Cooling:DX:TwoSpeed | ||||||||
| 1 ZONE PVAV 2 2SPD DX CLG COIL 2996KBTU/HR 9.5EER | Coil:Cooling:DX:TwoSpeed |
| DX Heating Coil Type | High Temperature Heating (net) Rating Capacity [W] | Low Temperature Heating (net) Rating Capacity [W] | HSPF [Btu/W-h] | Region Number | |
| None |
| Type | Design Coil Load [W] | Nominal Total Capacity [W] | Nominal Efficiency [W/W] | |
| BUILDING STORY 1 THERMALZONE REHEAT COIL | Coil:Heating:Water | 243940.06 | 230576.31 | - |
| BUILDING STORY 2 THERMALZONE REHEAT COIL | Coil:Heating:Water | 287148.75 | 271412.41 | - |
| BUILDING STORY 3 THERMALZONE REHEAT COIL | Coil:Heating:Water | 334401.84 | 316069.64 | - |
| 1 ZONE PVAV MAIN HTG COIL | Coil:Heating:Water | 301624.11 | 201369.05 | - |
| 1 ZONE PVAV 1 MAIN HTG COIL | Coil:Heating:Water | 346138.08 | 231087.29 | - |
| 1 ZONE PVAV 2 MAIN HTG COIL | Coil:Heating:Water | 167637.73 | 134665.52 | - |
| Type | Total Efficiency [W/W] | Delta Pressure [pa] | Max Air Flow Rate [m3/s] | Rated Electric Power [W] | Rated Power Per Max Air Flow Rate [W-s/m3] | Motor Heat In Air Fraction | Fan Energy Index | End Use Subcategory | Design Day Name for Fan Sizing Peak | Date/Time for Fan Sizing Peak | |
| 1 ZONE PVAV FAN | Fan:VariableVolume | 0.62 | 1389.92 | 29.31 | 65699.95 | 2241.44 | 1.00 | 1.11 | General | BUFFALO NIAGARA INTL AP ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 09:00:00 |
| 1 ZONE PVAV 1 FAN | Fan:VariableVolume | 0.62 | 1389.92 | 33.64 | 75396.01 | 2241.44 | 1.00 | 1.10 | General | BUFFALO NIAGARA INTL AP ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 09:00:00 |
| 1 ZONE PVAV 2 FAN | Fan:VariableVolume | 0.62 | 1389.92 | 38.22 | 85671.57 | 2241.44 | 1.00 | 1.10 | General | BUFFALO NIAGARA INTL AP ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 07:00:00 |
| Type | Control | Head [pa] | Water Flow [m3/s] | Electric Power [W] | Power Per Water Flow Rate [W-s/m3] | Motor Efficiency [W/W] | End Use Subcategory | |
| BOOSTER WATER LOOP PUMP | Pump:VariableSpeed | Continuous | 0.00 | 0.001916 | 0.00 | 0.00 | 1.00 | General |
| FULLSERVICERESTAURANT KITCHEN - 90.1-2013 SERVICE WATER LOOP WATER MAINS PRESSURE DRIVEN | Pump:VariableSpeed | Continuous | 0.00 | 0.014050 | 0.00 | 0.00 | 0.70 | General |
| HOT WATER LOOP PUMP | Pump:VariableSpeed | Intermittent | 179344.02 | 0.036766 | 9148.82 | 248840.07 | 0.92 | General |
| Type | Storage Volume [m3] | Input [W] | Thermal Efficiency [W/W] | Recovery Efficiency [W/W] | Energy Factor | |
| 6.0GAL ELECTRICITY BOOSTER WATER HEATER - 367KBTU/HR 1.0 THERM EFF | WaterHeater:Mixed | 0.02 | 107653.18 | 1.00 | 38.03 | 0.92 |
| 1913GAL NATURALGAS WATER HEATER - 1913KBTU/HR 0.802 THERM EFF | WaterHeater:Mixed | 7.24 | 560693.64 | 0.80 | 0.10 | 0.29 |
| DX Cooling Coil Type | Assocated Fan | Net Cooling Capacity [W] | COP [W/W] | EER [Btu/W-h] | IEER [Btu/W-h] | Supply Air Flow 100% [kg/s] | COP 75% Capacity [W/W] | EER 75% Capacity [Btu/W-h] | Supply Air Flow 75% [kg/s] | COP 50% Capacity [W/W] | EER 50% Capacity [Btu/W-h] | Supply Air Flow 50% [kg/s] | COP 25% Capacity [W/W] | EER 25% Capacity [Btu/W-h] | Supply Air Flow 25% [kg/s] | |
| 1 ZONE PVAV 2SPD DX CLG COIL 2214KBTU/HR 9.5EER | Coil:Cooling:DX:TwoSpeed | None | 704017.29 | 2.89 | 9.87 | 10.82 | 33.0472 | 3.13 | 10.67 | 26.2379 | 3.24 | 11.06 | 18.2881 | 3.30 | 11.26 | 8.1846 |
| 1 ZONE PVAV 1 2SPD DX CLG COIL 2625KBTU/HR 9.5EER | Coil:Cooling:DX:TwoSpeed | None | 807916.83 | 2.89 | 9.87 | 10.82 | 37.9243 | 3.13 | 10.67 | 30.1101 | 3.24 | 11.06 | 20.9870 | 3.30 | 11.26 | 9.3925 |
| 1 ZONE PVAV 2 2SPD DX CLG COIL 2996KBTU/HR 9.5EER | Coil:Cooling:DX:TwoSpeed | None | 918026.13 | 2.89 | 9.87 | 10.82 | 43.0930 | 3.13 | 10.67 | 34.2138 | 3.24 | 11.06 | 23.8473 | 3.30 | 11.26 | 10.6726 |
Report: HVAC Sizing Summary
For: Entire Facility
Timestamp: 2020-03-25 14:42:09
Zone Sensible Cooling| Calculated Design Load [W] | User Design Load [W] | User Design Load per Area [W/m2] | Calculated Design Air Flow [m3/s] | User Design Air Flow [m3/s] | Design Day Name | Date/Time Of Peak {TIMESTAMP} | Thermostat Setpoint Temperature at Peak Load [C] | Indoor Temperature at Peak Load [C] | Indoor Humidity Ratio at Peak Load [kgWater/kgAir] | Outdoor Temperature at Peak Load [C] | Outdoor Humidity Ratio at Peak Load [kgWater/kgAir] | Minimum Outdoor Air Flow Rate [m3/s] | Heat Gain Rate from DOAS [W] | |
