| PERIMETER_MID_ZN_1 ZN | 9230.66 | 9230.66 | 44.52 | 0.672 | 0.672 | HOUSTON BUSH INTERCONTINENTAL ANN CLG .4% CONDNS DB=>MWB | 7/21 13:40:00 | 24.00 | 24.00 | 0.00882 | 35.83 | 0.01519 | 0.090 | 0.00 |
| PERIMETER_MID_ZN_2 ZN | 9487.89 | 9487.89 | 72.28 | 0.690 | 0.690 | HOUSTON BUSH INTERCONTINENTAL ANN CLG .4% CONDNS DB=>MWB | 7/21 09:30:00 | 24.00 | 24.00 | 0.00870 | 31.30 | 0.01519 | 0.057 | 0.00 |
| PERIMETER_MID_ZN_3 ZN | 8247.83 | 8247.83 | 39.78 | 0.600 | 0.600 | HOUSTON BUSH INTERCONTINENTAL ANN CLG .4% CONDNS DB=>MWB | 7/21 14:50:00 | 24.00 | 24.00 | 0.00886 | 36.00 | 0.01519 | 0.090 | 0.00 |
| PERIMETER_MID_ZN_4 ZN | 10001.35 | 10001.35 | 76.20 | 0.728 | 0.728 | HOUSTON BUSH INTERCONTINENTAL ANN CLG .4% CONDNS DB=>MWB | 7/21 17:00:00 | 24.00 | 24.00 | 0.00869 | 34.59 | 0.01519 | 0.057 | 0.00 |
| PERIMETER_TOP_ZN_1 ZN | 10194.53 | 10194.53 | 49.17 | 0.742 | 0.742 | HOUSTON BUSH INTERCONTINENTAL ANN CLG .4% CONDNS DB=>MWB | 7/21 13:50:00 | 24.00 | 24.00 | 0.00880 | 35.92 | 0.01519 | 0.090 | 0.00 |
| PERIMETER_TOP_ZN_2 ZN | 9578.53 | 9578.53 | 72.97 | 0.697 | 0.697 | HOUSTON BUSH INTERCONTINENTAL ANN CLG .4% CONDNS DB=>MWB | 7/21 09:40:00 | 24.00 | 24.00 | 0.00871 | 31.59 | 0.01519 | 0.057 | 0.00 |
| PERIMETER_TOP_ZN_3 ZN | 9315.68 | 9315.68 | 44.93 | 0.678 | 0.678 | HOUSTON BUSH INTERCONTINENTAL ANN CLG .4% CONDNS DB=>MWB | 7/21 15:00:00 | 24.00 | 24.00 | 0.00883 | 36.00 | 0.01519 | 0.090 | 0.00 |
| PERIMETER_TOP_ZN_4 ZN | 10633.36 | 10633.36 | 81.01 | 0.774 | 0.774 | HOUSTON BUSH INTERCONTINENTAL ANN CLG .4% CONDNS DB=>MWB | 7/21 17:00:00 | 24.00 | 24.00 | 0.00869 | 34.59 | 0.01519 | 0.057 | 0.00 |
| Calculated Design Load [W] | User Design Load [W] | User Design Load per Area [W/m2] | Calculated Design Air Flow [m3/s] | User Design Air Flow [m3/s] | Design Day Name | Date/Time Of Peak {TIMESTAMP} | Thermostat Setpoint Temperature at Peak Load [C] | Indoor Temperature at Peak Load [C] | Indoor Humidity Ratio at Peak Load [kgWater/kgAir] | Outdoor Temperature at Peak Load [C] | Outdoor Humidity Ratio at Peak Load [kgWater/kgAir] | Minimum Outdoor Air Flow Rate [m3/s] | Heat Gain Rate from DOAS [W] | |
| CORE_BOTTOM ZN | 6119.06 | 6119.06 | 6.22 | 0.257 | 0.425 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 21.00 | 21.00 | 0.00800 | -1.60 | 0.00331 | 0.425 | 0.00 |
| CORE_MID ZN | 11092.71 | 11092.71 | 11.28 | 0.469 | 0.469 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 21.00 | 21.00 | 0.00800 | -1.60 | 0.00331 | 0.425 | 0.00 |
| CORE_TOP ZN | 20153.65 | 20153.65 | 20.49 | 0.858 | 0.858 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 21.00 | 21.00 | 0.00800 | -1.60 | 0.00331 | 0.425 | 0.00 |
| PERIMETER_BOT_ZN_1 ZN | 5993.00 | 5993.00 | 28.90 | 0.256 | 0.256 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 21.00 | 21.00 | 0.00766 | -1.60 | 0.00331 | 0.090 | 0.00 |
| PERIMETER_BOT_ZN_2 ZN | 4040.52 | 4040.52 | 30.78 | 0.172 | 0.172 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 21.00 | 21.00 | 0.00770 | -1.60 | 0.00331 | 0.057 | 0.00 |
| PERIMETER_BOT_ZN_3 ZN | 5950.14 | 5950.14 | 28.70 | 0.254 | 0.254 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 21.00 | 21.00 | 0.00766 | -1.60 | 0.00331 | 0.090 | 0.00 |
| PERIMETER_BOT_ZN_4 ZN | 4040.47 | 4040.47 | 30.78 | 0.172 | 0.172 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 21.00 | 21.00 | 0.00770 | -1.60 | 0.00331 | 0.057 | 0.00 |
| PERIMETER_MID_ZN_1 ZN | 7435.33 | 7435.33 | 35.86 | 0.318 | 0.318 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 21.00 | 21.00 | 0.00775 | -1.60 | 0.00331 | 0.090 | 0.00 |
| PERIMETER_MID_ZN_2 ZN | 4961.84 | 4961.84 | 37.80 | 0.212 | 0.212 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 21.00 | 21.00 | 0.00779 | -1.60 | 0.00331 | 0.057 | 0.00 |
| PERIMETER_MID_ZN_3 ZN | 7429.71 | 7429.71 | 35.83 | 0.317 | 0.317 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 21.00 | 21.00 | 0.00775 | -1.60 | 0.00331 | 0.090 | 0.00 |
| PERIMETER_MID_ZN_4 ZN | 4961.73 | 4961.73 | 37.80 | 0.212 | 0.212 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 21.00 | 21.00 | 0.00779 | -1.60 | 0.00331 | 0.057 | 0.00 |
| PERIMETER_TOP_ZN_1 ZN | 9223.99 | 9223.99 | 44.49 | 0.394 | 0.394 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 21.00 | 21.00 | 0.00787 | -1.60 | 0.00331 | 0.090 | 0.00 |
| PERIMETER_TOP_ZN_2 ZN | 6088.91 | 6088.91 | 46.39 | 0.260 | 0.260 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 21.00 | 21.00 | 0.00788 | -1.60 | 0.00331 | 0.057 | 0.00 |
| PERIMETER_TOP_ZN_3 ZN | 9230.50 | 9230.50 | 44.52 | 0.395 | 0.395 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 21.00 | 21.00 | 0.00787 | -1.60 | 0.00331 | 0.090 | 0.00 |
| PERIMETER_TOP_ZN_4 ZN | 6088.72 | 6088.72 | 46.39 | 0.260 | 0.260 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 21.00 | 21.00 | 0.00788 | -1.60 | 0.00331 | 0.057 | 0.00 |
| Calculated cooling [m3/s] | User cooling [m3/s] | Calculated heating [m3/s] | User heating [m3/s] | Adjusted cooling [m3/s] | Adjusted heating [m3/s] | Adjusted main [m3/s] | Calculated Heating Air Flow Ratio [] | User Heating Air Flow Ratio [] | |
| 15 ZONE VAV | 13.60 | 13.60 | 4.97 | 4.97 | 13.6030 | 4.9744 | 13.6030 | 0.3657 | 0.3000 |
| Previous Design Volume Flow Rate [m3/s] | Algorithm Volume Flow Rate [m3/s] | Coincident Design Volume Flow Rate [m3/s] | Coincident Size Adjusted | Peak Sizing Period Name | Peak Day into Period {TIMESTAMP}[day] | Peak Hour Of Day {TIMESTAMP}[hr] | Peak Step Start Minute {TIMESTAMP}[min] | |
| None |
| Coil Type | HVAC Type | HVAC Name | Coil Final Gross Total Capacity [W] | Coil Final Gross Sensible Capacity [W] | Coil Final Reference Air Volume Flow Rate [m3/s] | Coil Final Reference Plant Fluid Volume Flow Rate [m3/s] | Coil U-value Times Area Value [W/K] | Design Day Name at Sensible Ideal Loads Peak | Date/Time at Sensible Ideal Loads Peak | Design Day Name at Air Flow Ideal Loads Peak | Date/Time at Air Flow Ideal Loads Peak | Coil Total Capacity at Ideal Loads Peak [W] | Coil Sensible Capacity at Ideal Loads Peak [W] | Coil Air Volume Flow Rate at Ideal Loads Peak [m3/s] | Coil Entering Air Drybulb at Ideal Loads Peak [C] | Coil Entering Air Wetbulb at Ideal Loads Peak [C] | Coil Entering Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Coil Leaving Air Drybulb at Ideal Loads Peak [C] | Coil Leaving Air Wetbulb at Ideal Loads Peak [C] | Coil Leaving Air Humidity Ratio at Ideal Loads Peak [C] | Outdoor Air Drybulb at Ideal Loads Peak [C] | Outdoor Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Outdoor Air Wetbulb at Ideal Loads Peak [C] | Outdoor Air Flow Percentage at Ideal Loads Peak [%] | Zone Air Drybulb at Ideal Loads Peak [C] | Zone Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Zone Air Relative Humidity at Ideal Loads Peak [%] | Zone Sensible Heat Gain at Ideal Loads Peak [W] | Zone Latent Heat Gain at Ideal Loads Peak [W] | Coil Total Capacity at Rating Conditions [W] | Coil Sensible Capacity at Rating Conditions [W] | |
| CORE_BOTTOM ZN REHEAT COIL | COIL:HEATING:WATER | ZONEHVAC:AIRDISTRIBUTIONUNIT | ADU CORE_BOTTOM ZN VAV TERMINAL | 9090.101 | 9090.101 | 0.295256 | 0.00019883 | 584.519 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 16538.31 | 9090.10 | 0.295256 | 12.78 | 11.55 | 0.00800000 | 40.00 | 21.11 | 0.00800000 | -1.60 | 0.00331476 | -1.60 | 0.0000 | 21.00 | 0.00800000 | 51.5458 | 6119.06 | 0.00 | 9113.36 | 9113.36 |
| CORE_MID ZN REHEAT COIL | COIL:HEATING:WATER | ZONEHVAC:AIRDISTRIBUTIONUNIT | ADU CORE_MID ZN VAV TERMINAL | 15814.026 | 15814.026 | 0.469194 | 0.00034590 | 1144.217 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 28755.78 | 15814.03 | 0.469194 | 12.78 | 11.55 | 0.00800000 | 40.00 | 21.11 | 0.00800000 | -1.60 | 0.00331476 | -1.60 | 0.0000 | 21.00 | 0.00800000 | 51.5459 | 11092.71 | 0.00 | 15851.30 | 15851.30 |
| CORE_TOP ZN REHEAT COIL | COIL:HEATING:WATER | ZONEHVAC:AIRDISTRIBUTIONUNIT | ADU CORE_TOP ZN VAV TERMINAL | 28786.864 | 28786.864 | 0.857950 | 0.00062965 | 2068.782 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 52348.07 | 28786.86 | 0.857950 | 12.78 | 11.55 | 0.00800000 | 40.00 | 21.11 | 0.00800000 | -1.60 | 0.00331476 | -1.60 | 0.0000 | 21.00 | 0.00800000 | 51.5459 | 20153.65 | 0.00 | 28855.73 | 28855.73 |
| PERIMETER_BOT_ZN_1 ZN REHEAT COIL | COIL:HEATING:WATER | ZONEHVAC:AIRDISTRIBUTIONUNIT | ADU PERIMETER_BOT_ZN_1 ZN VAV TERMINAL | 8564.316 | 8564.316 | 0.255723 | 0.00018733 | 613.750 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 15574.08 | 8564.32 | 0.255723 | 12.78 | 11.55 | 0.00800000 | 40.00 | 21.11 | 0.00800000 | -1.60 | 0.00331476 | -1.60 | 0.0000 | 21.00 | 0.00766035 | 49.3873 | 5993.00 | 0.00 | 8584.80 | 8584.80 |
| PERIMETER_BOT_ZN_2 ZN REHEAT COIL | COIL:HEATING:WATER | ZONEHVAC:AIRDISTRIBUTIONUNIT | ADU PERIMETER_BOT_ZN_2 ZN VAV TERMINAL | 5774.749 | 5774.749 | 0.172460 | 0.00012631 | 413.728 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 10501.30 | 5774.75 | 0.172460 | 12.78 | 11.55 | 0.00800000 | 40.00 | 21.11 | 0.00800000 | -1.60 | 0.00331476 | -1.60 | 0.0000 | 21.00 | 0.00769850 | 49.6301 | 4040.52 | 0.00 | 5788.56 | 5788.56 |
| PERIMETER_BOT_ZN_3 ZN REHEAT COIL | COIL:HEATING:WATER | ZONEHVAC:AIRDISTRIBUTIONUNIT | ADU PERIMETER_BOT_ZN_3 ZN VAV TERMINAL | 8502.953 | 8502.953 | 0.253885 | 0.00018598 | 609.372 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 15462.49 | 8502.95 | 0.253885 | 12.78 | 11.55 | 0.00800000 | 40.00 | 21.11 | 0.00800000 | -1.60 | 0.00331476 | -1.60 | 0.0000 | 21.00 | 0.00765599 | 49.3595 | 5950.14 | 0.00 | 8523.29 | 8523.29 |
| PERIMETER_BOT_ZN_4 ZN REHEAT COIL | COIL:HEATING:WATER | ZONEHVAC:AIRDISTRIBUTIONUNIT | ADU PERIMETER_BOT_ZN_4 ZN VAV TERMINAL | 5774.676 | 5774.676 | 0.172458 | 0.00012631 | 413.723 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 10501.17 | 5774.68 | 0.172458 | 12.78 | 11.55 | 0.00800000 | 40.00 | 21.11 | 0.00800000 | -1.60 | 0.00331476 | -1.60 | 0.0000 | 21.00 | 0.00769852 | 49.6302 | 4040.47 | 0.00 | 5788.49 | 5788.49 |
| PERIMETER_MID_ZN_1 ZN REHEAT COIL | COIL:HEATING:WATER | ZONEHVAC:AIRDISTRIBUTIONUNIT | ADU PERIMETER_MID_ZN_1 ZN VAV TERMINAL | 10628.803 | 10628.803 | 0.317540 | 0.00023248 | 761.074 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 19328.36 | 10628.80 | 0.317540 | 12.78 | 11.55 | 0.00800000 | 40.00 | 21.11 | 0.00800000 | -1.60 | 0.00331476 | -1.60 | 0.0000 | 21.00 | 0.00775231 | 49.9725 | 7435.33 | 0.00 | 10654.23 | 10654.23 |
| PERIMETER_MID_ZN_2 ZN REHEAT COIL | COIL:HEATING:WATER | ZONEHVAC:AIRDISTRIBUTIONUNIT | ADU PERIMETER_MID_ZN_2 ZN VAV TERMINAL | 7093.581 | 7093.581 | 0.211953 | 0.00015516 | 507.832 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 12899.61 | 7093.58 | 0.211953 | 12.78 | 11.55 | 0.00800000 | 40.00 | 21.11 | 0.00800000 | -1.60 | 0.00331476 | -1.60 | 0.0000 | 21.00 | 0.00778584 | 50.1857 | 4961.84 | 0.00 | 7110.55 | 7110.55 |
| PERIMETER_MID_ZN_3 ZN REHEAT COIL | COIL:HEATING:WATER | ZONEHVAC:AIRDISTRIBUTIONUNIT | ADU PERIMETER_MID_ZN_3 ZN VAV TERMINAL | 10620.763 | 10620.763 | 0.317300 | 0.00023231 | 760.500 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 19313.74 | 10620.76 | 0.317300 | 12.78 | 11.55 | 0.00800000 | 40.00 | 21.11 | 0.00800000 | -1.60 | 0.00331476 | -1.60 | 0.0000 | 21.00 | 0.00775210 | 49.9712 | 7429.71 | 0.00 | 10646.17 | 10646.17 |
| PERIMETER_MID_ZN_4 ZN REHEAT COIL | COIL:HEATING:WATER | ZONEHVAC:AIRDISTRIBUTIONUNIT | ADU PERIMETER_MID_ZN_4 ZN VAV TERMINAL | 7093.420 | 7093.420 | 0.211948 | 0.00015515 | 507.821 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 12899.31 | 7093.42 | 0.211948 | 12.78 | 11.55 | 0.00800000 | 40.00 | 21.11 | 0.00800000 | -1.60 | 0.00331476 | -1.60 | 0.0000 | 21.00 | 0.00778586 | 50.1859 | 4961.73 | 0.00 | 7110.39 | 7110.39 |
| PERIMETER_TOP_ZN_1 ZN REHEAT COIL | COIL:HEATING:WATER | ZONEHVAC:AIRDISTRIBUTIONUNIT | ADU PERIMETER_TOP_ZN_1 ZN VAV TERMINAL | 13189.996 | 13189.996 | 0.394250 | 0.00028850 | 943.775 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 23985.91 | 13190.00 | 0.394250 | 12.78 | 11.55 | 0.00800000 | 40.00 | 21.11 | 0.00800000 | -1.60 | 0.00331476 | -1.60 | 0.0000 | 21.00 | 0.00787378 | 50.7445 | 9223.99 | 0.00 | 13221.55 | 13221.55 |
| PERIMETER_TOP_ZN_2 ZN REHEAT COIL | COIL:HEATING:WATER | ZONEHVAC:AIRDISTRIBUTIONUNIT | ADU PERIMETER_TOP_ZN_2 ZN VAV TERMINAL | 8707.355 | 8707.355 | 0.260288 | 0.00019045 | 622.943 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 15834.27 | 8707.35 | 0.260288 | 12.78 | 11.55 | 0.00800000 | 40.00 | 21.11 | 0.00800000 | -1.60 | 0.00331476 | -1.60 | 0.0000 | 21.00 | 0.00788170 | 50.7948 | 6088.91 | 0.00 | 8728.18 | 8728.18 |
| PERIMETER_TOP_ZN_3 ZN REHEAT COIL | COIL:HEATING:WATER | ZONEHVAC:AIRDISTRIBUTIONUNIT | ADU PERIMETER_TOP_ZN_3 ZN VAV TERMINAL | 13199.316 | 13199.316 | 0.394530 | 0.00028871 | 944.438 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 24002.86 | 13199.32 | 0.394530 | 12.78 | 11.55 | 0.00800000 | 40.00 | 21.11 | 0.00800000 | -1.60 | 0.00331476 | -1.60 | 0.0000 | 21.00 | 0.00787413 | 50.7467 | 9230.50 | 0.00 | 13230.89 | 13230.89 |
| PERIMETER_TOP_ZN_4 ZN REHEAT COIL | COIL:HEATING:WATER | ZONEHVAC:AIRDISTRIBUTIONUNIT | ADU PERIMETER_TOP_ZN_4 ZN VAV TERMINAL | 8707.092 | 8707.092 | 0.260281 | 0.00019045 | 622.924 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 15833.79 | 8707.09 | 0.260281 | 12.78 | 11.55 | 0.00800000 | 40.00 | 21.11 | 0.00800000 | -1.60 | 0.00331476 | -1.60 | 0.0000 | 21.00 | 0.00788170 | 50.7949 | 6088.72 | 0.00 | 8727.92 | 8727.92 |
