Program Version:EnergyPlus, Version 8.9.0-eba93e8e1b, YMD=2018.07.11 10:44
Tabular Output Report in Format: HTML
Building: 90.1-2004-SmallOffice-ASHRAE 169-2006-5A created: 2018-04-11 13:55:36 -0400
Environment: RUN PERIOD 1 ** Chicago Ohare Intl Ap IL USA TMY3 WMO#=725300
Simulation Timestamp: 2018-07-11 10:44:46
Report: Annual Building Utility Performance Summary
For: Entire Facility
Timestamp: 2018-07-11 10:44:46
Values gathered over 8760.00 hours| Total Energy [GJ] | Energy Per Total Building Area [MJ/m2] | Energy Per Conditioned Building Area [MJ/m2] | |
| Total Site Energy | 271.45 | 531.04 | 531.04 |
| Net Site Energy | 271.45 | 531.04 | 531.04 |
| Total Source Energy | 859.67 | 1681.80 | 1681.80 |
| Net Source Energy | 859.67 | 1681.80 | 1681.80 |
| Site=>Source Conversion Factor | |
| Electricity | 3.167 |
| Natural Gas | 1.084 |
| District Cooling | 1.056 |
| District Heating | 3.613 |
| Steam | 0.300 |
| Gasoline | 1.050 |
| Diesel | 1.050 |
| Coal | 1.050 |
| Fuel Oil #1 | 1.050 |
| Fuel Oil #2 | 1.050 |
| Propane | 1.050 |
| Other Fuel 1 | 1.000 |
| Other Fuel 2 | 1.000 |
| Area [m2] | |
| Total Building Area | 511.16 |
| Net Conditioned Building Area | 511.16 |
| Unconditioned Building Area | 0.00 |
| Electricity [GJ] | Natural Gas [GJ] | Additional Fuel [GJ] | District Cooling [GJ] | District Heating [GJ] | Water [m3] | |
| Heating | 49.13 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | 22.53 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 72.23 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 25.67 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 53.79 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 30.10 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 18.01 | 0.00 | 0.00 | 0.00 | 0.00 | 30.01 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total End Uses | 271.45 | 0.00 | 0.00 | 0.00 | 0.00 | 30.01 |
| Subcategory | Electricity [GJ] | Natural Gas [GJ] | Additional Fuel [GJ] | District Cooling [GJ] | District Heating [GJ] | Water [m3] | |
| Heating | General | 49.13 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | General | 22.53 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | General | 72.23 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | General | 25.67 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | General | 53.79 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | General | 30.10 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | General | 18.01 | 0.00 | 0.00 | 0.00 | 0.00 | 30.01 |
| Refrigeration | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Electricity Intensity [MJ/m2] | Natural Gas Intensity [MJ/m2] | Additional Fuel Intensity [MJ/m2] | District Cooling Intensity [MJ/m2] | District Heating Intensity [MJ/m2] | Water Intensity [m3/m2] | |
| Lighting | 191.52 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| HVAC | 234.30 | 0.00 | 0.00 | 0.00 | 0.00 | 0.06 |
| Other | 105.23 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total | 531.04 | 0.00 | 0.00 | 0.00 | 0.00 | 0.06 |
| Electricity Intensity [MJ/m2] | Natural Gas Intensity [MJ/m2] | Additional Fuel Intensity [MJ/m2] | District Cooling Intensity [MJ/m2] | District Heating Intensity [MJ/m2] | Water Intensity [m3/m2] | |
| Lighting | 191.52 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| HVAC | 234.30 | 0.00 | 0.00 | 0.00 | 0.00 | 0.06 |
| Other | 105.23 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total | 531.04 | 0.00 | 0.00 | 0.00 | 0.00 | 0.06 |
| Electricity [GJ] | Percent Electricity [%] | |
| Fuel-Fired Power Generation | 0.000 | 0.00 |
| High Temperature Geothermal* | 0.000 | 0.00 |
| Photovoltaic Power | 0.000 | 0.00 |
| Wind Power | 0.000 | 0.00 |
| Power Conversion | 0.000 | 0.00 |
| Net Decrease in On-Site Storage | 0.000 | 0.00 |
| Total On-Site Electric Sources | 0.000 | 0.00 |
| Electricity Coming From Utility | 271.445 | 100.00 |
| Surplus Electricity Going To Utility | 0.000 | 0.00 |
| Net Electricity From Utility | 271.445 | 100.00 |
| Total On-Site and Utility Electric Sources | 271.445 | 100.00 |
| Total Electricity End Uses | 271.445 | 100.00 |
| Heat [GJ] | Percent Heat [%] | |
| Water-Side Heat Recovery | 0.00 | |
| Air to Air Heat Recovery for Cooling | 0.00 | |
| Air to Air Heat Recovery for Heating | 0.00 | |
| High-Temperature Geothermal* | 0.00 | |
| Solar Water Thermal | 0.00 | |
| Solar Air Thermal | 0.00 | |
| Total On-Site Thermal Sources | 0.00 |
| Water [m3] | Percent Water [%] | |
| Rainwater Collection | 0.00 | 0.00 |
| Condensate Collection | 0.00 | 0.00 |
| Groundwater Well | 0.00 | 0.00 |
| Total On Site Water Sources | 0.00 | 0.00 |
| - | - | - |
| Initial Storage | 0.00 | 0.00 |
| Final Storage | 0.00 | 0.00 |
| Change in Storage | 0.00 | 0.00 |
| - | - | - |
| Water Supplied by Utility | 30.01 | 100.00 |
| - | - | - |
| Total On Site, Change in Storage, and Utility Water Sources | 30.01 | 100.00 |
| Total Water End Uses | 30.01 | 100.00 |
| Degrees [deltaC] | |
| Tolerance for Zone Heating Setpoint Not Met Time | 0.20 |
| Tolerance for Zone Cooling Setpoint Not Met Time | 0.20 |
| Facility [Hours] | |
| Time Setpoint Not Met During Occupied Heating | 770.83 |
| Time Setpoint Not Met During Occupied Cooling | 133.67 |
| Time Not Comfortable Based on Simple ASHRAE 55-2004 | 2395.17 |
Table of Contents
TopBUILDING ENERGY PERFORMANCE - ELECTRICITY
| Meter |BUILDING ENERGY PERFORMANCE - ELECTRICITY PEAK DEMAND
| Meter |Life-Cycle Cost Report
| Entire Facility |Report: Input Verification and Results Summary
For: Entire Facility
Timestamp: 2018-07-11 10:44:46
General| Value | |
| Program Version and Build | EnergyPlus, Version 8.9.0-eba93e8e1b, YMD=2018.07.11 10:44 |
| RunPeriod | RUN PERIOD 1 |
| Weather File | Chicago Ohare Intl Ap IL USA TMY3 WMO#=725300 |
| Latitude [deg] | 41.98 |
| Longitude [deg] | -87.9 |
| Elevation [m] | 201.00 |
| Time Zone | -6.0 |
| North Axis Angle [deg] | 0.00 |
| Rotation for Appendix G [deg] | 0.00 |
| Hours Simulated [hrs] | 8760.00 |
| Total | North (315 to 45 deg) | East (45 to 135 deg) | South (135 to 225 deg) | West (225 to 315 deg) | |
| Gross Wall Area [m2] | 281.51 | 84.45 | 56.30 | 84.45 | 56.30 |
| Above Ground Wall Area [m2] | 281.51 | 84.45 | 56.30 | 84.45 | 56.30 |
| Window Opening Area [m2] | 55.78 | 16.73 | 11.16 | 16.73 | 11.16 |
| Gross Window-Wall Ratio [%] | 19.81 | 19.81 | 19.81 | 19.81 | 19.81 |
| Above Ground Window-Wall Ratio [%] | 19.81 | 19.81 | 19.81 | 19.81 | 19.81 |
| Total | North (315 to 45 deg) | East (45 to 135 deg) | South (135 to 225 deg) | West (225 to 315 deg) | |
| Gross Wall Area [m2] | 281.51 | 84.45 | 56.30 | 84.45 | 56.30 |
| Above Ground Wall Area [m2] | 281.51 | 84.45 | 56.30 | 84.45 | 56.30 |
| Window Opening Area [m2] | 55.78 | 16.73 | 11.16 | 16.73 | 11.16 |
| Gross Window-Wall Ratio [%] | 19.81 | 19.81 | 19.81 | 19.81 | 19.81 |
| Above Ground Window-Wall Ratio [%] | 19.81 | 19.81 | 19.81 | 19.81 | 19.81 |
| Total | |
| Gross Roof Area [m2] | 598.76 |
| Skylight Area [m2] | 0.00 |
| Skylight-Roof Ratio [%] | 0.00 |
| Area [m2] | Conditioned (Y/N) | Part of Total Floor Area (Y/N) | Volume [m3] | Multipliers | Above Ground Gross Wall Area [m2] | Underground Gross Wall Area [m2] | Window Glass Area [m2] | Opening Area [m2] | Lighting [W/m2] | People [m2 per person] | Plug and Process [W/m2] | |
| ATTIC ZN | 567.98 | No | No | 720.19 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | |||
| CORE_ZN ZN | 149.66 | Yes | Yes | 456.46 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 10.7639 | 16.59 | 6.7813 |
| PERIMETER_ZN_1 ZN | 113.45 | Yes | Yes | 346.02 | 1.00 | 84.45 | 0.00 | 16.73 | 16.73 | 10.7639 | 16.59 | 6.7813 |
| PERIMETER_ZN_2 ZN | 67.30 | Yes | Yes | 205.27 | 1.00 | 56.30 | 0.00 | 11.16 | 11.16 | 10.7639 | 16.59 | 6.7813 |
| PERIMETER_ZN_3 ZN | 113.45 | Yes | Yes | 346.02 | 1.00 | 84.45 | 0.00 | 16.73 | 16.73 | 10.7639 | 16.59 | 6.7813 |
| PERIMETER_ZN_4 ZN | 67.30 | Yes | Yes | 205.26 | 1.00 | 56.30 | 0.00 | 11.16 | 11.16 | 10.7639 | 16.59 | 6.7813 |
| Total | 511.16 | 1559.03 | 281.51 | 0.00 | 55.78 | 55.78 | 10.7639 | 16.59 | 6.7813 | |||
| Conditioned Total | 511.16 | 1559.03 | 281.51 | 0.00 | 55.78 | 55.78 | 10.7639 | 16.59 | 6.7813 | |||
| Unconditioned Total | 567.98 | 720.19 | 0.00 | 0.00 | 0.00 | 0.00 | 0.0000 | 0.0000 | ||||
| Not Part of Total | 567.98 | 720.19 | 0.00 | 0.00 | 0.00 | 0.00 | 0.0000 | 0.0000 |
Report: Demand End Use Components Summary
For: Entire Facility
Timestamp: 2018-07-11 10:44:46
End Uses| Electricity [W] | Natural Gas [W] | Propane [W] | District Cooling [W] | Steam [W] | Water [m3/s] | |
| Time of Peak | 17-JUL-08:39 | - | - | - | - | 02-JAN-12:09 |
| Heating | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | 12919.18 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 4951.85 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 3466.29 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 1410.72 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 571.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total End Uses | 23319.04 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Subcategory | Electricity [W] | Natural Gas [W] | Propane [W] | District Cooling [W] | Steam [W] | Water [m3/s] | |
| Heating | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | General | 12919.18 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | General | 4951.85 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | General | 3466.29 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | General | 1410.72 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | General | 571.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
Report: Source Energy End Use Components Summary
For: Entire Facility
Timestamp: 2018-07-11 10:44:46
Values gathered over 8760.00 hours| Source Electricity [GJ] | Source Natural Gas [GJ] | Source Additional Fuel [GJ] | Source District Cooling [GJ] | Source District Heating [GJ] | |
| Heating | 155.59 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | 71.34 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 228.74 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 81.30 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 170.35 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 95.33 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 57.03 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total Source Energy End Use Components | 859.67 | 0.00 | 0.00 | 0.00 | 0.00 |
| Source Electricity [MJ/m2] | Source Natural Gas [MJ/m2] | Source Additional Fuel [MJ/m2] | Source District Cooling [MJ/m2] | Source District Heating [MJ/m2] | |
| Heating | 304.40 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | 139.56 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 447.49 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 159.04 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 333.26 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 186.49 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 111.57 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total Source Energy End Use Components | 1681.80 | 0.00 | 0.00 | 0.00 | 0.00 |
| Source Electricity [MJ/m2] | Source Natural Gas [MJ/m2] | Source Additional Fuel [MJ/m2] | Source District Cooling [MJ/m2] | Source District Heating [MJ/m2] | |
| Heating | 304.40 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | 139.56 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 447.49 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 159.04 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 333.26 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 186.49 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 111.57 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total Source Energy End Use Components | 1681.80 | 0.00 | 0.00 | 0.00 | 0.00 |
Report: Component Sizing Summary
For: Entire Facility
Timestamp: 2018-07-11 10:44:46
ZoneHVAC:PackagedTerminalHeatPump| Design Size Cooling Supply Air Flow Rate [m3/s] | Design Size Heating Supply Air Flow Rate [m3/s] | Design Size No Load Supply Air Flow Rate [m3/s] | Design Size Outdoor Air Flow Rate During Cooling Operation [m3/s] | Design Size Outdoor Air Flow Rate During Heating Operation [m3/s] | Design Size Outdoor Air Flow Rate When No Cooling or Heating is Needed [m3/s] | Design Size Maximum Supply Air Temperature from Supplemental Heater [C] | |
| ZONE1PTHP | 0.320977 | 0.320977 | 0.320977 | 0.076026 | 0.076026 | 0.076026 | 40.00 |
| ZONE2PTHP | 0.354581 | 0.354581 | 0.354581 | 0.057633 | 0.057633 | 0.057633 | 40.00 |
| ZONE3PTHP | 0.316882 | 0.316882 | 0.316882 | 0.034188 | 0.034188 | 0.034188 | 40.00 |
| ZONE4PTHP | 0.332520 | 0.332520 | 0.332520 | 0.057633 | 0.057633 | 0.057633 | 40.00 |
| ZONE5PTHP | 0.355959 | 0.355959 | 0.355959 | 0.034188 | 0.034188 | 0.034188 | 40.00 |
| Design Size Rated Air Flow Rate [m3/s] | Design Size Gross Rated Total Cooling Capacity [W] | Design Size Gross Rated Sensible Heat Ratio | |
| ZONE1PTHPDXCOOLCOIL | 0.320977 | 6405.66 | 0.772959 |
| ZONE2PTHPDXCOOLCOIL | 0.354581 | 6832.55 | 0.787838 |
| ZONE3PTHPDXCOOLCOIL | 0.316882 | 5245.52 | 0.800655 |
| ZONE4PTHPDXCOOLCOIL | 0.332520 | 6236.55 | 0.798493 |
| ZONE5PTHPDXCOOLCOIL | 0.355959 | 6024.04 | 0.800620 |
| Design Size Rated Air Flow Rate [m3/s] | Design Size Gross Rated Heating Capacity [W] | Design Size Resistive Defrost Heater Capacity [W] | User-Specified Resistive Defrost Heater Capacity [W] | |
| ZONE1PTHPDXHEATCOIL | 0.320977 | 6405.66 | 6405.66 | 2000.00 |
| ZONE2PTHPDXHEATCOIL | 0.354581 | 6832.55 | 6832.55 | 2000.00 |
| ZONE3PTHPDXHEATCOIL | 0.316882 | 5245.52 | 5245.52 | 2000.00 |
| ZONE4PTHPDXHEATCOIL | 0.332520 | 6236.55 | 6236.55 | 2000.00 |
| ZONE5PTHPDXHEATCOIL | 0.355959 | 6024.04 | 6024.04 | 2000.00 |
| Design Size Maximum Flow Rate [m3/s] | |
| ZONE1PTHPFAN | 0.320977 |
| ZONE1PTHPFAN 3 | 0.354581 |
| ZONE3PTHPFAN | 0.316882 |
| ZONE4PTHPFAN | 0.332520 |
| ZONE5PTHPFAN | 0.355959 |
| User-Specified Nominal Capacity [W] | |
| ZONE1PTHPELECHTGBACKUPCOIL | 0.000000 |
| ZONE2PTHPELECHTGBACKUPCOIL | 0.000000 |
| ZONE3PTHPELECHTGBACKUPCOIL | 0.000000 |
| ZONE4PTHPELECHTGBACKUPCOIL | 0.000000 |
| ZONE5PTHPELECHTGBACKUPCOIL | 0.000000 |
| Design Size Cooling Supply Air Flow Rate [m3/s] | Design Size Heating Supply Air Flow Rate [m3/s] | Design Size No Cooling Supply Air Flow Rate [m3/s] | Design Size No Heating Supply Air Flow Rate [m3/s] | Design Size Outdoor Air Flow Rate During Cooling Operation [m3/s] | Design Size Outdoor Air Flow Rate During Heating Operation [m3/s] | Design Size Outdoor Air Flow Rate When No Cooling or Heating is Needed [m3/s] | |
| VRF ZONE TERMINAL | 0.320977 | 0.320977 | 0.320977 | 0.320977 | 0.076026 | 0.076026 | 0.076026 |
| VRF ZONE TERMINAL 1 | 0.354581 | 0.354581 | 0.354581 | 0.354581 | 0.057633 | 0.057633 | 0.057633 |