| BUILDING STORY 1 THERMALZONE | 341571.28 | 392806.97 | 101.02 | 25.488 | 29.312 | BUFFALO NIAGARA INTL AP ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 09:00:00 | 24.00 | 23.96 | 0.01000 | 25.18 | 0.01335 | 13.926 | 0.00 |
| BUILDING STORY 2 THERMALZONE | 391714.40 | 450471.56 | 115.85 | 29.250 | 33.637 | BUFFALO NIAGARA INTL AP ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 09:00:00 | 24.00 | 23.95 | 0.01019 | 25.18 | 0.01335 | 13.926 | 0.00 |
| BUILDING STORY 3 THERMALZONE | 541954.14 | 623247.26 | 160.28 | 33.236 | 38.222 | BUFFALO NIAGARA INTL AP ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 07:00:00 | 26.00 | 26.33 | 0.01112 | 21.84 | 0.01335 | 6.045 | 0.00 |
| Calculated Design Load [W] | User Design Load [W] | User Design Load per Area [W/m2] | Calculated Design Air Flow [m3/s] | User Design Air Flow [m3/s] | Design Day Name | Date/Time Of Peak {TIMESTAMP} | Thermostat Setpoint Temperature at Peak Load [C] | Indoor Temperature at Peak Load [C] | Indoor Humidity Ratio at Peak Load [kgWater/kgAir] | Outdoor Temperature at Peak Load [C] | Outdoor Humidity Ratio at Peak Load [kgWater/kgAir] | Minimum Outdoor Air Flow Rate [m3/s] | Heat Gain Rate from DOAS [W] | |
| BUILDING STORY 1 THERMALZONE | 33660.20 | 42075.25 | 10.82 | 0.970 | 13.926 | BUFFALO NIAGARA INTL AP ANN HTG 99.6% CONDNS DB 1 | 1/21 24:00:00 | 21.00 | 21.00 | 0.00779 | -16.30 | 0.00092 | 13.926 | 0.00 |
| BUILDING STORY 2 THERMALZONE | 44772.79 | 55965.98 | 14.39 | 1.290 | 13.926 | BUFFALO NIAGARA INTL AP ANN HTG 99.6% CONDNS DB 1 | 1/21 24:00:00 | 21.00 | 21.00 | 0.00683 | -16.30 | 0.00092 | 13.926 | 0.00 |
| BUILDING STORY 3 THERMALZONE | 109075.84 | 136344.79 | 35.06 | 2.938 | 6.045 | BUFFALO NIAGARA INTL AP ANN HTG 99.6% CONDNS DB 1 | 1/21 24:00:00 | 19.00 | 18.99 | 0.00563 | -16.30 | 0.00092 | 6.045 | 0.00 |
| Calculated cooling [m3/s] | User cooling [m3/s] | Calculated heating [m3/s] | User heating [m3/s] | Adjusted cooling [m3/s] | Adjusted heating [m3/s] | Adjusted main [m3/s] | Calculated Heating Air Flow Ratio [] | User Heating Air Flow Ratio [] | |
| 1 ZONE PVAV | 29.31 | 29.31 | 13.93 | 13.93 | 29.3115 | 20.5181 | 29.3115 | 0.7000 | 0.3000 |
| 1 ZONE PVAV 1 | 33.64 | 33.64 | 13.93 | 13.93 | 33.6373 | 23.5461 | 33.6373 | 0.7000 | 0.3000 |
| 1 ZONE PVAV 2 | 38.22 | 38.22 | 6.05 | 6.05 | 38.2217 | 26.7552 | 38.2217 | 0.7000 | 0.3000 |
| Previous Design Volume Flow Rate [m3/s] | Algorithm Volume Flow Rate [m3/s] | Coincident Design Volume Flow Rate [m3/s] | Coincident Size Adjusted | Peak Sizing Period Name | Peak Day into Period {TIMESTAMP}[day] | Peak Hour Of Day {TIMESTAMP}[hr] | Peak Step Start Minute {TIMESTAMP}[min] | |
| None |
| Coil Type | HVAC Type | HVAC Name | Coil Final Gross Total Capacity [W] | Coil Final Gross Sensible Capacity [W] | Coil Final Reference Air Volume Flow Rate [m3/s] | Coil Final Reference Plant Fluid Volume Flow Rate [m3/s] | Coil U-value Times Area Value [W/K] | Design Day Name at Sensible Ideal Loads Peak | Date/Time at Sensible Ideal Loads Peak | Design Day Name at Air Flow Ideal Loads Peak | Date/Time at Air Flow Ideal Loads Peak | Coil Total Capacity at Ideal Loads Peak [W] | Coil Sensible Capacity at Ideal Loads Peak [W] | Coil Air Volume Flow Rate at Ideal Loads Peak [m3/s] | Coil Entering Air Drybulb at Ideal Loads Peak [C] | Coil Entering Air Wetbulb at Ideal Loads Peak [C] | Coil Entering Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Coil Leaving Air Drybulb at Ideal Loads Peak [C] | Coil Leaving Air Wetbulb at Ideal Loads Peak [C] | Coil Leaving Air Humidity Ratio at Ideal Loads Peak [C] | Outdoor Air Drybulb at Ideal Loads Peak [C] | Outdoor Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Outdoor Air Wetbulb at Ideal Loads Peak [C] | Outdoor Air Flow Percentage at Ideal Loads Peak [%] | Zone Air Drybulb at Ideal Loads Peak [C] | Zone Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Zone Air Relative Humidity at Ideal Loads Peak [%] | Zone Sensible Heat Gain at Ideal Loads Peak [W] | Zone Latent Heat Gain at Ideal Loads Peak [W] | Coil Total Capacity at Rating Conditions [W] | Coil Sensible Capacity at Rating Conditions [W] | |