| 15 ZONE VAV CLG COIL | Coil:Cooling:Water | AirLoopHVAC | 15 ZONE VAV | 295772.855 | -999.000 | 13.603023 | 0.01255794 | -999.000 | HOUSTON BUSH INTERCONTINENTAL ANN CLG .4% CONDNS DB=>MWB | 7/21 15:10:00 | HOUSTON BUSH INTERCONTINENTAL ANN CLG .4% CONDNS DB=>MWB | 7/21 15:40:00 | 295772.86 | 239292.39 | 13.603023 | 25.89 | 18.11 | 0.00985498 | 11.52 | 11.52 | 0.00850000 | 35.90 | 0.01519472 | 24.77 | 15.8149 | 24.00 | 0.00881262 | 47.2620 | 186485.47 | 0.00 | 317786.96 | 243583.17 |
| 15 ZONE VAV MAIN HTG COIL | Coil:Heating:Water | AirLoopHVAC | 15 ZONE VAV | 19132.025 | 19132.025 | 4.080907 | 0.00041847 | 604.801 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 00:10:00 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 31488.55 | 19132.02 | 4.080907 | -1.60 | -1.60 | 0.00331476 | 12.78 | 11.55 | 0.00800000 | -1.60 | 0.00331476 | -1.60 | 52.7164 | 21.00 | 0.00786184 | 50.6684 | 716.45 | 0.00 | 19978.25 | 19978.25 |
Report: Coil Sizing Details
For: Entire Facility
Timestamp: 2019-04-09 23:11:28
Coils| Coil Type | Coil Location | HVAC Type | HVAC Name | Zone Name(s) | System Sizing Method Concurrence | System Sizing Method Capacity | System Sizing Method Air Flow | Autosized Coil Capacity? | Autosized Coil Airflow? | Autosized Coil Water Flow? | OA Pretreated prior to coil inlet? | Coil Final Gross Total Capacity [W] | Coil Final Gross Sensible Capacity [W] | Coil Final Reference Air Volume Flow Rate [m3/s] | Coil Final Reference Plant Fluid Volume Flow Rate [m3/s] | Coil U-value Times Area Value [W/K] | Terminal Unit Reheat Coil Multiplier | DX Coil Capacity Increase Ratio from Too Low Flow/Capacity Ratio | DX Coil Capacity Decrease Ratio from Too High Flow/Capacity Ratio | Moist Air Heat Capacity [J/kg-K] | Dry Air Heat Capacity [J/kg-K] | Standard Air Density Adjusted for Elevation [kg/m3] | Supply Fan Name for Coil | Supply Fan Type for Coil | Supply Fan Maximum Air Volume Flow Rate [m3/s] | Supply Fan Maximum Air Mass Flow Rate [kg/s] | Plant Name for Coil | Plant Fluid Specific Heat Capacity [J/kg-K] | Plant Fluid Density [kg/m3] | Plant Maximum Fluid Mass Flow Rate [kg/s] | Plant Design Fluid Return Temperature [C] | Plant Design Fluid Supply Temperature [C] | Plant Design Fluid Temperature Difference [deltaC] | Plant Design Capacity [W] | Coil Capacity Percentage of Plant Design Capacity [%] | Coil Fluid Flow Rate Percentage of Plant Design Flow Rate [%] | Design Day Name at Sensible Ideal Loads Peak | Date/Time at Sensible Ideal Loads Peak | Design Day Name at Total Ideal Loads Peak | Date/Time at Total Ideal Loads Peak | Design Day Name at Air Flow Ideal Loads Peak | Date/Time at Air Flow Ideal Loads Peak | Coil Total Capacity at Ideal Loads Peak [W] | Coil Sensible Capacity at Ideal Loads Peak [W] | Coil Off-Rating Capacity Modifier at Ideal Loads Peak [ ] | Coil Air Mass Flow Rate at Ideal Loads Peak [kg/s] | Coil Air Volume Flow Rate at Ideal Loads Peak [m3/s] | Coil Entering Air Drybulb at Ideal Loads Peak [C] | Coil Entering Air Wetbulb at Ideal Loads Peak [C] | Coil Entering Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Coil Entering Air Enthalpy at Ideal Loads Peak [J/KG-K] | Coil Leaving Air Drybulb at Ideal Loads Peak [C] | Coil Leaving Air Wetbulb at Ideal Loads Peak [C] | Coil Leaving Air Humidity Ratio at Ideal Loads Peak [C] | Coil Leaving Air Enthalpy at Ideal Loads Peak [J/KG-K] | Coil Plant Fluid Mass Flow Rate at Ideal Loads Peak [kg/s] | Coil Entering Plant Fluid Temperature at Ideal Loads Peak [C] | Coil Leaving Plant Fluid Temperature at Ideal Loads Peak [C] | Coil Plant Fluid Temperature Difference at Ideal Loads Peak [deltaC] | Supply Fan Air Heat Gain at Ideal Loads Peak [W] | Coil and Fan Net Total Capacity at Ideal Loads Peak [W] | Outdoor Air Drybulb at Ideal Loads Peak [C] | Outdoor Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Outdoor Air Wetbulb at Ideal Loads Peak [C] | Outdoor Air Volume Flow Rate at Ideal Loads Peak [m3/s] | Outdoor Air Flow Percentage at Ideal Loads Peak [%] | System Return Air Drybulb at Ideal Loads Peak [C] | System Return Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Zone Air Drybulb at Ideal Loads Peak [C] | Zone Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Zone Air Relative Humidity at Ideal Loads Peak [%] | Zone Sensible Heat Gain at Ideal Loads Peak [W] | Zone Latent Heat Gain at Ideal Loads Peak [W] | Coil Total Capacity at Rating Conditions [W] | Coil Sensible Capacity at Rating Conditions [W] | Coil Air Mass Flow Rate at Rating Conditions [kg/s] | Coil Entering Air Drybulb at Rating Conditions [C] | Coil Entering Air Wetbulb at Rating Conditions [C] | Coil Entering Air Humidity Ratio at Rating Conditions [KGWATER/KGDRYAIR] | Coil Entering Air Enthalpy at Rating Conditions [J/KG-K] | Coil Leaving Air Drybulb at Rating Conditions [C] | Coil Leaving Air Wetbulb at Rating Conditions [C] | Coil Leaving Air Humidity Ratio at Rating Conditions [KGWATER/KGDRYAIR] | Coil Leaving Air Enthalpy at Rating Conditions [J/KG-K] | |
| CORE_BOTTOM ZN REHEAT COIL | COIL:HEATING:WATER | Zone Equipment | ZONEHVAC:AIRDISTRIBUTIONUNIT | ADU CORE_BOTTOM ZN VAV TERMINAL | CORE_BOTTOM ZN | N/A | N/A | N/A | Yes | Yes | Yes | No | 9090.101 | 9090.101 | 0.295256 | 0.00019883 | 584.519 | 1.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.2002 | unknown | unknown | -999.0 | -999.0 | 4197.9300 | 999.8980 | 3.95158240 | 37.78 | 48.89 | 11.11 | 184316.29 | 8.9728 | 5.031049 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | unknown | unknown | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 16538.31 | 9090.10 | 1.0000 | 0.35435799 | 0.295256 | 12.78 | 11.55 | 0.00800000 | 33037.2 | 40.00 | 21.11 | 0.00800000 | 60796.0 | 0.19880604 | 60.00 | 48.89 | 11.11 | 0.000 | 16538.31 | -1.60 | 0.00331476 | -1.60 | 0.00000000 | 0.0000 | 20.61 | 0.00800000 | 21.00 | 0.00800000 | 51.5458 | 6119.06 | 0.00 | 9113.36 | 9113.36 | 0.35435799 | 12.78 | 11.58 | 0.00800000 | 33037.2 | 38.00 | 20.55 | 0.00800000 | 58755.1 | |
| CORE_MID ZN REHEAT COIL | COIL:HEATING:WATER | Zone Equipment | ZONEHVAC:AIRDISTRIBUTIONUNIT | ADU CORE_MID ZN VAV TERMINAL | CORE_MID ZN | N/A | N/A | N/A | Yes | Yes | Yes | No | 15814.026 | 15814.026 | 0.469194 | 0.00034590 | 1144.217 | 1.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.2002 | unknown | unknown | -999.0 | -999.0 | 4197.9300 | 999.8980 | 3.95158240 | 37.78 | 48.89 | 11.11 | 184316.29 | 15.6013 | 8.752504 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | unknown | unknown | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 28755.78 | 15814.03 | 1.0000 | 0.56311379 | 0.469194 | 12.78 | 11.55 | 0.00800000 | 33037.2 | 40.00 | 21.11 | 0.00800000 | 60796.0 | 0.34586239 | 60.00 | 48.89 | 11.11 | 0.000 | 28755.78 | -1.60 | 0.00331476 | -1.60 | 0.00000000 | 0.0000 | 20.87 | 0.00800000 | 21.00 | 0.00800000 | 51.5459 | 11092.71 | 0.00 | 15851.30 | 15851.30 | 0.56311379 | 12.78 | 11.58 | 0.00800000 | 33037.2 | 40.38 | 21.26 | 0.00800000 | 61186.5 | |
| CORE_TOP ZN REHEAT COIL | COIL:HEATING:WATER | Zone Equipment | ZONEHVAC:AIRDISTRIBUTIONUNIT | ADU CORE_TOP ZN VAV TERMINAL | CORE_TOP ZN | N/A | N/A | N/A | Yes | Yes | Yes | No | 28786.864 | 28786.864 | 0.857950 | 0.00062965 | 2068.782 | 1.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.2002 | unknown | unknown | -999.0 | -999.0 | 4197.9300 | 999.8980 | 3.95158240 | 37.78 | 48.89 | 11.11 | 184316.29 | 28.4012 | 15.932510 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | unknown | unknown | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 52348.07 | 28786.86 | 1.0000 | 1.02968849 | 0.857950 | 12.78 | 11.55 | 0.00800000 | 33037.2 | 40.00 | 21.11 | 0.00800000 | 60796.0 | 0.62958626 | 60.00 | 48.89 | 11.11 | 0.000 | 52348.07 | -1.60 | 0.00331476 | -1.60 | 0.00000000 | 0.0000 | 20.92 | 0.00800000 | 21.00 | 0.00800000 | 51.5459 | 20153.65 | 0.00 | 28855.73 | 28855.73 | 1.02968849 | 12.78 | 11.58 | 0.00800000 | 33037.2 | 40.26 | 21.23 | 0.00800000 | 61060.9 | |
| PERIMETER_BOT_ZN_1 ZN REHEAT COIL | COIL:HEATING:WATER | Zone Equipment | ZONEHVAC:AIRDISTRIBUTIONUNIT | ADU PERIMETER_BOT_ZN_1 ZN VAV TERMINAL | PERIMETER_BOT_ZN_1 ZN | N/A | N/A | N/A | Yes | Yes | Yes | No | 8564.316 | 8564.316 | 0.255723 | 0.00018733 | 613.750 | 1.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.2002 | unknown | unknown | -999.0 | -999.0 | 4197.9300 | 999.8980 | 3.95158240 | 37.78 | 48.89 | 11.11 | 184316.29 | 8.4496 | 4.740046 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | unknown | unknown | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 15574.08 | 8564.32 | 1.0000 | 0.30691224 | 0.255723 | 12.78 | 11.55 | 0.00800000 | 33037.2 | 40.00 | 21.11 | 0.00800000 | 60796.0 | 0.18730681 | 60.00 | 48.89 | 11.11 | 0.000 | 15574.08 | -1.60 | 0.00331476 | -1.60 | 0.00000000 | 0.0000 | 20.91 | 0.00766035 | 21.00 | 0.00766035 | 49.3873 | 5993.00 | 0.00 | 8584.80 | 8584.80 | 0.30691224 | 12.78 | 11.58 | 0.00800000 | 33037.2 | 40.21 | 21.21 | 0.00800000 | 61008.7 | |
| PERIMETER_BOT_ZN_2 ZN REHEAT COIL | COIL:HEATING:WATER | Zone Equipment | ZONEHVAC:AIRDISTRIBUTIONUNIT | ADU PERIMETER_BOT_ZN_2 ZN VAV TERMINAL | PERIMETER_BOT_ZN_2 ZN | N/A | N/A | N/A | Yes | Yes | Yes | No | 5774.749 | 5774.749 | 0.172460 | 0.00012631 | 413.728 | 1.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.2002 | unknown | unknown | -999.0 | -999.0 | 4197.9300 | 999.8980 | 3.95158240 | 37.78 | 48.89 | 11.11 | 184316.29 | 5.6974 | 3.196119 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | unknown | unknown | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 10501.30 | 5774.75 | 1.0000 | 0.20698181 | 0.172460 | 12.78 | 11.55 | 0.00800000 | 33037.2 | 40.00 | 21.11 | 0.00800000 | 60796.0 | 0.12629729 | 60.00 | 48.89 | 11.11 | 0.000 | 10501.30 | -1.60 | 0.00331476 | -1.60 | 0.00000000 | 0.0000 | 20.91 | 0.00769850 | 21.00 | 0.00769850 | 49.6301 | 4040.52 | 0.00 | 5788.56 | 5788.56 | 0.20698181 | 12.78 | 11.58 | 0.00800000 | 33037.2 | 40.20 | 21.21 | 0.00800000 | 61003.7 | |
| PERIMETER_BOT_ZN_3 ZN REHEAT COIL | COIL:HEATING:WATER | Zone Equipment | ZONEHVAC:AIRDISTRIBUTIONUNIT | ADU PERIMETER_BOT_ZN_3 ZN VAV TERMINAL | PERIMETER_BOT_ZN_3 ZN | N/A | N/A | N/A | Yes | Yes | Yes | No | 8502.953 | 8502.953 | 0.253885 | 0.00018598 | 609.372 | 1.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.2002 | unknown | unknown | -999.0 | -999.0 | 4197.9300 | 999.8980 | 3.95158240 | 37.78 | 48.89 | 11.11 | 184316.29 | 8.3891 | 4.706083 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | unknown | unknown | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 15462.49 | 8502.95 | 1.0000 | 0.30470660 | 0.253885 | 12.78 | 11.55 | 0.00800000 | 33037.2 | 40.00 | 21.11 | 0.00800000 | 60796.0 | 0.18596476 | 60.00 | 48.89 | 11.11 | 0.000 | 15462.49 | -1.60 | 0.00331476 | -1.60 | 0.00000000 | 0.0000 | 20.91 | 0.00765599 | 21.00 | 0.00765599 | 49.3595 | 5950.14 | 0.00 | 8523.29 | 8523.29 | 0.30470660 | 12.78 | 11.58 | 0.00800000 | 33037.2 | 40.21 | 21.21 | 0.00800000 | 61009.3 | |
| PERIMETER_BOT_ZN_4 ZN REHEAT COIL | COIL:HEATING:WATER | Zone Equipment | ZONEHVAC:AIRDISTRIBUTIONUNIT | ADU PERIMETER_BOT_ZN_4 ZN VAV TERMINAL | PERIMETER_BOT_ZN_4 ZN | N/A | N/A | N/A | Yes | Yes | Yes | No | 5774.676 | 5774.676 | 0.172458 | 0.00012631 | 413.723 | 1.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.2002 | unknown | unknown | -999.0 | -999.0 | 4197.9300 | 999.8980 | 3.95158240 | 37.78 | 48.89 | 11.11 | 184316.29 | 5.6974 | 3.196078 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | unknown | unknown | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 10501.17 | 5774.68 | 1.0000 | 0.20697920 | 0.172458 | 12.78 | 11.55 | 0.00800000 | 33037.2 | 40.00 | 21.11 | 0.00800000 | 60796.0 | 0.12629567 | 60.00 | 48.89 | 11.11 | 0.000 | 10501.17 | -1.60 | 0.00331476 | -1.60 | 0.00000000 | 0.0000 | 20.91 | 0.00769852 | 21.00 | 0.00769852 | 49.6302 | 4040.47 | 0.00 | 5788.49 | 5788.49 | 0.20697920 | 12.78 | 11.58 | 0.00800000 | 33037.2 | 40.20 | 21.21 | 0.00800000 | 61003.7 | |
| PERIMETER_MID_ZN_1 ZN REHEAT COIL | COIL:HEATING:WATER | Zone Equipment | ZONEHVAC:AIRDISTRIBUTIONUNIT | ADU PERIMETER_MID_ZN_1 ZN VAV TERMINAL | PERIMETER_MID_ZN_1 ZN | N/A | N/A | N/A | Yes | Yes | Yes | No | 10628.803 | 10628.803 | 0.317540 | 0.00023248 | 761.074 | 1.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.2002 | unknown | unknown | -999.0 | -999.0 | 4197.9300 | 999.8980 | 3.95158240 | 37.78 | 48.89 | 11.11 | 184316.29 | 10.4865 | 5.882666 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | unknown | unknown | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 19328.36 | 10628.80 | 1.0000 | 0.38110355 | 0.317540 | 12.78 | 11.55 | 0.00800000 | 33037.2 | 40.00 | 21.11 | 0.00800000 | 60796.0 | 0.23245839 | 60.00 | 48.89 | 11.11 | 0.000 | 19328.36 | -1.60 | 0.00331476 | -1.60 | 0.00000000 | 0.0000 | 20.95 | 0.00775231 | 21.00 | 0.00775231 | 49.9725 | 7435.33 | 0.00 | 10654.23 | 10654.23 | 0.38110355 | 12.78 | 11.58 | 0.00800000 | 33037.2 | 40.19 | 21.21 | 0.00800000 | 60993.4 | |
| PERIMETER_MID_ZN_2 ZN REHEAT COIL | COIL:HEATING:WATER | Zone Equipment | ZONEHVAC:AIRDISTRIBUTIONUNIT | ADU PERIMETER_MID_ZN_2 ZN VAV TERMINAL | PERIMETER_MID_ZN_2 ZN | N/A | N/A | N/A | Yes | Yes | Yes | No | 7093.581 | 7093.581 | 0.211953 | 0.00015516 | 507.832 | 1.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.2002 | unknown | unknown | -999.0 | -999.0 | 4197.9300 | 999.8980 | 3.95158240 | 37.78 | 48.89 | 11.11 | 184316.29 | 6.9986 | 3.926046 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | unknown | unknown | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 12899.61 | 7093.58 | 1.0000 | 0.25437985 | 0.211953 | 12.78 | 11.55 | 0.00800000 | 33037.2 | 40.00 | 21.11 | 0.00800000 | 60796.0 | 0.15514093 | 60.00 | 48.89 | 11.11 | 0.000 | 12899.61 | -1.60 | 0.00331476 | -1.60 | 0.00000000 | 0.0000 | 20.95 | 0.00778584 | 21.00 | 0.00778584 | 50.1857 | 4961.84 | 0.00 | 7110.55 | 7110.55 | 0.25437985 | 12.78 | 11.58 | 0.00800000 | 33037.2 | 40.19 | 21.21 | 0.00800000 | 60989.7 | |