| VRF ZONE TERMINAL 2 | 0.316882 | 0.316882 | 0.316882 | 0.316882 | 0.034188 | 0.034188 | 0.034188 |
| VRF ZONE TERMINAL 3 | 0.332520 | 0.332520 | 0.332520 | 0.332520 | 0.057633 | 0.057633 | 0.057633 |
| VRF ZONE TERMINAL 4 | 0.355959 | 0.355959 | 0.355959 | 0.355959 | 0.034188 | 0.034188 | 0.034188 |
| Design Size Rated Air Flow Rate [m3/s] | Design Size Gross Rated Total Cooling Capacity [W] | Design Size Gross Rated Sensible Heat Ratio | |
| VRF ZONE TERMINAL COOLING COIL | 0.320977 | 6497.33 | 0.767656 |
| VRF ZONE TERMINAL COOLING COIL 1 | 0.354581 | 6979.87 | 0.779172 |
| VRF ZONE TERMINAL COOLING COIL 2 | 0.316882 | 5348.20 | 0.800596 |
| VRF ZONE TERMINAL COOLING COIL 3 | 0.332520 | 6361.99 | 0.790095 |
| VRF ZONE TERMINAL COOLING COIL 4 | 0.355959 | 6204.40 | 0.800166 |
| Design Size Rated Air Flow Rate [m3/s] | Design Size Gross Rated Heating Capacity [W] | |
| VRF ZONE TERMINAL HEATING COIL | 0.320977 | 6497.33 |
| VRF ZONE TERMINAL HEATING COIL 1 | 0.354581 | 6979.87 |
| VRF ZONE TERMINAL HEATING COIL 2 | 0.316882 | 5348.20 |
| VRF ZONE TERMINAL HEATING COIL 3 | 0.332520 | 6361.99 |
| VRF ZONE TERMINAL HEATING COIL 4 | 0.355959 | 6204.40 |
| Design Size Maximum Flow Rate [m3/s] | |
| VRF ZONE TERMINAL FAN | 0.320977 |
| VRF ZONE TERMINAL FAN 1 | 0.354581 |
| VRF ZONE TERMINAL FAN 2 | 0.316882 |
| VRF ZONE TERMINAL FAN 3 | 0.332520 |
| VRF ZONE TERMINAL FAN 4 | 0.355959 |
| Design Size Rated Total Cooling Capacity (gross) [W] | Design Size Rated Total Heating Capacity [W] | Design Size Resistive Defrost Heater Capacity | User-Specified Resistive Defrost Heater Capacity | Design Size Evaporative Condenser Air Flow Rate [m3/s] | Design Size Evaporative Condenser Pump Rated Power Consumption [W] | |
| VRF SYSTEM | 31391.78 | 31391.78 | 31391.78 | 0.000000 | 3.58 | 133.92 |
| Maximum Loop Flow Rate [m3/s] | Plant Loop Volume [m3] | |
| MAIN SERVICE WATER LOOP | 0.000004 | 0.000485 |
| Design Flow Rate [m3/s] | Design Power Consumption [W] | |
| SERVICE WATER LOOP PUMP | 0.000004 | 0.000000 |
| Use Side Design Flow Rate [m3/s] | |
| 40.0GAL ELECTRICITY WATER HEATER - 40KBTU/HR 1.0 THERM EFF | 0.000004 |
Report: Surface Shadowing Summary
For: Entire Facility
Timestamp: 2018-07-11 10:44:46
Surfaces (Walls, Roofs, etc) that may be Shadowed by Other Surfaces| Possible Shadow Receivers | |
| PERIMETER_ZN_1_WALL_SOUTH | ATTIC_SOFFIT_EAST | ATTIC_SOFFIT_SOUTH | ATTIC_SOFFIT_WEST | |
| PERIMETER_ZN_2_WALL_EAST | ATTIC_SOFFIT_EAST | ATTIC_SOFFIT_NORTH | ATTIC_SOFFIT_SOUTH | |
| PERIMETER_ZN_3_WALL_NORTH | ATTIC_SOFFIT_EAST | ATTIC_SOFFIT_NORTH | ATTIC_SOFFIT_WEST | |
| PERIMETER_ZN_4_WALL_WEST | ATTIC_SOFFIT_NORTH | ATTIC_SOFFIT_SOUTH | ATTIC_SOFFIT_WEST | |
| Possible Shadow Receivers | |
| PERIMETER_ZN_1_WALL_SOUTH | PERIMETER_ZN_1_WALL_SOUTH_DOOR | PERIMETER_ZN_1_WALL_SOUTH_WINDOW_1 | PERIMETER_ZN_1_WALL_SOUTH_WINDOW_2 | PERIMETER_ZN_1_WALL_SOUTH_WINDOW_3 | PERIMETER_ZN_1_WALL_SOUTH_WINDOW_4 | PERIMETER_ZN_1_WALL_SOUTH_WINDOW_5 | PERIMETER_ZN_1_WALL_SOUTH_WINDOW_6 | |
| PERIMETER_ZN_2_WALL_EAST | PERIMETER_ZN_2_WALL_EAST_WINDOW_1 | PERIMETER_ZN_2_WALL_EAST_WINDOW_2 | PERIMETER_ZN_2_WALL_EAST_WINDOW_3 | PERIMETER_ZN_2_WALL_EAST_WINDOW_4 | |
| PERIMETER_ZN_3_WALL_NORTH | PERIMETER_ZN_3_WALL_NORTH_WINDOW_1 | PERIMETER_ZN_3_WALL_NORTH_WINDOW_2 | PERIMETER_ZN_3_WALL_NORTH_WINDOW_3 | PERIMETER_ZN_3_WALL_NORTH_WINDOW_4 | PERIMETER_ZN_3_WALL_NORTH_WINDOW_5 | PERIMETER_ZN_3_WALL_NORTH_WINDOW_6 | |
| PERIMETER_ZN_4_WALL_WEST | PERIMETER_ZN_4_WALL_WEST_WINDOW_1 | PERIMETER_ZN_4_WALL_WEST_WINDOW_2 | PERIMETER_ZN_4_WALL_WEST_WINDOW_3 | PERIMETER_ZN_4_WALL_WEST_WINDOW_4 | |
Report: Adaptive Comfort Summary
For: Entire Facility
Timestamp: 2018-07-11 10:44:46
Time Not Meeting the Adaptive Comfort Models during Occupied Hours| ASHRAE55 90% Acceptability Limits [Hours] | ASHRAE55 80% Acceptability Limits [Hours] | CEN15251 Category I Acceptability Limits [Hours] | CEN15251 Category II Acceptability Limits [Hours] | CEN15251 Category III Acceptability Limits [Hours] |
Report: Initialization Summary
For: Entire Facility
Timestamp: 2018-07-11 10:44:46
Version| Version ID | |
| 1 | 8.9 |
| #TimeSteps | Minutes per TimeStep {minutes} | |
| 1 | 6 | 10 |
| Minimum System TimeStep {minutes} | Max HVAC Iterations | Minimum Plant Iterations | Maximum Plant Iterations | |
| 1 | 1 | 20 | 2 | 8 |
| Do Zone Sizing | Do System Sizing | Do Plant Sizing | Do Design Days | Do Weather Simulation | Do HVAC Sizing Simulation | |
| 1 | Yes | Yes | Yes | No | Yes | No |
| Tolerance for Time Heating Setpoint Not Met | Tolerance for Zone Cooling Setpoint Not Met Time | |
| 1 | 0.200 | 0.200 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | 19.27 | 19.18 | 19.29 | 19.59 | 19.96 | 22.25 | 22.94 | 23.08 | 23.06 | 20.85 | 20.16 | 19.63 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | -1.89 | -3.06 | -0.99 | 2.23 | 10.68 | 17.20 | 21.60 | 22.94 | 20.66 | 15.60 | 8.83 | 2.56 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 |
| Jan{dimensionless} | Feb{dimensionless} | Mar{dimensionless} | Apr{dimensionless} | May{dimensionless} | Jun{dimensionless} | Jul{dimensionless} | Aug{dimensionless} | Sep{dimensionless} | Oct{dimensionless} | Nov{dimensionless} | Dec{dimensionless} | |
| 1 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 |
| Normal | Daylighting {dimensionless} | |
| 1 | 1.000 | 1.000 |
| Jan{dimensionless} | Feb{dimensionless} | Mar{dimensionless} | Apr{dimensionless} | May{dimensionless} | Jun{dimensionless} | Jul{dimensionless} | Aug{dimensionless} | Sep{dimensionless} | Oct{dimensionless} | Nov{dimensionless} | Dec{dimensionless} | |
| 1 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 |
| Jan{dimensionless} | Feb{dimensionless} | Mar{dimensionless} | Apr{dimensionless} | May{dimensionless} | Jun{dimensionless} | Jul{dimensionless} | Aug{dimensionless} | Sep{dimensionless} | Oct{dimensionless} | Nov{dimensionless} | Dec{dimensionless} | |
| 1 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 |
| Wind Sensor Height Above Ground {m} | Wind Speed Profile Exponent {} | Wind Speed Profile Boundary Layer Thickness {m} | Air Temperature Sensor Height Above Ground {m} | Wind Speed Modifier Coefficient-Internal | Temperature Modifier Coefficient-Internal | |
| 1 | 10.000 | 0.140 | 270.000 | 1.500 | 1.586 | 9.750E-003 |
| Location Name | Latitude {N+/S- Deg} | Longitude {E+/W- Deg} | Time Zone Number {GMT+/-} | Elevation {m} | Standard Pressure at Elevation {Pa} | Standard RhoAir at Elevation | |
| 1 | Chicago Ohare Intl Ap IL USA TMY3 WMO#=725300 | 41.98 | -87.92 | -6.00 | 201.00 | 98934 | 1.1759 |
| Building Name | North Axis {deg} | Terrain | Loads Convergence Tolerance Value | Temperature Convergence Tolerance Value | Solar Distribution | Maximum Number of Warmup Days | Minimum Number of Warmup Days | |
| 1 | 90.1-2004-SmallOffice-ASHRAE 169-2006-5A created: 2018-04-11 13:55:36 -0400 | 0.000 | City | 4.00000E-002 | 0.20000 | FullInteriorAndExterior | 25 | 6 |
| Algorithm {Simple TARP CeilingDiffuser AdaptiveConvectionAlgorithm} |
|
| 1 | TARP |
| Algorithm {SimpleCombined TARP MoWitt DOE-2 AdaptiveConvectionAlgorithm} |
|
| 1 | TARP |
| Value {Anisotropic} | |
| 1 | Anisotropic |
| Value {ThirdOrderBackwardDifference AnalyticalSolution EulerMethod} |
|
| 1 | ThirdOrderBackwardDifference |
| Simulation {Yes/No} | Carbon Dioxide Concentration | |
| 1 | No | N/A |
| Simulation {Yes/No} | Generic Contaminant Concentration | |
| 1 | No | N/A |
| Enforce Mass Balance |
Adjust Zone Mixing |
Adjust Zone Infiltration {AddInfiltration AdjustInfiltration None} |
Infiltration Zones {MixingSourceZonesOnly AllZones} |
|
| 1 | No | N/A | N/A | N/A |
| Value {RegulaFalsi Bisection BisectionThenRegulaFalsi RegulaFalsiThenBisection} |
|
| 1 | RegulaFalsi |
| Wind Speed Profile Exponent {} | Wind Speed Profile Boundary Layer Thickness {m} | Air Temperature Gradient Coefficient {K/m} | |
| 1 | 0.330 | 460.000 | 6.500000E-003 |
| Starting Corner | Vertex Input Direction | Coordinate System | Daylight Reference Point Coordinate System | Rectangular (Simple) Surface Coordinate System | |
| 1 | UpperLeftCorner | Counterclockwise | RelativeCoordinateSystem | RelativeCoordinateSystem | RelativeToZoneOrigin |
| Value {CTF - ConductionTransferFunction EMPD - MoisturePenetrationDepthConductionTransferFunction CondFD - ConductionFiniteDifference HAMT - CombinedHeatAndMoistureFiniteElement} - Description |
Inside Surface Max Temperature Limit{C} |
Surface Convection Coefficient Lower Limit {W/m2-K} |
Surface Convection Coefficient Upper Limit {W/m2-K} |
|
| 1 | CTF - ConductionTransferFunction | 200 | 0.10 | 1000.0 |
| Number of Fixed Detached Shades | Number of Building Detached Shades | Number of Attached Shades | |
| 1 | 0 | 0 | 0 |
| Number of Zones | Number of Zone Surfaces | Number of SubSurfaces | |
| 1 | 6 | 69 | 21 |
| Zone Name | North Axis {deg} | Origin X-Coordinate {m} | Origin Y-Coordinate {m} | Origin Z-Coordinate {m} | Centroid X-Coordinate {m} | Centroid Y-Coordinate {m} | Centroid Z-Coordinate {m} | Type | Zone Multiplier | Zone List Multiplier | Minimum X {m} | Maximum X {m} | Minimum Y {m} | Maximum Y {m} | Minimum Z {m} | Maximum Z {m} | Ceiling Height {m} | Volume {m3} | Zone Inside Convection Algorithm {Simple-Detailed-CeilingDiffuser-TrombeWall} | Zone Outside Convection Algorithm {Simple-Detailed-Tarp-MoWitt-DOE-2-BLAST} | Floor Area {m2} | Exterior Gross Wall Area {m2} | Exterior Net Wall Area {m2} | Exterior Window Area {m2} | Number of Surfaces | Number of SubSurfaces | Number of Shading SubSurfaces | Part of Total Building Area | |
| 1 | ATTIC ZN | 0.0 | 0.00 | 0.00 | 0.00 | 13.85 | 9.23 | 3.70 | 1 | 1 | 1 | -0.60 | 28.29 | -0.60 | 19.06 | 3.05 | 6.33 | 1.64 | 720.19 | TARP | TARP | 567.98 | 0.00 | 0.00 | 0.00 | 13 | 0 | 0 | No |
| 2 | CORE_ZN ZN | 0.0 | 0.00 | 0.00 | 0.00 | 13.85 | 9.23 | 1.53 | 1 | 1 | 1 | 5.00 | 22.69 | 5.00 | 13.46 | 0.00 | 3.05 | 3.05 | 456.46 | TARP | TARP | 149.66 | 0.00 | 0.00 | 0.00 | 6 | 0 | 0 | Yes |
| 3 | PERIMETER_ZN_1 ZN | 0.0 | 0.00 | 0.00 | 0.00 | 13.85 | 2.21 | 1.53 | 1 | 1 | 1 | 0.00 | 27.69 | 0.00 | 5.00 | 0.00 | 3.05 | 3.05 | 346.02 | TARP | TARP | 113.45 | 84.45 | 63.82 | 16.73 | 6 | 7 | 0 | Yes |
| 4 | PERIMETER_ZN_2 ZN | 0.0 | 0.00 | 0.00 | 0.00 | 25.64 | 9.23 | 1.53 | 1 | 1 | 1 | 22.69 | 27.69 | 0.00 | 18.46 | 0.00 | 3.05 | 3.05 | 205.27 | TARP | TARP | 67.30 | 56.30 | 45.15 | 11.16 | 6 | 4 | 0 | Yes |
| 5 | PERIMETER_ZN_3 ZN | 0.0 | 0.00 | 0.00 | 0.00 | 13.85 | 16.25 | 1.53 | 1 | 1 | 1 | 0.00 | 27.69 | 13.46 | 18.46 | 0.00 | 3.05 | 3.05 | 346.02 | TARP | TARP | 113.45 | 84.45 | 67.72 | 16.73 | 6 | 6 | 0 | Yes |
| 6 | PERIMETER_ZN_4 ZN | 0.0 | 0.00 | 0.00 | 0.00 | 2.05 | 9.23 | 1.53 | 1 | 1 | 1 | 0.00 | 5.00 | 0.00 | 18.46 | 0.00 | 3.05 | 3.05 | 205.27 | TARP | TARP | 67.30 | 56.30 | 45.15 | 11.16 | 6 | 4 | 0 | Yes |
| Zone Name | Floor Area {m2} | # Occupants | Area per Occupant {m2/person} | Occupant per Area {person/m2} | Interior Lighting {W/m2} | Electric Load {W/m2} | Gas Load {W/m2} | Other Load {W/m2} | Hot Water Eq {W/m2} | Steam Equipment {W/m2} | Sum Loads per Area {W/m2} | Outdoor Controlled Baseboard Heat | |
| 1 | ATTIC ZN | 567.98 | 0.0 | N/A | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | No |
| 2 | CORE_ZN ZN | 149.66 | 9.0 | 16.590 | 6.028E-002 | 10.764 | 6.781 | 0.000 | 0.000 | 0.000 | 0.000 | 17.545 | No |
| 3 | PERIMETER_ZN_1 ZN | 113.45 | 6.8 | 16.590 | 6.028E-002 | 10.764 | 6.781 | 0.000 | 0.000 | 0.000 | 0.000 | 17.545 | No |
| 4 | PERIMETER_ZN_2 ZN | 67.30 | 4.1 | 16.590 | 6.028E-002 | 10.764 | 6.781 | 0.000 | 0.000 | 0.000 | 0.000 | 17.545 | No |
| 5 | PERIMETER_ZN_3 ZN | 113.45 | 6.8 | 16.590 | 6.028E-002 | 10.764 | 6.781 | 0.000 | 0.000 | 0.000 | 0.000 | 17.545 | No |
| 6 | PERIMETER_ZN_4 ZN | 67.30 | 4.1 | 16.590 | 6.028E-002 | 10.764 | 6.781 | 0.000 | 0.000 | 0.000 | 0.000 | 17.545 | No |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Number of People {} | People/Floor Area {person/m2} | Floor Area per person {m2/person} | Fraction Radiant | Fraction Convected | Sensible Fraction Calculation | Activity level | ASHRAE 55 Warnings | Carbon Dioxide Generation Rate | Nominal Minimum Number of People | Nominal Maximum Number of People | |
| 1 | CORE_ZN ZN OFFICE WHOLEBUILDING - SM OFFICE PEOPLE | OFFICESMALL BLDG_OCC_SCH | CORE_ZN ZN | 149.66 | 9.0 | 9.0 | 6.028E-002 | 16.590 | 0.300 | 0.700 | AutoCalculate | OFFICESMALL ACTIVITY_SCH | No | 3.8200E-008 | 0 | 9 |
| 2 | PERIMETER_ZN_1 ZN OFFICE WHOLEBUILDING - SM OFFICE PEOPLE | OFFICESMALL BLDG_OCC_SCH | PERIMETER_ZN_1 ZN | 113.45 | 6.8 | 6.8 | 6.028E-002 | 16.590 | 0.300 | 0.700 | AutoCalculate | OFFICESMALL ACTIVITY_SCH | No | 3.8200E-008 | 0 | 7 |
| 3 | PERIMETER_ZN_2 ZN OFFICE WHOLEBUILDING - SM OFFICE PEOPLE | OFFICESMALL BLDG_OCC_SCH | PERIMETER_ZN_2 ZN | 67.30 | 4.1 | 4.1 | 6.028E-002 | 16.590 | 0.300 | 0.700 | AutoCalculate | OFFICESMALL ACTIVITY_SCH | No | 3.8200E-008 | 0 | 4 |
| 4 | PERIMETER_ZN_3 ZN OFFICE WHOLEBUILDING - SM OFFICE PEOPLE | OFFICESMALL BLDG_OCC_SCH | PERIMETER_ZN_3 ZN | 113.45 | 6.8 | 6.8 | 6.028E-002 | 16.590 | 0.300 | 0.700 | AutoCalculate | OFFICESMALL ACTIVITY_SCH | No | 3.8200E-008 | 0 | 7 |
| 5 | PERIMETER_ZN_4 ZN OFFICE WHOLEBUILDING - SM OFFICE PEOPLE | OFFICESMALL BLDG_OCC_SCH | PERIMETER_ZN_4 ZN | 67.30 | 4.1 | 4.1 | 6.028E-002 | 16.590 | 0.300 | 0.700 | AutoCalculate | OFFICESMALL ACTIVITY_SCH | No | 3.8200E-008 | 0 | 4 |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Lighting Level {W} | Lights/Floor Area {W/m2} | Lights per person {W/person} | Fraction Return Air | Fraction Radiant | Fraction Short Wave | Fraction Convected | Fraction Replaceable | End-Use Category | Nominal Minimum Lighting Level {W} | Nominal Maximum Lighting Level {W} | |
| 1 | CORE_ZN ZN OFFICE WHOLEBUILDING - SM OFFICE LIGHTS | OFFICESMALL BLDG_LIGHT_SCH | CORE_ZN ZN | 149.66 | 9.0 | 1610.899 | 10.764 | 178.571 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 1610.899 |
| 2 | PERIMETER_ZN_1 ZN OFFICE WHOLEBUILDING - SM OFFICE LIGHTS | OFFICESMALL BLDG_LIGHT_SCH | PERIMETER_ZN_1 ZN | 113.45 | 6.8 | 1221.166 | 10.764 | 178.571 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 1221.166 |
| 3 | PERIMETER_ZN_2 ZN OFFICE WHOLEBUILDING - SM OFFICE LIGHTS | OFFICESMALL BLDG_LIGHT_SCH | PERIMETER_ZN_2 ZN | 67.30 | 4.1 | 724.411 | 10.764 | 178.571 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 724.411 |
| 4 | PERIMETER_ZN_3 ZN OFFICE WHOLEBUILDING - SM OFFICE LIGHTS | OFFICESMALL BLDG_LIGHT_SCH | PERIMETER_ZN_3 ZN | 113.45 | 6.8 | 1221.166 | 10.764 | 178.571 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 1221.166 |