| BUILDING STORY 1 THERMALZONE REHEAT COIL | COIL:HEATING:WATER | ZONEHVAC:AIRDISTRIBUTIONUNIT | ADU BUILDING STORY 1 THERMALZONE VAV TERMINAL | 243940.057 | 243940.057 | 20.518056 | 0.00533566 | 4329.248 | BUFFALO NIAGARA INTL AP ANN HTG 99.6% CONDNS DB 1 | 1/21 24:00:00 | BUFFALO NIAGARA INTL AP ANN HTG 99.6% CONDNS DB 1 | 1/21 24:00:00 | 230576.31 | 243940.06 | 20.518056 | 12.78 | 11.36 | 0.00800000 | 50.00 | 23.63 | 0.00800000 | -16.30 | 0.00092409 | -16.30 | 0.0000 | 21.00 | 0.00779318 | 49.1323 | 42075.25 | 0.00 | 244188.11 | 244188.11 |
| BUILDING STORY 2 THERMALZONE REHEAT COIL | COIL:HEATING:WATER | ZONEHVAC:AIRDISTRIBUTIONUNIT | ADU BUILDING STORY 2 THERMALZONE VAV TERMINAL | 287148.753 | 287148.753 | 23.546130 | 0.00628076 | 5113.657 | BUFFALO NIAGARA INTL AP ANN HTG 99.6% CONDNS DB 1 | 1/21 24:00:00 | BUFFALO NIAGARA INTL AP ANN HTG 99.6% CONDNS DB 1 | 1/21 24:00:00 | 271412.41 | 287148.75 | 23.546130 | 12.78 | 11.36 | 0.00800000 | 50.00 | 23.63 | 0.00800000 | -16.30 | 0.00092409 | -16.30 | 0.0000 | 21.00 | 0.00682570 | 43.1051 | 55965.98 | 0.00 | 287438.10 | 287438.10 |
| BUILDING STORY 3 THERMALZONE REHEAT COIL | COIL:HEATING:WATER | ZONEHVAC:AIRDISTRIBUTIONUNIT | ADU BUILDING STORY 3 THERMALZONE VAV TERMINAL | 334401.843 | 334401.843 | 26.755183 | 0.00731432 | 5975.605 | BUFFALO NIAGARA INTL AP ANN HTG 99.6% CONDNS DB 1 | 1/21 24:00:00 | BUFFALO NIAGARA INTL AP ANN HTG 99.6% CONDNS DB 1 | 1/21 24:00:00 | 316069.64 | 334401.84 | 26.755183 | 12.78 | 11.36 | 0.00800000 | 50.00 | 23.63 | 0.00800000 | -16.30 | 0.00092409 | -16.30 | 0.0000 | 18.99 | 0.00562994 | 40.3419 | 136344.79 | 0.00 | 334735.81 | 334735.81 |
| 1 ZONE PVAV 2SPD DX CLG COIL 2214KBTU/HR 9.5EER | Coil:Cooling:DX:TwoSpeed | AirLoopHVAC | 1 ZONE PVAV | 727874.552 | 508117.011 | 29.311508 | -999.0 | -999.000 | BUFFALO NIAGARA INTL AP ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 14:00:00 | BUFFALO NIAGARA INTL AP ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 09:00:00 | 696577.61 | 444726.58 | 29.311508 | 27.21 | 20.03 | 0.01212311 | 10.92 | 10.92 | 0.00850000 | 30.30 | 0.01334551 | 21.80 | 47.5114 | 23.96 | 0.00999847 | 52.4644 | 315610.16 | 0.00 | 727416.78 | 504744.51 |
| 1 ZONE PVAV MAIN HTG COIL | Coil:Heating:Water | AirLoopHVAC | 1 ZONE PVAV | 301624.108 | 301624.108 | 8.793452 | 0.00659738 | 3962.859 | BUFFALO NIAGARA INTL AP ANN HTG 99.6% CONDNS DB 1 | 1/21 01:00:00 | BUFFALO NIAGARA INTL AP ANN HTG 99.6% CONDNS DB 1 | 1/21 01:00:00 | 201369.05 | 301624.11 | 8.793452 | -16.30 | -16.30 | 0.00092409 | 12.78 | 11.36 | 0.00800000 | -16.30 | 0.00092409 | -16.30 | 158.3713 | 21.00 | 0.00779318 | 49.1323 | 33655.03 | 0.00 | 229905.50 | 229905.50 |
| 1 ZONE PVAV 1 2SPD DX CLG COIL 2625KBTU/HR 9.5EER | Coil:Cooling:DX:TwoSpeed | AirLoopHVAC | 1 ZONE PVAV 1 | 835294.967 | 583105.401 | 33.637328 | -999.0 | -999.000 | BUFFALO NIAGARA INTL AP ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 14:00:00 | BUFFALO NIAGARA INTL AP ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 09:00:00 | 805887.32 | 526955.04 | 33.637328 | 26.79 | 19.66 | 0.01179899 | 10.92 | 10.92 | 0.00850000 | 30.30 | 0.01334551 | 21.80 | 41.4013 | 23.95 | 0.01019485 | 53.5026 | 381206.58 | 0.00 | 834769.64 | 579235.19 |
| 1 ZONE PVAV 1 MAIN HTG COIL | Coil:Heating:Water | AirLoopHVAC | 1 ZONE PVAV 1 | 346138.079 | 346138.079 | 10.091199 | 0.00757102 | 4547.701 | BUFFALO NIAGARA INTL AP ANN HTG 99.6% CONDNS DB 1 | 1/21 01:00:00 | BUFFALO NIAGARA INTL AP ANN HTG 99.6% CONDNS DB 1 | 1/21 01:00:00 | 231087.29 | 346138.08 | 10.091199 | -16.30 | -16.30 | 0.00092409 | 12.78 | 11.36 | 0.00800000 | -16.30 | 0.00092409 | -16.30 | 138.0045 | 21.00 | 0.00682570 | 43.1051 | 44736.70 | 0.00 | 263835.17 | 263835.17 |
| 1 ZONE PVAV 2 2SPD DX CLG COIL 2996KBTU/HR 9.5EER | Coil:Cooling:DX:TwoSpeed | AirLoopHVAC | 1 ZONE PVAV 2 | 949135.577 | 662575.620 | 38.221690 | -999.0 | -999.000 | BUFFALO NIAGARA INTL AP ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 15:00:00 | BUFFALO NIAGARA INTL AP ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 07:00:00 | 925137.99 | 642863.74 | 38.221690 | 26.71 | 19.20 | 0.01122235 | 10.92 | 10.92 | 0.00850000 | 30.30 | 0.01334551 | 21.80 | 15.8162 | 26.33 | 0.01112089 | 50.5802 | 478805.44 | 0.00 | 948538.65 | 658177.94 |