| PERIMETER_MID_ZN_3 ZN REHEAT COIL | COIL:HEATING:WATER | Zone Equipment | ZONEHVAC:AIRDISTRIBUTIONUNIT | ADU PERIMETER_MID_ZN_3 ZN VAV TERMINAL | PERIMETER_MID_ZN_3 ZN | N/A | N/A | N/A | Yes | Yes | Yes | No | 10620.763 | 10620.763 | 0.317300 | 0.00023231 | 760.500 | 1.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.2002 | unknown | unknown | -999.0 | -999.0 | 4197.9300 | 999.8980 | 3.95158240 | 37.78 | 48.89 | 11.11 | 184316.29 | 10.4786 | 5.878216 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | unknown | unknown | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 19313.74 | 10620.76 | 1.0000 | 0.38081477 | 0.317300 | 12.78 | 11.55 | 0.00800000 | 33037.2 | 40.00 | 21.11 | 0.00800000 | 60796.0 | 0.23228255 | 60.00 | 48.89 | 11.11 | 0.000 | 19313.74 | -1.60 | 0.00331476 | -1.60 | 0.00000000 | 0.0000 | 20.95 | 0.00775210 | 21.00 | 0.00775210 | 49.9712 | 7429.71 | 0.00 | 10646.17 | 10646.17 | 0.38081477 | 12.78 | 11.58 | 0.00800000 | 33037.2 | 40.19 | 21.21 | 0.00800000 | 60993.5 | |
| PERIMETER_MID_ZN_4 ZN REHEAT COIL | COIL:HEATING:WATER | Zone Equipment | ZONEHVAC:AIRDISTRIBUTIONUNIT | ADU PERIMETER_MID_ZN_4 ZN VAV TERMINAL | PERIMETER_MID_ZN_4 ZN | N/A | N/A | N/A | Yes | Yes | Yes | No | 7093.420 | 7093.420 | 0.211948 | 0.00015515 | 507.821 | 1.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.2002 | unknown | unknown | -999.0 | -999.0 | 4197.9300 | 999.8980 | 3.95158240 | 37.78 | 48.89 | 11.11 | 184316.29 | 6.9985 | 3.925957 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | unknown | unknown | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 12899.31 | 7093.42 | 1.0000 | 0.25437411 | 0.211948 | 12.78 | 11.55 | 0.00800000 | 33037.2 | 40.00 | 21.11 | 0.00800000 | 60796.0 | 0.15513741 | 60.00 | 48.89 | 11.11 | 0.000 | 12899.31 | -1.60 | 0.00331476 | -1.60 | 0.00000000 | 0.0000 | 20.95 | 0.00778586 | 21.00 | 0.00778586 | 50.1859 | 4961.73 | 0.00 | 7110.39 | 7110.39 | 0.25437411 | 12.78 | 11.58 | 0.00800000 | 33037.2 | 40.19 | 21.21 | 0.00800000 | 60989.6 | |
| PERIMETER_TOP_ZN_1 ZN REHEAT COIL | COIL:HEATING:WATER | Zone Equipment | ZONEHVAC:AIRDISTRIBUTIONUNIT | ADU PERIMETER_TOP_ZN_1 ZN VAV TERMINAL | PERIMETER_TOP_ZN_1 ZN | N/A | N/A | N/A | Yes | Yes | Yes | No | 13189.996 | 13189.996 | 0.394250 | 0.00028850 | 943.775 | 1.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.2002 | unknown | unknown | -999.0 | -999.0 | 4197.9300 | 999.8980 | 3.95158240 | 37.78 | 48.89 | 11.11 | 184316.29 | 13.0135 | 7.300195 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | unknown | unknown | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 23985.91 | 13190.00 | 1.0000 | 0.47316881 | 0.394250 | 12.78 | 11.55 | 0.00800000 | 33037.2 | 40.00 | 21.11 | 0.00800000 | 60796.0 | 0.28847324 | 60.00 | 48.89 | 11.11 | 0.000 | 23985.91 | -1.60 | 0.00331476 | -1.60 | 0.00000000 | 0.0000 | 20.95 | 0.00787378 | 21.00 | 0.00787378 | 50.7445 | 9223.99 | 0.00 | 13221.55 | 13221.55 | 0.47316881 | 12.78 | 11.58 | 0.00800000 | 33037.2 | 40.18 | 21.20 | 0.00800000 | 60979.7 | |
| PERIMETER_TOP_ZN_2 ZN REHEAT COIL | COIL:HEATING:WATER | Zone Equipment | ZONEHVAC:AIRDISTRIBUTIONUNIT | ADU PERIMETER_TOP_ZN_2 ZN VAV TERMINAL | PERIMETER_TOP_ZN_2 ZN | N/A | N/A | N/A | Yes | Yes | Yes | No | 8707.355 | 8707.355 | 0.260288 | 0.00019045 | 622.943 | 1.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.2002 | unknown | unknown | -999.0 | -999.0 | 4197.9300 | 999.8980 | 3.95158240 | 37.78 | 48.89 | 11.11 | 184316.29 | 8.5908 | 4.819213 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | unknown | unknown | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 15834.27 | 8707.35 | 1.0000 | 0.31239138 | 0.260288 | 12.78 | 11.55 | 0.00800000 | 33037.2 | 40.00 | 21.11 | 0.00800000 | 60796.0 | 0.19043515 | 60.00 | 48.89 | 11.11 | 0.000 | 15834.27 | -1.60 | 0.00331476 | -1.60 | 0.00000000 | 0.0000 | 20.95 | 0.00788170 | 21.00 | 0.00788170 | 50.7948 | 6088.91 | 0.00 | 8728.18 | 8728.18 | 0.31239138 | 12.78 | 11.58 | 0.00800000 | 33037.2 | 40.18 | 21.20 | 0.00800000 | 60977.1 | |
| PERIMETER_TOP_ZN_3 ZN REHEAT COIL | COIL:HEATING:WATER | Zone Equipment | ZONEHVAC:AIRDISTRIBUTIONUNIT | ADU PERIMETER_TOP_ZN_3 ZN VAV TERMINAL | PERIMETER_TOP_ZN_3 ZN | N/A | N/A | N/A | Yes | Yes | Yes | No | 13199.316 | 13199.316 | 0.394530 | 0.00028871 | 944.438 | 1.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.2002 | unknown | unknown | -999.0 | -999.0 | 4197.9300 | 999.8980 | 3.95158240 | 37.78 | 48.89 | 11.11 | 184316.29 | 13.0226 | 7.305354 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | unknown | unknown | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 24002.86 | 13199.32 | 1.0000 | 0.47350435 | 0.394530 | 12.78 | 11.55 | 0.00800000 | 33037.2 | 40.00 | 21.11 | 0.00800000 | 60796.0 | 0.28867708 | 60.00 | 48.89 | 11.11 | 0.000 | 24002.86 | -1.60 | 0.00331476 | -1.60 | 0.00000000 | 0.0000 | 20.95 | 0.00787413 | 21.00 | 0.00787413 | 50.7467 | 9230.50 | 0.00 | 13230.89 | 13230.89 | 0.47350435 | 12.78 | 11.58 | 0.00800000 | 33037.2 | 40.18 | 21.20 | 0.00800000 | 60979.7 | |
| PERIMETER_TOP_ZN_4 ZN REHEAT COIL | COIL:HEATING:WATER | Zone Equipment | ZONEHVAC:AIRDISTRIBUTIONUNIT | ADU PERIMETER_TOP_ZN_4 ZN VAV TERMINAL | PERIMETER_TOP_ZN_4 ZN | N/A | N/A | N/A | Yes | Yes | Yes | No | 8707.092 | 8707.092 | 0.260281 | 0.00019045 | 622.924 | 1.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.2002 | unknown | unknown | -999.0 | -999.0 | 4197.9300 | 999.8980 | 3.95158240 | 37.78 | 48.89 | 11.11 | 184316.29 | 8.5906 | 4.819067 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | unknown | unknown | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 15833.79 | 8707.09 | 1.0000 | 0.31238197 | 0.260281 | 12.78 | 11.55 | 0.00800000 | 33037.2 | 40.00 | 21.11 | 0.00800000 | 60796.0 | 0.19042940 | 60.00 | 48.89 | 11.11 | 0.000 | 15833.79 | -1.60 | 0.00331476 | -1.60 | 0.00000000 | 0.0000 | 20.95 | 0.00788170 | 21.00 | 0.00788170 | 50.7949 | 6088.72 | 0.00 | 8727.92 | 8727.92 | 0.31238197 | 12.78 | 11.58 | 0.00800000 | 33037.2 | 40.18 | 21.20 | 0.00800000 | 60977.1 | |
| 15 ZONE VAV CLG COIL | Coil:Cooling:Water | AirLoop | AirLoopHVAC | 15 ZONE VAV | PERIMETER_TOP_ZN_4 ZN; CORE_MID ZN; CORE_TOP ZN; PERIMETER_BOT_ZN_1 ZN; PERIMETER_BOT_ZN_2 ZN; PERIMETER_BOT_ZN_3 ZN; PERIMETER_BOT_ZN_4 ZN; PERIMETER_TOP_ZN_3 ZN; PERIMETER_MID_ZN_2 ZN; PERIMETER_MID_ZN_3 ZN; PERIMETER_MID_ZN_4 ZN; PERIMETER_TOP_ZN_1 ZN; PERIMETER_TOP_ZN_2 ZN; PERIMETER_MID_ZN_1 ZN; CORE_BOTTOM ZN; | Coincident | CoolingDesignCapacity | N/A | Yes | Yes | Yes | No | 295772.855 | -999.000 | 13.603023 | 0.01255794 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1023.1599 | 1004.8586 | 1.2002 | 15 ZONE VAV FAN | Fan:VariableVolume | 13.603023 | 16.32599124 | 4197.9300 | 999.8980 | 12.55666340 | 12.28 | 6.67 | 5.61 | 295772.86 | 100.0000 | 100.000000 | HOUSTON BUSH INTERCONTINENTAL ANN CLG .4% CONDNS DB=>MWB | 7/21 15:10:00 | HOUSTON BUSH INTERCONTINENTAL ANN CLG .4% CONDNS DB=>MWB | 7/21 15:10:00 | HOUSTON BUSH INTERCONTINENTAL ANN CLG .4% CONDNS DB=>MWB | 7/21 15:40:00 | 295772.86 | 239292.39 | 1.0000 | 16.32599124 | 13.603023 | 25.89 | 18.11 | 0.00985498 | 51131.9 | 11.52 | 11.52 | 0.00850000 | 33015.2 | 12.55666340 | 6.67 | 12.28 | 5.61 | 21019.617 | 274753.24 | 35.90 | 0.01519472 | 24.77 | 2.15130787 | 15.8149 | 24.00 | 0.00884874 | 24.00 | 0.00881262 | 47.2620 | 186485.47 | 0.00 | 317786.96 | 243583.17 | 16.32599124 | 25.89 | 18.15 | 0.00985498 | 51131.9 | 11.30 | 11.01 | 0.00805275 | 31666.8 | |
| 15 ZONE VAV MAIN HTG COIL | Coil:Heating:Water | AirLoop | AirLoopHVAC | 15 ZONE VAV | PERIMETER_TOP_ZN_4 ZN; CORE_MID ZN; CORE_TOP ZN; PERIMETER_BOT_ZN_1 ZN; PERIMETER_BOT_ZN_2 ZN; PERIMETER_BOT_ZN_3 ZN; PERIMETER_BOT_ZN_4 ZN; PERIMETER_TOP_ZN_3 ZN; PERIMETER_MID_ZN_2 ZN; PERIMETER_MID_ZN_3 ZN; PERIMETER_MID_ZN_4 ZN; PERIMETER_TOP_ZN_1 ZN; PERIMETER_TOP_ZN_2 ZN; PERIMETER_MID_ZN_1 ZN; CORE_BOTTOM ZN; | Coincident | HeatingDesignCapacity | N/A | Yes | Yes | Yes | No | 19132.025 | 19132.025 | 4.080907 | 0.00041847 | 604.801 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.2002 | 15 ZONE VAV FAN | Fan:VariableVolume | 13.603023 | 16.32599124 | 4197.9300 | 999.8980 | 3.95158240 | 37.78 | 48.89 | 11.11 | 184316.29 | 17.0840 | 10.588898 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 00:10:00 | unknown | unknown | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | 31488.55 | 19132.02 | 1.0000 | 4.89779737 | 4.080907 | -1.60 | -1.60 | 0.00331476 | 6672.4 | 12.78 | 11.55 | 0.00800000 | 33037.2 | 0.41842903 | 60.00 | 48.89 | 11.11 | 0.000 | 31488.55 | -1.60 | 0.00331476 | -1.60 | 2.15130787 | 52.7164 | 20.59 | 0.00091319 | 21.00 | 0.00786184 | 50.6684 | 716.45 | 0.00 | 19978.25 | 19978.25 | 4.89779737 | 7.22 | 1.88 | 0.00217921 | 12736.5 | 11.27 | 4.10 | 0.00217921 | 16815.5 |
Report: System Summary
For: Entire Facility
Timestamp: 2019-04-09 23:11:28
Economizer| High Limit Shutoff Control | Minimum Outdoor Air [m3/s] | Maximum Outdoor Air [m3/s] | Return Air Temp Limit | Return Air Enthalpy Limit | Outdoor Air Temperature Limit [C] | Outdoor Air Enthalpy Limit [C] | |
| 15 ZONE VAV OA CONTROLLER | DifferentialEnthalpy | 0.00 | 13.60 | - |
| Controller:MechanicalVentilation Name | Outdoor Air Per Person [m3/s-person] | Outdoor Air Per Area [m3/s-m2] | Outdoor Air Per Zone [m3/s] | Outdoor Air ACH [ach] | Outdoor Air Method | Outdoor Air Schedule Name | Air Distribution Effectiveness in Cooling Mode | Air Distribution Effectiveness in Heating Mode | Air Distribution Effectiveness Schedule Name | |
| CORE_BOTTOM ZN | 15 ZONE VAV VENT CONTROLLER | 0.000000 | 0.000432 | 0.000000 | 0.000000 | Sum | 1.00 | 1.00 | ||
| CORE_MID ZN | 15 ZONE VAV VENT CONTROLLER | 0.000000 | 0.000432 | 0.000000 | 0.000000 | Sum | 1.00 | 1.00 | ||
| CORE_TOP ZN | 15 ZONE VAV VENT CONTROLLER | 0.000000 | 0.000432 | 0.000000 | 0.000000 | Sum | 1.00 | 1.00 | ||
| PERIMETER_BOT_ZN_1 ZN | 15 ZONE VAV VENT CONTROLLER | 0.000000 | 0.000432 | 0.000000 | 0.000000 | Sum | 1.00 | 1.00 | ||
| PERIMETER_BOT_ZN_2 ZN | 15 ZONE VAV VENT CONTROLLER | 0.000000 | 0.000432 | 0.000000 | 0.000000 | Sum | 1.00 | 1.00 | ||
| PERIMETER_BOT_ZN_3 ZN | 15 ZONE VAV VENT CONTROLLER | 0.000000 | 0.000432 | 0.000000 | 0.000000 | Sum | 1.00 | 1.00 | ||
| PERIMETER_BOT_ZN_4 ZN | 15 ZONE VAV VENT CONTROLLER | 0.000000 | 0.000432 | 0.000000 | 0.000000 | Sum | 1.00 | 1.00 | ||
| PERIMETER_MID_ZN_1 ZN | 15 ZONE VAV VENT CONTROLLER | 0.000000 | 0.000432 | 0.000000 | 0.000000 | Sum | 1.00 | 1.00 | ||
| PERIMETER_MID_ZN_2 ZN | 15 ZONE VAV VENT CONTROLLER | 0.000000 | 0.000432 | 0.000000 | 0.000000 | Sum | 1.00 | 1.00 | ||
| PERIMETER_MID_ZN_3 ZN | 15 ZONE VAV VENT CONTROLLER | 0.000000 | 0.000432 | 0.000000 | 0.000000 | Sum | 1.00 | 1.00 | ||
| PERIMETER_MID_ZN_4 ZN | 15 ZONE VAV VENT CONTROLLER | 0.000000 | 0.000432 | 0.000000 | 0.000000 | Sum | 1.00 | 1.00 | ||
| PERIMETER_TOP_ZN_1 ZN | 15 ZONE VAV VENT CONTROLLER | 0.000000 | 0.000432 | 0.000000 | 0.000000 | Sum | 1.00 | 1.00 | ||
| PERIMETER_TOP_ZN_2 ZN | 15 ZONE VAV VENT CONTROLLER | 0.000000 | 0.000432 | 0.000000 | 0.000000 | Sum | 1.00 | 1.00 | ||
| PERIMETER_TOP_ZN_3 ZN | 15 ZONE VAV VENT CONTROLLER | 0.000000 | 0.000432 | 0.000000 | 0.000000 | Sum | 1.00 | 1.00 | ||
| PERIMETER_TOP_ZN_4 ZN | 15 ZONE VAV VENT CONTROLLER | 0.000000 | 0.000432 | 0.000000 | 0.000000 | Sum | 1.00 | 1.00 |
| Winter Clothes [hr] | Summer Clothes [hr] | Summer or Winter Clothes [hr] | |
| CORE_BOTTOM ZN | 1293.17 | 910.17 | 0.67 |
| CORE_MID ZN | 1964.67 | 588.50 | 3.67 |
| CORE_TOP ZN | 1962.83 | 645.33 | 21.00 |
| PERIMETER_BOT_ZN_1 ZN | 2073.17 | 1559.83 | 834.00 |
| PERIMETER_BOT_ZN_2 ZN | 1725.33 | 1016.17 | 53.83 |
| PERIMETER_BOT_ZN_3 ZN | 1581.33 | 1161.67 | 98.33 |
| PERIMETER_BOT_ZN_4 ZN | 1682.83 | 1137.50 | 104.00 |
| PERIMETER_MID_ZN_1 ZN | 2207.00 | 523.33 | 54.67 |
| PERIMETER_MID_ZN_2 ZN | 2070.17 | 760.17 | 52.83 |
| PERIMETER_MID_ZN_3 ZN | 1978.17 | 881.33 | 88.00 |
| PERIMETER_MID_ZN_4 ZN | 2062.50 | 839.17 | 89.67 |
| PERIMETER_TOP_ZN_1 ZN | 2212.50 | 605.33 | 91.50 |
| PERIMETER_TOP_ZN_2 ZN | 2093.00 | 790.67 | 93.33 |
| PERIMETER_TOP_ZN_3 ZN | 2032.00 | 921.67 | 150.67 |
| PERIMETER_TOP_ZN_4 ZN | 2106.50 | 895.83 | 151.17 |
| FIRSTFLOOR_PLENUM ZN | 0.00 | 0.00 | 0.00 |
| MIDFLOOR_PLENUM ZN | 0.00 | 0.00 | 0.00 |
| TOPFLOOR_PLENUM ZN | 0.00 | 0.00 | 0.00 |
| Facility | 2502.50 | 1906.17 | 893.00 |
| During Heating [hr] | During Cooling [hr] | During Occupied Heating [hr] | During Occupied Cooling [hr] | |
| CORE_BOTTOM ZN | 0.00 | 62.83 | 0.00 | 0.33 |
| CORE_MID ZN | 0.00 | 141.17 | 0.00 | 0.00 |
| CORE_TOP ZN | 0.33 | 178.67 | 0.17 | 0.00 |
| PERIMETER_BOT_ZN_1 ZN | 145.50 | 490.17 | 131.00 | 326.67 |
| PERIMETER_BOT_ZN_2 ZN | 2.17 | 131.83 | 0.17 | 0.33 |
| PERIMETER_BOT_ZN_3 ZN | 2.33 | 99.17 | 0.33 | 0.00 |
| PERIMETER_BOT_ZN_4 ZN | 2.33 | 174.00 | 0.17 | 0.00 |
| PERIMETER_MID_ZN_1 ZN | 1.50 | 280.00 | 0.17 | 43.00 |
| PERIMETER_MID_ZN_2 ZN | 2.17 | 206.67 | 0.17 | 0.33 |
| PERIMETER_MID_ZN_3 ZN | 2.50 | 180.17 | 0.17 | 0.00 |
| PERIMETER_MID_ZN_4 ZN | 2.33 | 247.33 | 0.17 | 0.00 |
| PERIMETER_TOP_ZN_1 ZN | 6.00 | 295.83 | 0.33 | 27.00 |
| PERIMETER_TOP_ZN_2 ZN | 7.17 | 234.33 | 0.33 | 0.33 |
| PERIMETER_TOP_ZN_3 ZN | 8.33 | 221.50 | 0.67 | 0.00 |
| PERIMETER_TOP_ZN_4 ZN | 6.67 | 275.00 | 0.33 | 0.00 |
| FIRSTFLOOR_PLENUM ZN | 0.00 | 0.00 | 0.00 | 0.00 |
| MIDFLOOR_PLENUM ZN | 0.00 | 0.00 | 0.00 | 0.00 |