| 5 | PERIMETER_ZN_4 ZN OFFICE WHOLEBUILDING - SM OFFICE LIGHTS | OFFICESMALL BLDG_LIGHT_SCH | PERIMETER_ZN_4 ZN | 67.30 | 4.1 | 724.411 | 10.764 | 178.571 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 724.411 |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Equipment Level {W} | Equipment/Floor Area {W/m2} | Equipment per person {W/person} | Fraction Latent | Fraction Radiant | Fraction Lost | Fraction Convected | End-Use SubCategory | Nominal Minimum Equipment Level {W} | Nominal Maximum Equipment Level {W} | |
| 1 | CORE_ZN ZN OFFICE WHOLEBUILDING - SM OFFICE ELEC EQUIP | OFFICESMALL BLDG_EQUIP_SCH | CORE_ZN ZN | 149.66 | 9.0 | 1014.866 | 6.781 | 112.500 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 1014.866 |
| 2 | PERIMETER_ZN_1 ZN OFFICE WHOLEBUILDING - SM OFFICE ELEC EQUIP | OFFICESMALL BLDG_EQUIP_SCH | PERIMETER_ZN_1 ZN | 113.45 | 6.8 | 769.334 | 6.781 | 112.500 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 769.334 |
| 3 | PERIMETER_ZN_2 ZN OFFICE WHOLEBUILDING - SM OFFICE ELEC EQUIP | OFFICESMALL BLDG_EQUIP_SCH | PERIMETER_ZN_2 ZN | 67.30 | 4.1 | 456.379 | 6.781 | 112.500 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 456.379 |
| 4 | PERIMETER_ZN_3 ZN OFFICE WHOLEBUILDING - SM OFFICE ELEC EQUIP | OFFICESMALL BLDG_EQUIP_SCH | PERIMETER_ZN_3 ZN | 113.45 | 6.8 | 769.334 | 6.781 | 112.500 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 769.334 |
| 5 | PERIMETER_ZN_4 ZN OFFICE WHOLEBUILDING - SM OFFICE ELEC EQUIP | OFFICESMALL BLDG_EQUIP_SCH | PERIMETER_ZN_4 ZN | 67.30 | 4.1 | 456.379 | 6.781 | 112.500 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 456.379 |
| Calculation Method | Value {days} | Allowable Number Figures in Shadow Overlap {} | Polygon Clipping Algorithm | Sky Diffuse Modeling Algorithm | External Shading Calculation Method | Output External Shading Calculation Results | Disable Self-Shading Within Shading Zone Groups | Disable Self-Shading From Shading Zone Groups to Other Zones | |
| 1 | AverageOverDaysInFrequency | 30 | 15000 | SutherlandHodgman | SimpleSkyDiffuseModeling | InternalCalculation | No | No | No |
| Type | Name | Volume {m3} | Maximum Capacity {W} | Standard Rated Recovery Efficiency | Standard Rated Energy Factor | |
| 1 | WaterHeater:Mixed | 40.0GAL ELECTRICITY WATER HEATER - 40KBTU/HR 1.0 THERM EFF | 0.1514 | 11722.8 | 0.985 | 0.5080 |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Design Volume Flow Rate {m3/s} | Volume Flow Rate/Floor Area {m3/s/m2} | Volume Flow Rate/Exterior Surface Area {m3/s/m2} | ACH - Air Changes per Hour | Equation A - Constant Term Coefficient {} | Equation B - Temperature Term Coefficient {1/C} | Equation C - Velocity Term Coefficient {s/m} | Equation D - Velocity Squared Term Coefficient {s2/m2} | |
| 1 | PERIMETER_ZN_1 INFILTRATION | OFFICESMALL INFIL_QUARTER_ON_SCH | PERIMETER_ZN_1 ZN | 113.45 | 6.8 | 9.059E-002 | 7.985E-004 | 1.025E-003 | 0.942 | 0.000 | 0.000 | 0.224 | 0.000 |
| 2 | PERIMETER_ZN_2 INFILTRATION | OFFICESMALL INFIL_QUARTER_ON_SCH | PERIMETER_ZN_2 ZN | 67.30 | 4.1 | 5.772E-002 | 8.577E-004 | 1.025E-003 | 1.012 | 0.000 | 0.000 | 0.224 | 0.000 |
| 3 | PERIMETER_ZN_3 INFILTRATION | OFFICESMALL INFIL_QUARTER_ON_SCH | PERIMETER_ZN_3 ZN | 113.45 | 6.8 | 8.659E-002 | 7.632E-004 | 1.025E-003 | 0.901 | 0.000 | 0.000 | 0.224 | 0.000 |
| 4 | PERIMETER_ZN_4 INFILTRATION | OFFICESMALL INFIL_QUARTER_ON_SCH | PERIMETER_ZN_4 ZN | 67.30 | 4.1 | 5.772E-002 | 8.577E-004 | 1.025E-003 | 1.012 | 0.000 | 0.000 | 0.224 | 0.000 |
| Simple | |
| 1 | Simple |
| Zone Name | Mixing/Mundt/UCSDDV/UCSDCV/UCSDUFI/UCSDUFE/User Defined | |
| 1 | ATTIC ZN | Mixing/Well-Stirred |
| 2 | CORE_ZN ZN | Mixing/Well-Stirred |
| 3 | PERIMETER_ZN_1 ZN | Mixing/Well-Stirred |
| 4 | PERIMETER_ZN_2 ZN | Mixing/Well-Stirred |
| 5 | PERIMETER_ZN_3 ZN | Mixing/Well-Stirred |
| 6 | PERIMETER_ZN_4 ZN | Mixing/Well-Stirred |
| No Multizone or Distribution/Multizone with Distribution/Multizone without Distribution/Multizone with Distribution only during Fan Operation | |
| 1 | NoMultizoneOrDistribution |
| Sensible Heat Capacity Multiplier | Moisture Capacity Multiplier | Carbon Dioxide Capacity Multiplier | Generic Contaminant Capacity Multiplier | |
| 1 | 1.000 | 1.000 | 1.000 | 1.000 |
| Value | |
| 1 | 6 |
| Sizing Factor ID | Value | |
| 1 | Global | 1.2000 |
| 2 | Zone CORE_ZN ZN | 1.2000 |
| 3 | Zone PERIMETER_ZN_1 ZN | 1.2000 |
| 4 | Zone PERIMETER_ZN_2 ZN | 1.2000 |
| 5 | Zone PERIMETER_ZN_3 ZN | 1.2000 |
| 6 | Zone PERIMETER_ZN_4 ZN | 1.2000 |
| Sizing Factor ID | Value | |
| 1 | Global | 1.2000 |
| 2 | Zone CORE_ZN ZN | 1.2000 |
| 3 | Zone PERIMETER_ZN_1 ZN | 1.2000 |
| 4 | Zone PERIMETER_ZN_2 ZN | 1.2000 |
| 5 | Zone PERIMETER_ZN_3 ZN | 1.2000 |
| 6 | Zone PERIMETER_ZN_4 ZN | 1.2000 |
| Zone Name | Load Type | Calc Des Load {W} | User Des Load {W} | Calc Des Air Flow Rate {m3/s} | User Des Air Flow Rate {m3/s} | Design Day Name | Date/Time of Peak | Temperature at Peak {C} | Humidity Ratio at Peak {kgWater/kgDryAir} | Floor Area {m2} | # Occupants | Calc Outdoor Air Flow Rate {m3/s} | Calc DOAS Heat Addition Rate {W} | |
| 1 | CORE_ZN ZN | Cooling | 3559.67250 | 4271.60700 | 0.26748 | 0.32098 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 18:50:00 | 29.46750 | 1.49611E-002 | 149.65740 | 9.02103 | 7.60260E-002 | 0.00000 |
| 2 | CORE_ZN ZN | Heating | 3059.26650 | 3671.11980 | 0.13507 | 0.16208 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | -20.00000 | 6.49857E-004 | 149.65740 | 9.02103 | 7.60260E-002 | 0.00000 |
| 3 | PERIMETER_ZN_1 ZN | Cooling | 3932.24998 | 4718.69997 | 0.29548 | 0.35458 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 13:30:00 | 33.03750 | 1.49611E-002 | 113.45000 | 6.83853 | 5.76326E-002 | 0.00000 |
| 4 | PERIMETER_ZN_1 ZN | Heating | 6500.87873 | 7801.05448 | 0.28696 | 0.34436 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | -20.00000 | 6.49857E-004 | 113.45000 | 6.83853 | 5.76326E-002 | 0.00000 |
| 5 | PERIMETER_ZN_2 ZN | Cooling | 3514.18351 | 4217.02021 | 0.26407 | 0.31688 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 08:50:00 | 27.19250 | 1.49611E-002 | 67.30000 | 4.05670 | 3.41884E-002 | 0.00000 |
| 6 | PERIMETER_ZN_2 ZN | Heating | 3920.75512 | 4704.90615 | 0.17307 | 0.20768 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | -20.00000 | 6.49857E-004 | 67.30000 | 4.05670 | 3.41884E-002 | 0.00000 |
| 7 | PERIMETER_ZN_3 ZN | Cooling | 3687.60030 | 4425.12036 | 0.27710 | 0.33252 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 18:30:00 | 29.99250 | 1.49611E-002 | 113.45000 | 6.83853 | 5.76326E-002 | 0.00000 |
| 8 | PERIMETER_ZN_3 ZN | Heating | 6100.04922 | 7320.05906 | 0.26927 | 0.32313 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | -20.00000 | 6.49857E-004 | 113.45000 | 6.83853 | 5.76326E-002 | 0.00000 |
| 9 | PERIMETER_ZN_4 ZN | Cooling | 3947.57086 | 4737.08503 | 0.29663 | 0.35596 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 17:00:00 | 31.83000 | 1.49611E-002 | 67.30000 | 4.05670 | 3.41884E-002 | 0.00000 |
| 10 | PERIMETER_ZN_4 ZN | Heating | 3955.11138 | 4746.13365 | 0.17459 | 0.20950 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | -20.00000 | 6.49857E-004 | 67.30000 | 4.05670 | 3.41884E-002 | 0.00000 |
| Component Type | Component Name | Input Field Description | Value | |
| 1 | ZoneHVAC:PackagedTerminalHeatPump | ZONE1PTHP | Design Size Cooling Supply Air Flow Rate [m3/s] | 0.32098 |
| 2 | ZoneHVAC:PackagedTerminalHeatPump | ZONE1PTHP | Design Size Heating Supply Air Flow Rate [m3/s] | 0.32098 |
| 3 | ZoneHVAC:PackagedTerminalHeatPump | ZONE1PTHP | Design Size No Load Supply Air Flow Rate [m3/s] | 0.32098 |
| 4 | ZoneHVAC:PackagedTerminalHeatPump | ZONE1PTHP | Design Size Outdoor Air Flow Rate During Cooling Operation [m3/s] | 7.60260E-002 |
| 5 | ZoneHVAC:PackagedTerminalHeatPump | ZONE1PTHP | Design Size Outdoor Air Flow Rate During Heating Operation [m3/s] | 7.60260E-002 |
| 6 | ZoneHVAC:PackagedTerminalHeatPump | ZONE1PTHP | Design Size Outdoor Air Flow Rate When No Cooling or Heating is Needed [m3/s] | 7.60260E-002 |
| 7 | ZoneHVAC:PackagedTerminalHeatPump | ZONE1PTHP | Design Size Maximum Supply Air Temperature from Supplemental Heater [C] | 40.00000 |
| 8 | Coil:Cooling:DX:SingleSpeed | ZONE1PTHPDXCOOLCOIL | Design Size Rated Air Flow Rate [m3/s] | 0.32098 |
| 9 | Coil:Cooling:DX:SingleSpeed | ZONE1PTHPDXCOOLCOIL | Design Size Gross Rated Total Cooling Capacity [W] | 6405.66193 |
| 10 | Coil:Cooling:DX:SingleSpeed | ZONE1PTHPDXCOOLCOIL | Design Size Gross Rated Sensible Heat Ratio | 0.77296 |
| 11 | Coil:Heating:DX:SingleSpeed | ZONE1PTHPDXHEATCOIL | Design Size Rated Air Flow Rate [m3/s] | 0.32098 |
| 12 | Coil:Heating:DX:SingleSpeed | ZONE1PTHPDXHEATCOIL | Design Size Gross Rated Heating Capacity [W] | 6405.66193 |
| 13 | Coil:Heating:DX:SingleSpeed | ZONE1PTHPDXHEATCOIL | Design Size Resistive Defrost Heater Capacity [W] | 6405.66193 |
| 14 | Coil:Heating:DX:SingleSpeed | ZONE1PTHPDXHEATCOIL | User-Specified Resistive Defrost Heater Capacity [W] | 2000.00000 |
| 15 | Fan:ConstantVolume | ZONE1PTHPFAN | Design Size Maximum Flow Rate [m3/s] | 0.32098 |
| 16 | Coil:Heating:Electric | ZONE1PTHPELECHTGBACKUPCOIL | User-Specified Nominal Capacity [W] | 0.00000 |
| 17 | ZoneHVAC:TerminalUnit:VariableRefrigerantFlow | VRF ZONE TERMINAL | Design Size Cooling Supply Air Flow Rate [m3/s] | 0.32098 |
| 18 | ZoneHVAC:TerminalUnit:VariableRefrigerantFlow | VRF ZONE TERMINAL | Design Size Heating Supply Air Flow Rate [m3/s] | 0.32098 |
| 19 | ZoneHVAC:TerminalUnit:VariableRefrigerantFlow | VRF ZONE TERMINAL | Design Size No Cooling Supply Air Flow Rate [m3/s] | 0.32098 |
| 20 | ZoneHVAC:TerminalUnit:VariableRefrigerantFlow | VRF ZONE TERMINAL | Design Size No Heating Supply Air Flow Rate [m3/s] | 0.32098 |
| 21 | ZoneHVAC:TerminalUnit:VariableRefrigerantFlow | VRF ZONE TERMINAL | Design Size Outdoor Air Flow Rate During Cooling Operation [m3/s] | 7.60260E-002 |
| 22 | ZoneHVAC:TerminalUnit:VariableRefrigerantFlow | VRF ZONE TERMINAL | Design Size Outdoor Air Flow Rate During Heating Operation [m3/s] | 7.60260E-002 |
| 23 | ZoneHVAC:TerminalUnit:VariableRefrigerantFlow | VRF ZONE TERMINAL | Design Size Outdoor Air Flow Rate When No Cooling or Heating is Needed [m3/s] | 7.60260E-002 |
| 24 | Coil:Cooling:DX:VariableRefrigerantFlow | VRF ZONE TERMINAL COOLING COIL | Design Size Rated Air Flow Rate [m3/s] | 0.32098 |
| 25 | Coil:Cooling:DX:VariableRefrigerantFlow | VRF ZONE TERMINAL COOLING COIL | Design Size Gross Rated Total Cooling Capacity [W] | 6497.32652 |
| 26 | Coil:Cooling:DX:VariableRefrigerantFlow | VRF ZONE TERMINAL COOLING COIL | Design Size Gross Rated Sensible Heat Ratio | 0.76766 |
| 27 | Coil:Heating:DX:VariableRefrigerantFlow | VRF ZONE TERMINAL HEATING COIL | Design Size Rated Air Flow Rate [m3/s] | 0.32098 |
| 28 | Coil:Heating:DX:VariableRefrigerantFlow | VRF ZONE TERMINAL HEATING COIL | Design Size Gross Rated Heating Capacity [W] | 6497.32652 |
| 29 | Fan:OnOff | VRF ZONE TERMINAL FAN | Design Size Maximum Flow Rate [m3/s] | 0.32098 |
| 30 | ZoneHVAC:PackagedTerminalHeatPump | ZONE2PTHP | Design Size Cooling Supply Air Flow Rate [m3/s] | 0.35458 |
| 31 | ZoneHVAC:PackagedTerminalHeatPump | ZONE2PTHP | Design Size Heating Supply Air Flow Rate [m3/s] | 0.35458 |
| 32 | ZoneHVAC:PackagedTerminalHeatPump | ZONE2PTHP | Design Size No Load Supply Air Flow Rate [m3/s] | 0.35458 |
| 33 | ZoneHVAC:PackagedTerminalHeatPump | ZONE2PTHP | Design Size Outdoor Air Flow Rate During Cooling Operation [m3/s] | 5.76326E-002 |
| 34 | ZoneHVAC:PackagedTerminalHeatPump | ZONE2PTHP | Design Size Outdoor Air Flow Rate During Heating Operation [m3/s] | 5.76326E-002 |
| 35 | ZoneHVAC:PackagedTerminalHeatPump | ZONE2PTHP | Design Size Outdoor Air Flow Rate When No Cooling or Heating is Needed [m3/s] | 5.76326E-002 |
| 36 | ZoneHVAC:PackagedTerminalHeatPump | ZONE2PTHP | Design Size Maximum Supply Air Temperature from Supplemental Heater [C] | 40.00000 |
| 37 | Coil:Cooling:DX:SingleSpeed | ZONE2PTHPDXCOOLCOIL | Design Size Rated Air Flow Rate [m3/s] | 0.35458 |
| 38 | Coil:Cooling:DX:SingleSpeed | ZONE2PTHPDXCOOLCOIL | Design Size Gross Rated Total Cooling Capacity [W] | 6832.54806 |
| 39 | Coil:Cooling:DX:SingleSpeed | ZONE2PTHPDXCOOLCOIL | Design Size Gross Rated Sensible Heat Ratio | 0.78784 |
| 40 | Coil:Heating:DX:SingleSpeed | ZONE2PTHPDXHEATCOIL | Design Size Rated Air Flow Rate [m3/s] | 0.35458 |
| 41 | Coil:Heating:DX:SingleSpeed | ZONE2PTHPDXHEATCOIL | Design Size Gross Rated Heating Capacity [W] | 6832.54806 |
| 42 | Coil:Heating:DX:SingleSpeed | ZONE2PTHPDXHEATCOIL | Design Size Resistive Defrost Heater Capacity [W] | 6832.54806 |
| 43 | Coil:Heating:DX:SingleSpeed | ZONE2PTHPDXHEATCOIL | User-Specified Resistive Defrost Heater Capacity [W] | 2000.00000 |
| 44 | Fan:ConstantVolume | ZONE1PTHPFAN 3 | Design Size Maximum Flow Rate [m3/s] | 0.35458 |
| 45 | Coil:Heating:Electric | ZONE2PTHPELECHTGBACKUPCOIL | User-Specified Nominal Capacity [W] | 0.00000 |
| 46 | ZoneHVAC:TerminalUnit:VariableRefrigerantFlow | VRF ZONE TERMINAL 1 | Design Size Cooling Supply Air Flow Rate [m3/s] | 0.35458 |
| 47 | ZoneHVAC:TerminalUnit:VariableRefrigerantFlow | VRF ZONE TERMINAL 1 | Design Size Heating Supply Air Flow Rate [m3/s] | 0.35458 |
| 48 | ZoneHVAC:TerminalUnit:VariableRefrigerantFlow | VRF ZONE TERMINAL 1 | Design Size No Cooling Supply Air Flow Rate [m3/s] | 0.35458 |
| 49 | ZoneHVAC:TerminalUnit:VariableRefrigerantFlow | VRF ZONE TERMINAL 1 | Design Size No Heating Supply Air Flow Rate [m3/s] | 0.35458 |
| 50 | ZoneHVAC:TerminalUnit:VariableRefrigerantFlow | VRF ZONE TERMINAL 1 | Design Size Outdoor Air Flow Rate During Cooling Operation [m3/s] | 5.76326E-002 |
| 51 | ZoneHVAC:TerminalUnit:VariableRefrigerantFlow | VRF ZONE TERMINAL 1 | Design Size Outdoor Air Flow Rate During Heating Operation [m3/s] | 5.76326E-002 |
| 52 | ZoneHVAC:TerminalUnit:VariableRefrigerantFlow | VRF ZONE TERMINAL 1 | Design Size Outdoor Air Flow Rate When No Cooling or Heating is Needed [m3/s] | 5.76326E-002 |
| 53 | Coil:Cooling:DX:VariableRefrigerantFlow | VRF ZONE TERMINAL COOLING COIL 1 | Design Size Rated Air Flow Rate [m3/s] | 0.35458 |
| 54 | Coil:Cooling:DX:VariableRefrigerantFlow | VRF ZONE TERMINAL COOLING COIL 1 | Design Size Gross Rated Total Cooling Capacity [W] | 6979.86675 |
| 55 | Coil:Cooling:DX:VariableRefrigerantFlow | VRF ZONE TERMINAL COOLING COIL 1 | Design Size Gross Rated Sensible Heat Ratio | 0.77917 |
| 56 | Coil:Heating:DX:VariableRefrigerantFlow | VRF ZONE TERMINAL HEATING COIL 1 | Design Size Rated Air Flow Rate [m3/s] | 0.35458 |
| 57 | Coil:Heating:DX:VariableRefrigerantFlow | VRF ZONE TERMINAL HEATING COIL 1 | Design Size Gross Rated Heating Capacity [W] | 6979.86675 |
| 58 | Fan:OnOff | VRF ZONE TERMINAL FAN 1 | Design Size Maximum Flow Rate [m3/s] | 0.35458 |
| 59 | ZoneHVAC:PackagedTerminalHeatPump | ZONE3PTHP | Design Size Cooling Supply Air Flow Rate [m3/s] | 0.31688 |