| 1 ZONE PVAV 2 MAIN HTG COIL | Coil:Heating:Water | AirLoopHVAC | 1 ZONE PVAV 2 | 167637.730 | 167637.730 | 11.466507 | 0.00366671 | 2496.621 | BUFFALO NIAGARA INTL AP ANN HTG 99.6% CONDNS DB 1 | 1/21 01:00:00 | BUFFALO NIAGARA INTL AP ANN HTG 99.6% CONDNS DB 1 | 1/21 01:00:00 | 134665.52 | 167637.73 | 11.466507 | -16.30 | -16.30 | 0.00092409 | 12.78 | 11.36 | 0.00800000 | -16.30 | 0.00092409 | -16.30 | 52.7205 | 18.99 | 0.00562994 | 40.3419 | 109074.59 | 0.00 | 153916.64 | 153916.64 |
Report: Coil Sizing Details
For: Entire Facility
Timestamp: 2020-03-25 14:42:09
Coils| Coil Type | Coil Location | HVAC Type | HVAC Name | Zone Name(s) | System Sizing Method Concurrence | System Sizing Method Capacity | System Sizing Method Air Flow | Autosized Coil Capacity? | Autosized Coil Airflow? | Autosized Coil Water Flow? | OA Pretreated prior to coil inlet? | Coil Final Gross Total Capacity [W] | Coil Final Gross Sensible Capacity [W] | Coil Final Reference Air Volume Flow Rate [m3/s] | Coil Final Reference Plant Fluid Volume Flow Rate [m3/s] | Coil U-value Times Area Value [W/K] | Terminal Unit Reheat Coil Multiplier | DX Coil Capacity Increase Ratio from Too Low Flow/Capacity Ratio | DX Coil Capacity Decrease Ratio from Too High Flow/Capacity Ratio | Moist Air Heat Capacity [J/kg-K] | Dry Air Heat Capacity [J/kg-K] | Standard Air Density Adjusted for Elevation [kg/m3] | Supply Fan Name for Coil | Supply Fan Type for Coil | Supply Fan Maximum Air Volume Flow Rate [m3/s] | Supply Fan Maximum Air Mass Flow Rate [kg/s] | Plant Name for Coil | Plant Fluid Specific Heat Capacity [J/kg-K] | Plant Fluid Density [kg/m3] | Plant Maximum Fluid Mass Flow Rate [kg/s] | Plant Design Fluid Return Temperature [C] | Plant Design Fluid Supply Temperature [C] | Plant Design Fluid Temperature Difference [deltaC] | Plant Design Capacity [W] | Coil Capacity Percentage of Plant Design Capacity [%] | Coil Fluid Flow Rate Percentage of Plant Design Flow Rate [%] | Design Day Name at Sensible Ideal Loads Peak | Date/Time at Sensible Ideal Loads Peak | Design Day Name at Total Ideal Loads Peak | Date/Time at Total Ideal Loads Peak | Design Day Name at Air Flow Ideal Loads Peak | Date/Time at Air Flow Ideal Loads Peak | Coil Total Capacity at Ideal Loads Peak [W] | Coil Sensible Capacity at Ideal Loads Peak [W] | Coil Off-Rating Capacity Modifier at Ideal Loads Peak [ ] | Coil Air Mass Flow Rate at Ideal Loads Peak [kg/s] | Coil Air Volume Flow Rate at Ideal Loads Peak [m3/s] | Coil Entering Air Drybulb at Ideal Loads Peak [C] | Coil Entering Air Wetbulb at Ideal Loads Peak [C] | Coil Entering Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Coil Entering Air Enthalpy at Ideal Loads Peak [J/KG-K] | Coil Leaving Air Drybulb at Ideal Loads Peak [C] | Coil Leaving Air Wetbulb at Ideal Loads Peak [C] | Coil Leaving Air Humidity Ratio at Ideal Loads Peak [C] | Coil Leaving Air Enthalpy at Ideal Loads Peak [J/KG-K] | Coil Plant Fluid Mass Flow Rate at Ideal Loads Peak [kg/s] | Coil Entering Plant Fluid Temperature at Ideal Loads Peak [C] | Coil Leaving Plant Fluid Temperature at Ideal Loads Peak [C] | Coil Plant Fluid Temperature Difference at Ideal Loads Peak [deltaC] | Supply Fan Air Heat Gain at Ideal Loads Peak [W] | Coil and Fan Net Total Capacity at Ideal Loads Peak [W] | Outdoor Air Drybulb at Ideal Loads Peak [C] | Outdoor Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Outdoor Air Wetbulb at Ideal Loads Peak [C] | Outdoor Air Volume Flow Rate at Ideal Loads Peak [m3/s] | Outdoor Air Flow Percentage at Ideal Loads Peak [%] | System Return Air Drybulb at Ideal Loads Peak [C] | System Return Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Zone Air Drybulb at Ideal Loads Peak [C] | Zone Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Zone Air Relative Humidity at Ideal Loads Peak [%] | Zone Sensible Heat Gain at Ideal Loads Peak [W] | Zone Latent Heat Gain at Ideal Loads Peak [W] | Coil Total Capacity at Rating Conditions [W] | Coil Sensible Capacity at Rating Conditions [W] | Coil Air Mass Flow Rate at Rating Conditions [kg/s] | Coil Entering Air Drybulb at Rating Conditions [C] | Coil Entering Air Wetbulb at Rating Conditions [C] | Coil Entering Air Humidity Ratio at Rating Conditions [KGWATER/KGDRYAIR] | Coil Entering Air Enthalpy at Rating Conditions [J/KG-K] | Coil Leaving Air Drybulb at Rating Conditions [C] | Coil Leaving Air Wetbulb at Rating Conditions [C] | Coil Leaving Air Humidity Ratio at Rating Conditions [KGWATER/KGDRYAIR] | Coil Leaving Air Enthalpy at Rating Conditions [J/KG-K] | |