| TOPFLOOR_PLENUM ZN | 0.00 | 0.00 | 0.00 | 0.00 |
| Facility | 148.33 | 689.33 | 131.00 | 332.50 |
Report: Outdoor Air Summary
For: Entire Facility
Timestamp: 2019-04-09 23:11:28
Average Outdoor Air During Occupied Hours| Average Number of Occupants | Nominal Number of Occupants | Zone Volume [m3] | Mechanical Ventilation [ach] | Infiltration [ach] | AFN Infiltration [ach] | Simple Ventilation [ach] | |
| CORE_BOTTOM ZN | 40.12 | 52.93 | 2698.04 | 0.872 | 0.000 | 0.000 | 0.000 |
| CORE_MID ZN | 40.12 | 52.93 | 2698.04 | 0.580 | 0.000 | 0.000 | 0.000 |
| CORE_TOP ZN | 40.12 | 52.93 | 2698.04 | 0.592 | 0.000 | 0.000 | 0.000 |
| PERIMETER_BOT_ZN_1 ZN | 8.46 | 11.16 | 568.77 | 0.826 | 2.352 | 0.000 | 0.000 |
| PERIMETER_BOT_ZN_2 ZN | 5.35 | 7.06 | 360.08 | 0.775 | 0.028 | 0.000 | 0.000 |
| PERIMETER_BOT_ZN_3 ZN | 8.46 | 11.16 | 568.77 | 0.423 | 0.026 | 0.000 | 0.000 |
| PERIMETER_BOT_ZN_4 ZN | 5.35 | 7.06 | 360.05 | 0.739 | 0.028 | 0.000 | 0.000 |
| PERIMETER_MID_ZN_1 ZN | 8.46 | 11.16 | 568.77 | 1.040 | 0.041 | 0.000 | 0.000 |
| PERIMETER_MID_ZN_2 ZN | 5.35 | 7.06 | 360.08 | 0.983 | 0.044 | 0.000 | 0.000 |
| PERIMETER_MID_ZN_3 ZN | 8.46 | 11.16 | 568.77 | 0.606 | 0.041 | 0.000 | 0.000 |
| PERIMETER_MID_ZN_4 ZN | 5.35 | 7.06 | 360.05 | 0.912 | 0.044 | 0.000 | 0.000 |
| PERIMETER_TOP_ZN_1 ZN | 8.46 | 11.16 | 568.77 | 1.064 | 0.050 | 0.000 | 0.000 |
| PERIMETER_TOP_ZN_2 ZN | 5.35 | 7.06 | 360.08 | 1.007 | 0.052 | 0.000 | 0.000 |
| PERIMETER_TOP_ZN_3 ZN | 8.46 | 11.16 | 568.77 | 0.660 | 0.050 | 0.000 | 0.000 |
| PERIMETER_TOP_ZN_4 ZN | 5.35 | 7.06 | 360.05 | 0.968 | 0.052 | 0.000 | 0.000 |
| Average Number of Occupants | Nominal Number of Occupants | Zone Volume [m3] | Mechanical Ventilation [ach] | Infiltration [ach] | AFN Infiltration [ach] | Simple Ventilation [ach] | |
| CORE_BOTTOM ZN | 40.12 | 52.93 | 2698.04 | 0.085 | 0.000 | 0.000 | 0.000 |
| CORE_MID ZN | 40.12 | 52.93 | 2698.04 | 0.111 | 0.000 | 0.000 | 0.000 |
| CORE_TOP ZN | 40.12 | 52.93 | 2698.04 | 0.135 | 0.000 | 0.000 | 0.000 |
| PERIMETER_BOT_ZN_1 ZN | 8.46 | 11.16 | 568.77 | 0.070 | 0.000 | 0.000 | 0.000 |
| PERIMETER_BOT_ZN_2 ZN | 5.35 | 7.06 | 360.08 | 0.124 | 0.000 | 0.000 | 0.000 |
| PERIMETER_BOT_ZN_3 ZN | 8.46 | 11.16 | 568.77 | 0.069 | 0.000 | 0.000 | 0.000 |
| PERIMETER_BOT_ZN_4 ZN | 5.35 | 7.06 | 360.05 | 0.117 | 0.000 | 0.000 | 0.000 |
| PERIMETER_MID_ZN_1 ZN | 8.46 | 11.16 | 568.77 | 0.174 | 0.000 | 0.000 | 0.000 |
| PERIMETER_MID_ZN_2 ZN | 5.35 | 7.06 | 360.08 | 0.186 | 0.000 | 0.000 | 0.000 |
| PERIMETER_MID_ZN_3 ZN | 8.46 | 11.16 | 568.77 | 0.155 | 0.000 | 0.000 | 0.000 |
| PERIMETER_MID_ZN_4 ZN | 5.35 | 7.06 | 360.05 | 0.156 | 0.000 | 0.000 | 0.000 |
| PERIMETER_TOP_ZN_1 ZN | 8.46 | 11.16 | 568.77 | 0.172 | 0.000 | 0.000 | 0.000 |
| PERIMETER_TOP_ZN_2 ZN | 5.35 | 7.06 | 360.08 | 0.171 | 0.000 | 0.000 | 0.000 |
| PERIMETER_TOP_ZN_3 ZN | 8.46 | 11.16 | 568.77 | 0.150 | 0.000 | 0.000 | 0.000 |
| PERIMETER_TOP_ZN_4 ZN | 5.35 | 7.06 | 360.05 | 0.166 | 0.000 | 0.000 | 0.000 |
Report: Object Count Summary
For: Entire Facility
Timestamp: 2019-04-09 23:11:28
Surfaces by Class| Total | Outdoors | |
| Wall | 72 | 24 |
| Floor | 30 | 5 |
| Roof | 26 | 1 |
| Internal Mass | 15 | 0 |
| Building Detached Shading | 0 | 0 |
| Fixed Detached Shading | 0 | 0 |
| Window | 12 | 12 |
| Door | 0 | 0 |
| Glass Door | 0 | 0 |
| Shading | 0 | 0 |
| Overhang | 0 | 0 |
| Fin | 0 | 0 |
| Tubular Daylighting Device Dome | 0 | 0 |
| Tubular Daylighting Device Diffuser | 0 | 0 |
| Count | |
| HVAC Air Loops | 1 |
| Conditioned Zones | 15 |
| Unconditioned Zones | 3 |
| Supply Plenums | 0 |
| Return Plenums | 0 |
| Count | |
| IDF Objects | 0 |
| Defaulted Fields | 0 |
| Fields with Defaults | 0 |
| Autosized Fields | 0 |
| Autosizable Fields | 0 |
| Autocalculated Fields | 0 |
| Autocalculatable Fields | 0 |
Report: Energy Meters
For: Entire Facility
Timestamp: 2019-04-09 23:11:28
Annual and Peak Values - Electricity| Electricity Annual Value [GJ] | Electricity Minimum Value [W] | Timestamp of Minimum {TIMESTAMP} | Electricity Maximum Value [W] | Timestamp of Maximum {TIMESTAMP} | |
| Electricity:Facility | 1758.63 | 11011.01 | 25-JUN-17:10 | 172594.12 | 02-AUG-16:00 |
| Electricity:Building | 1099.64 | 11011.01 | 25-JUN-17:10 | 89438.18 | 29-MAR-07:10 |
| Electricity:Zone:CORE_BOTTOM ZN | 367.50 | 2266.26 | 01-JAN-00:10 | 35791.38 | 02-JAN-08:10 |
| InteriorLights:Electricity | 335.95 | 1491.68 | 01-JAN-10:30 | 34128.53 | 22-NOV-17:00 |
| InteriorLights:Electricity:Zone:CORE_BOTTOM ZN | 79.86 | 374.30 | 01-JAN-06:10 | 6737.34 | 02-JAN-08:10 |
| General:InteriorLights:Electricity | 335.95 | 1491.68 | 01-JAN-10:30 | 34128.53 | 22-NOV-17:00 |
| Electricity:Zone:CORE_MID ZN | 196.96 | 2266.26 | 01-JAN-00:10 | 13548.12 | 02-JAN-08:10 |
| InteriorLights:Electricity:Zone:CORE_MID ZN | 79.86 | 374.30 | 01-JAN-06:10 | 6737.34 | 02-JAN-08:10 |
| Electricity:Zone:CORE_TOP ZN | 196.96 | 2266.26 | 01-JAN-00:10 | 13548.12 | 02-JAN-08:10 |
| InteriorLights:Electricity:Zone:CORE_TOP ZN | 79.86 | 374.30 | 01-JAN-06:10 | 6737.34 | 02-JAN-08:10 |
| Electricity:Zone:PERIMETER_BOT_ZN_1 ZN | 34.42 | 429.89 | 12-MAR-17:10 | 2856.06 | 22-NOV-16:50 |
| InteriorLights:Electricity:Zone:PERIMETER_BOT_ZN_1 ZN | 9.74 | 37.64 | 01-JAN-07:50 | 1420.29 | 22-NOV-16:50 |
| Electricity:Zone:PERIMETER_BOT_ZN_2 ZN | 21.87 | 272.16 | 25-JUN-17:10 | 1808.12 | 08-NOV-17:00 |
| InteriorLights:Electricity:Zone:PERIMETER_BOT_ZN_2 ZN | 6.25 | 23.83 | 01-JAN-07:50 | 899.16 | 08-NOV-17:00 |
| Electricity:Zone:PERIMETER_BOT_ZN_3 ZN | 34.65 | 429.89 | 02-APR-17:10 | 2856.06 | 08-NOV-17:00 |
| InteriorLights:Electricity:Zone:PERIMETER_BOT_ZN_3 ZN | 9.97 | 37.64 | 01-JAN-10:30 | 1420.29 | 08-NOV-17:00 |
| Electricity:Zone:PERIMETER_BOT_ZN_4 ZN | 21.86 | 272.14 | 12-MAR-17:10 | 1808.00 | 29-MAR-07:10 |
| InteriorLights:Electricity:Zone:PERIMETER_BOT_ZN_4 ZN | 6.24 | 23.83 | 01-JAN-10:30 | 899.10 | 29-MAR-07:10 |
| Electricity:Zone:PERIMETER_MID_ZN_1 ZN | 34.41 | 429.89 | 12-MAR-17:10 | 2856.06 | 22-NOV-16:50 |
| InteriorLights:Electricity:Zone:PERIMETER_MID_ZN_1 ZN | 9.72 | 37.64 | 01-JAN-07:50 | 1420.29 | 22-NOV-16:50 |
| Electricity:Zone:PERIMETER_MID_ZN_2 ZN | 21.85 | 272.16 | 21-MAY-17:10 | 1808.12 | 08-NOV-17:00 |
| InteriorLights:Electricity:Zone:PERIMETER_MID_ZN_2 ZN | 6.23 | 23.83 | 01-JAN-07:50 | 899.16 | 08-NOV-17:00 |
| Electricity:Zone:PERIMETER_MID_ZN_3 ZN | 34.61 | 429.89 | 02-APR-17:10 | 2856.06 | 08-NOV-17:00 |
| InteriorLights:Electricity:Zone:PERIMETER_MID_ZN_3 ZN | 9.92 | 37.64 | 01-JAN-10:10 | 1420.29 | 08-NOV-17:00 |
| Electricity:Zone:PERIMETER_MID_ZN_4 ZN | 21.84 | 272.14 | 12-MAR-17:10 | 1808.00 | 29-MAR-07:10 |
| InteriorLights:Electricity:Zone:PERIMETER_MID_ZN_4 ZN | 6.22 | 23.83 | 01-JAN-10:10 | 899.10 | 29-MAR-07:10 |
| Electricity:Zone:PERIMETER_TOP_ZN_1 ZN | 34.41 | 429.89 | 12-MAR-17:10 | 2856.06 | 22-NOV-16:50 |
| InteriorLights:Electricity:Zone:PERIMETER_TOP_ZN_1 ZN | 9.72 | 37.64 | 01-JAN-07:50 | 1420.29 | 22-NOV-16:50 |
| Electricity:Zone:PERIMETER_TOP_ZN_2 ZN | 21.85 | 272.16 | 21-MAY-17:10 | 1808.12 | 08-NOV-17:00 |
| InteriorLights:Electricity:Zone:PERIMETER_TOP_ZN_2 ZN | 6.23 | 23.83 | 01-JAN-07:50 | 899.16 | 08-NOV-17:00 |
| Electricity:Zone:PERIMETER_TOP_ZN_3 ZN | 34.61 | 429.89 | 02-APR-17:10 | 2856.06 | 08-NOV-17:00 |
| InteriorLights:Electricity:Zone:PERIMETER_TOP_ZN_3 ZN | 9.92 | 37.64 | 01-JAN-10:10 | 1420.29 | 08-NOV-17:00 |
| Electricity:Zone:PERIMETER_TOP_ZN_4 ZN | 21.84 | 272.14 | 12-MAR-17:10 | 1808.00 | 29-MAR-07:10 |
| InteriorLights:Electricity:Zone:PERIMETER_TOP_ZN_4 ZN | 6.22 | 23.83 | 01-JAN-10:10 | 899.10 | 29-MAR-07:10 |
| InteriorEquipment:Electricity | 763.69 | 9281.18 | 01-JAN-00:10 | 56743.84 | 02-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:CORE_BOTTOM ZN | 287.63 | 1832.20 | 01-JAN-00:10 | 29054.04 | 02-JAN-08:10 |
| General:InteriorEquipment:Electricity | 763.69 | 9281.18 | 01-JAN-00:10 | 56743.84 | 02-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:CORE_MID ZN | 117.09 | 1832.20 | 01-JAN-00:10 | 6810.78 | 02-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:CORE_TOP ZN | 117.09 | 1832.20 | 01-JAN-00:10 | 6810.78 | 02-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:PERIMETER_BOT_ZN_1 ZN | 24.68 | 386.24 | 01-JAN-00:10 | 1435.77 | 02-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:PERIMETER_BOT_ZN_2 ZN | 15.63 | 244.52 | 01-JAN-00:10 | 908.96 | 02-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:PERIMETER_BOT_ZN_3 ZN | 24.68 | 386.24 | 01-JAN-00:10 | 1435.77 | 02-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:PERIMETER_BOT_ZN_4 ZN | 15.63 | 244.51 | 01-JAN-00:10 | 908.90 | 02-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:PERIMETER_MID_ZN_1 ZN | 24.68 | 386.24 | 01-JAN-00:10 | 1435.77 | 02-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:PERIMETER_MID_ZN_2 ZN | 15.63 | 244.52 | 01-JAN-00:10 | 908.96 | 02-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:PERIMETER_MID_ZN_3 ZN | 24.68 | 386.24 | 01-JAN-00:10 | 1435.77 | 02-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:PERIMETER_MID_ZN_4 ZN | 15.63 | 244.51 | 01-JAN-00:10 | 908.90 | 02-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:PERIMETER_TOP_ZN_1 ZN | 24.68 | 386.24 | 01-JAN-00:10 | 1435.77 | 02-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:PERIMETER_TOP_ZN_2 ZN | 15.63 | 244.52 | 01-JAN-00:10 | 908.96 | 02-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:PERIMETER_TOP_ZN_3 ZN | 24.68 | 386.24 | 01-JAN-00:10 | 1435.77 | 02-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:PERIMETER_TOP_ZN_4 ZN | 15.63 | 244.51 | 01-JAN-00:10 | 908.90 | 02-JAN-08:10 |
| ElectricityPurchased:Facility | 1758.63 | 11011.01 | 25-JUN-17:10 | 172594.12 | 02-AUG-16:00 |
| ElectricityPurchased:Plant | 1758.63 | 11011.01 | 25-JUN-17:10 | 172594.12 | 02-AUG-16:00 |
| Cogeneration:ElectricityPurchased | 1758.63 | 11011.01 | 25-JUN-17:10 | 172594.12 | 02-AUG-16:00 |
| ElectricitySurplusSold:Facility | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| ElectricitySurplusSold:Plant | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| Cogeneration:ElectricitySurplusSold | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| ElectricityNet:Facility | 1758.63 | 11011.01 | 25-JUN-17:10 | 172594.12 | 02-AUG-16:00 |
| ElectricityNet:Plant | 1758.63 | 11011.01 | 25-JUN-17:10 | 172594.12 | 02-AUG-16:00 |
| Cogeneration:ElectricityNet | 1758.63 | 11011.01 | 25-JUN-17:10 | 172594.12 | 02-AUG-16:00 |
| Electricity:HVAC | 72.24 | 0.00 | 01-JAN-00:10 | 16355.74 | 28-AUG-15:40 |
| Fans:Electricity | 60.10 | 0.00 | 01-JAN-00:10 | 14762.17 | 28-AUG-15:40 |
| General:Fans:Electricity | 60.10 | 0.00 | 01-JAN-00:10 | 14762.17 | 28-AUG-15:40 |
| ExteriorLights:Electricity | 104.80 | 0.00 | 01-JAN-07:30 | 8099.48 | 01-JAN-06:10 |
| General:ExteriorLights:Electricity | 104.80 | 0.00 | 01-JAN-07:30 | 8099.48 | 01-JAN-06:10 |
| HeatRecovery:Electricity | 12.14 | 0.00 | 01-JAN-00:10 | 1593.56 | 02-JAN-08:10 |
| Electricity:Plant | 481.95 | 0.00 | 01-JAN-00:10 | 80123.27 | 02-AUG-16:00 |
| Cooling:Electricity | 413.75 | 0.00 | 01-JAN-00:10 | 75728.07 | 02-AUG-16:00 |
| General:Cooling:Electricity | 413.75 | 0.00 | 01-JAN-00:10 | 75728.07 | 02-AUG-16:00 |
| Heating:Electricity | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| Boiler Parasitic:Heating:Electricity | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| Pumps:Electricity | 68.19 | 0.00 | 01-JAN-00:10 | 4871.78 | 23-JAN-07:40 |
| General:Pumps:Electricity | 68.19 | 0.00 | 01-JAN-00:10 | 4871.78 | 23-JAN-07:40 |
| Gas Annual Value [GJ] | Gas Minimum Value [W] | Timestamp of Minimum {TIMESTAMP} | Gas Maximum Value [W] | Timestamp of Maximum {TIMESTAMP} | |
| Gas:Facility | 105.71 | 1276.95 | 01-JAN-00:10 | 170761.81 | 23-JAN-07:10 |
| Gas:Plant | 105.71 | 1276.95 | 01-JAN-00:10 | 170761.81 | 23-JAN-07:10 |
| WaterSystems:Gas | 79.12 | 1276.95 | 01-JAN-00:10 | 8609.32 | 25-JAN-12:10 |
| General:WaterSystems:Gas | 79.12 | 1276.95 | 01-JAN-00:10 | 8609.32 | 25-JAN-12:10 |
| Heating:Gas | 26.59 | 0.00 | 01-JAN-00:10 | 169484.86 | 23-JAN-07:10 |
| General:Heating:Gas | 26.59 | 0.00 | 01-JAN-00:10 | 169484.86 | 23-JAN-07:10 |
| Cooling Annual Value [GJ] | Cooling Minimum Value [W] | Timestamp of Minimum {TIMESTAMP} | Cooling Maximum Value [W] | Timestamp of Maximum {TIMESTAMP} | |
| PlantLoopCoolingDemand:Facility | 1295.97 | 0.00 | 01-JAN-00:10 | 221643.04 | 28-AUG-15:20 |
| PlantLoopCoolingDemand:HVAC | 1295.97 | 0.00 | 01-JAN-00:10 | 221643.04 | 28-AUG-15:20 |
| CoolingCoils:PlantLoopCoolingDemand | 1295.97 | 0.00 | 01-JAN-00:10 | 221643.04 | 28-AUG-15:20 |
| Annual Value [m3] | Minimum Value [m3/s] | Timestamp of Minimum {TIMESTAMP} | Maximum Value [m3/s] | Timestamp of Maximum {TIMESTAMP} | |
| Water:Facility | 278.19 | 0.00 | 01-JAN-00:10 | 0.00 | 02-JAN-12:10 |
| Water:Plant | 278.19 | 0.00 | 01-JAN-00:10 | 0.00 | 02-JAN-12:10 |
| WaterSystems:Water | 278.19 | 0.00 | 01-JAN-00:10 | 0.00 | 02-JAN-12:10 |
| General:WaterSystems:Water | 278.19 | 0.00 | 01-JAN-00:10 | 0.00 | 02-JAN-12:10 |
| MainsWater:Facility | 278.19 | 0.00 | 01-JAN-00:10 | 0.00 | 02-JAN-12:10 |
| MainsWater:Plant | 278.19 | 0.00 | 01-JAN-00:10 | 0.00 | 02-JAN-12:10 |
| WaterSystems:MainsWater | 278.19 | 0.00 | 01-JAN-00:10 | 0.00 | 02-JAN-12:10 |
| General:WaterSystems:MainsWater | 278.19 | 0.00 | 01-JAN-00:10 | 0.00 | 02-JAN-12:10 |
| Annual Value [kg] | Minimum Value [kg/s] | Timestamp of Minimum {TIMESTAMP} | Maximum Value [kg/s] | Timestamp of Maximum {TIMESTAMP} | |
| Carbon Equivalent:Facility | 0.00 | 0.000 | 01-JAN-00:10 | 0.000 | 01-JAN-00:10 |