| 60 | ZoneHVAC:PackagedTerminalHeatPump | ZONE3PTHP | Design Size Heating Supply Air Flow Rate [m3/s] | 0.31688 |
| 61 | ZoneHVAC:PackagedTerminalHeatPump | ZONE3PTHP | Design Size No Load Supply Air Flow Rate [m3/s] | 0.31688 |
| 62 | ZoneHVAC:PackagedTerminalHeatPump | ZONE3PTHP | Design Size Outdoor Air Flow Rate During Cooling Operation [m3/s] | 3.41884E-002 |
| 63 | ZoneHVAC:PackagedTerminalHeatPump | ZONE3PTHP | Design Size Outdoor Air Flow Rate During Heating Operation [m3/s] | 3.41884E-002 |
| 64 | ZoneHVAC:PackagedTerminalHeatPump | ZONE3PTHP | Design Size Outdoor Air Flow Rate When No Cooling or Heating is Needed [m3/s] | 3.41884E-002 |
| 65 | ZoneHVAC:PackagedTerminalHeatPump | ZONE3PTHP | Design Size Maximum Supply Air Temperature from Supplemental Heater [C] | 40.00000 |
| 66 | Coil:Cooling:DX:SingleSpeed | ZONE3PTHPDXCOOLCOIL | Design Size Rated Air Flow Rate [m3/s] | 0.31688 |
| 67 | Coil:Cooling:DX:SingleSpeed | ZONE3PTHPDXCOOLCOIL | Design Size Gross Rated Total Cooling Capacity [W] | 5245.51539 |
| 68 | Coil:Cooling:DX:SingleSpeed | ZONE3PTHPDXCOOLCOIL | Design Size Gross Rated Sensible Heat Ratio | 0.80066 |
| 69 | Coil:Heating:DX:SingleSpeed | ZONE3PTHPDXHEATCOIL | Design Size Rated Air Flow Rate [m3/s] | 0.31688 |
| 70 | Coil:Heating:DX:SingleSpeed | ZONE3PTHPDXHEATCOIL | Design Size Gross Rated Heating Capacity [W] | 5245.51539 |
| 71 | Coil:Heating:DX:SingleSpeed | ZONE3PTHPDXHEATCOIL | Design Size Resistive Defrost Heater Capacity [W] | 5245.51539 |
| 72 | Coil:Heating:DX:SingleSpeed | ZONE3PTHPDXHEATCOIL | User-Specified Resistive Defrost Heater Capacity [W] | 2000.00000 |
| 73 | Fan:ConstantVolume | ZONE3PTHPFAN | Design Size Maximum Flow Rate [m3/s] | 0.31688 |
| 74 | Coil:Heating:Electric | ZONE3PTHPELECHTGBACKUPCOIL | User-Specified Nominal Capacity [W] | 0.00000 |
| 75 | ZoneHVAC:TerminalUnit:VariableRefrigerantFlow | VRF ZONE TERMINAL 2 | Design Size Cooling Supply Air Flow Rate [m3/s] | 0.31688 |
| 76 | ZoneHVAC:TerminalUnit:VariableRefrigerantFlow | VRF ZONE TERMINAL 2 | Design Size Heating Supply Air Flow Rate [m3/s] | 0.31688 |
| 77 | ZoneHVAC:TerminalUnit:VariableRefrigerantFlow | VRF ZONE TERMINAL 2 | Design Size No Cooling Supply Air Flow Rate [m3/s] | 0.31688 |
| 78 | ZoneHVAC:TerminalUnit:VariableRefrigerantFlow | VRF ZONE TERMINAL 2 | Design Size No Heating Supply Air Flow Rate [m3/s] | 0.31688 |
| 79 | ZoneHVAC:TerminalUnit:VariableRefrigerantFlow | VRF ZONE TERMINAL 2 | Design Size Outdoor Air Flow Rate During Cooling Operation [m3/s] | 3.41884E-002 |
| 80 | ZoneHVAC:TerminalUnit:VariableRefrigerantFlow | VRF ZONE TERMINAL 2 | Design Size Outdoor Air Flow Rate During Heating Operation [m3/s] | 3.41884E-002 |
| 81 | ZoneHVAC:TerminalUnit:VariableRefrigerantFlow | VRF ZONE TERMINAL 2 | Design Size Outdoor Air Flow Rate When No Cooling or Heating is Needed [m3/s] | 3.41884E-002 |
| 82 | Coil:Cooling:DX:VariableRefrigerantFlow | VRF ZONE TERMINAL COOLING COIL 2 | Design Size Rated Air Flow Rate [m3/s] | 0.31688 |
| 83 | Coil:Cooling:DX:VariableRefrigerantFlow | VRF ZONE TERMINAL COOLING COIL 2 | Design Size Gross Rated Total Cooling Capacity [W] | 5348.20460 |
| 84 | Coil:Cooling:DX:VariableRefrigerantFlow | VRF ZONE TERMINAL COOLING COIL 2 | Design Size Gross Rated Sensible Heat Ratio | 0.80060 |
| 85 | Coil:Heating:DX:VariableRefrigerantFlow | VRF ZONE TERMINAL HEATING COIL 2 | Design Size Rated Air Flow Rate [m3/s] | 0.31688 |
| 86 | Coil:Heating:DX:VariableRefrigerantFlow | VRF ZONE TERMINAL HEATING COIL 2 | Design Size Gross Rated Heating Capacity [W] | 5348.20460 |
| 87 | Fan:OnOff | VRF ZONE TERMINAL FAN 2 | Design Size Maximum Flow Rate [m3/s] | 0.31688 |
| 88 | ZoneHVAC:PackagedTerminalHeatPump | ZONE4PTHP | Design Size Cooling Supply Air Flow Rate [m3/s] | 0.33252 |
| 89 | ZoneHVAC:PackagedTerminalHeatPump | ZONE4PTHP | Design Size Heating Supply Air Flow Rate [m3/s] | 0.33252 |
| 90 | ZoneHVAC:PackagedTerminalHeatPump | ZONE4PTHP | Design Size No Load Supply Air Flow Rate [m3/s] | 0.33252 |
| 91 | ZoneHVAC:PackagedTerminalHeatPump | ZONE4PTHP | Design Size Outdoor Air Flow Rate During Cooling Operation [m3/s] | 5.76326E-002 |
| 92 | ZoneHVAC:PackagedTerminalHeatPump | ZONE4PTHP | Design Size Outdoor Air Flow Rate During Heating Operation [m3/s] | 5.76326E-002 |
| 93 | ZoneHVAC:PackagedTerminalHeatPump | ZONE4PTHP | Design Size Outdoor Air Flow Rate When No Cooling or Heating is Needed [m3/s] | 5.76326E-002 |
| 94 | ZoneHVAC:PackagedTerminalHeatPump | ZONE4PTHP | Design Size Maximum Supply Air Temperature from Supplemental Heater [C] | 40.00000 |
| 95 | Coil:Cooling:DX:SingleSpeed | ZONE4PTHPDXCOOLCOIL | Design Size Rated Air Flow Rate [m3/s] | 0.33252 |
| 96 | Coil:Cooling:DX:SingleSpeed | ZONE4PTHPDXCOOLCOIL | Design Size Gross Rated Total Cooling Capacity [W] | 6236.54784 |
| 97 | Coil:Cooling:DX:SingleSpeed | ZONE4PTHPDXCOOLCOIL | Design Size Gross Rated Sensible Heat Ratio | 0.79849 |
| 98 | Coil:Heating:DX:SingleSpeed | ZONE4PTHPDXHEATCOIL | Design Size Rated Air Flow Rate [m3/s] | 0.33252 |
| 99 | Coil:Heating:DX:SingleSpeed | ZONE4PTHPDXHEATCOIL | Design Size Gross Rated Heating Capacity [W] | 6236.54784 |
| 100 | Coil:Heating:DX:SingleSpeed | ZONE4PTHPDXHEATCOIL | Design Size Resistive Defrost Heater Capacity [W] | 6236.54784 |
| 101 | Coil:Heating:DX:SingleSpeed | ZONE4PTHPDXHEATCOIL | User-Specified Resistive Defrost Heater Capacity [W] | 2000.00000 |
| 102 | Fan:ConstantVolume | ZONE4PTHPFAN | Design Size Maximum Flow Rate [m3/s] | 0.33252 |
| 103 | Coil:Heating:Electric | ZONE4PTHPELECHTGBACKUPCOIL | User-Specified Nominal Capacity [W] | 0.00000 |
| 104 | ZoneHVAC:TerminalUnit:VariableRefrigerantFlow | VRF ZONE TERMINAL 3 | Design Size Cooling Supply Air Flow Rate [m3/s] | 0.33252 |
| 105 | ZoneHVAC:TerminalUnit:VariableRefrigerantFlow | VRF ZONE TERMINAL 3 | Design Size Heating Supply Air Flow Rate [m3/s] | 0.33252 |
| 106 | ZoneHVAC:TerminalUnit:VariableRefrigerantFlow | VRF ZONE TERMINAL 3 | Design Size No Cooling Supply Air Flow Rate [m3/s] | 0.33252 |
| 107 | ZoneHVAC:TerminalUnit:VariableRefrigerantFlow | VRF ZONE TERMINAL 3 | Design Size No Heating Supply Air Flow Rate [m3/s] | 0.33252 |
| 108 | ZoneHVAC:TerminalUnit:VariableRefrigerantFlow | VRF ZONE TERMINAL 3 | Design Size Outdoor Air Flow Rate During Cooling Operation [m3/s] | 5.76326E-002 |
| 109 | ZoneHVAC:TerminalUnit:VariableRefrigerantFlow | VRF ZONE TERMINAL 3 | Design Size Outdoor Air Flow Rate During Heating Operation [m3/s] | 5.76326E-002 |
| 110 | ZoneHVAC:TerminalUnit:VariableRefrigerantFlow | VRF ZONE TERMINAL 3 | Design Size Outdoor Air Flow Rate When No Cooling or Heating is Needed [m3/s] | 5.76326E-002 |
| 111 | Coil:Cooling:DX:VariableRefrigerantFlow | VRF ZONE TERMINAL COOLING COIL 3 | Design Size Rated Air Flow Rate [m3/s] | 0.33252 |
| 112 | Coil:Cooling:DX:VariableRefrigerantFlow | VRF ZONE TERMINAL COOLING COIL 3 | Design Size Gross Rated Total Cooling Capacity [W] | 6361.98689 |
| 113 | Coil:Cooling:DX:VariableRefrigerantFlow | VRF ZONE TERMINAL COOLING COIL 3 | Design Size Gross Rated Sensible Heat Ratio | 0.79010 |
| 114 | Coil:Heating:DX:VariableRefrigerantFlow | VRF ZONE TERMINAL HEATING COIL 3 | Design Size Rated Air Flow Rate [m3/s] | 0.33252 |
| 115 | Coil:Heating:DX:VariableRefrigerantFlow | VRF ZONE TERMINAL HEATING COIL 3 | Design Size Gross Rated Heating Capacity [W] | 6361.98689 |
| 116 | Fan:OnOff | VRF ZONE TERMINAL FAN 3 | Design Size Maximum Flow Rate [m3/s] | 0.33252 |
| 117 | ZoneHVAC:PackagedTerminalHeatPump | ZONE5PTHP | Design Size Cooling Supply Air Flow Rate [m3/s] | 0.35596 |
| 118 | ZoneHVAC:PackagedTerminalHeatPump | ZONE5PTHP | Design Size Heating Supply Air Flow Rate [m3/s] | 0.35596 |
| 119 | ZoneHVAC:PackagedTerminalHeatPump | ZONE5PTHP | Design Size No Load Supply Air Flow Rate [m3/s] | 0.35596 |
| 120 | ZoneHVAC:PackagedTerminalHeatPump | ZONE5PTHP | Design Size Outdoor Air Flow Rate During Cooling Operation [m3/s] | 3.41884E-002 |
| 121 | ZoneHVAC:PackagedTerminalHeatPump | ZONE5PTHP | Design Size Outdoor Air Flow Rate During Heating Operation [m3/s] | 3.41884E-002 |
| 122 | ZoneHVAC:PackagedTerminalHeatPump | ZONE5PTHP | Design Size Outdoor Air Flow Rate When No Cooling or Heating is Needed [m3/s] | 3.41884E-002 |
| 123 | ZoneHVAC:PackagedTerminalHeatPump | ZONE5PTHP | Design Size Maximum Supply Air Temperature from Supplemental Heater [C] | 40.00000 |
| 124 | Coil:Cooling:DX:SingleSpeed | ZONE5PTHPDXCOOLCOIL | Design Size Rated Air Flow Rate [m3/s] | 0.35596 |
| 125 | Coil:Cooling:DX:SingleSpeed | ZONE5PTHPDXCOOLCOIL | Design Size Gross Rated Total Cooling Capacity [W] | 6024.04196 |
| 126 | Coil:Cooling:DX:SingleSpeed | ZONE5PTHPDXCOOLCOIL | Design Size Gross Rated Sensible Heat Ratio | 0.80062 |
| 127 | Coil:Heating:DX:SingleSpeed | ZONE5PTHPDXHEATCOIL | Design Size Rated Air Flow Rate [m3/s] | 0.35596 |
| 128 | Coil:Heating:DX:SingleSpeed | ZONE5PTHPDXHEATCOIL | Design Size Gross Rated Heating Capacity [W] | 6024.04196 |
| 129 | Coil:Heating:DX:SingleSpeed | ZONE5PTHPDXHEATCOIL | Design Size Resistive Defrost Heater Capacity [W] | 6024.04196 |
| 130 | Coil:Heating:DX:SingleSpeed | ZONE5PTHPDXHEATCOIL | User-Specified Resistive Defrost Heater Capacity [W] | 2000.00000 |
| 131 | Fan:ConstantVolume | ZONE5PTHPFAN | Design Size Maximum Flow Rate [m3/s] | 0.35596 |
| 132 | Coil:Heating:Electric | ZONE5PTHPELECHTGBACKUPCOIL | User-Specified Nominal Capacity [W] | 0.00000 |
| 133 | ZoneHVAC:TerminalUnit:VariableRefrigerantFlow | VRF ZONE TERMINAL 4 | Design Size Cooling Supply Air Flow Rate [m3/s] | 0.35596 |
| 134 | ZoneHVAC:TerminalUnit:VariableRefrigerantFlow | VRF ZONE TERMINAL 4 | Design Size Heating Supply Air Flow Rate [m3/s] | 0.35596 |
| 135 | ZoneHVAC:TerminalUnit:VariableRefrigerantFlow | VRF ZONE TERMINAL 4 | Design Size No Cooling Supply Air Flow Rate [m3/s] | 0.35596 |
| 136 | ZoneHVAC:TerminalUnit:VariableRefrigerantFlow | VRF ZONE TERMINAL 4 | Design Size No Heating Supply Air Flow Rate [m3/s] | 0.35596 |
| 137 | ZoneHVAC:TerminalUnit:VariableRefrigerantFlow | VRF ZONE TERMINAL 4 | Design Size Outdoor Air Flow Rate During Cooling Operation [m3/s] | 3.41884E-002 |
| 138 | ZoneHVAC:TerminalUnit:VariableRefrigerantFlow | VRF ZONE TERMINAL 4 | Design Size Outdoor Air Flow Rate During Heating Operation [m3/s] | 3.41884E-002 |
| 139 | ZoneHVAC:TerminalUnit:VariableRefrigerantFlow | VRF ZONE TERMINAL 4 | Design Size Outdoor Air Flow Rate When No Cooling or Heating is Needed [m3/s] | 3.41884E-002 |
| 140 | Coil:Cooling:DX:VariableRefrigerantFlow | VRF ZONE TERMINAL COOLING COIL 4 | Design Size Rated Air Flow Rate [m3/s] | 0.35596 |
| 141 | Coil:Cooling:DX:VariableRefrigerantFlow | VRF ZONE TERMINAL COOLING COIL 4 | Design Size Gross Rated Total Cooling Capacity [W] | 6204.40017 |
| 142 | Coil:Cooling:DX:VariableRefrigerantFlow | VRF ZONE TERMINAL COOLING COIL 4 | Design Size Gross Rated Sensible Heat Ratio | 0.80017 |
| 143 | Coil:Heating:DX:VariableRefrigerantFlow | VRF ZONE TERMINAL HEATING COIL 4 | Design Size Rated Air Flow Rate [m3/s] | 0.35596 |
| 144 | Coil:Heating:DX:VariableRefrigerantFlow | VRF ZONE TERMINAL HEATING COIL 4 | Design Size Gross Rated Heating Capacity [W] | 6204.40017 |
| 145 | Fan:OnOff | VRF ZONE TERMINAL FAN 4 | Design Size Maximum Flow Rate [m3/s] | 0.35596 |
| 146 | AirConditioner:VariableRefrigerantFlow | VRF SYSTEM | Design Size Rated Total Cooling Capacity (gross) [W] | 31391.78493 |
| 147 | AirConditioner:VariableRefrigerantFlow | VRF SYSTEM | Design Size Rated Total Heating Capacity [W] | 31391.78493 |
| 148 | AirConditioner:VariableRefrigerantFlow | VRF SYSTEM | Design Size Resistive Defrost Heater Capacity | 31391.78493 |
| 149 | AirConditioner:VariableRefrigerantFlow | VRF SYSTEM | User-Specified Resistive Defrost Heater Capacity | 1.00000E-007 |
| 150 | AirConditioner:VariableRefrigerantFlow | VRF SYSTEM | Design Size Evaporative Condenser Air Flow Rate [m3/s] | 3.57866 |
| 151 | AirConditioner:VariableRefrigerantFlow | VRF SYSTEM | Design Size Evaporative Condenser Pump Rated Power Consumption [W] | 133.91735 |
| 152 | PlantLoop | MAIN SERVICE WATER LOOP | Maximum Loop Flow Rate [m3/s] | 4.03777E-006 |
| 153 | PlantLoop | MAIN SERVICE WATER LOOP | Plant Loop Volume [m3] | 4.84533E-004 |
| 154 | Pump:ConstantSpeed | SERVICE WATER LOOP PUMP | Design Flow Rate [m3/s] | 4.03777E-006 |
| 155 | Pump:ConstantSpeed | SERVICE WATER LOOP PUMP | Design Power Consumption [W] | 6.27470E-009 |
| 156 | WaterHeater:Mixed | 40.0GAL ELECTRICITY WATER HEATER - 40KBTU/HR 1.0 THERM EFF | Use Side Design Flow Rate [m3/s] | 4.03777E-006 |
| Component Type | Component Name | Standard Rating (Net) Cooling Capacity {W} | Standard Rated Net COP {W/W} | EER {Btu/W-h} | SEER {Btu/W-h} | IEER {Btu/W-h} | |
| 1 | Coil:Cooling:DX:SingleSpeed | ZONE1PTHPDXCOOLCOIL | 6173.6 | 2.61 | 8.90 | 8.98 | 9.09 |
| 2 | Coil:Cooling:DX:SingleSpeed | ZONE2PTHPDXCOOLCOIL | 6575.6 | 2.60 | 8.85 | 8.93 | 9.02 |
| 3 | Coil:Cooling:DX:SingleSpeed | ZONE3PTHPDXCOOLCOIL | 5013.7 | 2.53 | 8.64 | 8.70 | 8.70 |
| 4 | Coil:Cooling:DX:SingleSpeed | ZONE4PTHPDXCOOLCOIL | 5995.1 | 2.58 | 8.82 | 8.89 | 8.97 |
| 5 | Coil:Cooling:DX:SingleSpeed | ZONE5PTHPDXCOOLCOIL | 5763.9 | 2.54 | 8.67 | 8.73 | 8.74 |
| Component Type | Component Name | High Temperature Heating (net) Rating Capacity {W} | Low Temperature Heating (net) Rating Capacity {W} | HSPF {Btu/W-h} | Region Number | |
| 1 | Coil:Heating:DX:SingleSpeed | ZONE1PTHPDXHEATCOIL | 5286.4 | 5108.5 | 12.36 | 4 |
| 2 | Coil:Heating:DX:SingleSpeed | ZONE2PTHPDXHEATCOIL | 5648.1 | 5458.4 | 12.20 | 4 |
| 3 | Coil:Heating:DX:SingleSpeed | ZONE3PTHPDXHEATCOIL | 4370.8 | 4225.1 | 11.86 | 4 |
| 4 | Coil:Heating:DX:SingleSpeed | ZONE4PTHPDXHEATCOIL | 5162.3 | 4989.1 | 12.27 | 4 |
| 5 | Coil:Heating:DX:SingleSpeed | ZONE5PTHPDXHEATCOIL | 5013.3 | 4846.0 | 11.72 | 4 |
| VRF System Type | VRF System Name | VRF System Cooling Combination Ratio | VRF System Heating Combination Ratio | VRF System Cooling Piping Correction Factor | VRF System Heating Piping Correction Factor | |
| 1 | AirConditioner:VariableRefrigerantFlow | VRF SYSTEM | 1.00000 | 1.00000 | 0.94689 | 1.00000 |
| Environment Name | Environment Type | Start Date | End Date | Start DayOfWeek | Duration {#days} | Source:Start DayOfWeek | Use Daylight Saving | Use Holidays | Apply Weekend Holiday Rule | Use Rain Values | Use Snow Values | |
| 1 | RUN PERIOD 1 | WeatherFileRunPeriod | 01/01 | 12/31 | Sunday | 365 | Use RunPeriod Specified Day | No | No | No | Yes | Yes |
| Daylight Saving Indicator | Source | Start Date | End Date | |
| 1 | No | RunPeriod Object |
| NumberofWarmupDays | |
| 1 | 25 |
| Style | Unit Conversion | |
| 1 | HTML | None |