| BUILDING STORY 1 THERMALZONE REHEAT COIL | COIL:HEATING:WATER | Zone Equipment | ZONEHVAC:AIRDISTRIBUTIONUNIT | ADU BUILDING STORY 1 THERMALZONE VAV TERMINAL | BUILDING STORY 1 THERMALZONE | N/A | N/A | N/A | Yes | Yes | Yes | No | 243940.057 | 243940.057 | 20.518056 | 0.00533566 | 4329.248 | 1.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1739 | unknown | unknown | -999.0 | -999.0 | 4197.9300 | 999.8980 | 36.76210047 | 71.11 | 82.22 | 11.11 | 1714719.16 | 13.4469 | 14.512548 | BUFFALO NIAGARA INTL AP ANN HTG 99.6% CONDNS DB 1 | 1/21 24:00:00 | unknown | unknown | BUFFALO NIAGARA INTL AP ANN HTG 99.6% CONDNS DB 1 | 1/21 24:00:00 | 230576.31 | 243940.06 | 1.0000 | 24.08666504 | 20.518056 | 12.78 | 11.36 | 0.00800000 | 33037.2 | 50.00 | 23.63 | 0.00800000 | 70993.1 | 5.33511762 | 60.00 | 48.89 | 11.11 | 0.000 | 230576.31 | -16.30 | 0.00092409 | -16.30 | 0.00000000 | 0.0000 | 21.00 | 0.00779318 | 21.00 | 0.00779318 | 49.1323 | 42075.25 | 0.00 | 244188.11 | 244188.11 | 24.08666504 | 12.78 | 11.58 | 0.00800000 | 33037.2 | 22.72 | 15.47 | 0.00800000 | 43175.1 | |
| BUILDING STORY 2 THERMALZONE REHEAT COIL | COIL:HEATING:WATER | Zone Equipment | ZONEHVAC:AIRDISTRIBUTIONUNIT | ADU BUILDING STORY 2 THERMALZONE VAV TERMINAL | BUILDING STORY 2 THERMALZONE | N/A | N/A | N/A | Yes | Yes | Yes | No | 287148.753 | 287148.753 | 23.546130 | 0.00628076 | 5113.657 | 1.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1739 | unknown | unknown | -999.0 | -999.0 | 4197.9300 | 999.8980 | 36.76210047 | 71.11 | 82.22 | 11.11 | 1714719.16 | 15.8284 | 17.083132 | BUFFALO NIAGARA INTL AP ANN HTG 99.6% CONDNS DB 1 | 1/21 24:00:00 | unknown | unknown | BUFFALO NIAGARA INTL AP ANN HTG 99.6% CONDNS DB 1 | 1/21 24:00:00 | 271412.41 | 287148.75 | 1.0000 | 27.64139785 | 23.546130 | 12.78 | 11.36 | 0.00800000 | 33037.2 | 50.00 | 23.63 | 0.00800000 | 70993.1 | 6.28011810 | 60.00 | 48.89 | 11.11 | 0.000 | 271412.41 | -16.30 | 0.00092409 | -16.30 | 0.00000000 | 0.0000 | 21.00 | 0.00682570 | 21.00 | 0.00682570 | 43.1051 | 55965.98 | 0.00 | 287438.10 | 287438.10 | 27.64139785 | 12.78 | 11.58 | 0.00800000 | 33037.2 | 22.98 | 15.57 | 0.00800000 | 43436.0 | |
| BUILDING STORY 3 THERMALZONE REHEAT COIL | COIL:HEATING:WATER | Zone Equipment | ZONEHVAC:AIRDISTRIBUTIONUNIT | ADU BUILDING STORY 3 THERMALZONE VAV TERMINAL | BUILDING STORY 3 THERMALZONE | N/A | N/A | N/A | Yes | Yes | Yes | No | 334401.843 | 334401.843 | 26.755183 | 0.00731432 | 5975.605 | 1.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1739 | unknown | unknown | -999.0 | -999.0 | 4197.9300 | 999.8980 | 36.76210047 | 71.11 | 82.22 | 11.11 | 1714719.16 | 18.4327 | 19.894326 | BUFFALO NIAGARA INTL AP ANN HTG 99.6% CONDNS DB 1 | 1/21 24:00:00 | unknown | unknown | BUFFALO NIAGARA INTL AP ANN HTG 99.6% CONDNS DB 1 | 1/21 24:00:00 | 316069.64 | 334401.84 | 1.0000 | 31.40858633 | 26.755183 | 12.78 | 11.36 | 0.00800000 | 33037.2 | 50.00 | 23.63 | 0.00800000 | 70993.1 | 7.31357196 | 60.00 | 48.89 | 11.11 | 0.000 | 316069.64 | -16.30 | 0.00092409 | -16.30 | 0.00000000 | 0.0000 | 18.99 | 0.00562994 | 18.99 | 0.00562994 | 40.3419 | 136344.79 | 0.00 | 334735.81 | 334735.81 | 31.40858633 | 12.78 | 11.58 | 0.00800000 | 33037.2 | 23.23 | 15.66 | 0.00800000 | 43694.6 | |
| 1 ZONE PVAV 2SPD DX CLG COIL 2214KBTU/HR 9.5EER | Coil:Cooling:DX:TwoSpeed | AirLoop | AirLoopHVAC | 1 ZONE PVAV | BUILDING STORY 1 THERMALZONE | Coincident | CoolingDesignCapacity | N/A | Yes | Yes | unknown | No | 727874.552 | 508117.011 | 29.311508 | -999.0 | -999.000 | -999.0000 | 1.00000 | 0.88912 | 1027.3763 | 1004.8586 | 1.1739 | 1 ZONE PVAV FAN | Fan:VariableVolume | 29.311508 | 34.40952148 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | BUFFALO NIAGARA INTL AP ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 14:00:00 | BUFFALO NIAGARA INTL AP ANN CLG .4% CONDNS WB=>MDB 1 | 7/21 14:00:00 | BUFFALO NIAGARA INTL AP ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 09:00:00 | 696577.61 | 444726.58 | 1.0449 | 34.40952148 | 29.311508 | 27.21 | 20.03 | 0.01212311 | 58272.6 | 10.92 | 10.92 | 0.00850000 | 32402.7 | -999.0 | -999.00 | -999.00 | -999.00 | 65699.948 | 630877.66 | 30.30 | 0.01334551 | 21.80 | 13.92630387 | 47.5114 | 23.97 | 0.01084411 | 23.96 | 0.00999847 | 52.4644 | 315610.16 | 0.00 | 727416.78 | 504744.51 | 33.04719725 | 26.67 | 19.44 | 0.01117891 | 55307.7 | 11.70 | 11.68 | 0.00853708 | 33296.3 | |