| CarbonEquivalentEmissions:Carbon Equivalent | 0.00 | 0.000 | 01-JAN-00:10 | 0.000 | 01-JAN-00:10 |
| Annual Value [m3] | Minimum Value [m3/s] | Timestamp of Minimum {TIMESTAMP} | Maximum Value [m3/s] | Timestamp of Maximum {TIMESTAMP} | |
| None |
| Annual Value [L] | Minimum Value [L] | Timestamp of Minimum {TIMESTAMP} | Maximum Value [L] | Timestamp of Maximum {TIMESTAMP} | |
| None |
| Annual Value [GJ] | Minimum Value [W] | Timestamp of Minimum {TIMESTAMP} | Maximum Value [W] | Timestamp of Maximum {TIMESTAMP} | |
| PlantLoopHeatingDemand:Facility | 45.83 | 0.00 | 01-JAN-00:10 | 174819.94 | 23-JAN-07:10 |
| PlantLoopHeatingDemand:Plant | 22.83 | 0.00 | 01-JAN-00:10 | 3244.93 | 25-JAN-12:40 |
| WaterSystems:PlantLoopHeatingDemand | 22.83 | 0.00 | 01-JAN-00:10 | 3244.93 | 25-JAN-12:40 |
| General:WaterSystems:PlantLoopHeatingDemand | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| EnergyTransfer:Facility | 6049.77 | 0.00 | 01-JAN-00:10 | 968041.41 | 29-AUG-15:10 |
| EnergyTransfer:Building | 1158.98 | 0.00 | 01-JAN-00:10 | 165126.84 | 28-AUG-15:40 |
| EnergyTransfer:Zone:CORE_BOTTOM ZN | 223.23 | 0.00 | 01-JAN-00:10 | 29322.55 | 02-AUG-08:00 |
| Heating:EnergyTransfer | 13.49 | 0.00 | 01-JAN-00:10 | 90857.31 | 23-JAN-07:20 |
| Heating:EnergyTransfer:Zone:CORE_BOTTOM ZN | 0.00 | 0.00 | 01-JAN-00:10 | 1229.32 | 02-JAN-07:10 |
| Cooling:EnergyTransfer | 1145.48 | 0.00 | 01-JAN-00:10 | 165126.84 | 28-AUG-15:40 |
| Cooling:EnergyTransfer:Zone:CORE_BOTTOM ZN | 223.22 | 0.00 | 01-JAN-00:10 | 29322.55 | 02-AUG-08:00 |
| EnergyTransfer:Zone:CORE_MID ZN | 173.64 | 0.00 | 01-JAN-00:10 | 21214.17 | 28-AUG-08:00 |
| Heating:EnergyTransfer:Zone:CORE_MID ZN | 0.02 | 0.00 | 01-JAN-00:10 | 6087.56 | 02-JAN-07:10 |
| Cooling:EnergyTransfer:Zone:CORE_MID ZN | 173.62 | 0.00 | 01-JAN-00:10 | 21214.17 | 28-AUG-08:00 |
| EnergyTransfer:Zone:CORE_TOP ZN | 191.98 | 0.00 | 01-JAN-00:10 | 26506.17 | 28-AUG-15:00 |
| Heating:EnergyTransfer:Zone:CORE_TOP ZN | 0.35 | 0.00 | 01-JAN-00:10 | 17533.52 | 23-JAN-06:10 |
| Cooling:EnergyTransfer:Zone:CORE_TOP ZN | 191.64 | 0.00 | 01-JAN-00:10 | 26506.17 | 28-AUG-15:00 |
| EnergyTransfer:Zone:FIRSTFLOOR_PLENUM ZN | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| Heating:EnergyTransfer:Zone:FIRSTFLOOR_PLENUM ZN | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| Cooling:EnergyTransfer:Zone:FIRSTFLOOR_PLENUM ZN | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| EnergyTransfer:Zone:MIDFLOOR_PLENUM ZN | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| Heating:EnergyTransfer:Zone:MIDFLOOR_PLENUM ZN | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| Cooling:EnergyTransfer:Zone:MIDFLOOR_PLENUM ZN | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| EnergyTransfer:Zone:PERIMETER_BOT_ZN_1 ZN | 58.22 | 0.00 | 01-JAN-00:10 | 11575.82 | 02-AUG-16:30 |
| Heating:EnergyTransfer:Zone:PERIMETER_BOT_ZN_1 ZN | 6.40 | 0.00 | 01-JAN-00:10 | 9456.45 | 23-JAN-07:40 |
| Cooling:EnergyTransfer:Zone:PERIMETER_BOT_ZN_1 ZN | 51.83 | 0.00 | 01-JAN-00:10 | 11575.82 | 02-AUG-16:30 |
| EnergyTransfer:Zone:PERIMETER_BOT_ZN_2 ZN | 33.80 | 0.00 | 01-JAN-00:10 | 8248.68 | 31-JUL-09:00 |
| Heating:EnergyTransfer:Zone:PERIMETER_BOT_ZN_2 ZN | 0.34 | 0.00 | 01-JAN-00:10 | 3746.39 | 11-FEB-07:10 |
| Cooling:EnergyTransfer:Zone:PERIMETER_BOT_ZN_2 ZN | 33.46 | 0.00 | 01-JAN-00:10 | 8248.68 | 31-JUL-09:00 |
| EnergyTransfer:Zone:PERIMETER_BOT_ZN_3 ZN | 33.64 | 0.00 | 01-JAN-00:10 | 6892.14 | 20-JUL-13:30 |
| Heating:EnergyTransfer:Zone:PERIMETER_BOT_ZN_3 ZN | 0.63 | 0.00 | 01-JAN-00:10 | 5322.56 | 23-JAN-07:20 |
| Cooling:EnergyTransfer:Zone:PERIMETER_BOT_ZN_3 ZN | 33.01 | 0.00 | 01-JAN-00:10 | 6892.14 | 20-JUL-13:30 |
| EnergyTransfer:Zone:PERIMETER_BOT_ZN_4 ZN | 33.97 | 0.00 | 01-JAN-00:10 | 9015.10 | 01-AUG-16:00 |
| Heating:EnergyTransfer:Zone:PERIMETER_BOT_ZN_4 ZN | 0.43 | 0.00 | 01-JAN-00:10 | 3734.44 | 11-FEB-07:10 |
| Cooling:EnergyTransfer:Zone:PERIMETER_BOT_ZN_4 ZN | 33.54 | 0.00 | 01-JAN-00:10 | 9015.10 | 01-AUG-16:00 |
| EnergyTransfer:Zone:PERIMETER_MID_ZN_1 ZN | 64.43 | 0.00 | 01-JAN-00:10 | 10591.81 | 28-OCT-13:50 |
| Heating:EnergyTransfer:Zone:PERIMETER_MID_ZN_1 ZN | 0.28 | 0.00 | 01-JAN-00:10 | 5658.02 | 23-JAN-07:20 |
| Cooling:EnergyTransfer:Zone:PERIMETER_MID_ZN_1 ZN | 64.15 | 0.00 | 01-JAN-00:10 | 10591.81 | 28-OCT-13:50 |
| EnergyTransfer:Zone:PERIMETER_MID_ZN_2 ZN | 42.71 | 0.00 | 01-JAN-00:10 | 9244.43 | 31-JUL-09:00 |
| Heating:EnergyTransfer:Zone:PERIMETER_MID_ZN_2 ZN | 0.27 | 0.00 | 01-JAN-00:10 | 4309.40 | 23-JAN-07:20 |
| Cooling:EnergyTransfer:Zone:PERIMETER_MID_ZN_2 ZN | 42.44 | 0.00 | 01-JAN-00:10 | 9244.43 | 31-JUL-09:00 |
| EnergyTransfer:Zone:PERIMETER_MID_ZN_3 ZN | 46.77 | 0.00 | 01-JAN-00:10 | 7900.04 | 20-JUL-13:30 |
| Heating:EnergyTransfer:Zone:PERIMETER_MID_ZN_3 ZN | 0.51 | 0.00 | 01-JAN-00:10 | 6437.76 | 23-JAN-07:20 |
| Cooling:EnergyTransfer:Zone:PERIMETER_MID_ZN_3 ZN | 46.26 | 0.00 | 01-JAN-00:10 | 7900.04 | 20-JUL-13:30 |
| EnergyTransfer:Zone:PERIMETER_MID_ZN_4 ZN | 42.55 | 0.00 | 01-JAN-00:10 | 9672.61 | 01-AUG-16:00 |
| Heating:EnergyTransfer:Zone:PERIMETER_MID_ZN_4 ZN | 0.33 | 0.00 | 01-JAN-00:10 | 4257.10 | 23-JAN-07:20 |
| Cooling:EnergyTransfer:Zone:PERIMETER_MID_ZN_4 ZN | 42.21 | 0.00 | 01-JAN-00:10 | 9672.61 | 01-AUG-16:00 |
| EnergyTransfer:Zone:PERIMETER_TOP_ZN_1 ZN | 69.39 | 0.00 | 01-JAN-00:10 | 11586.19 | 28-OCT-13:50 |
| Heating:EnergyTransfer:Zone:PERIMETER_TOP_ZN_1 ZN | 0.87 | 0.00 | 01-JAN-00:10 | 8388.97 | 23-JAN-07:20 |
| Cooling:EnergyTransfer:Zone:PERIMETER_TOP_ZN_1 ZN | 68.51 | 0.00 | 01-JAN-00:10 | 11586.19 | 28-OCT-13:50 |
| EnergyTransfer:Zone:PERIMETER_TOP_ZN_2 ZN | 45.70 | 0.00 | 01-JAN-00:10 | 9527.36 | 31-JUL-09:00 |
| Heating:EnergyTransfer:Zone:PERIMETER_TOP_ZN_2 ZN | 0.72 | 0.00 | 01-JAN-00:10 | 6351.62 | 23-JAN-07:20 |
| Cooling:EnergyTransfer:Zone:PERIMETER_TOP_ZN_2 ZN | 44.98 | 0.00 | 01-JAN-00:10 | 9527.36 | 31-JUL-09:00 |
| EnergyTransfer:Zone:PERIMETER_TOP_ZN_3 ZN | 52.76 | 0.00 | 01-JAN-00:10 | 8987.26 | 31-JUL-14:30 |
| Heating:EnergyTransfer:Zone:PERIMETER_TOP_ZN_3 ZN | 1.44 | 0.00 | 01-JAN-00:10 | 8956.46 | 13-FEB-06:10 |
| Cooling:EnergyTransfer:Zone:PERIMETER_TOP_ZN_3 ZN | 51.31 | 0.00 | 01-JAN-00:10 | 8987.26 | 31-JUL-14:30 |
| EnergyTransfer:Zone:PERIMETER_TOP_ZN_4 ZN | 46.20 | 0.00 | 01-JAN-00:10 | 10525.98 | 01-AUG-16:00 |
| Heating:EnergyTransfer:Zone:PERIMETER_TOP_ZN_4 ZN | 0.92 | 0.00 | 01-JAN-00:10 | 6337.84 | 23-JAN-07:20 |
| Cooling:EnergyTransfer:Zone:PERIMETER_TOP_ZN_4 ZN | 45.28 | 0.00 | 01-JAN-00:10 | 10525.98 | 01-AUG-16:00 |
| EnergyTransfer:Zone:TOPFLOOR_PLENUM ZN | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| Heating:EnergyTransfer:Zone:TOPFLOOR_PLENUM ZN | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| Cooling:EnergyTransfer:Zone:TOPFLOOR_PLENUM ZN | 0.00 | 0.00 | 01-JAN-00:10 | 0.00 | 01-JAN-00:10 |
| EnergyTransfer:Plant | 3322.34 | 0.00 | 01-JAN-00:10 | 522076.58 | 29-AUG-15:10 |
| WaterSystems:EnergyTransfer | 22.83 | 0.00 | 01-JAN-00:10 | 3244.93 | 25-JAN-12:40 |
| General:WaterSystems:EnergyTransfer | 22.83 | 0.00 | 01-JAN-00:10 | 3244.93 | 25-JAN-12:40 |
| EnergyTransfer:HVAC | 1568.45 | 0.00 | 01-JAN-00:10 | 285901.15 | 04-AUG-16:00 |
| HeatingCoils:EnergyTransfer | 22.99 | 0.00 | 01-JAN-00:10 | 173738.51 | 23-JAN-07:10 |
| PlantLoopHeatingDemand:HVAC | 22.99 | 0.00 | 01-JAN-00:10 | 173738.51 | 23-JAN-07:10 |
| HeatingCoils:PlantLoopHeatingDemand | 22.99 | 0.00 | 01-JAN-00:10 | 173738.51 | 23-JAN-07:10 |
| CoolingCoils:EnergyTransfer | 1295.97 | 0.00 | 01-JAN-00:10 | 221643.04 | 28-AUG-15:20 |
| HeatRecoveryForHeating:EnergyTransfer | 26.50 | 0.00 | 01-JAN-00:10 | 54179.93 | 25-DEC-08:50 |
| HeatRecoveryForCooling:EnergyTransfer | 222.99 | 0.00 | 01-JAN-00:10 | 69389.97 | 31-JUL-11:00 |
| Chillers:EnergyTransfer | 1354.87 | 0.00 | 01-JAN-00:10 | 225289.80 | 28-AUG-15:20 |
| HeatRejection:EnergyTransfer | 1921.79 | 0.00 | 01-JAN-00:10 | 296390.99 | 29-AUG-15:10 |
| Boilers:EnergyTransfer | 22.85 | 0.00 | 01-JAN-00:10 | 171322.33 | 23-JAN-07:10 |
Report: Sensible Heat Gain Summary
For: Entire Facility
Timestamp: 2019-04-09 23:11:28
Annual Building Sensible Heat Gain Components| HVAC Zone Eq & Other Sensible Air Heating [GJ] | HVAC Zone Eq & Other Sensible Air Cooling [GJ] | HVAC Terminal Unit Sensible Air Heating [GJ] | HVAC Terminal Unit Sensible Air Cooling [GJ] | HVAC Input Heated Surface Heating [GJ] | HVAC Input Cooled Surface Cooling [GJ] | People Sensible Heat Addition [GJ] | Lights Sensible Heat Addition [GJ] | Equipment Sensible Heat Addition [GJ] | Window Heat Addition [GJ] | Interzone Air Transfer Heat Addition [GJ] | Infiltration Heat Addition [GJ] | Opaque Surface Conduction and Other Heat Addition [GJ] | Equipment Sensible Heat Removal [GJ] | Window Heat Removal [GJ] | Interzone Air Transfer Heat Removal [GJ] | Infiltration Heat Removal [GJ] | Opaque Surface Conduction and Other Heat Removal [GJ] | |
| CORE_BOTTOM ZN | 0.000 | 0.000 | 0.002 | -223.223 | 0.000 | 0.000 | 30.477 | 79.861 | 287.635 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | -174.751 |
| CORE_MID ZN | 0.000 | 0.000 | 0.018 | -173.623 | 0.000 | 0.000 | 30.542 | 79.861 | 117.094 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | -53.892 |
| CORE_TOP ZN | 0.000 | 0.000 | 0.347 | -191.636 | 0.000 | 0.000 | 30.712 | 79.861 | 117.094 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | -36.378 |
| PERIMETER_BOT_ZN_1 ZN | 0.000 | 0.000 | 6.397 | -51.823 | 0.000 | 0.000 | 6.599 | 9.738 | 24.685 | 59.899 | 0.000 | 9.855 | 0.001 | 0.000 | -21.111 | 0.000 | -18.454 | -25.785 |
| PERIMETER_BOT_ZN_2 ZN | 0.000 | 0.000 | 0.336 | -33.463 | 0.000 | 0.000 | 4.160 | 6.247 | 15.627 | 36.054 | 0.000 | 0.199 | 0.001 | 0.000 | -14.009 | 0.000 | -0.881 | -14.270 |
| PERIMETER_BOT_ZN_3 ZN | 0.000 | 0.000 | 0.627 | -33.009 | 0.000 | 0.000 | 6.593 | 9.969 | 24.685 | 28.465 | 0.000 | 0.300 | 0.001 | 0.000 | -22.756 | 0.000 | -1.305 | -13.569 |
| PERIMETER_BOT_ZN_4 ZN | 0.000 | 0.000 | 0.427 | -33.544 | 0.000 | 0.000 | 4.206 | 6.238 | 15.626 | 37.559 | 0.000 | 0.193 | 0.001 | 0.000 | -14.940 | 0.000 | -0.886 | -14.879 |
| PERIMETER_MID_ZN_1 ZN | 0.000 | 0.000 | 0.278 | -64.147 | 0.000 | 0.000 | 6.474 | 9.721 | 24.685 | 57.341 | 0.000 | 0.395 | 0.003 | 0.000 | -24.566 | 0.000 | -2.443 | -7.739 |
| PERIMETER_MID_ZN_2 ZN | 0.000 | 0.000 | 0.267 | -42.437 | 0.000 | 0.000 | 4.139 | 6.226 | 15.627 | 34.455 | 0.000 | 0.272 | 0.002 | 0.000 | -16.026 | 0.000 | -1.551 | -0.972 |
| PERIMETER_MID_ZN_3 ZN | 0.000 | 0.000 | 0.510 | -46.259 | 0.000 | 0.000 | 6.554 | 9.924 | 24.685 | 26.623 | 0.000 | 0.405 | 5.912 | 0.000 | -26.050 | 0.000 | -2.304 | 0.000 |
| PERIMETER_MID_ZN_4 ZN | 0.000 | 0.000 | 0.333 | -42.213 | 0.000 | 0.000 | 4.167 | 6.215 | 15.626 | 36.025 | 0.000 | 0.267 | 0.000 | 0.000 | -17.024 | 0.000 | -1.564 | -1.834 |
| PERIMETER_TOP_ZN_1 ZN | 0.000 | 0.000 | 0.873 | -68.511 | 0.000 | 0.000 | 6.509 | 9.721 | 24.685 | 56.703 | 0.000 | 0.463 | 0.001 | 0.000 | -23.964 | 0.000 | -2.843 | -3.636 |
| PERIMETER_TOP_ZN_2 ZN | 0.000 | 0.000 | 0.721 | -44.982 | 0.000 | 0.000 | 4.161 | 6.226 | 15.627 | 34.055 | 0.000 | 0.314 | 1.343 | 0.000 | -15.662 | 0.000 | -1.805 | -0.000 |
| PERIMETER_TOP_ZN_3 ZN | 0.000 | 0.000 | 1.441 | -51.313 | 0.000 | 0.000 | 6.600 | 9.924 | 24.685 | 26.092 | 0.000 | 0.471 | 10.072 | 0.000 | -25.298 | 0.000 | -2.674 | -0.000 |
| PERIMETER_TOP_ZN_4 ZN | 0.000 | 0.000 | 0.916 | -45.283 | 0.000 | 0.000 | 4.193 | 6.215 | 15.626 | 35.578 | 0.000 | 0.312 | 0.811 | 0.000 | -16.553 | 0.000 | -1.816 | -0.000 |
| FIRSTFLOOR_PLENUM ZN | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.469 | 2.643 | 0.000 | 0.000 | 0.000 | -3.112 | -0.000 |
| MIDFLOOR_PLENUM ZN | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.512 | 3.691 | 0.000 | 0.000 | 0.000 | -4.203 | -0.000 |
| TOPFLOOR_PLENUM ZN | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.273 | 4.059 | 0.000 | 0.000 | 0.000 | -4.333 | -0.000 |
| Total Facility | 0.000 | 0.000 | 13.494 | -1145.466 | 0.000 | 0.000 | 156.087 | 335.948 | 763.692 | 468.850 | 0.000 | 14.700 | 28.542 | 0.000 | -237.959 | 0.000 | -50.173 | -347.706 |
| Time of Peak {TIMESTAMP} | HVAC Zone Eq & Other Sensible Air Heating [W] | HVAC Zone Eq & Other Sensible Air Cooling [W] | HVAC Terminal Unit Sensible Air Heating [W] | HVAC Terminal Unit Sensible Air Cooling [W] | HVAC Input Heated Surface Heating [W] | HVAC Input Cooled Surface Cooling [W] | People Sensible Heat Addition [W] | Lights Sensible Heat Addition [W] | Equipment Sensible Heat Addition [W] | Window Heat Addition [W] | Interzone Air Transfer Heat Addition [W] | Infiltration Heat Addition [W] | Opaque Surface Conduction and Other Heat Addition [W] | Equipment Sensible Heat Removal [W] | Window Heat Removal [W] | Interzone Air Transfer Heat Removal [W] | Infiltration Heat Removal [W] | Opaque Surface Conduction and Other Heat Removal [W] | |
| CORE_BOTTOM ZN | 11-JAN-08:14 | 0.00 | 0.00 | 0.00 | -59253.85 | 0.00 | 0.00 | 3606.35 | 6737.34 | 29054.04 | 0.00 | 0.00 | 0.00 | 19856.12 | 0.00 | -0.00 | 0.00 | 0.00 | 0.00 |
| CORE_MID ZN | 28-AUG-05:04 | 0.00 | 0.00 | 0.00 | -35315.65 | 0.00 | 0.00 | 0.00 | 748.59 | 3027.01 | 0.00 | 0.00 | 0.00 | 31540.04 | 0.00 | -0.00 | 0.00 | 0.00 | 0.00 |
| CORE_TOP ZN | 28-AUG-05:04 | 0.00 | 0.00 | 0.00 | -37150.34 | 0.00 | 0.00 | 0.00 | 748.59 | 3027.01 | 0.00 | 0.00 | 0.00 | 33374.73 | 0.00 | -0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_BOT_ZN_1 ZN | 02-AUG-16:30 | 0.00 | 0.00 | 0.00 | -11579.69 | 0.00 | 0.00 | 150.11 | 376.38 | 797.65 | 3589.56 | 0.00 | 12204.17 | 0.00 | 0.00 | -0.00 | 0.00 | 0.00 | -5538.18 |