| Zone Name | Environment Type/Name | Average Warmup Temperature Difference {deltaC} | Std Dev Warmup Temperature Difference {deltaC} | Max Temperature Pass/Fail Convergence | Min Temperature Pass/Fail Convergence | Average Warmup Load Difference {W} | Std Dev Warmup Load Difference {W} | Heating Load Pass/Fail Convergence | Cooling Load Pass/Fail Convergence | |
| 1 | ATTIC ZN | RunPeriod: RUN PERIOD 1 | 4.4846522239E-002 | 4.7735939291E-002 | Pass | Pass | 0.0000000000 | 0.0000000000 | Pass | Pass |
| 2 | CORE_ZN ZN | RunPeriod: RUN PERIOD 1 | 1.4353848126E-006 | 3.8692365394E-006 | Pass | Pass | 1.4382382516E-002 | 1.2518606237E-002 | Pass | Pass |
| 3 | PERIMETER_ZN_1 ZN | RunPeriod: RUN PERIOD 1 | 8.2949938292E-002 | 0.1048776329 | Pass | Pass | 1.4901990127 | 3.9645152053 | Fail | Fail |
| 4 | PERIMETER_ZN_2 ZN | RunPeriod: RUN PERIOD 1 | 6.4811454710E-002 | 9.3631177539E-002 | Pass | Pass | 0.8042092446 | 2.6801459414 | Fail | Fail |
| 5 | PERIMETER_ZN_3 ZN | RunPeriod: RUN PERIOD 1 | 7.6528530249E-002 | 9.2360756596E-002 | Pass | Pass | 0.3929637340 | 0.8459882496 | Fail | Fail |
| 6 | PERIMETER_ZN_4 ZN | RunPeriod: RUN PERIOD 1 | 7.1695598488E-002 | 9.1176832059E-002 | Pass | Pass | 1.0099456742 | 3.5682067411 | Fail | Pass |
Report: Climatic Data Summary
For: Entire Facility
Timestamp: 2018-07-11 10:44:46
SizingPeriod:DesignDay| Maximum Dry Bulb [C] | Daily Temperature Range [deltaC] | Humidity Value | Humidity Type | Wind Speed [m/s] | Wind Direction | |
| CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 33.30 | 10.50 | 23.70 | Wetbulb [C] | 5.20 | 230.00 |
| CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | -20.00 | 0.00 | -20.00 | Wetbulb [C] | 4.90 | 270.00 |
| Value | |
| None |
Report: Envelope Summary
For: Entire Facility
Timestamp: 2018-07-11 10:44:46
Opaque Exterior| Construction | Reflectance | U-Factor with Film [W/m2-K] | U-Factor no Film [W/m2-K] | Gross Area [m2] | Net Area [m2] | Azimuth [deg] | Tilt [deg] | Cardinal Direction | |
| ATTIC_SOFFIT_EAST | TYPICAL INSULATED EXTERIOR MASS FLOOR R-11.49 | 0.30 | 0.494 | 0.546 | 11.44 | 11.44 | 45.00 | 180.00 | |
| ATTIC_SOFFIT_NORTH | TYPICAL INSULATED EXTERIOR MASS FLOOR R-11.49 | 0.30 | 0.494 | 0.546 | 16.97 | 16.97 | 0.00 | 180.00 | |
| ATTIC_SOFFIT_SOUTH | TYPICAL INSULATED EXTERIOR MASS FLOOR R-11.49 | 0.30 | 0.494 | 0.546 | 16.97 | 16.97 | 0.00 | 180.00 | |
| ATTIC_SOFFIT_WEST | TYPICAL INSULATED EXTERIOR MASS FLOOR R-11.49 | 0.30 | 0.494 | 0.546 | 11.44 | 11.44 | 270.00 | 180.00 | |
| ATTIC_ROOF_EAST | TYPICAL IEAD ROOF R-15.87 | 0.23 | 0.358 | 0.376 | 101.87 | 101.87 | 90.00 | 18.45 | |
| ATTIC_ROOF_NORTH | TYPICAL IEAD ROOF R-15.87 | 0.23 | 0.358 | 0.376 | 197.51 | 197.51 | 0.00 | 18.45 | |
| ATTIC_ROOF_SOUTH | TYPICAL IEAD ROOF R-15.87 | 0.23 | 0.358 | 0.376 | 197.51 | 197.51 | 180.00 | 18.45 | |
| ATTIC_ROOF_WEST | TYPICAL IEAD ROOF R-15.87 | 0.23 | 0.358 | 0.376 | 101.87 | 101.87 | 270.00 | 18.45 | |
| CORE_ZN_FLOOR | TYPICAL INSULATED CARPETED 6IN SLAB FLOOR | 0.30 | 2.250 | 3.540 | 149.66 | 149.66 | 0.00 | 180.00 | |
| PERIMETER_ZN_1_WALL_SOUTH | TYPICAL INSULATED EXTERIOR MASS WALL R-8.13 | 0.30 | 0.698 | 0.780 | 84.45 | 63.82 | 180.00 | 90.00 | S |
| PERIMETER_ZN_1_FLOOR | TYPICAL INSULATED CARPETED 6IN SLAB FLOOR | 0.30 | 2.250 | 3.540 | 113.45 | 113.45 | 0.00 | 180.00 | |
| PERIMETER_ZN_2_WALL_EAST | TYPICAL INSULATED EXTERIOR MASS WALL R-8.13 | 0.30 | 0.698 | 0.780 | 56.30 | 45.15 | 90.00 | 90.00 | E |
| PERIMETER_ZN_2_FLOOR | TYPICAL INSULATED CARPETED 6IN SLAB FLOOR | 0.30 | 2.250 | 3.540 | 67.30 | 67.30 | 45.00 | 180.00 | |
| PERIMETER_ZN_3_WALL_NORTH | TYPICAL INSULATED EXTERIOR MASS WALL R-8.13 | 0.30 | 0.698 | 0.780 | 84.45 | 67.72 | 0.00 | 90.00 | N |
| PERIMETER_ZN_3_FLOOR | TYPICAL INSULATED CARPETED 6IN SLAB FLOOR | 0.30 | 2.250 | 3.540 | 113.45 | 113.45 | 0.00 | 180.00 | |
| PERIMETER_ZN_4_WALL_WEST | TYPICAL INSULATED EXTERIOR MASS WALL R-8.13 | 0.30 | 0.698 | 0.780 | 56.30 | 45.15 | 270.00 | 90.00 | W |
| PERIMETER_ZN_4_FLOOR | TYPICAL INSULATED CARPETED 6IN SLAB FLOOR | 0.30 | 2.250 | 3.540 | 67.30 | 67.30 | 270.00 | 180.00 |
| Construction | Glass Area [m2] | Frame Area [m2] | Divider Area [m2] | Area of One Opening [m2] | Area of Multiplied Openings [m2] | Glass U-Factor [W/m2-K] | Glass SHGC | Glass Visible Transmittance | Frame Conductance [W/m2-K] | Divider Conductance [W/m2-K] | Shade Control | Parent Surface | Azimuth [deg] | Tilt [deg] | Cardinal Direction | |
| PERIMETER_ZN_1_WALL_SOUTH_WINDOW_1 | U 0.57 SHGC 0.49 DBL BLUE 6MM/6MM AIR | 2.79 | 0.00 | 0.00 | 2.79 | 2.79 | 3.058 | 0.502 | 0.505 | No | PERIMETER_ZN_1_WALL_SOUTH | 180.00 | 90.00 | S | ||
| PERIMETER_ZN_1_WALL_SOUTH_WINDOW_2 | U 0.57 SHGC 0.49 DBL BLUE 6MM/6MM AIR | 2.79 | 0.00 | 0.00 | 2.79 | 2.79 | 3.058 | 0.502 | 0.505 | No | PERIMETER_ZN_1_WALL_SOUTH | 180.00 | 90.00 | S | ||
| PERIMETER_ZN_1_WALL_SOUTH_WINDOW_3 | U 0.57 SHGC 0.49 DBL BLUE 6MM/6MM AIR | 2.79 | 0.00 | 0.00 | 2.79 | 2.79 | 3.058 | 0.502 | 0.505 | No | PERIMETER_ZN_1_WALL_SOUTH | 180.00 | 90.00 | S | ||
| PERIMETER_ZN_1_WALL_SOUTH_WINDOW_4 | U 0.57 SHGC 0.49 DBL BLUE 6MM/6MM AIR | 2.79 | 0.00 | 0.00 | 2.79 | 2.79 | 3.058 | 0.502 | 0.505 | No | PERIMETER_ZN_1_WALL_SOUTH | 180.00 | 90.00 | S | ||
| PERIMETER_ZN_1_WALL_SOUTH_WINDOW_5 | U 0.57 SHGC 0.49 DBL BLUE 6MM/6MM AIR | 2.79 | 0.00 | 0.00 | 2.79 | 2.79 | 3.058 | 0.502 | 0.505 | No | PERIMETER_ZN_1_WALL_SOUTH | 180.00 | 90.00 | S | ||
| PERIMETER_ZN_1_WALL_SOUTH_WINDOW_6 | U 0.57 SHGC 0.49 DBL BLUE 6MM/6MM AIR | 2.79 | 0.00 | 0.00 | 2.79 | 2.79 | 3.058 | 0.502 | 0.505 | No | PERIMETER_ZN_1_WALL_SOUTH | 180.00 | 90.00 | S | ||
| PERIMETER_ZN_2_WALL_EAST_WINDOW_1 | U 0.57 SHGC 0.49 DBL BLUE 6MM/6MM AIR | 2.79 | 0.00 | 0.00 | 2.79 | 2.79 | 3.058 | 0.502 | 0.505 | No | PERIMETER_ZN_2_WALL_EAST | 90.00 | 90.00 | E | ||
| PERIMETER_ZN_2_WALL_EAST_WINDOW_2 | U 0.57 SHGC 0.49 DBL BLUE 6MM/6MM AIR | 2.79 | 0.00 | 0.00 | 2.79 | 2.79 | 3.058 | 0.502 | 0.505 | No | PERIMETER_ZN_2_WALL_EAST | 90.00 | 90.00 | E | ||
| PERIMETER_ZN_2_WALL_EAST_WINDOW_3 | U 0.57 SHGC 0.49 DBL BLUE 6MM/6MM AIR | 2.79 | 0.00 | 0.00 | 2.79 | 2.79 | 3.058 | 0.502 | 0.505 | No | PERIMETER_ZN_2_WALL_EAST | 90.00 | 90.00 | E | ||
| PERIMETER_ZN_2_WALL_EAST_WINDOW_4 | U 0.57 SHGC 0.49 DBL BLUE 6MM/6MM AIR | 2.79 | 0.00 | 0.00 | 2.79 | 2.79 | 3.058 | 0.502 | 0.505 | No | PERIMETER_ZN_2_WALL_EAST | 90.00 | 90.00 | E | ||
| PERIMETER_ZN_3_WALL_NORTH_WINDOW_1 | U 0.57 SHGC 0.49 DBL BLUE 6MM/6MM AIR | 2.79 | 0.00 | 0.00 | 2.79 | 2.79 | 3.058 | 0.502 | 0.505 | No | PERIMETER_ZN_3_WALL_NORTH | 0.00 | 90.00 | N | ||
| PERIMETER_ZN_3_WALL_NORTH_WINDOW_2 | U 0.57 SHGC 0.49 DBL BLUE 6MM/6MM AIR | 2.79 | 0.00 | 0.00 | 2.79 | 2.79 | 3.058 | 0.502 | 0.505 | No | PERIMETER_ZN_3_WALL_NORTH | 0.00 | 90.00 | N | ||
| PERIMETER_ZN_3_WALL_NORTH_WINDOW_3 | U 0.57 SHGC 0.49 DBL BLUE 6MM/6MM AIR | 2.79 | 0.00 | 0.00 | 2.79 | 2.79 | 3.058 | 0.502 | 0.505 | No | PERIMETER_ZN_3_WALL_NORTH | 0.00 | 90.00 | N | ||
| PERIMETER_ZN_3_WALL_NORTH_WINDOW_4 | U 0.57 SHGC 0.49 DBL BLUE 6MM/6MM AIR | 2.79 | 0.00 | 0.00 | 2.79 | 2.79 | 3.058 | 0.502 | 0.505 | No | PERIMETER_ZN_3_WALL_NORTH | 0.00 | 90.00 | N | ||
| PERIMETER_ZN_3_WALL_NORTH_WINDOW_5 | U 0.57 SHGC 0.49 DBL BLUE 6MM/6MM AIR | 2.79 | 0.00 | 0.00 | 2.79 | 2.79 | 3.058 | 0.502 | 0.505 | No | PERIMETER_ZN_3_WALL_NORTH | 0.00 | 90.00 | N | ||
| PERIMETER_ZN_3_WALL_NORTH_WINDOW_6 | U 0.57 SHGC 0.49 DBL BLUE 6MM/6MM AIR | 2.79 | 0.00 | 0.00 | 2.79 | 2.79 | 3.058 | 0.502 | 0.505 | No | PERIMETER_ZN_3_WALL_NORTH | 0.00 | 90.00 | N | ||
| PERIMETER_ZN_4_WALL_WEST_WINDOW_1 | U 0.57 SHGC 0.49 DBL BLUE 6MM/6MM AIR | 2.79 | 0.00 | 0.00 | 2.79 | 2.79 | 3.058 | 0.502 | 0.505 | No | PERIMETER_ZN_4_WALL_WEST | 270.00 | 90.00 | W | ||
| PERIMETER_ZN_4_WALL_WEST_WINDOW_2 | U 0.57 SHGC 0.49 DBL BLUE 6MM/6MM AIR | 2.79 | 0.00 | 0.00 | 2.79 | 2.79 | 3.058 | 0.502 | 0.505 | No | PERIMETER_ZN_4_WALL_WEST | 270.00 | 90.00 | W | ||
| PERIMETER_ZN_4_WALL_WEST_WINDOW_3 | U 0.57 SHGC 0.49 DBL BLUE 6MM/6MM AIR | 2.79 | 0.00 | 0.00 | 2.79 | 2.79 | 3.058 | 0.502 | 0.505 | No | PERIMETER_ZN_4_WALL_WEST | 270.00 | 90.00 | W | ||
| PERIMETER_ZN_4_WALL_WEST_WINDOW_4 | U 0.57 SHGC 0.49 DBL BLUE 6MM/6MM AIR | 2.79 | 0.00 | 0.00 | 2.79 | 2.79 | 3.058 | 0.502 | 0.505 | No | PERIMETER_ZN_4_WALL_WEST | 270.00 | 90.00 | W | ||
| Total or Average | 55.78 | 3.058 | 0.502 | 0.505 | ||||||||||||
| North Total or Average | 16.73 | 3.058 | 0.502 | 0.505 | ||||||||||||
| Non-North Total or Average | 39.04 | 3.058 | 0.502 | 0.505 |
| Construction | Area of One Opening [m2] | Area of Openings [m2] | Glass U-Factor [W/m2-K] | Glass SHGC | Glass Visible Transmittance | Parent Surface | |
| Total or Average | 0.00 | - | - | - |
| Construction | U-Factor with Film [W/m2-K] | U-Factor no Film [W/m2-K] | Gross Area [m2] | Parent Surface | |
| PERIMETER_ZN_1_WALL_SOUTH_DOOR | TYPICAL INSULATED METAL DOOR R-1.43 | 3.975 | 9.814 | 3.91 | PERIMETER_ZN_1_WALL_SOUTH |
Report: Shading Summary
For: Entire Facility
Timestamp: 2018-07-11 10:44:46
Sunlit Fraction| March 21 9am | March 21 noon | March 21 3pm | June 21 9am | June 21 noon | June 21 3pm | December 21 9am | December 21 noon | December 21 3pm | |
| PERIMETER_ZN_1_WALL_SOUTH_WINDOW_1 | 1.00 | 1.00 | 1.00 | 0.00 | 0.26 | 0.00 | 1.00 | 1.00 | 1.00 |
| PERIMETER_ZN_1_WALL_SOUTH_WINDOW_2 | 1.00 | 1.00 | 1.00 | 0.00 | 0.26 | 0.00 | 1.00 | 1.00 | 1.00 |
| PERIMETER_ZN_1_WALL_SOUTH_WINDOW_3 | 1.00 | 1.00 | 1.00 | 0.00 | 0.26 | 0.00 | 1.00 | 1.00 | 1.00 |
| PERIMETER_ZN_1_WALL_SOUTH_WINDOW_4 | 1.00 | 1.00 | 1.00 | 0.00 | 0.26 | 0.00 | 1.00 | 1.00 | 1.00 |
| PERIMETER_ZN_1_WALL_SOUTH_WINDOW_5 | 1.00 | 1.00 | 1.00 | 0.00 | 0.26 | 0.00 | 1.00 | 1.00 | 1.00 |
| PERIMETER_ZN_1_WALL_SOUTH_WINDOW_6 | 1.00 | 1.00 | 1.00 | 0.00 | 0.26 | 0.00 | 1.00 | 1.00 | 1.00 |
| PERIMETER_ZN_2_WALL_EAST_WINDOW_1 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.51 | 0.00 |
| PERIMETER_ZN_2_WALL_EAST_WINDOW_2 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 |
| PERIMETER_ZN_2_WALL_EAST_WINDOW_3 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 |
| PERIMETER_ZN_2_WALL_EAST_WINDOW_4 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 |
| PERIMETER_ZN_3_WALL_NORTH_WINDOW_1 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_ZN_3_WALL_NORTH_WINDOW_2 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_ZN_3_WALL_NORTH_WINDOW_3 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_ZN_3_WALL_NORTH_WINDOW_4 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_ZN_3_WALL_NORTH_WINDOW_5 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_ZN_3_WALL_NORTH_WINDOW_6 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_ZN_4_WALL_WEST_WINDOW_1 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 0.92 | 0.00 | 0.00 | 1.00 |
| PERIMETER_ZN_4_WALL_WEST_WINDOW_2 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 0.92 | 0.00 | 0.00 | 1.00 |
| PERIMETER_ZN_4_WALL_WEST_WINDOW_3 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 0.92 | 0.00 | 0.00 | 1.00 |
| PERIMETER_ZN_4_WALL_WEST_WINDOW_4 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 0.92 | 0.00 | 0.00 | 1.00 |
| Name | Type | Shaded Construction | Control | Glare Control | |
| None |
Report: Lighting Summary
For: Entire Facility
Timestamp: 2018-07-11 10:44:46
Interior Lighting| Zone | Lighting Power Density [W/m2] | Zone Area [m2] | Total Power [W] | End Use Subcategory | Schedule Name | Scheduled Hours/Week [hr] | Hours/Week > 1% [hr] | Full Load Hours/Week [hr] | Return Air Fraction | Conditioned (Y/N) | Consumption [GJ] | |
| CORE_ZN ZN OFFICE WHOLEBUILDING - SM OFFICE LIGHTS | CORE_ZN ZN | 10.7639 | 149.66 | 1610.90 | General | OFFICESMALL BLDG_LIGHT_SCH | 69.93 | 168.00 | 69.93 | 0.0000 | Y | 21.15 |
| PERIMETER_ZN_1 ZN OFFICE WHOLEBUILDING - SM OFFICE LIGHTS | PERIMETER_ZN_1 ZN | 10.7639 | 113.45 | 1221.17 | General | OFFICESMALL BLDG_LIGHT_SCH | 69.93 | 168.00 | 69.93 | 0.0000 | Y | 16.03 |
| PERIMETER_ZN_2 ZN OFFICE WHOLEBUILDING - SM OFFICE LIGHTS | PERIMETER_ZN_2 ZN | 10.7639 | 67.30 | 724.41 | General | OFFICESMALL BLDG_LIGHT_SCH | 69.93 | 168.00 | 69.93 | 0.0000 | Y | 9.51 |
| PERIMETER_ZN_3 ZN OFFICE WHOLEBUILDING - SM OFFICE LIGHTS | PERIMETER_ZN_3 ZN | 10.7639 | 113.45 | 1221.17 | General | OFFICESMALL BLDG_LIGHT_SCH | 69.93 | 168.00 | 69.93 | 0.0000 | Y | 16.03 |
| PERIMETER_ZN_4 ZN OFFICE WHOLEBUILDING - SM OFFICE LIGHTS | PERIMETER_ZN_4 ZN | 10.7639 | 67.30 | 724.41 | General | OFFICESMALL BLDG_LIGHT_SCH | 69.93 | 168.00 | 69.93 | 0.0000 | Y | 9.51 |
| Interior Lighting Total | 10.7639 | 511.16 | 5502.05 | 72.23 |
| Zone | Control Name | Daylighting Method | Control Type | Fraction Controlled | Lighting Installed in Zone [W] | Lighting Controlled [W] | |
| None |
| Total Watts | Astronomical Clock/Schedule | Schedule Name | Scheduled Hours/Week [hr] | Hours/Week > 1% [hr] | Full Load Hours/Week [hr] | Consumption [GJ] | |
| NONDIMMING EXTERIOR LIGHTS DEF | 1634.00 | AstronomicalClock | - | 83.69 | 83.69 | 25.67 | |
| Exterior Lighting Total | 1634.00 | 25.67 |
Report: Equipment Summary
For: Entire Facility
Timestamp: 2018-07-11 10:44:46
Central Plant| Type | Nominal Capacity [W] | Nominal Efficiency [W/W] | IPLV in SI Units [W/W] | IPLV in IP Units [Btu/W-h] | |
| None |
| Type | Design Coil Load [W] | Nominal Total Capacity [W] | Nominal Sensible Capacity [W] | Nominal Latent Capacity [W] | Nominal Sensible Heat Ratio | Nominal Efficiency [W/W] | Nominal Coil UA Value [W/C] | Nominal Coil Surface Area [m2] | |
| ZONE1PTHPDXCOOLCOIL | Coil:Cooling:DX:SingleSpeed | 6405.66 | 4951.31 | 1454.35 | 0.77 | 3.00 | |||
| ZONE2PTHPDXCOOLCOIL | Coil:Cooling:DX:SingleSpeed | 6832.55 | 5382.94 | 1449.61 | 0.79 | 3.00 | |||
| ZONE3PTHPDXCOOLCOIL | Coil:Cooling:DX:SingleSpeed | 5245.52 | 4199.85 | 1045.67 | 0.80 | 3.00 | |||
| ZONE4PTHPDXCOOLCOIL | Coil:Cooling:DX:SingleSpeed | 6236.55 | 4979.84 | 1256.71 | 0.80 | 3.00 | |||
| ZONE5PTHPDXCOOLCOIL | Coil:Cooling:DX:SingleSpeed | 6024.04 | 4822.97 | 1201.07 | 0.80 | 3.00 |
| DX Cooling Coil Type | Standard Rated Net Cooling Capacity [W] | Standard Rated Net COP [W/W] | EER [Btu/W-h] | SEER [Btu/W-h] | IEER [Btu/W-h] | |
| ZONE1PTHPDXCOOLCOIL | 6173.6 | 2.61 | 8.90 | 8.98 | 9.09 | |
| ZONE2PTHPDXCOOLCOIL | 6575.6 | 2.60 | 8.85 | 8.93 | 9.02 | |
| ZONE3PTHPDXCOOLCOIL | 5013.7 | 2.53 | 8.64 | 8.70 | 8.70 | |
| ZONE4PTHPDXCOOLCOIL | 5995.1 | 2.58 | 8.82 | 8.89 | 8.97 | |
| ZONE5PTHPDXCOOLCOIL | 5763.9 | 2.54 | 8.67 | 8.73 | 8.74 |
| DX Cooling Coil Type | Rated Net Cooling Capacity Test A [W] | Rated Electric Power Test A [W] | Rated Net Cooling Capacity Test B [W] | Rated Electric Power Test B [W] | Rated Net Cooling Capacity Test C [W] | Rated Electric Power Test C [W] | Rated Net Cooling Capacity Test D [W] | Rated Electric Power Test D [W] | |
| ZONE1PTHPDXCOOLCOIL | Coil:Cooling:DX:SingleSpeed | ||||||||
| ZONE2PTHPDXCOOLCOIL | Coil:Cooling:DX:SingleSpeed | ||||||||