| 1 ZONE PVAV MAIN HTG COIL | Coil:Heating:Water | AirLoop | AirLoopHVAC | 1 ZONE PVAV | BUILDING STORY 1 THERMALZONE | Coincident | HeatingDesignCapacity | N/A | Yes | Yes | Yes | No | 301624.108 | 301624.108 | 8.793452 | 0.00659738 | 3962.859 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1739 | 1 ZONE PVAV FAN | Fan:VariableVolume | 29.311508 | 34.40952148 | 4197.9300 | 999.8980 | 36.76210047 | 71.11 | 82.22 | 11.11 | 1714719.16 | 11.7436 | 17.944304 | BUFFALO NIAGARA INTL AP ANN HTG 99.6% CONDNS DB 1 | 1/21 01:00:00 | unknown | unknown | BUFFALO NIAGARA INTL AP ANN HTG 99.6% CONDNS DB 1 | 1/21 01:00:00 | 201369.05 | 301624.11 | 1.0000 | 10.32285645 | 8.793452 | -16.30 | -16.30 | 0.00092409 | -14095.8 | 12.78 | 11.36 | 0.00800000 | 33037.2 | 6.59670293 | 60.00 | 48.89 | 11.11 | 0.000 | 201369.05 | -16.30 | 0.00092409 | -16.30 | 13.92630387 | 158.3713 | 21.00 | 0.00779313 | 21.00 | 0.00779318 | 49.1323 | 33655.03 | 0.00 | 229905.50 | 229905.50 | 10.32285645 | 7.22 | 0.06 | 0.00092409 | 9580.7 | 29.35 | 11.20 | 0.00092409 | 31852.2 | |
| 1 ZONE PVAV 1 2SPD DX CLG COIL 2625KBTU/HR 9.5EER | Coil:Cooling:DX:TwoSpeed | AirLoop | AirLoopHVAC | 1 ZONE PVAV 1 | BUILDING STORY 2 THERMALZONE | Coincident | CoolingDesignCapacity | N/A | Yes | Yes | unknown | No | 835294.967 | 583105.401 | 33.637328 | -999.0 | -999.000 | -999.0000 | 1.00000 | 0.92516 | 1026.7737 | 1004.8586 | 1.1739 | 1 ZONE PVAV 1 FAN | Fan:VariableVolume | 33.637328 | 39.48771122 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | BUFFALO NIAGARA INTL AP ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 14:00:00 | BUFFALO NIAGARA INTL AP ANN CLG .4% CONDNS WB=>MDB 1 | 7/21 08:00:00 | BUFFALO NIAGARA INTL AP ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 09:00:00 | 805887.32 | 526955.04 | 1.0365 | 39.48771122 | 33.637328 | 26.79 | 19.66 | 0.01179899 | 57016.1 | 10.92 | 10.92 | 0.00850000 | 32401.6 | -999.0 | -999.00 | -999.00 | -999.00 | 75396.008 | 730491.31 | 30.30 | 0.01334551 | 21.80 | 13.92630387 | 41.4013 | 23.98 | 0.01055861 | 23.95 | 0.01019485 | 53.5026 | 381206.58 | 0.00 | 834769.64 | 579235.19 | 37.92433389 | 26.67 | 19.44 | 0.01117891 | 55307.7 | 11.70 | 11.68 | 0.00853708 | 33296.3 | |
| 1 ZONE PVAV 1 MAIN HTG COIL | Coil:Heating:Water | AirLoop | AirLoopHVAC | 1 ZONE PVAV 1 | BUILDING STORY 2 THERMALZONE | Coincident | HeatingDesignCapacity | N/A | Yes | Yes | Yes | No | 346138.079 | 346138.079 | 10.091199 | 0.00757102 | 4547.701 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1739 | 1 ZONE PVAV 1 FAN | Fan:VariableVolume | 33.637328 | 39.48771122 | 4197.9300 | 999.8980 | 36.76210047 | 71.11 | 82.22 | 11.11 | 1714719.16 | 13.4767 | 20.592541 | BUFFALO NIAGARA INTL AP ANN HTG 99.6% CONDNS DB 1 | 1/21 01:00:00 | unknown | unknown | BUFFALO NIAGARA INTL AP ANN HTG 99.6% CONDNS DB 1 | 1/21 01:00:00 | 231087.29 | 346138.08 | 1.0000 | 11.84631337 | 10.091199 | -16.30 | -16.30 | 0.00092409 | -14095.8 | 12.78 | 11.36 | 0.00800000 | 33037.2 | 7.57025059 | 60.00 | 48.89 | 11.11 | 0.000 | 231087.29 | -16.30 | 0.00092409 | -16.30 | 13.92630387 | 138.0045 | 21.00 | 0.00682477 | 21.00 | 0.00682570 | 43.1051 | 44736.70 | 0.00 | 263835.17 | 263835.17 | 11.84631337 | 7.22 | 0.06 | 0.00092409 | 9580.7 | 29.35 | 11.20 | 0.00092409 | 31852.2 | |
| 1 ZONE PVAV 2 2SPD DX CLG COIL 2996KBTU/HR 9.5EER | Coil:Cooling:DX:TwoSpeed | AirLoop | AirLoopHVAC | 1 ZONE PVAV 2 | BUILDING STORY 3 THERMALZONE | Coincident | CoolingDesignCapacity | N/A | Yes | Yes | unknown | No | 949135.577 | 662575.620 | 38.221690 | -999.0 | -999.000 | -999.0000 | 1.00000 | 0.97619 | 1025.7018 | 1004.8586 | 1.1739 | 1 ZONE PVAV 2 FAN | Fan:VariableVolume | 38.221690 | 44.86940904 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | BUFFALO NIAGARA INTL AP ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 15:00:00 | BUFFALO NIAGARA INTL AP ANN CLG .4% CONDNS WB=>MDB 1 | 7/21 15:00:00 | BUFFALO NIAGARA INTL AP ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 07:00:00 | 925137.99 | 642863.74 | 1.0259 | 44.86940904 | 38.221690 | 26.71 | 19.20 | 0.01122235 | 55461.3 | 10.92 | 10.92 | 0.00850000 | 32399.6 | -999.0 | -999.00 | -999.00 | -999.00 | 85671.573 | 839466.42 | 30.30 | 0.01334551 | 21.80 | 6.04520110 | 15.8162 | 25.97 | 0.01078515 | 26.33 | 0.01112089 | 50.5802 | 478805.44 | 0.00 | 948538.65 | 658177.94 | 43.09296227 | 26.67 | 19.44 | 0.01117891 | 55307.7 | 11.70 | 11.68 | 0.00853708 | 33296.3 | |