| PERIMETER_BOT_ZN_2 ZN | 27-AUG-09:12 | 0.00 | 0.00 | 0.00 | -12022.20 | 0.00 | 0.00 | 0.00 | 23.83 | 305.30 | 8747.98 | 0.00 | 8.11 | 2936.98 | 0.00 | -0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_BOT_ZN_3 ZN | 13-AUG-12:42 | 0.00 | 0.00 | 0.00 | -8725.63 | 0.00 | 0.00 | 0.00 | 37.64 | 482.24 | 4458.38 | 0.00 | 231.69 | 3515.69 | 0.00 | -0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_BOT_ZN_4 ZN | 26-AUG-16:22 | 0.00 | 0.00 | 0.00 | -12913.75 | 0.00 | 0.00 | 0.00 | 23.83 | 302.97 | 9480.50 | 0.00 | 19.99 | 3086.47 | 0.00 | -0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_MID_ZN_1 ZN | 29-OCT-12:42 | 0.00 | 0.00 | 0.00 | -13264.48 | 0.00 | 0.00 | 0.00 | 37.64 | 482.24 | 12648.71 | 0.00 | 21.93 | 73.97 | 0.00 | -0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_MID_ZN_2 ZN | 27-AUG-09:12 | 0.00 | 0.00 | 0.00 | -13369.01 | 0.00 | 0.00 | 0.00 | 23.83 | 305.30 | 8615.11 | 0.00 | 10.36 | 4414.41 | 0.00 | -0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_MID_ZN_3 ZN | 13-AUG-13:22 | 0.00 | 0.00 | 0.00 | -10537.00 | 0.00 | 0.00 | 0.00 | 37.64 | 482.24 | 3975.68 | 0.00 | 353.11 | 5688.33 | 0.00 | -0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_MID_ZN_4 ZN | 27-AUG-16:32 | 0.00 | 0.00 | 0.00 | -14251.80 | 0.00 | 0.00 | 0.00 | 23.83 | 305.28 | 8641.74 | 0.00 | 43.84 | 5237.11 | 0.00 | -0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_TOP_ZN_1 ZN | 29-OCT-13:22 | 0.00 | 0.00 | 0.00 | -14743.61 | 0.00 | 0.00 | 0.00 | 37.64 | 482.24 | 11764.90 | 0.00 | 31.81 | 2427.01 | 0.00 | -0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_TOP_ZN_2 ZN | 27-AUG-09:12 | 0.00 | 0.00 | 0.00 | -13602.08 | 0.00 | 0.00 | 0.00 | 23.83 | 305.30 | 8560.94 | 0.00 | 11.12 | 4700.90 | 0.00 | -0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_TOP_ZN_3 ZN | 13-AUG-13:22 | 0.00 | 0.00 | 0.00 | -12250.06 | 0.00 | 0.00 | 0.00 | 37.64 | 482.24 | 3806.68 | 0.00 | 399.66 | 7523.84 | 0.00 | -0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_TOP_ZN_4 ZN | 27-AUG-16:32 | 0.00 | 0.00 | 0.00 | -15473.74 | 0.00 | 0.00 | 0.00 | 23.83 | 305.28 | 8514.07 | 0.00 | 49.46 | 6581.10 | 0.00 | -0.00 | 0.00 | 0.00 | 0.00 |
| FIRSTFLOOR_PLENUM ZN | - | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| MIDFLOOR_PLENUM ZN | - | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| TOPFLOOR_PLENUM ZN | - | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total Facility | 02-AUG-17:42 | 0.00 | 0.00 | 0.00 | -210761.57 | 0.00 | 0.00 | 0.00 | 9057.92 | 19201.98 | 47911.67 | 0.00 | 2740.03 | 131849.97 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Time of Peak {TIMESTAMP} | HVAC Zone Eq & Other Sensible Air Heating [W] | HVAC Zone Eq & Other Sensible Air Cooling [W] | HVAC Terminal Unit Sensible Air Heating [W] | HVAC Terminal Unit Sensible Air Cooling [W] | HVAC Input Heated Surface Heating [W] | HVAC Input Cooled Surface Cooling [W] | People Sensible Heat Addition [W] | Lights Sensible Heat Addition [W] | Equipment Sensible Heat Addition [W] | Window Heat Addition [W] | Interzone Air Transfer Heat Addition [W] | Infiltration Heat Addition [W] | Opaque Surface Conduction and Other Heat Addition [W] | Equipment Sensible Heat Removal [W] | Window Heat Removal [W] | Interzone Air Transfer Heat Removal [W] | Infiltration Heat Removal [W] | Opaque Surface Conduction and Other Heat Removal [W] | |
| CORE_BOTTOM ZN | 02-JAN-07:02 | 0.00 | 0.00 | 6146.60 | -0.00 | 0.00 | 0.00 | 890.17 | 2245.78 | 14309.83 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | 0.00 | 0.00 | -23592.37 |
| CORE_MID ZN | 02-JAN-07:02 | 0.00 | 0.00 | 15578.80 | -0.00 | 0.00 | 0.00 | 912.22 | 2245.78 | 3027.01 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | 0.00 | 0.00 | -21763.80 |
| CORE_TOP ZN | 23-JAN-06:02 | 0.00 | 0.00 | 26542.64 | -0.00 | 0.00 | 0.00 | 0.00 | 748.59 | 3027.01 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | 0.00 | 0.00 | -30318.25 |
| PERIMETER_BOT_ZN_1 ZN | 11-JAN-07:12 | 0.00 | 0.00 | 9674.58 | -0.00 | 0.00 | 0.00 | 245.10 | 473.43 | 638.12 | 0.00 | 0.00 | 0.00 | 11152.14 | 0.00 | -3376.10 | 0.00 | -18807.28 | 0.00 |
| PERIMETER_BOT_ZN_2 ZN | 13-FEB-06:02 | 0.00 | 0.00 | 6212.64 | -0.00 | 0.00 | 0.00 | 0.00 | 99.91 | 403.98 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -1917.83 | 0.00 | -56.19 | -4742.51 |
| PERIMETER_BOT_ZN_3 ZN | 23-JAN-05:02 | 0.00 | 0.00 | 6879.10 | -0.00 | 0.00 | 0.00 | 0.00 | 183.01 | 514.99 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -3847.23 | 0.00 | -191.36 | -3538.51 |
| PERIMETER_BOT_ZN_4 ZN | 06-MAR-07:02 | 0.00 | 0.00 | 6663.23 | -0.00 | 0.00 | 0.00 | 122.35 | 261.39 | 403.96 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -1446.43 | 0.00 | -30.41 | -5974.09 |
| PERIMETER_MID_ZN_1 ZN | 13-FEB-06:02 | 0.00 | 0.00 | 8788.84 | -0.00 | 0.00 | 0.00 | 0.00 | 157.81 | 638.12 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -2799.70 | 0.00 | -130.83 | -6654.24 |
| PERIMETER_MID_ZN_2 ZN | 23-JAN-05:02 | 0.00 | 0.00 | 7694.61 | -0.00 | 0.00 | 0.00 | 0.00 | 115.86 | 326.03 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -2504.03 | 0.00 | -197.07 | -5435.40 |
| PERIMETER_MID_ZN_3 ZN | 23-JAN-05:02 | 0.00 | 0.00 | 8316.12 | -0.00 | 0.00 | 0.00 | 0.00 | 183.01 | 514.99 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -3758.83 | 0.00 | -291.65 | -4963.63 |
| PERIMETER_MID_ZN_4 ZN | 23-JAN-05:02 | 0.00 | 0.00 | 7798.24 | -0.00 | 0.00 | 0.00 | 0.00 | 115.85 | 326.01 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -2461.24 | 0.00 | -198.73 | -5580.13 |
| PERIMETER_TOP_ZN_1 ZN | 23-JAN-05:02 | 0.00 | 0.00 | 10599.34 | -0.00 | 0.00 | 0.00 | 0.00 | 183.01 | 514.99 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -3493.87 | 0.00 | -338.79 | -7464.68 |
| PERIMETER_TOP_ZN_2 ZN | 13-FEB-06:02 | 0.00 | 0.00 | 9021.74 | -0.00 | 0.00 | 0.00 | 0.00 | 99.91 | 403.98 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -1647.69 | 0.00 | -92.28 | -7785.66 |
| PERIMETER_TOP_ZN_3 ZN | 23-JAN-05:02 | 0.00 | 0.00 | 9828.55 | -0.00 | 0.00 | 0.00 | 0.00 | 183.01 | 514.99 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -3480.90 | 0.00 | -331.80 | -6713.85 |
| PERIMETER_TOP_ZN_4 ZN | 23-JAN-05:02 | 0.00 | 0.00 | 9443.94 | -0.00 | 0.00 | 0.00 | 0.00 | 115.85 | 326.01 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -2280.33 | 0.00 | -227.09 | -7378.38 |
| FIRSTFLOOR_PLENUM ZN | - | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| MIDFLOOR_PLENUM ZN | - | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| TOPFLOOR_PLENUM ZN | - | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total Facility | 23-JAN-07:02 | 0.00 | 0.00 | 135429.98 | 0.00 | 0.00 | 0.00 | 4800.69 | 11376.18 | 26616.40 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -37476.87 | 0.00 | -25267.85 | -115478.53 |
Report: Standard 62.1 Summary
For: Entire Facility
Timestamp: 2019-04-09 23:11:28
System Ventilation Requirements for Cooling| Sum of Zone Primary Air Flow - Vpz-sum [m3/s] | System Population - Ps | Sum of Zone Population - Pz-sum | Occupant Diversity - D | Uncorrected Outdoor Air Intake Airflow - Vou [m3/s] | System Primary Airflow - Vps [m3/s] | Average Outdoor Air Fraction - Xs | System Ventilation Efficiency - Ev | Outdoor Air Intake Flow - Vot [m3/s] | Percent Outdoor Air - %OA | Environment Name of Peak System Population - Ps | Date and Time of Last Peak System Population - Ps | |
| 15 ZONE VAV | 15.2505 | 0.0000 | 268.1390 | 1.0000 | 2.1513 | 13.6030 | 1.0000 | 1.0000 | 2.1513 | 0.1581 |
| Sum of Zone Primary Air Flow - Vpz-sum [m3/s] | System Population - Ps | Sum of Zone Population - Pz-sum | Occupant Diversity - D | Uncorrected Outdoor Air Intake Airflow - Vou [m3/s] | System Primary Airflow - Vps [m3/s] | Average Outdoor Air Fraction - Xs | System Ventilation Efficiency - Ev | Outdoor Air Intake Flow Vot [m3/s] | Percent Outdoor Air - %OA | Environment Name of Peak System Population - Ps | Date and Time of Last Peak System Population - Ps | |
| 15 ZONE VAV | 7.6253 | 0.0000 | 268.1390 | 1.0000 | 2.1513 | 1.5251 | 0.4325 | 1.0000 | 2.1513 | 1.4106 |
| AirLoop Name | People Outdoor Air Rate - Rp [m3/s-person] | Zone Population - Pz | Area Outdoor Air Rate - Ra [m3/s-m2] | Zone Floor Area - Az [m2] | Breathing Zone Outdoor Airflow - Vbz [m3/s] | Cooling Zone Air Distribution Effectiveness - Ez-clg | Cooling Zone Outdoor Airflow - Voz-clg [m3/s] | Heating Zone Air Distribution Effectiveness - Ez-htg | Heating Zone Outdoor Airflow - Voz-htg [m3/s] | |
| CORE_BOTTOM ZN | 15 ZONE VAV | 0.000000 | 52.9335 | 0.000432 | 983.54 | 0.4247 | 1.0000 | 0.4247 | 1.000 | 0.4247 |
| CORE_MID ZN | 15 ZONE VAV | 0.000000 | 52.9335 | 0.000432 | 983.54 | 0.4247 | 1.0000 | 0.4247 | 1.000 | 0.4247 |
| CORE_TOP ZN | 15 ZONE VAV | 0.000000 | 52.9335 | 0.000432 | 983.54 | 0.4247 | 1.0000 | 0.4247 | 1.000 | 0.4247 |
| PERIMETER_BOT_ZN_1 ZN | 15 ZONE VAV | 0.000000 | 11.1588 | 0.000432 | 207.34 | 0.0895 | 1.0000 | 0.0895 | 1.000 | 0.0895 |
| PERIMETER_BOT_ZN_2 ZN | 15 ZONE VAV | 0.000000 | 7.0645 | 0.000432 | 131.26 | 0.0567 | 1.0000 | 0.0567 | 1.000 | 0.0567 |
| PERIMETER_BOT_ZN_3 ZN | 15 ZONE VAV | 0.000000 | 11.1588 | 0.000432 | 207.34 | 0.0895 | 1.0000 | 0.0895 | 1.000 | 0.0895 |
| PERIMETER_BOT_ZN_4 ZN | 15 ZONE VAV | 0.000000 | 7.0640 | 0.000432 | 131.25 | 0.0567 | 1.0000 | 0.0567 | 1.000 | 0.0567 |
| PERIMETER_MID_ZN_1 ZN | 15 ZONE VAV | 0.000000 | 11.1588 | 0.000432 | 207.34 | 0.0895 | 1.0000 | 0.0895 | 1.000 | 0.0895 |
| PERIMETER_MID_ZN_2 ZN | 15 ZONE VAV | 0.000000 | 7.0645 | 0.000432 | 131.26 | 0.0567 | 1.0000 | 0.0567 | 1.000 | 0.0567 |
| PERIMETER_MID_ZN_3 ZN | 15 ZONE VAV | 0.000000 | 11.1588 | 0.000432 | 207.34 | 0.0895 | 1.0000 | 0.0895 | 1.000 | 0.0895 |
| PERIMETER_MID_ZN_4 ZN | 15 ZONE VAV | 0.000000 | 7.0640 | 0.000432 | 131.25 | 0.0567 | 1.0000 | 0.0567 | 1.000 | 0.0567 |
| PERIMETER_TOP_ZN_1 ZN | 15 ZONE VAV | 0.000000 | 11.1588 | 0.000432 | 207.34 | 0.0895 | 1.0000 | 0.0895 | 1.000 | 0.0895 |
| PERIMETER_TOP_ZN_2 ZN | 15 ZONE VAV | 0.000000 | 7.0645 | 0.000432 | 131.26 | 0.0567 | 1.0000 | 0.0567 | 1.000 | 0.0567 |
| PERIMETER_TOP_ZN_3 ZN | 15 ZONE VAV | 0.000000 | 11.1588 | 0.000432 | 207.34 | 0.0895 | 1.0000 | 0.0895 | 1.000 | 0.0895 |
| PERIMETER_TOP_ZN_4 ZN | 15 ZONE VAV | 0.000000 | 7.0640 | 0.000432 | 131.25 | 0.0567 | 1.0000 | 0.0567 | 1.000 | 0.0567 |
| People Outdoor Air Rate - Rp [m3/s-person] | Sum of Zone Population - Pz-sum | Area Outdoor Air Rate - Ra [m3/s-m2] | Sum of Zone Floor Area - Az-sum [m2] | Breathing Zone Outdoor Airflow - Vbz [m3/s] | Cooling Zone Outdoor Airflow - Voz-clg [m3/s] | Heating Zone Outdoor Airflow - Voz-htg [m3/s] | |
| 15 ZONE VAV | 0.000000 | 268.14 | 0.000432 | 4982.1859 | 2.1513 | 2.1513 | 2.1513 |
| AirLoop Name | Box Type | Zone Primary Airflow - Vpz [m3/s] | Zone Discharge Airflow - Vdz [m3/s] | Minimum Zone Primary Airflow - Vpz-min [m3/s] | Zone Outdoor Airflow Cooling - Voz-clg [m3/s] | Primary Outdoor Air Fraction - Zpz | Primary Air Fraction - Ep | Secondary Recirculation Fraction- Er | Supply Air Fraction- Fa | Mixed Air Fraction - Fb | Outdoor Air Fraction - Fc | Zone Ventilation Efficiency - Evz | |
| CORE_BOTTOM ZN | 15 ZONE VAV | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 2.9526 | 2.9526 | 0.2953 | 0.4247 | 0.0000 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| CORE_MID ZN | 15 ZONE VAV | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 2.1111 | 2.1111 | 0.2111 | 0.4247 | 0.0000 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| CORE_TOP ZN | 15 ZONE VAV | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 2.2102 | 2.2102 | 0.2210 | 0.4247 | 0.0000 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| PERIMETER_BOT_ZN_1 ZN | 15 ZONE VAV | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.5830 | 0.5830 | 0.0583 | 0.0895 | 0.0000 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| PERIMETER_BOT_ZN_2 ZN | 15 ZONE VAV | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.6323 | 0.6323 | 0.0632 | 0.0567 | 0.0000 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| PERIMETER_BOT_ZN_3 ZN | 15 ZONE VAV | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.5097 | 0.5097 | 0.0510 | 0.0895 | 0.0000 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| PERIMETER_BOT_ZN_4 ZN | 15 ZONE VAV | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.6722 | 0.6722 | 0.0672 | 0.0567 | 0.0000 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| PERIMETER_MID_ZN_1 ZN | 15 ZONE VAV | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.6716 | 0.6716 | 0.0672 | 0.0895 | 0.0000 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| PERIMETER_MID_ZN_2 ZN | 15 ZONE VAV | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.6903 | 0.6903 | 0.0690 | 0.0567 | 0.0000 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| PERIMETER_MID_ZN_3 ZN | 15 ZONE VAV | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.6001 | 0.6001 | 0.0600 | 0.0895 | 0.0000 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| PERIMETER_MID_ZN_4 ZN | 15 ZONE VAV | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.7276 | 0.7276 | 0.0728 | 0.0567 | 0.0000 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| PERIMETER_TOP_ZN_1 ZN | 15 ZONE VAV | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.7417 | 0.7417 | 0.0742 | 0.0895 | 0.0000 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| PERIMETER_TOP_ZN_2 ZN | 15 ZONE VAV | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.6969 | 0.6969 | 0.0697 | 0.0567 | 0.0000 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| PERIMETER_TOP_ZN_3 ZN | 15 ZONE VAV | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.6778 | 0.6778 | 0.0678 | 0.0895 | 0.0000 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| PERIMETER_TOP_ZN_4 ZN | 15 ZONE VAV | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.7736 | 0.7736 | 0.0774 | 0.0567 | 0.0000 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| Sum of Zone Primary Airflow - Vpz-sum [m3/s] | System Primary Airflow - Vps [m3/s] | Sum of Zone Discharge Airflow - Vdz-sum [m3/s] | Sum of Min Zone Primary Airflow - Vpz-min [m3/s] | Zone Outdoor Airflow Cooling - Voz-clg [m3/s] | Zone Ventilation Efficiency - Evz-min | |