| ZONE3PTHPDXCOOLCOIL | Coil:Cooling:DX:SingleSpeed | ||||||||
| ZONE4PTHPDXCOOLCOIL | Coil:Cooling:DX:SingleSpeed | ||||||||
| ZONE5PTHPDXCOOLCOIL | Coil:Cooling:DX:SingleSpeed |
| DX Heating Coil Type | High Temperature Heating (net) Rating Capacity [W] | Low Temperature Heating (net) Rating Capacity [W] | HSPF [Btu/W-h] | Region Number | |
| ZONE1PTHPDXHEATCOIL | Coil:Heating:DX:SingleSpeed | 5286.4 | 5108.5 | 12.36 | 4 |
| ZONE2PTHPDXHEATCOIL | Coil:Heating:DX:SingleSpeed | 5648.1 | 5458.4 | 12.20 | 4 |
| ZONE3PTHPDXHEATCOIL | Coil:Heating:DX:SingleSpeed | 4370.8 | 4225.1 | 11.86 | 4 |
| ZONE4PTHPDXHEATCOIL | Coil:Heating:DX:SingleSpeed | 5162.3 | 4989.1 | 12.27 | 4 |
| ZONE5PTHPDXHEATCOIL | Coil:Heating:DX:SingleSpeed | 5013.3 | 4846.0 | 11.72 | 4 |
| Type | Design Coil Load [W] | Nominal Total Capacity [W] | Nominal Efficiency [W/W] | |
| ZONE1PTHPDXHEATCOIL | Coil:Heating:DX:SingleSpeed | 6405.66 | 5.00 | |
| ZONE1PTHPELECHTGBACKUPCOIL | Coil:Heating:Electric | 0.00 | 1.00 | |
| ZONE2PTHPDXHEATCOIL | Coil:Heating:DX:SingleSpeed | 6832.55 | 5.00 | |
| ZONE2PTHPELECHTGBACKUPCOIL | Coil:Heating:Electric | 0.00 | 1.00 | |
| ZONE3PTHPDXHEATCOIL | Coil:Heating:DX:SingleSpeed | 5245.52 | 5.00 | |
| ZONE3PTHPELECHTGBACKUPCOIL | Coil:Heating:Electric | 0.00 | 1.00 | |
| ZONE4PTHPDXHEATCOIL | Coil:Heating:DX:SingleSpeed | 6236.55 | 5.00 | |
| ZONE4PTHPELECHTGBACKUPCOIL | Coil:Heating:Electric | 0.00 | 1.00 | |
| ZONE5PTHPDXHEATCOIL | Coil:Heating:DX:SingleSpeed | 6024.04 | 5.00 | |
| ZONE5PTHPELECHTGBACKUPCOIL | Coil:Heating:Electric | 0.00 | 1.00 |
| Type | Total Efficiency [W/W] | Delta Pressure [pa] | Max Air Flow Rate [m3/s] | Rated Electric Power [W] | Rated Power Per Max Air Flow Rate [W-s/m3] | Motor Heat In Air Fraction | End Use | Design Day Name for Fan Sizing Peak | Date/Time for Fan Sizing Peak | |
| ZONE1PTHPFAN | Fan:ConstantVolume | 0.70 | 250.00 | 0.32 | 114.63 | 357.14 | 1.00 | General | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | test 1/2 00:00:00 |
| VRF ZONE TERMINAL FAN | Fan:OnOff | 0.60 | 300.00 | 0.32 | 160.49 | 500.00 | 1.00 | General | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | test 1/2 00:00:00 |
| ZONE1PTHPFAN 3 | Fan:ConstantVolume | 0.70 | 250.00 | 0.35 | 126.64 | 357.14 | 1.00 | General | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | test 1/2 00:00:00 |
| VRF ZONE TERMINAL FAN 1 | Fan:OnOff | 0.60 | 300.00 | 0.35 | 177.29 | 500.00 | 1.00 | General | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | test 1/2 00:00:00 |
| ZONE3PTHPFAN | Fan:ConstantVolume | 0.70 | 250.00 | 0.32 | 113.17 | 357.14 | 1.00 | General | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | test 1/2 00:00:00 |
| VRF ZONE TERMINAL FAN 2 | Fan:OnOff | 0.60 | 300.00 | 0.32 | 158.44 | 500.00 | 1.00 | General | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | test 1/2 00:00:00 |
| ZONE4PTHPFAN | Fan:ConstantVolume | 0.70 | 250.00 | 0.33 | 118.76 | 357.14 | 1.00 | General | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | test 1/2 00:00:00 |
| VRF ZONE TERMINAL FAN 3 | Fan:OnOff | 0.60 | 300.00 | 0.33 | 166.26 | 500.00 | 1.00 | General | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | test 1/2 00:00:00 |
| ZONE5PTHPFAN | Fan:ConstantVolume | 0.70 | 250.00 | 0.36 | 127.13 | 357.14 | 1.00 | General | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | test 1/2 00:00:00 |
| VRF ZONE TERMINAL FAN 4 | Fan:OnOff | 0.60 | 300.00 | 0.36 | 177.98 | 500.00 | 1.00 | General | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | test 1/2 00:00:00 |
| Type | Control | Head [pa] | Water Flow [m3/s] | Electric Power [W] | Power Per Water Flow Rate [W-s/m3] | Motor Efficiency [W/W] | |
| SERVICE WATER LOOP PUMP | Pump:ConstantSpeed | Intermittent | 0.00 | 0.000004 | 0.00 | 0.00 | 0.82 |
| Type | Storage Volume [m3] | Input [W] | Thermal Efficiency [W/W] | Recovery Efficiency [W/W] | Energy Factor | |
| 40.0GAL ELECTRICITY WATER HEATER - 40KBTU/HR 1.0 THERM EFF | WaterHeater:Mixed | 0.15 | 11722.84 | 1.00 | 0.99 | 0.51 |
Report: HVAC Sizing Summary
For: Entire Facility
Timestamp: 2018-07-11 10:44:46
Zone Sensible Cooling| Calculated Design Load [W] | User Design Load [W] | User Design Load per Area [W/m2] | Calculated Design Air Flow [m3/s] | User Design Air Flow [m3/s] | Design Day Name | Date/Time Of Peak {TIMESTAMP} | Thermostat Setpoint Temperature at Peak Load [C] | Indoor Temperature at Peak Load [C] | Indoor Humidity Ratio at Peak Load [kgWater/kgAir] | Outdoor Temperature at Peak Load [C] | Outdoor Humidity Ratio at Peak Load [kgWater/kgAir] | Minimum Outdoor Air Flow Rate [m3/s] | Heat Gain Rate from DOAS [W] | |
| CORE_ZN ZN | 3559.67 | 4271.61 | 28.54 | 0.267 | 0.321 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 18:50:00 | 23.89 | 23.89 | 0.00906 | 29.47 | 0.01496 | 0.076 | 0.00 |
| PERIMETER_ZN_1 ZN | 3932.25 | 4718.70 | 41.59 | 0.295 | 0.355 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 13:30:00 | 23.89 | 23.89 | 0.00901 | 33.04 | 0.01496 | 0.058 | 0.00 |
| PERIMETER_ZN_2 ZN | 3514.18 | 4217.02 | 62.66 | 0.264 | 0.317 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 08:50:00 | 23.89 | 23.89 | 0.00885 | 27.19 | 0.01496 | 0.034 | 0.00 |
| PERIMETER_ZN_3 ZN | 3687.60 | 4425.12 | 39.01 | 0.277 | 0.333 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 18:30:00 | 23.89 | 23.89 | 0.00903 | 29.99 | 0.01496 | 0.058 | 0.00 |
| PERIMETER_ZN_4 ZN | 3947.57 | 4737.09 | 70.39 | 0.297 | 0.356 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 17:00:00 | 23.89 | 23.89 | 0.00881 | 31.83 | 0.01496 | 0.034 | 0.00 |
| Calculated Design Load [W] | User Design Load [W] | User Design Load per Area [W/m2] | Calculated Design Air Flow [m3/s] | User Design Air Flow [m3/s] | Design Day Name | Date/Time Of Peak {TIMESTAMP} | Thermostat Setpoint Temperature at Peak Load [C] | Indoor Temperature at Peak Load [C] | Indoor Humidity Ratio at Peak Load [kgWater/kgAir] | Outdoor Temperature at Peak Load [C] | Outdoor Humidity Ratio at Peak Load [kgWater/kgAir] | Minimum Outdoor Air Flow Rate [m3/s] | Heat Gain Rate from DOAS [W] | |
| CORE_ZN ZN | 3059.27 | 3671.12 | 24.53 | 0.135 | 0.162 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 21.11 | 21.11 | 0.00800 | -20.00 | 0.00065 | 0.076 | 0.00 |
| PERIMETER_ZN_1 ZN | 6500.88 | 7801.05 | 68.76 | 0.287 | 0.344 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | 21.11 | 21.11 | 0.00735 | -20.00 | 0.00065 | 0.058 | 0.00 |
| PERIMETER_ZN_2 ZN | 3920.76 | 4704.91 | 69.91 | 0.173 | 0.208 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | 21.11 | 21.11 | 0.00732 | -20.00 | 0.00065 | 0.034 | 0.00 |
| PERIMETER_ZN_3 ZN | 6100.05 | 7320.06 | 64.52 | 0.269 | 0.323 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | 21.11 | 21.11 | 0.00734 | -20.00 | 0.00065 | 0.058 | 0.00 |
| PERIMETER_ZN_4 ZN | 3955.11 | 4746.13 | 70.52 | 0.175 | 0.210 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | 21.11 | 21.11 | 0.00732 | -20.00 | 0.00065 | 0.034 | 0.00 |
| Calculated cooling [m3/s] | User cooling [m3/s] | Calculated heating [m3/s] | User heating [m3/s] | Adjusted cooling [m3/s] | Adjusted heating [m3/s] | Adjusted main [m3/s] | Calculated Heating Air Flow Ratio [] | User Heating Air Flow Ratio [] | |
| None |
| Previous Design Volume Flow Rate [m3/s] | Algorithm Volume Flow Rate [m3/s] | Coincident Design Volume Flow Rate [m3/s] | Coincident Size Adjusted | Peak Sizing Period Name | Peak Day into Period {TIMESTAMP}[day] | Peak Hour Of Day {TIMESTAMP}[hr] | Peak Step Start Minute {TIMESTAMP}[min] | |
| None |
| Coil Type | HVAC Type | HVAC Name | Coil Final Gross Total Capacity [W] | Coil Final Gross Sensible Capacity [W] | Coil Final Reference Air Volume Flow Rate [m3/s] | Coil Final Reference Plant Fluid Volume Flow Rate [m3/s] | Coil U-value Times Area Value [W/K] | Design Day Name at Sensible Ideal Loads Peak | Date/Time at Sensible Ideal Loads Peak | Design Day Name at Air Flow Ideal Loads Peak | Date/Time at Air Flow Ideal Loads Peak | Coil Total Capacity at Ideal Loads Peak [W] | Coil Sensible Capacity at Ideal Loads Peak [W] | Coil Air Volume Flow Rate at Ideal Loads Peak [m3/s] | Coil Entering Air Drybulb at Ideal Loads Peak [C] | Coil Entering Air Wetbulb at Ideal Loads Peak [C] | Coil Entering Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Coil Leaving Air Drybulb at Ideal Loads Peak [C] | Coil Leaving Air Wetbulb at Ideal Loads Peak [C] | Coil Leaving Air Humidity Ratio at Ideal Loads Peak [C] | Outdoor Air Drybulb at Ideal Loads Peak [C] | Outdoor Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Outdoor Air Wetbulb at Ideal Loads Peak [C] | Outdoor Air Flow Percentage at Ideal Loads Peak [%] | Zone Air Drybulb at Ideal Loads Peak [C] | Zone Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Zone Air Relative Humidity at Ideal Loads Peak [%] | Zone Sensible Heat Gain at Ideal Loads Peak [W] | Zone Latent Heat Gain at Ideal Loads Peak [W] | Coil Total Capacity at Rating Conditions [W] | Coil Sensible Capacity at Rating Conditions [W] | |
| ZONE1PTHPDXCOOLCOIL | COIL:COOLING:DX:SINGLESPEED | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE1PTHP or VRF ZONE TERMINAL | 6405.662 | 4951.313 | 0.320977 | -999.0 | -999.000 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 18:50:00 | unknown | 7/21 18:50:00 | 6370.41 | 4717.85 | 0.320977 | 25.21 | 18.15 | 0.01046033 | 12.80 | 11.88 | 0.00850000 | 29.47 | 0.01496114 | 22.67 | 23.6858 | 23.89 | 0.00906340 | 47.9201 | 4271.61 | 0.00 | 6421.79 | 4920.49 |
| ZONE1PTHPDXHEATCOIL | COIL:HEATING:DX:SINGLESPEED | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE1PTHP or VRF ZONE TERMINAL | 6405.662 | 6405.662 | 0.320977 | -999.0 | -999.000 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 6405.66 | 6405.66 | 0.320977 | 1.83 | 1.83 | 0.00455227 | 40.00 | 20.87 | 0.00800000 | -20.00 | 0.00064986 | -20.00 | 23.6858 | 21.11 | 0.00800000 | 50.1625 | 3671.12 | 0.00 | 5038.19 | 5038.19 |
| ZONE1PTHPELECHTGBACKUPCOIL | COIL:HEATING:ELECTRIC | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE1PTHP or VRF ZONE TERMINAL | 0.000 | 0.000 | -999.0 | -999.0 | -999.000 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 0.00 | 0.00 | 0.162078 | 1.83 | 1.83 | 0.00455227 | 40.00 | 20.87 | 0.00800000 | -20.00 | 0.00064986 | -20.00 | 46.9070 | 21.11 | 0.00800000 | 50.1625 | 3671.12 | 0.00 | -999.00 | -999.00 |
| ZONE2PTHPDXCOOLCOIL | COIL:COOLING:DX:SINGLESPEED | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE2PTHP or VRF ZONE TERMINAL 1 | 6832.548 | 5382.941 | 0.354581 | -999.0 | -999.000 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 13:30:00 | unknown | 7/21 13:30:00 | 6982.19 | 5539.80 | 0.354581 | 25.38 | 17.82 | 0.00997423 | 12.80 | 11.88 | 0.00850000 | 33.04 | 0.01496113 | 23.63 | 16.2537 | 23.89 | 0.00900636 | 47.6236 | 4718.70 | 0.00 | 6849.75 | 5347.69 |
| ZONE2PTHPDXHEATCOIL | COIL:HEATING:DX:SINGLESPEED | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE2PTHP or VRF ZONE TERMINAL 1 | 6832.548 | 6832.548 | 0.354581 | -999.0 | -999.000 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | 6832.55 | 6832.55 | 0.354581 | 14.23 | 10.15 | 0.00623058 | 40.00 | 20.87 | 0.00800000 | -20.00 | 0.00064986 | -20.00 | 16.2537 | 21.11 | 0.00735233 | 46.1576 | 7801.05 | 0.00 | 5373.94 | 5373.94 |
| ZONE2PTHPELECHTGBACKUPCOIL | COIL:HEATING:ELECTRIC | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE2PTHP or VRF ZONE TERMINAL 1 | 0.000 | 0.000 | -999.0 | -999.0 | -999.000 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | 0.00 | 0.00 | 0.344357 | 14.23 | 10.15 | 0.00623058 | 40.00 | 20.87 | 0.00800000 | -20.00 | 0.00064986 | -20.00 | 16.7363 | 21.11 | 0.00735233 | 46.1576 | 7801.05 | 0.00 | -999.00 | -999.00 |
| ZONE3PTHPDXCOOLCOIL | COIL:COOLING:DX:SINGLESPEED | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE3PTHP or VRF ZONE TERMINAL 2 | 5245.515 | 4199.849 | 0.316882 | -999.0 | -999.000 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 08:50:00 | unknown | 7/21 08:50:00 | 5293.28 | 4437.43 | 0.316882 | 24.24 | 17.06 | 0.00950554 | 12.80 | 11.88 | 0.00850000 | 27.19 | 0.01496113 | 22.04 | 10.7890 | 23.89 | 0.00884575 | 46.7860 | 4217.02 | 0.00 | 5258.72 | 4170.45 |
| ZONE3PTHPDXHEATCOIL | COIL:HEATING:DX:SINGLESPEED | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE3PTHP or VRF ZONE TERMINAL 2 | 5245.515 | 5245.515 | 0.316882 | -999.0 | -999.000 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | 5245.52 | 5245.52 | 0.316882 | 14.34 | 10.19 | 0.00622123 | 40.00 | 20.87 | 0.00800000 | -20.00 | 0.00064986 | -20.00 | 10.7890 | 21.11 | 0.00731910 | 45.9518 | 4704.91 | 0.00 | 4125.71 | 4125.71 |
| ZONE3PTHPELECHTGBACKUPCOIL | COIL:HEATING:ELECTRIC | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE3PTHP or VRF ZONE TERMINAL 2 | 0.000 | 0.000 | -999.0 | -999.0 | -999.000 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | 0.00 | 0.00 | 0.207684 | 14.34 | 10.19 | 0.00622123 | 40.00 | 20.87 | 0.00800000 | -20.00 | 0.00064986 | -20.00 | 16.4618 | 21.11 | 0.00731910 | 45.9518 | 4704.91 | 0.00 | -999.00 | -999.00 |
| ZONE4PTHPDXCOOLCOIL | COIL:COOLING:DX:SINGLESPEED | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE4PTHP or VRF ZONE TERMINAL 3 | 6236.548 | 4979.841 | 0.332520 | -999.0 | -999.000 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 18:30:00 | unknown | 7/21 18:30:00 | 6277.21 | 4887.61 | 0.332520 | 24.95 | 17.75 | 0.01006141 | 12.80 | 11.88 | 0.00850000 | 29.99 | 0.01496113 | 22.81 | 17.3321 | 23.89 | 0.00903414 | 47.7683 | 4425.12 | 0.00 | 6252.25 | 4945.27 |
| ZONE4PTHPDXHEATCOIL | COIL:HEATING:DX:SINGLESPEED | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE4PTHP or VRF ZONE TERMINAL 3 | 6236.548 | 6236.548 | 0.332520 | -999.0 | -999.000 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | 6236.55 | 6236.55 | 0.332520 | 13.78 | 9.86 | 0.00614787 | 40.00 | 20.87 | 0.00800000 | -20.00 | 0.00064986 | -20.00 | 17.3321 | 21.11 | 0.00734136 | 46.0892 | 7320.06 | 0.00 | 4905.17 | 4905.17 |
| ZONE4PTHPELECHTGBACKUPCOIL | COIL:HEATING:ELECTRIC | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE4PTHP or VRF ZONE TERMINAL 3 | 0.000 | 0.000 | -999.0 | -999.0 | -999.000 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | 0.00 | 0.00 | 0.323126 | 13.78 | 9.86 | 0.00614787 | 40.00 | 20.87 | 0.00800000 | -20.00 | 0.00064986 | -20.00 | 17.8359 | 21.11 | 0.00734136 | 46.0892 | 7320.06 | 0.00 | -999.00 | -999.00 |
| ZONE5PTHPDXCOOLCOIL | COIL:COOLING:DX:SINGLESPEED | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE5PTHP or VRF ZONE TERMINAL 4 | 6024.042 | 4822.968 | 0.355959 | -999.0 | -999.000 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 17:00:00 | unknown | 7/21 17:00:00 | 6216.52 | 5327.03 | 0.355959 | 24.65 | 17.11 | 0.00939748 | 12.80 | 11.88 | 0.00850000 | 31.83 | 0.01496113 | 23.31 | 9.6046 | 23.89 | 0.00880633 | 46.5803 | 4737.09 | 0.00 | 6039.21 | 4789.94 |