| 1 ZONE PVAV 2 MAIN HTG COIL | Coil:Heating:Water | AirLoop | AirLoopHVAC | 1 ZONE PVAV 2 | BUILDING STORY 3 THERMALZONE | Coincident | HeatingDesignCapacity | N/A | Yes | Yes | Yes | No | 167637.730 | 167637.730 | 11.466507 | 0.00366671 | 2496.621 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1739 | 1 ZONE PVAV 2 FAN | Fan:VariableVolume | 38.221690 | 44.86940904 | 4197.9300 | 999.8980 | 36.76210047 | 71.11 | 82.22 | 11.11 | 1714719.16 | 7.8535 | 9.973150 | BUFFALO NIAGARA INTL AP ANN HTG 99.6% CONDNS DB 1 | 1/21 01:00:00 | unknown | unknown | BUFFALO NIAGARA INTL AP ANN HTG 99.6% CONDNS DB 1 | 1/21 01:00:00 | 134665.52 | 167637.73 | 1.0000 | 13.46082271 | 11.466507 | -16.30 | -16.30 | 0.00092409 | -14095.8 | 12.78 | 11.36 | 0.00800000 | 33037.2 | 3.66633925 | 60.00 | 48.89 | 11.11 | 0.000 | 134665.52 | -16.30 | 0.00092409 | -16.30 | 6.04520110 | 52.7205 | 18.99 | 0.00562992 | 18.99 | 0.00562994 | 40.3419 | 109074.59 | 0.00 | 153916.64 | 153916.64 | 13.46082271 | 7.22 | 3.22 | 0.00314898 | 15174.9 | 18.54 | 8.87 | 0.00314898 | 26609.3 |
Report: System Summary
For: Entire Facility
Timestamp: 2020-03-25 14:42:09
Economizer| High Limit Shutoff Control | Minimum Outdoor Air [m3/s] | Maximum Outdoor Air [m3/s] | Return Air Temp Limit | Return Air Enthalpy Limit | Outdoor Air Temperature Limit [C] | Outdoor Air Enthalpy Limit [C] | |
| None |
| Controller:MechanicalVentilation Name | Outdoor Air Per Person [m3/s-person] | Outdoor Air Per Area [m3/s-m2] | Outdoor Air Per Zone [m3/s] | Outdoor Air ACH [ach] | Outdoor Air Method | Outdoor Air Schedule Name | Air Distribution Effectiveness in Cooling Mode | Air Distribution Effectiveness in Heating Mode | Air Distribution Effectiveness Schedule Name | |
| BUILDING STORY 1 THERMALZONE | 1 ZONE PVAV VENTILATION CONTROLLER | 0.000000 | 0.003581 | 0.000000 | 0.000000 | Sum | 1.00 | 1.00 | ||
| BUILDING STORY 2 THERMALZONE | 1 ZONE PVAV 1 VENTILATION CONTROLLER | 0.000000 | 0.003581 | 0.000000 | 0.000000 | Sum | 1.00 | 1.00 | ||
| BUILDING STORY 3 THERMALZONE | 1 ZONE PVAV 2 VENTILATION CONTROLLER | 0.000000 | 0.001555 | 0.000000 | 0.000000 | Sum | 1.00 | 1.00 |
| Winter Clothes [hr] | Summer Clothes [hr] | Summer or Winter Clothes [hr] | |
| BUILDING STORY 1 THERMALZONE | 50.00 | 7089.00 | 28.00 |
| BUILDING STORY 2 THERMALZONE | 36.00 | 7077.00 | 11.00 |
| BUILDING STORY 3 THERMALZONE | 2466.00 | 4657.00 | 547.00 |
| Facility | 2495.00 | 7194.00 | 555.00 |
| During Heating [hr] | During Cooling [hr] | During Occupied Heating [hr] | During Occupied Cooling [hr] | |
| BUILDING STORY 1 THERMALZONE | 0.00 | 0.00 | 0.00 | 0.00 |
| BUILDING STORY 2 THERMALZONE | 0.00 | 0.00 | 0.00 | 0.00 |
| BUILDING STORY 3 THERMALZONE | 0.00 | 4.00 | 0.00 | 0.00 |
| Facility | 0.00 | 4.00 | 0.00 | 0.00 |
Report: Outdoor Air Summary
For: Entire Facility
Timestamp: 2020-03-25 14:42:09
Average Outdoor Air During Occupied Hours| Average Number of Occupants | Nominal Number of Occupants | Zone Volume [m3] | Mechanical Ventilation [ach] | Infiltration [ach] | AFN Infiltration [ach] | Simple Ventilation [ach] | |
| BUILDING STORY 1 THERMALZONE | 1284.27 | 2929.89 | 11665.53 | 3.743 | 0.009 | 0.000 | 0.000 |
| BUILDING STORY 2 THERMALZONE | 1284.27 | 2929.89 | 11665.53 | 3.742 | 0.077 | 0.000 | 0.000 |
| BUILDING STORY 3 THERMALZONE | 154.15 | 703.34 | 11665.53 | 1.630 | 0.446 | 0.000 | 0.000 |
| Average Number of Occupants | Nominal Number of Occupants | Zone Volume [m3] | Mechanical Ventilation [ach] | Infiltration [ach] | AFN Infiltration [ach] | Simple Ventilation [ach] | |
| BUILDING STORY 1 THERMALZONE | 1284.27 | 2929.89 | 11665.53 | 0.000 | 0.000 | 0.000 | 0.000 |
| BUILDING STORY 2 THERMALZONE | 1284.27 | 2929.89 | 11665.53 | 0.000 | 0.000 | 0.000 | 0.000 |
| BUILDING STORY 3 THERMALZONE | 154.15 | 703.34 | 11665.53 | 0.000 | 0.000 | 0.000 | 0.000 |
Report: Object Count Summary
For: Entire Facility
Timestamp: 2020-03-25 14:42:09
Surfaces by Class| Total | Outdoors | |
| Wall | 12 | 12 |
| Floor | 3 | 1 |
| Roof | 3 | 1 |
| Internal Mass | 33 | 0 |
| Building Detached Shading | 60 | 60 |
| Fixed Detached Shading | 0 | 0 |
| Window | 12 | 12 |
| Door | 0 | 0 |
| Glass Door | 0 | 0 |
| Shading | 0 | 0 |
| Overhang | 0 | 0 |