| 15 ZONE VAV | 15.2505 | 13.6030 | 15.2505 | 1.5251 | 2.1513 | 1.0000 |
| AirLoop Name | Box Type | Zone Primary Airflow - Vpz [m3/s] | Zone Discharge Airflow - Vdz [m3/s] | Minimum Zone Primary Airflow - Vpz-min [m3/s] | Zone Outdoor Airflow Heating - Voz-htg [m3/s] | Primary Outdoor Air Fraction - Zpz | Primary Air Fraction - Ep | Secondary Recirculation Fraction- Er | Supply Air Fraction- Fa | Mixed Air Fraction - Fb | Outdoor Air Fraction - Fc | Zone Ventilation Efficiency - Evz | |
| CORE_BOTTOM ZN | 15 ZONE VAV | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 1.4763 | 1.4763 | 0.2953 | 0.4247 | 1.0000 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| CORE_MID ZN | 15 ZONE VAV | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 1.0555 | 1.0555 | 0.2111 | 0.4247 | 0.9052 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| CORE_TOP ZN | 15 ZONE VAV | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 1.1051 | 1.1051 | 0.2210 | 0.4247 | 0.4950 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| PERIMETER_BOT_ZN_1 ZN | 15 ZONE VAV | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.2915 | 0.2915 | 0.0583 | 0.0895 | 0.3501 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| PERIMETER_BOT_ZN_2 ZN | 15 ZONE VAV | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.3161 | 0.3161 | 0.0632 | 0.0567 | 0.3287 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| PERIMETER_BOT_ZN_3 ZN | 15 ZONE VAV | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.2549 | 0.2549 | 0.0510 | 0.0895 | 0.3526 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| PERIMETER_BOT_ZN_4 ZN | 15 ZONE VAV | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.3361 | 0.3361 | 0.0672 | 0.0567 | 0.3286 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| PERIMETER_MID_ZN_1 ZN | 15 ZONE VAV | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.3358 | 0.3358 | 0.0672 | 0.0895 | 0.2819 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| PERIMETER_MID_ZN_2 ZN | 15 ZONE VAV | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.3451 | 0.3451 | 0.0690 | 0.0567 | 0.2674 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| PERIMETER_MID_ZN_3 ZN | 15 ZONE VAV | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.3000 | 0.3000 | 0.0600 | 0.0895 | 0.2822 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| PERIMETER_MID_ZN_4 ZN | 15 ZONE VAV | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.3638 | 0.3638 | 0.0728 | 0.0567 | 0.2674 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| PERIMETER_TOP_ZN_1 ZN | 15 ZONE VAV | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.3708 | 0.3708 | 0.0742 | 0.0895 | 0.2271 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| PERIMETER_TOP_ZN_2 ZN | 15 ZONE VAV | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.3484 | 0.3484 | 0.0697 | 0.0567 | 0.2178 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| PERIMETER_TOP_ZN_3 ZN | 15 ZONE VAV | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.3389 | 0.3389 | 0.0678 | 0.0895 | 0.2269 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| PERIMETER_TOP_ZN_4 ZN | 15 ZONE VAV | AIRTERMINAL:SINGLEDUCT:VAV:REHEAT | 0.3868 | 0.3868 | 0.0774 | 0.0567 | 0.2177 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| Sum of Zone Primary Airflow - Vpz-sum [m3/s] | System Primary Airflow - Vps [m3/s] | Sum of Zone Discharge Airflow - Vdz-sum [m3/s] | Sum of Min Zone Primary Airflow - Vpz-min [m3/s] | Zone Outdoor Airflow Heating - Voz-htg [m3/s] | Zone Ventilation Efficiency - Evz-min | |
| 15 ZONE VAV | 7.6253 | 1.5251 | 1.5251 | 1.5251 | 2.1513 | 1.0000 |
Report: LEED Summary
For: Entire Facility
Timestamp: 2019-04-09 23:11:28
Sec1.1A-General Information| Data | |
| Weather File | RUN PERIOD 1 ** Houston Bush Intercontinental TX USA TMY3 WMO#=722430 |
| Total gross floor area [m2] | 4982.19 |
| Principal Heating Source | Natural Gas |
| Space Area [m2] | Regularly Occupied Area [m2] | Unconditioned Area [m2] | Typical Hours/Week in Operation [hr/wk] | |
| CORE_BOTTOM ZN | 983.54 | 983.54 | 0.00 | 58.84 |
| CORE_MID ZN | 983.54 | 983.54 | 0.00 | 58.84 |
| CORE_TOP ZN | 983.54 | 983.54 | 0.00 | 58.84 |
| PERIMETER_BOT_ZN_1 ZN | 207.34 | 207.34 | 0.00 | 58.84 |
| PERIMETER_BOT_ZN_2 ZN | 131.26 | 131.26 | 0.00 | 58.84 |
| PERIMETER_BOT_ZN_3 ZN | 207.34 | 207.34 | 0.00 | 58.84 |
| PERIMETER_BOT_ZN_4 ZN | 131.25 | 131.25 | 0.00 | 58.84 |
| PERIMETER_MID_ZN_1 ZN | 207.34 | 207.34 | 0.00 | 58.84 |
| PERIMETER_MID_ZN_2 ZN | 131.26 | 131.26 | 0.00 | 58.84 |
| PERIMETER_MID_ZN_3 ZN | 207.34 | 207.34 | 0.00 | 58.84 |
| PERIMETER_MID_ZN_4 ZN | 131.25 | 131.25 | 0.00 | 58.84 |
| PERIMETER_TOP_ZN_1 ZN | 207.34 | 207.34 | 0.00 | 58.84 |
| PERIMETER_TOP_ZN_2 ZN | 131.26 | 131.26 | 0.00 | 58.84 |
| PERIMETER_TOP_ZN_3 ZN | 207.34 | 207.34 | 0.00 | 58.84 |
| PERIMETER_TOP_ZN_4 ZN | 131.25 | 131.25 | 0.00 | 58.84 |
| FIRSTFLOOR_PLENUM ZN | 1660.73 | 0.00 | 1660.73 | 0.00 |
| MIDFLOOR_PLENUM ZN | 1660.73 | 0.00 | 1660.73 | 0.00 |
| TOPFLOOR_PLENUM ZN | 1660.73 | 0.00 | 1660.73 | 0.00 |
| Totals | 4982.19 | 4982.19 | 0.00 |
| Data | |
| Number of hours heating loads not met | 131.00 |
| Number of hours cooling loads not met | 332.50 |
| Number of hours not met | 463.50 |
| Utility Rate | Virtual Rate [$/unit energy] | Units of Energy | Units of Demand | |
| None |
| Electric Energy Use [GJ] | Electric Demand [W] | Natural Gas Energy Use [GJ] | Natural Gas Demand [W] | Additional Fuel Use [GJ] | Additional Fuel Demand [W] | District Cooling Use [GJ] | District Cooling Demand [W] | District Heating Use [GJ] | District Heating Demand [W] | |
| Heating -- General | 0.00 | 0.00 | 26.59 | 169484.86 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heating -- Boiler Parasitic | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling -- General | 413.75 | 75728.07 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting -- General | 335.95 | 34128.53 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting -- General | 104.80 | 8099.48 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment -- General | 763.69 | 56743.84 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment -- Not Subdivided | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans -- General | 60.10 | 14762.17 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps -- General | 68.19 | 4871.78 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection -- Not Subdivided | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification -- Not Subdivided | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery -- Not Subdivided | 12.14 | 1593.56 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems -- General | 0.00 | 0.00 | 79.12 | 8609.32 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration -- Not Subdivided | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators -- Not Subdivided | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Process Subtotal [GJ] | Total Energy Use [GJ] | |
| Electricity | 763.69 | 1758.63 |
| Natural Gas | 0.00 | 105.71 |
| Additional | 0.00 | 0.00 |
| Total | 763.69 | 1864.34 |
| Process Subtotal [$] | Total Energy Cost [$] | |
| Electricity | 0.00 | |
| Natural Gas | 0.00 | |
| Additional | 0.00 | |
| Total | 0.00 |
| Rated Capacity [kW] | Annual Energy Generated [GJ] | |
| Photovoltaic | 0.00 | 0.00 |
| Wind | 0.00 | 0.00 |
| Electricty [MJ/m2] | |
| Interior Lighting (All) | 67.43 |
| Space Heating | 0.00 |
| Space Cooling | 83.05 |
| Fans (All) | 12.06 |
| Service Water Heating | 0.00 |
| Receptacle Equipment | 153.28 |
| Miscellaneous (All) | 352.98 |
| Subtotal | 352.98 |
| Natural Gas [MJ/m2] | |
| Space Heating | 5.34 |
| Service Water Heating | 15.88 |
| Miscellaneous (All) | 21.22 |
| Subtotal | 21.22 |
| Additional [MJ/m2] | |
| Subtotal | 0.00 |
| Miscellaneous | 0.00 |
| Percent [%] | |
| Interior Lighting (All) | 18.02 |
| Space Heating | 1.43 |
| Space Cooling | 22.19 |
| Fans (All) | 3.22 |
| Service Water Heating | 4.24 |
| Receptacle Equipment | 40.96 |
| Miscellaneous | 9.93 |
| Equivalent Full Load Hours of Operation Per Year [hr] | Hours > 1% [hr] | |
| None |
| First Object Used | Month Assumed | 11am First Wednesday [C] | Days with Same 11am Value | 11pm First Wednesday [C] | Days with Same 11pm Value | |
| OFFICEMEDIUM HTGSETP_SCH_YES_OPTIMUM | OFFICE WHOLEBUILDING - MD OFFICE THERMOSTAT 1 | January | 21.00 | 365 | 15.60 | 365 |
| OFFICEMEDIUM CLGSETP_SCH_YES_OPTIMUM | OFFICE WHOLEBUILDING - MD OFFICE THERMOSTAT 1 | July | 24.00 | 365 | 26.70 | 365 |
Report: BUILDING ENERGY PERFORMANCE - ELECTRICITY
For: Meter
Timestamp: 2019-04-09 23:11:28
Custom Monthly Report| INTERIORLIGHTS:ELECTRICITY [J] | EXTERIORLIGHTS:ELECTRICITY [J] | INTERIOREQUIPMENT:ELECTRICITY [J] | EXTERIOREQUIPMENT:ELECTRICITY [] | FANS:ELECTRICITY [J] | PUMPS:ELECTRICITY [J] | HEATING:ELECTRICITY [J] | COOLING:ELECTRICITY [J] | HEATREJECTION:ELECTRICITY [] | HUMIDIFIER:ELECTRICITY [] | HEATRECOVERY:ELECTRICITY [J] | WATERSYSTEMS:ELECTRICITY [] | COGENERATION:ELECTRICITY [] | REFRIGERATION:ELECTRICITY [] | |
| January | 0.289625E+11 | 0.104780E+11 | 0.645833E+11 | 0.00 | 0.196181E+10 | 0.322378E+10 | 0.00 | 0.612877E+10 | 0.00 | 0.00 | 0.506881E+09 | 0.00 | 0.00 | 0.00 |
| February | 0.260651E+11 | 0.889966E+10 | 0.586762E+11 | 0.00 | 0.213008E+10 | 0.385306E+10 | 0.00 | 0.122764E+11 | 0.00 | 0.00 | 0.595499E+09 | 0.00 | 0.00 | 0.00 |
| March | 0.294457E+11 | 0.906870E+10 | 0.661846E+11 | 0.00 | 0.286311E+10 | 0.520966E+10 | 0.00 | 0.202851E+11 | 0.00 | 0.00 | 0.680547E+09 | 0.00 | 0.00 | 0.00 |
| April | 0.261286E+11 | 0.798372E+10 | 0.608312E+11 | 0.00 | 0.348928E+10 | 0.572634E+10 | 0.00 | 0.280941E+11 | 0.00 | 0.00 | 0.855552E+09 | 0.00 | 0.00 | 0.00 |
| May | 0.290122E+11 | 0.755734E+10 | 0.661846E+11 | 0.00 | 0.538921E+10 | 0.684260E+10 | 0.00 | 0.441945E+11 | 0.00 | 0.00 | 0.139464E+10 | 0.00 | 0.00 | 0.00 |
| June | 0.276731E+11 | 0.697291E+10 | 0.636818E+11 | 0.00 | 0.806289E+10 | 0.678737E+10 | 0.00 | 0.557451E+11 | 0.00 | 0.00 | 0.146882E+10 | 0.00 | 0.00 | 0.00 |
| July | 0.270119E+11 | 0.734837E+10 | 0.633340E+11 | 0.00 | 0.926691E+10 | 0.714843E+10 | 0.00 | 0.621621E+11 | 0.00 | 0.00 | 0.143994E+10 | 0.00 | 0.00 | 0.00 |
| August | 0.291135E+11 | 0.793640E+10 | 0.661846E+11 | 0.00 | 0.940193E+10 | 0.733536E+10 | 0.00 | 0.642331E+11 | 0.00 | 0.00 | 0.154321E+10 | 0.00 | 0.00 | 0.00 |
| September | 0.271944E+11 | 0.843567E+10 | 0.624324E+11 | 0.00 | 0.811888E+10 | 0.657084E+10 | 0.00 | 0.536956E+11 | 0.00 | 0.00 | 0.136766E+10 | 0.00 | 0.00 | 0.00 |
| October | 0.284768E+11 | 0.953037E+10 | 0.645833E+11 | 0.00 | 0.430262E+10 | 0.602950E+10 | 0.00 | 0.326744E+11 | 0.00 | 0.00 | 0.867265E+09 | 0.00 | 0.00 | 0.00 |
| November | 0.286620E+11 | 0.993732E+10 | 0.636818E+11 | 0.00 | 0.300404E+10 | 0.517173E+10 | 0.00 | 0.220027E+11 | 0.00 | 0.00 | 0.703893E+09 | 0.00 | 0.00 | 0.00 |
| December | 0.282026E+11 | 0.106481E+11 | 0.633340E+11 | 0.00 | 0.210976E+10 | 0.429572E+10 | 0.00 | 0.122600E+11 | 0.00 | 0.00 | 0.718649E+09 | 0.00 | 0.00 | 0.00 |
| Annual Sum or Average | 0.335948E+12 | 0.104797E+12 | 0.763692E+12 | 0.601005E+11 | 0.681944E+11 | 0.00 | 0.413752E+12 | 0.121426E+11 | ||||||
| Minimum of Months | 0.260651E+11 | 0.697291E+10 | 0.586762E+11 | 0.00 | 0.196181E+10 | 0.322378E+10 | 0.00 | 0.612877E+10 | 0.00 | 0.00 | 0.506881E+09 | 0.00 | 0.00 | 0.00 |
| Maximum of Months | 0.294457E+11 | 0.106481E+11 | 0.661846E+11 | 0.00 | 0.940193E+10 | 0.733536E+10 | 0.00 | 0.642331E+11 | 0.00 | 0.00 | 0.154321E+10 | 0.00 | 0.00 | 0.00 |
Report: BUILDING ENERGY PERFORMANCE - NATURAL GAS
For: Meter
Timestamp: 2019-04-09 23:11:28
Custom Monthly Report| INTERIOREQUIPMENT:GAS [] | EXTERIOREQUIPMENT:GAS [] | HEATING:GAS [J] | COOLING:GAS [] | WATERSYSTEMS:GAS [J] | COGENERATION:GAS [] | |
| January | 0.00 | 0.00 | 0.953447E+10 | 0.00 | 0.740140E+10 | 0.00 |
| February | 0.00 | 0.00 | 0.640185E+10 | 0.00 | 0.668631E+10 | 0.00 |
| March | 0.00 | 0.00 | 0.185291E+10 | 0.00 | 0.726643E+10 | 0.00 |
| April | 0.00 | 0.00 | 0.520950E+09 | 0.00 | 0.653150E+10 | 0.00 |
| May | 0.00 | 0.00 | 0.127015E+09 | 0.00 | 0.656303E+10 | 0.00 |
| June | 0.00 | 0.00 | 1112014.57 | 0.00 | 0.601614E+10 | 0.00 |
| July | 0.00 | 0.00 | 0.00 | 0.00 | 0.596582E+10 | 0.00 |
| August | 0.00 | 0.00 | 0.00 | 0.00 | 0.610313E+10 | 0.00 |
| September | 0.00 | 0.00 | 20632345.38 | 0.00 | 0.604364E+10 | 0.00 |
| October | 0.00 | 0.00 | 0.737668E+09 | 0.00 | 0.658058E+10 | 0.00 |
| November | 0.00 | 0.00 | 0.140930E+10 | 0.00 | 0.679633E+10 | 0.00 |
| December | 0.00 | 0.00 | 0.598161E+10 | 0.00 | 0.716893E+10 | 0.00 |
| Annual Sum or Average | 0.265875E+11 | 0.791232E+11 | ||||
| Minimum of Months | 0.00 | 0.00 | 0.00 | 0.00 | 0.596582E+10 | 0.00 |
| Maximum of Months | 0.00 | 0.00 | 0.953447E+10 | 0.00 | 0.740140E+10 | 0.00 |
Report: BUILDING ENERGY PERFORMANCE - ELECTRICITY PEAK DEMAND
For: Meter
Timestamp: 2019-04-09 23:11:28