| ZONE5PTHPDXHEATCOIL | COIL:HEATING:DX:SINGLESPEED | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE5PTHP or VRF ZONE TERMINAL 4 | 6024.042 | 6024.042 | 0.355959 | -999.0 | -999.000 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | 6024.04 | 6024.04 | 0.355959 | 14.40 | 10.23 | 0.00623526 | 40.00 | 20.87 | 0.00800000 | -20.00 | 0.00064986 | -20.00 | 9.6046 | 21.11 | 0.00732447 | 45.9852 | 4746.13 | 0.00 | 4738.03 | 4738.03 |
| ZONE5PTHPELECHTGBACKUPCOIL | COIL:HEATING:ELECTRIC | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE5PTHP or VRF ZONE TERMINAL 4 | 0.000 | 0.000 | -999.0 | -999.0 | -999.000 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | 0.00 | 0.00 | 0.209504 | 14.40 | 10.23 | 0.00623526 | 40.00 | 20.87 | 0.00800000 | -20.00 | 0.00064986 | -20.00 | 16.3188 | 21.11 | 0.00732447 | 45.9852 | 4746.13 | 0.00 | -999.00 | -999.00 |
| VRF ZONE TERMINAL COOLING COIL | Coil:Cooling:DX:VariableRefrigerantFlow | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE1PTHP or VRF ZONE TERMINAL | 6497.327 | 4987.715 | 0.320977 | -999.0 | -999.000 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 18:50:00 | unknown | 7/21 18:50:00 | 6554.03 | 4853.84 | 0.320977 | 25.21 | 18.15 | 0.01046033 | 12.80 | 11.88 | 0.00850000 | 29.47 | 0.01496114 | 22.67 | 23.6858 | 23.89 | 0.00906340 | 47.9201 | 4271.61 | 0.00 | 6480.72 | 4944.12 |
| VRF ZONE TERMINAL HEATING COIL | Coil:Heating:DX:VariableRefrigerantFlow | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE1PTHP or VRF ZONE TERMINAL | 6497.327 | 0.000 | 0.320977 | -999.0 | -999.000 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 6497.33 | 6497.33 | 0.320977 | 1.83 | 1.83 | 0.00455227 | 40.00 | 20.87 | 0.00800000 | -20.00 | 0.00064986 | -20.00 | 23.6858 | 21.11 | 0.00800000 | 50.1625 | 3671.12 | 0.00 | 6400.05 | 6400.05 |
| VRF ZONE TERMINAL COOLING COIL 1 | Coil:Cooling:DX:VariableRefrigerantFlow | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE2PTHP or VRF ZONE TERMINAL 1 | 6979.867 | 5438.516 | 0.354581 | -999.0 | -999.000 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 13:30:00 | unknown | 7/21 13:30:00 | 7286.53 | 5781.26 | 0.354581 | 25.38 | 17.82 | 0.00997423 | 12.80 | 11.88 | 0.00850000 | 33.04 | 0.01496113 | 23.63 | 16.2537 | 23.89 | 0.00900636 | 47.6236 | 4718.70 | 0.00 | 6962.02 | 5390.43 |
| VRF ZONE TERMINAL HEATING COIL 1 | Coil:Heating:DX:VariableRefrigerantFlow | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE2PTHP or VRF ZONE TERMINAL 1 | 6979.867 | 0.000 | 0.354581 | -999.0 | -999.000 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | 6979.87 | 6979.87 | 0.354581 | 14.23 | 10.15 | 0.00623058 | 40.00 | 20.87 | 0.00800000 | -20.00 | 0.00064986 | -20.00 | 16.2537 | 21.11 | 0.00735233 | 46.1576 | 7801.05 | 0.00 | 6875.37 | 6875.37 |
| VRF ZONE TERMINAL COOLING COIL 2 | Coil:Cooling:DX:VariableRefrigerantFlow | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE3PTHP or VRF ZONE TERMINAL 2 | 5348.205 | 4281.751 | 0.316882 | -999.0 | -999.000 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 08:50:00 | unknown | 7/21 08:50:00 | 5551.72 | 4654.08 | 0.316882 | 24.24 | 17.06 | 0.00950554 | 12.80 | 11.88 | 0.00850000 | 27.19 | 0.01496113 | 22.04 | 10.7890 | 23.89 | 0.00884575 | 46.7860 | 4217.02 | 0.00 | 5334.53 | 4242.14 |
| VRF ZONE TERMINAL HEATING COIL 2 | Coil:Heating:DX:VariableRefrigerantFlow | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE3PTHP or VRF ZONE TERMINAL 2 | 5348.205 | 0.000 | 0.316882 | -999.0 | -999.000 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | 5348.20 | 5348.20 | 0.316882 | 14.34 | 10.19 | 0.00622123 | 40.00 | 20.87 | 0.00800000 | -20.00 | 0.00064986 | -20.00 | 10.7890 | 21.11 | 0.00731910 | 45.9518 | 4704.91 | 0.00 | 5268.13 | 5268.13 |
| VRF ZONE TERMINAL COOLING COIL 3 | Coil:Cooling:DX:VariableRefrigerantFlow | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE4PTHP or VRF ZONE TERMINAL 3 | 6361.987 | 5026.575 | 0.332520 | -999.0 | -999.000 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 18:30:00 | unknown | 7/21 18:30:00 | 6532.26 | 5086.20 | 0.332520 | 24.95 | 17.75 | 0.01006141 | 12.80 | 11.88 | 0.00850000 | 29.99 | 0.01496113 | 22.81 | 17.3321 | 23.89 | 0.00903414 | 47.7683 | 4425.12 | 0.00 | 6345.72 | 4980.54 |
| VRF ZONE TERMINAL HEATING COIL 3 | Coil:Heating:DX:VariableRefrigerantFlow | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE4PTHP or VRF ZONE TERMINAL 3 | 6361.987 | 0.000 | 0.332520 | -999.0 | -999.000 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | 6361.99 | 6361.99 | 0.332520 | 13.78 | 9.86 | 0.00614787 | 40.00 | 20.87 | 0.00800000 | -20.00 | 0.00064986 | -20.00 | 17.3321 | 21.11 | 0.00734136 | 46.0892 | 7320.06 | 0.00 | 6266.74 | 6266.74 |
| VRF ZONE TERMINAL COOLING COIL 4 | Coil:Cooling:DX:VariableRefrigerantFlow | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE5PTHP or VRF ZONE TERMINAL 4 | 6204.400 | 4964.550 | 0.355959 | -999.0 | -999.000 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 17:00:00 | unknown | 7/21 17:00:00 | 6594.34 | 5650.78 | 0.355959 | 24.65 | 17.11 | 0.00939748 | 12.80 | 11.88 | 0.00850000 | 31.83 | 0.01496113 | 23.31 | 9.6046 | 23.89 | 0.00880633 | 46.5803 | 4737.09 | 0.00 | 6188.54 | 4918.56 |
| VRF ZONE TERMINAL HEATING COIL 4 | Coil:Heating:DX:VariableRefrigerantFlow | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE5PTHP or VRF ZONE TERMINAL 4 | 6204.400 | 0.000 | 0.355959 | -999.0 | -999.000 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | 6204.40 | 6204.40 | 0.355959 | 14.40 | 10.23 | 0.00623526 | 40.00 | 20.87 | 0.00800000 | -20.00 | 0.00064986 | -20.00 | 9.6046 | 21.11 | 0.00732447 | 45.9852 | 4746.13 | 0.00 | 6111.51 | 6111.51 |
Report: Coil Sizing Details
For: Entire Facility
Timestamp: 2018-07-11 10:44:46
Coils| Coil Type | Coil Location | HVAC Type | HVAC Name | Zone Name(s) | System Sizing Method Concurrence | System Sizing Method Capacity | System Sizing Method Air Flow | Autosized Coil Capacity? | Autosized Coil Airflow? | Autosized Coil Water Flow? | OA Pretreated prior to coil inlet? | Coil Final Gross Total Capacity [W] | Coil Final Gross Sensible Capacity [W] | Coil Final Reference Air Volume Flow Rate [m3/s] | Coil Final Reference Plant Fluid Volume Flow Rate [m3/s] | Coil U-value Times Area Value [W/K] | Terminal Unit Reheat Coil Multiplier | DX Coil Capacity Increase Ratio from Too Low Flow/Capacity Ratio | DX Coil Capacity Decrease Ratio from Too High Flow/Capacity Ratio | Moist Air Heat Capacity [J/kg-K] | Dry Air Heat Capacity [J/kg-K] | Standard Air Density Adjusted for Elevation [kg/m3] | Supply Fan Name for Coil | Supply Fan Type for Coil | Supply Fan Maximum Air Volume Flow Rate [m3/s] | Supply Fan Maximum Air Mass Flow Rate [kg/s] | Plant Name for Coil | Plant Fluid Specific Heat Capacity [J/kg-K] | Plant Fluid Density [kg/m3] | Plant Maximum Fluid Mass Flow Rate [kg/s] | Plant Design Fluid Return Temperature [C] | Plant Design Fluid Supply Temperature [C] | Plant Design Fluid Temperature Difference [deltaC] | Plant Design Capacity [W] | Coil Capacity Percentage of Plant Design Capacity [%] | Coil Fluid Flow Rate Percentage of Plant Design Flow Rate [%] | Design Day Name at Sensible Ideal Loads Peak | Date/Time at Sensible Ideal Loads Peak | Design Day Name at Total Ideal Loads Peak | Date/Time at Total Ideal Loads Peak | Design Day Name at Air Flow Ideal Loads Peak | Date/Time at Air Flow Ideal Loads Peak | Coil Total Capacity at Ideal Loads Peak [W] | Coil Sensible Capacity at Ideal Loads Peak [W] | Coil Off-Rating Capacity Modifier at Ideal Loads Peak [ ] | Coil Air Mass Flow Rate at Ideal Loads Peak [kg/s] | Coil Air Volume Flow Rate at Ideal Loads Peak [m3/s] | Coil Entering Air Drybulb at Ideal Loads Peak [C] | Coil Entering Air Wetbulb at Ideal Loads Peak [C] | Coil Entering Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Coil Entering Air Enthalpy at Ideal Loads Peak [J/KG-K] | Coil Leaving Air Drybulb at Ideal Loads Peak [C] | Coil Leaving Air Wetbulb at Ideal Loads Peak [C] | Coil Leaving Air Humidity Ratio at Ideal Loads Peak [C] | Coil Leaving Air Enthalpy at Ideal Loads Peak [J/KG-K] | Coil Plant Fluid Mass Flow Rate at Ideal Loads Peak [kg/s] | Coil Entering Plant Fluid Temperature at Ideal Loads Peak [C] | Coil Leaving Plant Fluid Temperature at Ideal Loads Peak [C] | Coil Plant Fluid Temperature Difference at Ideal Loads Peak [deltaC] | Supply Fan Air Heat Gain at Ideal Loads Peak [W] | Coil and Fan Net Total Capacity at Ideal Loads Peak [W] | Outdoor Air Drybulb at Ideal Loads Peak [C] | Outdoor Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Outdoor Air Wetbulb at Ideal Loads Peak [C] | Outdoor Air Volume Flow Rate at Ideal Loads Peak [m3/s] | Outdoor Air Flow Percentage at Ideal Loads Peak [%] | System Return Air Drybulb at Ideal Loads Peak [C] | System Return Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Zone Air Drybulb at Ideal Loads Peak [C] | Zone Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Zone Air Relative Humidity at Ideal Loads Peak [%] | Zone Sensible Heat Gain at Ideal Loads Peak [W] | Zone Latent Heat Gain at Ideal Loads Peak [W] | Coil Total Capacity at Rating Conditions [W] | Coil Sensible Capacity at Rating Conditions [W] | Coil Air Mass Flow Rate at Rating Conditions [kg/s] | Coil Entering Air Drybulb at Rating Conditions [C] | Coil Entering Air Wetbulb at Rating Conditions [C] | Coil Entering Air Humidity Ratio at Rating Conditions [KGWATER/KGDRYAIR] | Coil Entering Air Enthalpy at Rating Conditions [J/KG-K] | Coil Leaving Air Drybulb at Rating Conditions [C] | Coil Leaving Air Wetbulb at Rating Conditions [C] | Coil Leaving Air Humidity Ratio at Rating Conditions [KGWATER/KGDRYAIR] | Coil Leaving Air Enthalpy at Rating Conditions [J/KG-K] | |
| ZONE1PTHPDXCOOLCOIL | COIL:COOLING:DX:SINGLESPEED | Zone Equipment | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE1PTHP or VRF ZONE TERMINAL | N/A | N/A | N/A | N/A | Yes | Yes | unknown | No | 6405.662 | 4951.313 | 0.320977 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1024.2852 | 1004.8586 | 1.1759 | ZONE1PTHPFAN | Fan:ConstantVolume | 0.320977 | 0.37743139 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 18:50:00 | unknown | unknown | unknown | 7/21 18:50:00 | 6370.41 | 4717.85 | 1.0055 | 0.37743139 | 0.320977 | 25.21 | 18.15 | 0.01046033 | 51983.0 | 12.80 | 11.88 | 0.00850000 | 34322.2 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 6370.41 | 29.47 | 0.01496114 | 22.67 | 0.07602596 | 23.6858 | 23.89 | 0.00906340 | 23.89 | 0.00906340 | 47.9201 | 4271.61 | 0.00 | 6421.79 | 4920.49 | 0.36248831 | 26.67 | 19.44 | 0.01117891 | 55307.7 | 13.39 | 13.37 | 0.00955506 | 37591.8 | |
| ZONE1PTHPDXHEATCOIL | COIL:HEATING:DX:SINGLESPEED | Zone Equipment | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE1PTHP or VRF ZONE TERMINAL | N/A | N/A | N/A | N/A | Yes | Yes | unknown | No | 6405.662 | 6405.662 | 0.320977 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1759 | ZONE1PTHPFAN | Fan:ConstantVolume | 0.320977 | 0.37743139 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | unknown | unknown | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 6405.66 | 6405.66 | 1.0000 | 0.37743139 | 0.320977 | 1.83 | 1.83 | 0.00455227 | 13235.8 | 40.00 | 20.87 | 0.00800000 | 60796.0 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 6405.66 | -20.00 | 0.00064986 | -20.00 | 0.07602596 | 23.6858 | 21.11 | 0.00800000 | 21.11 | 0.00800000 | 50.1625 | 3671.12 | 0.00 | 5038.19 | 5038.19 | 0.37076206 | 21.11 | 15.55 | 0.00874580 | 43428.1 | 34.42 | 20.01 | 0.00874580 | 57016.8 | |
| ZONE1PTHPELECHTGBACKUPCOIL | COIL:HEATING:ELECTRIC | Zone Equipment | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE1PTHP or VRF ZONE TERMINAL | N/A | N/A | N/A | N/A | No | No | unknown | No | 0.000 | 0.000 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1759 | ZONE1PTHPFAN | Fan:ConstantVolume | 0.320977 | 0.37743139 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | unknown | unknown | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 0.00 | 0.00 | 1.0000 | 0.19058523 | 0.162078 | 1.83 | 1.83 | 0.00455227 | 13235.8 | 40.00 | 20.87 | 0.00800000 | 60796.0 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 0.00 | -20.00 | 0.00064986 | -20.00 | 0.07602596 | 46.9070 | 21.11 | 0.00800000 | 21.11 | 0.00800000 | 50.1625 | 3671.12 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | |
| ZONE2PTHPDXCOOLCOIL | COIL:COOLING:DX:SINGLESPEED | Zone Equipment | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE2PTHP or VRF ZONE TERMINAL 1 | N/A | N/A | N/A | N/A | Yes | Yes | unknown | No | 6832.548 | 5382.941 | 0.354581 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1023.3816 | 1004.8586 | 1.1759 | ZONE1PTHPFAN 3 | Fan:ConstantVolume | 0.354581 | 0.41694602 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 13:30:00 | unknown | unknown | unknown | 7/21 13:30:00 | 6982.19 | 5539.80 | 0.9786 | 0.41694602 | 0.354581 | 25.38 | 17.82 | 0.00997423 | 50913.8 | 12.80 | 11.88 | 0.00850000 | 34322.2 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 6982.19 | 33.04 | 0.01496113 | 23.63 | 0.05763260 | 16.2537 | 23.89 | 0.00900636 | 23.89 | 0.00900636 | 47.6236 | 4718.70 | 0.00 | 6849.75 | 5347.69 | 0.40043850 | 26.67 | 19.44 | 0.01117891 | 55307.7 | 13.61 | 13.60 | 0.00970820 | 38202.1 | |
| ZONE2PTHPDXHEATCOIL | COIL:HEATING:DX:SINGLESPEED | Zone Equipment | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE2PTHP or VRF ZONE TERMINAL 1 | N/A | N/A | N/A | N/A | Yes | Yes | unknown | No | 6832.548 | 6832.548 | 0.354581 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1759 | ZONE1PTHPFAN 3 | Fan:ConstantVolume | 0.354581 | 0.41694602 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | unknown | unknown | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | 6832.55 | 6832.55 | 1.0000 | 0.41694602 | 0.354581 | 14.23 | 10.15 | 0.00623058 | 30043.1 | 40.00 | 20.87 | 0.00800000 | 60796.0 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 6832.55 | -20.00 | 0.00064986 | -20.00 | 0.05763260 | 16.2537 | 21.11 | 0.00735233 | 21.11 | 0.00735233 | 46.1576 | 7801.05 | 0.00 | 5373.94 | 5373.94 | 0.40957845 | 21.11 | 15.55 | 0.00874580 | 43428.1 | 33.96 | 19.87 | 0.00874580 | 56548.8 | |
| ZONE2PTHPELECHTGBACKUPCOIL | COIL:HEATING:ELECTRIC | Zone Equipment | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE2PTHP or VRF ZONE TERMINAL 1 | N/A | N/A | N/A | N/A | No | No | unknown | No | 0.000 | 0.000 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1759 | ZONE1PTHPFAN 3 | Fan:ConstantVolume | 0.354581 | 0.41694602 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | unknown | unknown | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | 0.00 | 0.00 | 1.0000 | 0.40492370 | 0.344357 | 14.23 | 10.15 | 0.00623058 | 30043.1 | 40.00 | 20.87 | 0.00800000 | 60796.0 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 0.00 | -20.00 | 0.00064986 | -20.00 | 0.05763260 | 16.7363 | 21.11 | 0.00735233 | 21.11 | 0.00735233 | 46.1576 | 7801.05 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | |
| ZONE3PTHPDXCOOLCOIL | COIL:COOLING:DX:SINGLESPEED | Zone Equipment | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE3PTHP or VRF ZONE TERMINAL 2 | N/A | N/A | N/A | N/A | Yes | Yes | unknown | No | 5245.515 | 4199.849 | 0.316882 | -999.0 | -999.000 | -999.0000 | 1.00893 | 1.00000 | 1022.5103 | 1004.8586 | 1.1759 | ZONE3PTHPFAN | Fan:ConstantVolume | 0.316882 | 0.37261620 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 08:50:00 | unknown | unknown | unknown | 7/21 08:50:00 | 5293.28 | 4437.43 | 0.9910 | 0.37261620 | 0.316882 | 24.24 | 17.06 | 0.00950554 | 48563.5 | 12.80 | 11.88 | 0.00850000 | 34322.2 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 5293.28 | 27.19 | 0.01496113 | 22.04 | 0.03418840 | 10.7890 | 23.89 | 0.00884575 | 23.89 | 0.00884575 | 46.7860 | 4217.02 | 0.00 | 5258.72 | 4170.45 | 0.35786377 | 26.67 | 19.44 | 0.01117891 | 55307.7 | 15.28 | 14.50 | 0.00998659 | 40612.9 | |
| ZONE3PTHPDXHEATCOIL | COIL:HEATING:DX:SINGLESPEED | Zone Equipment | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE3PTHP or VRF ZONE TERMINAL 2 | N/A | N/A | N/A | N/A | Yes | Yes | unknown | No | 5245.515 | 5245.515 | 0.316882 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1759 | ZONE3PTHPFAN | Fan:ConstantVolume | 0.316882 | 0.37261620 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | unknown | unknown | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | 5245.52 | 5245.52 | 1.0000 | 0.37261620 | 0.316882 | 14.34 | 10.19 | 0.00622123 | 30134.0 | 40.00 | 20.87 | 0.00800000 | 60796.0 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 5245.52 | -20.00 | 0.00064986 | -20.00 | 0.03418840 | 10.7890 | 21.11 | 0.00731910 | 21.11 | 0.00731910 | 45.9518 | 4704.91 | 0.00 | 4125.71 | 4125.71 | 0.36603196 | 21.11 | 15.55 | 0.00874580 | 43428.1 | 32.15 | 19.30 | 0.00874580 | 54699.5 | |
| ZONE3PTHPELECHTGBACKUPCOIL | COIL:HEATING:ELECTRIC | Zone Equipment | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE3PTHP or VRF ZONE TERMINAL 2 | N/A | N/A | N/A | N/A | No | No | unknown | No | 0.000 | 0.000 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1759 | ZONE3PTHPFAN | Fan:ConstantVolume | 0.316882 | 0.37261620 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | unknown | unknown | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | 0.00 | 0.00 | 1.0000 | 0.24421227 | 0.207684 | 14.34 | 10.19 | 0.00622123 | 30134.0 | 40.00 | 20.87 | 0.00800000 | 60796.0 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 0.00 | -20.00 | 0.00064986 | -20.00 | 0.03418840 | 16.4618 | 21.11 | 0.00731910 | 21.11 | 0.00731910 | 45.9518 | 4704.91 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | |
| ZONE4PTHPDXCOOLCOIL | COIL:COOLING:DX:SINGLESPEED | Zone Equipment | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE4PTHP or VRF ZONE TERMINAL 3 | N/A | N/A | N/A | N/A | Yes | Yes | unknown | No | 6236.548 | 4979.841 | 0.332520 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1023.5437 | 1004.8586 | 1.1759 | ZONE4PTHPFAN | Fan:ConstantVolume | 0.332520 | 0.39100531 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 18:30:00 | unknown | unknown | unknown | 7/21 18:30:00 | 6277.21 | 4887.61 | 0.9935 | 0.39100531 | 0.332520 | 24.95 | 17.75 | 0.01006141 | 50696.7 | 12.80 | 11.88 | 0.00850000 | 34322.2 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 6277.21 | 29.99 | 0.01496113 | 22.81 | 0.05763260 | 17.3321 | 23.89 | 0.00903414 | 23.89 | 0.00903414 | 47.7683 | 4425.12 | 0.00 | 6252.25 | 4945.27 | 0.37552483 | 26.67 | 19.44 | 0.01117891 | 55307.7 | 13.79 | 13.77 | 0.00981432 | 38658.3 | |
| ZONE4PTHPDXHEATCOIL | COIL:HEATING:DX:SINGLESPEED | Zone Equipment | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE4PTHP or VRF ZONE TERMINAL 3 | N/A | N/A | N/A | N/A | Yes | Yes | unknown | No | 6236.548 | 6236.548 | 0.332520 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1759 | ZONE4PTHPFAN | Fan:ConstantVolume | 0.332520 | 0.39100531 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | unknown | unknown | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | 6236.55 | 6236.55 | 1.0000 | 0.39100531 | 0.332520 | 13.78 | 9.86 | 0.00614787 | 29374.8 | 40.00 | 20.87 | 0.00800000 | 60796.0 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 6236.55 | -20.00 | 0.00064986 | -20.00 | 0.05763260 | 17.3321 | 21.11 | 0.00734136 | 21.11 | 0.00734136 | 46.0892 | 7320.06 | 0.00 | 4905.17 | 4905.17 | 0.38409612 | 21.11 | 15.55 | 0.00874580 | 43428.1 | 33.62 | 19.77 | 0.00874580 | 56198.8 | |
| ZONE4PTHPELECHTGBACKUPCOIL | COIL:HEATING:ELECTRIC | Zone Equipment | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE4PTHP or VRF ZONE TERMINAL 3 | N/A | N/A | N/A | N/A | No | No | unknown | No | 0.000 | 0.000 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1759 | ZONE4PTHPFAN | Fan:ConstantVolume | 0.332520 | 0.39100531 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | unknown | unknown | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | 0.00 | 0.00 | 1.0000 | 0.37995938 | 0.323126 | 13.78 | 9.86 | 0.00614787 | 29374.8 | 40.00 | 20.87 | 0.00800000 | 60796.0 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 0.00 | -20.00 | 0.00064986 | -20.00 | 0.05763260 | 17.8359 | 21.11 | 0.00734136 | 21.11 | 0.00734136 | 46.0892 | 7320.06 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | |
| ZONE5PTHPDXCOOLCOIL | COIL:COOLING:DX:SINGLESPEED | Zone Equipment | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE5PTHP or VRF ZONE TERMINAL 4 | N/A | N/A | N/A | N/A | Yes | Yes | unknown | No | 6024.042 | 4822.968 | 0.355959 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1022.3094 | 1004.8586 | 1.1759 | ZONE5PTHPFAN | Fan:ConstantVolume | 0.355959 | 0.41856664 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 17:00:00 | unknown | unknown | unknown | 7/21 17:00:00 | 6216.52 | 5327.03 | 0.9690 | 0.41856664 | 0.355959 | 24.65 | 17.11 | 0.00939748 | 48703.8 | 12.80 | 11.88 | 0.00850000 | 34322.2 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 6216.52 | 31.83 | 0.01496113 | 23.31 | 0.03418840 | 9.6046 | 23.89 | 0.00880633 | 23.89 | 0.00880633 | 46.5803 | 4737.09 | 0.00 | 6039.21 | 4789.94 | 0.40199496 | 26.67 | 19.44 | 0.01117891 | 55307.7 | 15.02 | 14.38 | 0.00996046 | 40284.6 | |
| ZONE5PTHPDXHEATCOIL | COIL:HEATING:DX:SINGLESPEED | Zone Equipment | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE5PTHP or VRF ZONE TERMINAL 4 | N/A | N/A | N/A | N/A | Yes | Yes | unknown | No | 6024.042 | 6024.042 | 0.355959 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1759 | ZONE5PTHPFAN | Fan:ConstantVolume | 0.355959 | 0.41856664 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | unknown | unknown | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | 6024.04 | 6024.04 | 1.0000 | 0.41856664 | 0.355959 | 14.40 | 10.23 | 0.00623526 | 30229.3 | 40.00 | 20.87 | 0.00800000 | 60796.0 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 6024.04 | -20.00 | 0.00064986 | -20.00 | 0.03418840 | 9.6046 | 21.11 | 0.00732447 | 21.11 | 0.00732447 | 45.9852 | 4746.13 | 0.00 | 4738.03 | 4738.03 | 0.41117044 | 21.11 | 15.55 | 0.00874580 | 43428.1 | 32.40 | 19.38 | 0.00874580 | 54951.4 | |
| ZONE5PTHPELECHTGBACKUPCOIL | COIL:HEATING:ELECTRIC | Zone Equipment | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE5PTHP or VRF ZONE TERMINAL 4 | N/A | N/A | N/A | N/A | No | No | unknown | No | 0.000 | 0.000 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1759 | ZONE5PTHPFAN | Fan:ConstantVolume | 0.355959 | 0.41856664 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | unknown | unknown | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | 0.00 | 0.00 | 1.0000 | 0.24635223 | 0.209504 | 14.40 | 10.23 | 0.00623526 | 30229.3 | 40.00 | 20.87 | 0.00800000 | 60796.0 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 0.00 | -20.00 | 0.00064986 | -20.00 | 0.03418840 | 16.3188 | 21.11 | 0.00732447 | 21.11 | 0.00732447 | 45.9852 | 4746.13 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | |
| VRF ZONE TERMINAL COOLING COIL | Coil:Cooling:DX:VariableRefrigerantFlow | Zone Equipment | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE1PTHP or VRF ZONE TERMINAL | N/A | N/A | N/A | N/A | Yes | Yes | unknown | No | 6497.327 | 4987.715 | 0.320977 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1024.2852 | 1004.8586 | 1.1759 | unknown | unknown | -999.0 | -999.0 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 18:50:00 | unknown | unknown | unknown | 7/21 18:50:00 | 6554.03 | 4853.84 | 0.9913 | 0.37743139 | 0.320977 | 25.21 | 18.15 | 0.01046033 | 51983.0 | 12.80 | 11.88 | 0.00850000 | 34322.2 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 6554.03 | 29.47 | 0.01496114 | 22.67 | 0.07602596 | 23.6858 | 23.89 | 0.00906340 | 23.89 | 0.00906340 | 47.9201 | 4271.61 | 0.00 | 6480.72 | 4944.12 | 0.36248831 | 26.67 | 19.44 | 0.01117891 | 55307.7 | 13.33 | 13.31 | 0.00951687 | 37429.3 | |
| VRF ZONE TERMINAL HEATING COIL | Coil:Heating:DX:VariableRefrigerantFlow | Zone Equipment | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE1PTHP or VRF ZONE TERMINAL | N/A | N/A | N/A | N/A | Yes | Yes | unknown | No | 6497.327 | 0.000 | 0.320977 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1759 | unknown | unknown | -999.0 | -999.0 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | unknown | unknown | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 6497.33 | 6497.33 | 1.0000 | 0.37743139 | 0.320977 | 1.83 | 1.83 | 0.00455227 | 13235.8 | 40.00 | 20.87 | 0.00800000 | 60796.0 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 6497.33 | -20.00 | 0.00064986 | -20.00 | 0.07602596 | 23.6858 | 21.11 | 0.00800000 | 21.11 | 0.00800000 | 50.1625 | 3671.12 | 0.00 | 6400.05 | 6400.05 | 0.37076206 | 21.11 | 15.55 | 0.00874580 | 43428.1 | 38.02 | 21.10 | 0.00874580 | 60690.0 | |
| VRF ZONE TERMINAL COOLING COIL 1 | Coil:Cooling:DX:VariableRefrigerantFlow | Zone Equipment | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE2PTHP or VRF ZONE TERMINAL 1 | N/A | N/A | N/A | N/A | Yes | Yes | unknown | No | 6979.867 | 5438.516 | 0.354581 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1023.3816 | 1004.8586 | 1.1759 | unknown | unknown | -999.0 | -999.0 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 13:30:00 | unknown | unknown | unknown | 7/21 13:30:00 | 7286.53 | 5781.26 | 0.9579 | 0.41694602 | 0.354581 | 25.38 | 17.82 | 0.00997423 | 50913.8 | 12.80 | 11.88 | 0.00850000 | 34322.2 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 7286.53 | 33.04 | 0.01496113 | 23.63 | 0.05763260 | 16.2537 | 23.89 | 0.00900636 | 23.89 | 0.00900636 | 47.6236 | 4718.70 | 0.00 | 6962.02 | 5390.43 | 0.40043850 | 26.67 | 19.44 | 0.01117891 | 55307.7 | 13.50 | 13.50 | 0.00964012 | 37921.7 | |
| VRF ZONE TERMINAL HEATING COIL 1 | Coil:Heating:DX:VariableRefrigerantFlow | Zone Equipment | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE2PTHP or VRF ZONE TERMINAL 1 | N/A | N/A | N/A | N/A | Yes | Yes | unknown | No | 6979.867 | 0.000 | 0.354581 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1759 | unknown | unknown | -999.0 | -999.0 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | unknown | unknown | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | 6979.87 | 6979.87 | 1.0000 | 0.41694602 | 0.354581 | 14.23 | 10.15 | 0.00623058 | 30043.1 | 40.00 | 20.87 | 0.00800000 | 60796.0 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 6979.87 | -20.00 | 0.00064986 | -20.00 | 0.05763260 | 16.2537 | 21.11 | 0.00735233 | 21.11 | 0.00735233 | 46.1576 | 7801.05 | 0.00 | 6875.37 | 6875.37 | 0.40957845 | 21.11 | 15.55 | 0.00874580 | 43428.1 | 37.55 | 20.96 | 0.00874580 | 60214.6 | |
| VRF ZONE TERMINAL COOLING COIL 2 | Coil:Cooling:DX:VariableRefrigerantFlow | Zone Equipment | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE3PTHP or VRF ZONE TERMINAL 2 | N/A | N/A | N/A | N/A | Yes | Yes | unknown | No | 5348.205 | 4281.751 | 0.316882 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1022.5103 | 1004.8586 | 1.1759 | unknown | unknown | -999.0 | -999.0 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 08:50:00 | unknown | unknown | unknown | 7/21 08:50:00 | 5551.72 | 4654.08 | 0.9633 | 0.37261620 | 0.316882 | 24.24 | 17.06 | 0.00950554 | 48563.5 | 12.80 | 11.88 | 0.00850000 | 34322.2 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 5551.72 | 27.19 | 0.01496113 | 22.04 | 0.03418840 | 10.7890 | 23.89 | 0.00884575 | 23.89 | 0.00884575 | 46.7860 | 4217.02 | 0.00 | 5334.53 | 4242.14 | 0.35786377 | 26.67 | 19.44 | 0.01117891 | 55307.7 | 15.08 | 14.43 | 0.00998207 | 40401.1 | |
| VRF ZONE TERMINAL HEATING COIL 2 | Coil:Heating:DX:VariableRefrigerantFlow | Zone Equipment | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE3PTHP or VRF ZONE TERMINAL 2 | N/A | N/A | N/A | N/A | Yes | Yes | unknown | No | 5348.205 | 0.000 | 0.316882 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1759 | unknown | unknown | -999.0 | -999.0 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | unknown | unknown | CHICAGO OHARE INTL AP ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | 5348.20 | 5348.20 | 1.0000 | 0.37261620 | 0.316882 | 14.34 | 10.19 | 0.00622123 | 30134.0 | 40.00 | 20.87 | 0.00800000 | 60796.0 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 5348.20 | -20.00 | 0.00064986 | -20.00 | 0.03418840 | 10.7890 | 21.11 | 0.00731910 | 21.11 | 0.00731910 | 45.9518 | 4704.91 | 0.00 | 5268.13 | 5268.13 | 0.36603196 | 21.11 | 15.55 | 0.00874580 | 43428.1 | 35.21 | 20.26 | 0.00874580 | 57820.7 | |
| VRF ZONE TERMINAL COOLING COIL 3 | Coil:Cooling:DX:VariableRefrigerantFlow | Zone Equipment | ZONEHVAC:PACKAGEDTERMINALHEATPUMP or ZONEHVAC:TERMINALUNIT:VARIABLEREFRIGERANTFLOW | ZONE4PTHP or VRF ZONE TERMINAL 3 | N/A | N/A | N/A | N/A | Yes | Yes | unknown | No | 6361.987 | 5026.575 | 0.332520 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1023.5437 | 1004.8586 | 1.1759 | unknown | unknown | -999.0 | -999.0 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | CHICAGO OHARE INTL AP ANN CLG .4% CONDNS DB=>MWB | 7/21 18:30:00 | unknown | unknown | unknown | 7/21 18:30:00 | 6532.26 | 5086.20 | 0.9739 | 0.39100531 | 0.332520 | 24.95 | 17.75 | 0.01006141 | 50696.7 | 12.80 | 11.88 | 0.00850000 | 34322.2 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 6532.26 | 29.99 | 0.01496113 | 22.81 | 0.05763260 | 17.3321 | 23.89 | 0.00903414 | 23.89 | 0.00903414 | 47.7683 | 4425.12 | 0.00 | 6345.72 | 4980.54 | 0.37552483 | 26.67 | 19.44 | 0.01117891 | 55307.7 | 13.70 | 13.68 | 0.00975355 | 38409.4 | |