| Fin | 0 | 0 |
| Tubular Daylighting Device Dome | 0 | 0 |
| Tubular Daylighting Device Diffuser | 0 | 0 |
| Count | |
| HVAC Air Loops | 3 |
| Conditioned Zones | 3 |
| Unconditioned Zones | 0 |
| Supply Plenums | 0 |
| Return Plenums | 0 |
| Count | |
| IDF Objects | 0 |
| Defaulted Fields | 0 |
| Fields with Defaults | 0 |
| Autosized Fields | 0 |
| Autosizable Fields | 0 |
| Autocalculated Fields | 0 |
| Autocalculatable Fields | 0 |
Report: Energy Meters
For: Entire Facility
Timestamp: 2020-03-25 14:42:09
Annual and Peak Values - Electricity| Electricity Annual Value [GJ] | Electricity Minimum Value [W] | Timestamp of Minimum {TIMESTAMP} | Electricity Maximum Value [W] | Timestamp of Maximum {TIMESTAMP} | |
| Electricity:Facility | 20012.46 | 92209.70 | 26-OCT-03:00 | 1366599.85 | 27-JUN-11:00 |
| Electricity:Building | 12184.58 | 55134.75 | 01-JAN-02:00 | 686176.98 | 01-JAN-12:00 |
| Electricity:Zone:BUILDING STORY 3 THERMALZONE | 8348.55 | 33860.41 | 01-JAN-02:00 | 476810.21 | 01-JAN-12:00 |
| InteriorLights:Electricity | 1962.18 | 16554.91 | 01-JAN-01:00 | 99321.33 | 01-JAN-11:00 |
| InteriorLights:Electricity:Zone:BUILDING STORY 3 THERMALZONE | 746.96 | 6064.90 | 01-JAN-01:00 | 36388.74 | 01-JAN-11:00 |
| General:InteriorLights:Electricity | 1962.18 | 16554.91 | 01-JAN-01:00 | 99321.33 | 01-JAN-11:00 |
| Electricity:Zone:BUILDING STORY 2 THERMALZONE | 1921.73 | 10637.17 | 01-JAN-02:00 | 104683.38 | 01-JAN-12:00 |
| InteriorLights:Electricity:Zone:BUILDING STORY 2 THERMALZONE | 611.32 | 5245.00 | 01-JAN-01:00 | 31466.30 | 01-JAN-11:00 |
| Electricity:Zone:BUILDING STORY 1 THERMALZONE | 1914.30 | 10637.17 | 01-JAN-02:00 | 104683.38 | 01-JAN-12:00 |
| InteriorLights:Electricity:Zone:BUILDING STORY 1 THERMALZONE | 603.89 | 5245.00 | 01-JAN-01:00 | 31466.30 | 01-JAN-11:00 |
| InteriorEquipment:Electricity | 10222.40 | 36727.38 | 01-JAN-02:00 | 586855.65 | 01-JAN-12:00 |
| InteriorEquipment:Electricity:Zone:BUILDING STORY 3 THERMALZONE | 7601.59 | 26628.47 | 01-JAN-02:00 | 440421.48 | 01-JAN-12:00 |
| Elevators:InteriorEquipment:Electricity | 691.10 | 0.00 | 01-JAN-02:00 | 81178.18 | 05-JAN-07:00 |
| General:InteriorEquipment:Electricity | 9531.31 | 36727.38 | 01-JAN-02:00 | 532547.04 | 01-JAN-12:00 |
| InteriorEquipment:Electricity:Zone:BUILDING STORY 2 THERMALZONE | 1310.41 | 5049.45 | 01-JAN-02:00 | 73217.09 | 01-JAN-12:00 |
| InteriorEquipment:Electricity:Zone:BUILDING STORY 1 THERMALZONE | 1310.41 | 5049.45 | 01-JAN-02:00 | 73217.09 | 01-JAN-12:00 |
| Electricity:Plant | 1726.33 | 51.49 | 26-OCT-03:00 | 111424.01 | 07-FEB-08:00 |
| WaterSystems:Electricity | 1715.99 | 51.49 | 26-OCT-03:00 | 107653.18 | 01-JAN-20:00 |
| Booster:WaterSystems:Electricity | 1715.99 | 51.49 | 26-OCT-03:00 | 107653.18 | 01-JAN-20:00 |
| ElectricityPurchased:Facility | 20012.46 | 92209.70 | 26-OCT-03:00 | 1366599.85 | 27-JUN-11:00 |
| ElectricityPurchased:Plant | 20012.46 | 92209.70 | 26-OCT-03:00 | 1366599.85 | 27-JUN-11:00 |
| Cogeneration:ElectricityPurchased | 20012.46 | 92209.70 | 26-OCT-03:00 | 1366599.85 | 27-JUN-11:00 |
| ElectricitySurplusSold:Facility | 0.00 | 0.00 | 01-JAN-01:00 | 0.00 | 01-JAN-01:00 |
| ElectricitySurplusSold:Plant | 0.00 | 0.00 | 01-JAN-01:00 | 0.00 | 01-JAN-01:00 |
| Cogeneration:ElectricitySurplusSold | 0.00 | 0.00 | 01-JAN-01:00 | 0.00 | 01-JAN-01:00 |
| ElectricityNet:Facility | 20012.46 | 92209.70 | 26-OCT-03:00 | 1366599.85 | 27-JUN-11:00 |
| ElectricityNet:Plant | 20012.46 | 92209.70 | 26-OCT-03:00 | 1366599.85 | 27-JUN-11:00 |
| Cogeneration:ElectricityNet | 20012.46 | 92209.70 | 26-OCT-03:00 | 1366599.85 | 27-JUN-11:00 |
| Electricity:HVAC | 5387.85 | 0.00 | 01-JAN-01:00 | 682765.27 | 27-JUN-13:00 |
| Fans:Electricity | 1843.72 | 0.00 | 01-JAN-01:00 | 81041.69 | 03-APR-07:00 |
| General:Fans:Electricity | 1843.72 | 0.00 | 01-JAN-01:00 | 81041.69 | 03-APR-07:00 |
| ExteriorLights:Electricity | 713.69 | 0.00 | 01-JAN-09:00 | 54118.48 | 01-JAN-07:00 |
| Building Facades:ExteriorLights:Electricity | 9.57 | 0.00 | 01-JAN-01:00 | 1227.83 | 01-JAN-07:00 |
| Main Entries:ExteriorLights:Electricity | 13.38 | 0.00 | 01-JAN-09:00 | 1005.05 | 01-JAN-07:00 |
| Other Doors:ExteriorLights:Electricity | 13.38 | 0.00 | 01-JAN-09:00 | 1005.05 | 01-JAN-07:00 |
| Parking Areas and Drives:ExteriorLights:Electricity | 677.36 | 0.00 | 01-JAN-09:00 | 50880.56 | 01-JAN-07:00 |