Custom Monthly Report| ELECTRICITY:FACILITY {Maximum}[W] | ELECTRICITY:FACILITY {TIMESTAMP} | INTERIORLIGHTS:ELECTRICITY {AT MAX/MIN} [W] | EXTERIORLIGHTS:ELECTRICITY {AT MAX/MIN} [W] | INTERIOREQUIPMENT:ELECTRICITY {AT MAX/MIN} [W] | EXTERIOREQUIPMENT:ELECTRICITY [] | FANS:ELECTRICITY {AT MAX/MIN} [W] | PUMPS:ELECTRICITY {AT MAX/MIN} [W] | HEATING:ELECTRICITY {AT MAX/MIN} [W] | COOLING:ELECTRICITY {AT MAX/MIN} [W] | HEATREJECTION:ELECTRICITY [] | HUMIDIFIER:ELECTRICITY [] | HEATRECOVERY:ELECTRICITY {AT MAX/MIN} [W] | WATERSYSTEMS:ELECTRICITY [] | COGENERATION:ELECTRICITY [] | |
| January | 110662.60 | 30-JAN-16:10 | 27173.76 | 0.00 | 49329.42 | 0.00 | 4587.42 | 4395.19 | 0.00 | 25176.82 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| February | 118158.22 | 23-FEB-16:10 | 26958.05 | 0.00 | 49329.42 | 0.00 | 4763.08 | 4395.19 | 0.00 | 32712.49 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| March | 124633.40 | 27-MAR-15:30 | 26850.19 | 0.00 | 49329.42 | 0.00 | 6637.58 | 4395.19 | 0.00 | 35827.45 | 0.00 | 0.00 | 1593.56 | 0.00 | 0.00 |
| April | 129606.44 | 21-APR-15:30 | 26850.19 | 0.00 | 49329.42 | 0.00 | 6577.15 | 4395.19 | 0.00 | 40860.92 | 0.00 | 0.00 | 1593.56 | 0.00 | 0.00 |
| May | 144079.42 | 24-MAY-15:30 | 26850.19 | 0.00 | 49329.42 | 0.00 | 8952.26 | 4395.19 | 0.00 | 52958.80 | 0.00 | 0.00 | 1593.56 | 0.00 | 0.00 |
| June | 154858.57 | 30-JUN-15:30 | 26850.19 | 0.00 | 49329.42 | 0.00 | 11960.27 | 4395.19 | 0.00 | 60729.93 | 0.00 | 0.00 | 1593.56 | 0.00 | 0.00 |
| July | 163386.52 | 31-JUL-15:09 | 26850.19 | 0.00 | 49329.42 | 0.00 | 13973.18 | 4395.19 | 0.00 | 67244.98 | 0.00 | 0.00 | 1593.56 | 0.00 | 0.00 |
| August | 172594.12 | 02-AUG-15:00 | 26850.19 | 0.00 | 49329.42 | 0.00 | 14697.68 | 4395.19 | 0.00 | 75728.07 | 0.00 | 0.00 | 1593.56 | 0.00 | 0.00 |
| September | 158275.60 | 20-SEP-15:30 | 26850.19 | 0.00 | 49329.42 | 0.00 | 12845.52 | 4395.19 | 0.00 | 63261.71 | 0.00 | 0.00 | 1593.56 | 0.00 | 0.00 |
| October | 140682.36 | 02-OCT-10:30 | 26850.19 | 0.00 | 48362.32 | 0.00 | 8109.33 | 4395.19 | 0.00 | 51371.76 | 0.00 | 0.00 | 1593.56 | 0.00 | 0.00 |
| November | 128276.92 | 01-NOV-15:50 | 28063.26 | 0.00 | 49329.42 | 0.00 | 6626.15 | 4395.19 | 0.00 | 38269.33 | 0.00 | 0.00 | 1593.56 | 0.00 | 0.00 |
| December | 119711.90 | 08-DEC-16:00 | 33420.61 | 0.00 | 49329.42 | 0.00 | 2922.75 | 4395.19 | 0.00 | 28050.37 | 0.00 | 0.00 | 1593.56 | 0.00 | 0.00 |
| Annual Sum or Average | |||||||||||||||
| Minimum of Months | 110662.60 | 26850.19 | 0.00 | 48362.32 | 0.00 | 2922.75 | 4395.19 | 0.00 | 25176.82 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Maximum of Months | 172594.12 | 33420.61 | 0.00 | 49329.42 | 0.00 | 14697.68 | 4395.19 | 0.00 | 75728.07 | 0.00 | 0.00 | 1593.56 | 0.00 | 0.00 |
Report: BUILDING ENERGY PERFORMANCE - NATURAL GAS PEAK DEMAND
For: Meter
Timestamp: 2019-04-09 23:11:28
Custom Monthly Report| GAS:FACILITY {Maximum}[W] | GAS:FACILITY {TIMESTAMP} | INTERIOREQUIPMENT:GAS [] | EXTERIOREQUIPMENT:GAS [] | HEATING:GAS {AT MAX/MIN} [W] | COOLING:GAS [] | WATERSYSTEMS:GAS {AT MAX/MIN} [W] | COGENERATION:GAS [] | |
| January | 170761.81 | 23-JAN-07:10 | 0.00 | 0.00 | 169484.86 | 0.00 | 1276.95 | 0.00 |
| February | 157837.45 | 13-FEB-07:10 | 0.00 | 0.00 | 156560.51 | 0.00 | 1276.95 | 0.00 |
| March | 60076.19 | 20-MAR-06:10 | 0.00 | 0.00 | 58799.24 | 0.00 | 1276.95 | 0.00 |
| April | 29331.98 | 07-APR-07:10 | 0.00 | 0.00 | 21135.80 | 0.00 | 8196.18 | 0.00 |
| May | 19465.73 | 04-MAY-06:19 | 0.00 | 0.00 | 11490.25 | 0.00 | 7975.48 | 0.00 |
| June | 8418.38 | 07-JUN-06:19 | 0.00 | 0.00 | 470.10 | 0.00 | 7948.28 | 0.00 |
| July | 8232.36 | 03-JUL-11:20 | 0.00 | 0.00 | 0.00 | 0.00 | 8232.36 | 0.00 |
| August | 8240.26 | 28-AUG-11:20 | 0.00 | 0.00 | 0.00 | 0.00 | 8240.26 | 0.00 |
| September | 13039.08 | 08-SEP-06:30 | 0.00 | 0.00 | 5091.05 | 0.00 | 7948.03 | 0.00 |
| October | 30058.44 | 13-OCT-06:10 | 0.00 | 0.00 | 28781.50 | 0.00 | 1276.95 | 0.00 |
| November | 60457.68 | 30-NOV-07:10 | 0.00 | 0.00 | 59180.73 | 0.00 | 1276.95 | 0.00 |
| December | 121523.80 | 25-DEC-07:10 | 0.00 | 0.00 | 120246.85 | 0.00 | 1276.95 | 0.00 |
| Annual Sum or Average | ||||||||
| Minimum of Months | 8232.36 | 0.00 | 0.00 | 0.00 | 0.00 | 1276.95 | 0.00 | |
| Maximum of Months | 170761.81 | 0.00 | 0.00 | 169484.86 | 0.00 | 8240.26 | 0.00 |
Report: Life-Cycle Cost Report
For: Entire Facility
Timestamp: 2019-04-09 23:11:28
Life-Cycle Cost Parameters| Value | |
| Name | LIFE CYCLE COST PARAMETERS |
| Discounting Convention | EndOfYear |
| Inflation Approach | ConstantDollar |
| Real Discount Rate | 0.0300 |
| Nominal Discount Rate | -- N/A -- |
| Inflation | -- N/A -- |
| Base Date | January 2011 |
| Service Date | January 2011 |
| Length of Study Period in Years | 25 |
| Tax rate | 0.0000 |
| Depreciation Method | None |
| U.S. AVG COMMERCIAL-ELECTRICITY | U.S. AVG COMMERCIAL-DISTILLATE OIL | U.S. AVG COMMERCIAL-RESIDUAL OIL | U.S. AVG COMMERCIAL-NATURAL GAS | U.S. AVG COMMERCIAL-COAL | |
| Resource | Electricity | FuelOil#1 | FuelOil#2 | Gas | Coal |
| Start Date | January 2011 | January 2011 | January 2011 | January 2011 | January 2011 |
| 1 | 0.983800 | 0.971400 | 0.846900 | 0.982300 | 0.997000 |
| 2 | 0.973000 | 0.973000 | 0.825700 | 0.955700 | 1.008900 |
| 3 | 0.963200 | 0.994200 | 0.868100 | 0.927900 | 1.008900 |
| 4 | 0.961100 | 1.016400 | 0.898800 | 0.925700 | 0.994100 |
| 5 | 0.957100 | 1.054100 | 0.928900 | 0.934600 | 0.994100 |
| 6 | 0.955300 | 1.092800 | 0.960400 | 0.941200 | 1.000000 |
| 7 | 0.953900 | 1.126700 | 0.989700 | 0.951200 | 1.003000 |
| 8 | 0.952100 | 1.158000 | 1.007500 | 0.964500 | 1.005900 |
| 9 | 0.954600 | 1.179200 | 1.031400 | 0.985600 | 1.008900 |
| 10 | 0.955000 | 1.196700 | 1.055400 | 1.006700 | 1.011900 |
| 11 | 0.955300 | 1.220000 | 1.086100 | 1.022200 | 1.014800 |
| 12 | 0.956400 | 1.233300 | 1.127800 | 1.041000 | 1.017800 |
| 13 | 0.957500 | 1.256600 | 1.149700 | 1.061000 | 1.020800 |
| 14 | 0.959600 | 1.270900 | 1.162000 | 1.078700 | 1.026700 |
| 15 | 0.961800 | 1.282600 | 1.174300 | 1.094200 | 1.029700 |
| 16 | 0.961400 | 1.298500 | 1.185200 | 1.109800 | 1.035600 |
| 17 | 0.961800 | 1.310200 | 1.194800 | 1.122000 | 1.041500 |
| 18 | 0.961800 | 1.325000 | 1.203700 | 1.130800 | 1.053400 |
| 19 | 0.959300 | 1.326100 | 1.207100 | 1.138600 | 1.056400 |
| 20 | 0.958900 | 1.328200 | 1.211900 | 1.148600 | 1.059300 |
| 21 | 0.960700 | 1.332400 | 1.213900 | 1.161900 | 1.065300 |
| 22 | 0.962500 | 1.335600 | 1.219400 | 1.176300 | 1.071200 |
| 23 | 0.965000 | 1.343100 | 1.227600 | 1.191800 | 1.074200 |
| 24 | 0.970800 | 1.351000 | 1.236500 | 1.211800 | 1.080100 |
| 25 | 0.975100 | 1.356800 | 1.242000 | 1.228400 | 1.083100 |
| DEFAULT COST | |
| Nonrecurring | |
| January 2011 | 0.00 |
| January 2012 | 0.00 |
| January 2013 | 0.00 |
| January 2014 | 0.00 |
| January 2015 | 0.00 |
| January 2016 | 0.00 |
| January 2017 | 0.00 |
| January 2018 | 0.00 |
| January 2019 | 0.00 |
| January 2020 | 0.00 |
| January 2021 | 0.00 |
| January 2022 | 0.00 |
| January 2023 | 0.00 |
| January 2024 | 0.00 |
| January 2025 | 0.00 |
| January 2026 | 0.00 |
| January 2027 | 0.00 |
| January 2028 | 0.00 |
| January 2029 | 0.00 |
| January 2030 | 0.00 |
| January 2031 | 0.00 |
| January 2032 | 0.00 |
| January 2033 | 0.00 |
| January 2034 | 0.00 |
| January 2035 | 0.00 |
| January 2011 | |
| January 2012 | |
| January 2013 | |
| January 2014 | |
| January 2015 | |
| January 2016 | |
| January 2017 | |
| January 2018 | |
| January 2019 | |
| January 2020 | |
| January 2021 | |
| January 2022 | |
| January 2023 | |
| January 2024 | |
| January 2025 | |
| January 2026 | |
| January 2027 | |
| January 2028 | |
| January 2029 | |
| January 2030 | |
| January 2031 | |
| January 2032 | |
| January 2033 | |
| January 2034 | |
| January 2035 |
| Construction | Salvage | OtherCapital | Total | |
| January 2011 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2012 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2013 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2014 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2015 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2016 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2017 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2018 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2019 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2020 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2021 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2022 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2023 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2024 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2025 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2026 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2027 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2028 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2029 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2030 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2031 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2032 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2033 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2034 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2035 | 0.00 | 0.00 | 0.00 | 0.00 |
| Energy | Water | Maintenance | Repair | Operation | Replacement | MinorOverhaul | MajorOverhaul | OtherOperational | Total | |
| January 2011 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2012 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2013 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2014 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2015 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2016 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2017 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2018 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2019 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2020 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2021 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2022 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2023 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2024 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2025 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2026 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2027 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2028 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2029 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2030 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2031 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2032 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2033 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2034 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| January 2035 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| January | February | March | April | May | June | July | August | September | October | November | December | |
| 2011 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| 2012 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| 2013 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| 2014 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| 2015 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| 2016 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| 2017 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| 2018 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| 2019 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| 2020 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| 2021 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| 2022 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| 2023 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| 2024 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| 2025 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| 2026 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| 2027 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| 2028 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| 2029 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| 2030 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| 2031 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| 2032 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| 2033 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| 2034 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| 2035 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Category | Kind | Cost | Present Value | Present Value Factor | |
| DEFAULT COST | Construction | Nonrecurring | 0.00 | 0.00 | - |
| TOTAL | 0.00 |
| Present Value | |
| Construction | 0.00 |
| Salvage | 0.00 |
| Other Capital | 0.00 |
| Energy | 0.00 |
| Water | 0.00 |
| Maintenance | 0.00 |
| Repair | 0.00 |
| Operation | 0.00 |
| Replacement | 0.00 |
| Minor Overhaul | 0.00 |
| Major Overhaul | 0.00 |
| Other Operational | 0.00 |
| Total Energy | 0.00 |
| Total Operation | 0.00 |
| Total Capital | 0.00 |
| Grand Total | 0.00 |
| Total Cost | Present Value of Costs | |
| January 2011 | 0.00 | 0.00 |
| January 2012 | 0.00 | 0.00 |
| January 2013 | 0.00 | 0.00 |
| January 2014 | 0.00 | 0.00 |
| January 2015 | 0.00 | 0.00 |
| January 2016 | 0.00 | 0.00 |
| January 2017 | 0.00 | 0.00 |
| January 2018 | 0.00 | 0.00 |
| January 2019 | 0.00 | 0.00 |
| January 2020 | 0.00 | 0.00 |
| January 2021 | 0.00 | 0.00 |
| January 2022 | 0.00 | 0.00 |
| January 2023 | 0.00 | 0.00 |
| January 2024 | 0.00 | 0.00 |
| January 2025 | 0.00 | 0.00 |
| January 2026 | 0.00 | 0.00 |
| January 2027 | 0.00 | 0.00 |
| January 2028 | 0.00 | 0.00 |
| January 2029 | 0.00 | 0.00 |
| January 2030 | 0.00 | 0.00 |
| January 2031 | 0.00 | 0.00 |
| January 2032 | 0.00 | 0.00 |
| January 2033 | 0.00 | 0.00 |
| January 2034 | 0.00 | 0.00 |
| January 2035 | 0.00 | 0.00 |
| TOTAL | 0.00 |