BOSSA NOVA A film review by Steve Rhodes Copyright 2000 Steve Rhodes RATING (0 TO ****): ***
Love is in the air in BOSSA NOVA, starring Amy Irving and directed by her husband Bruno Barreto. It's a comedic romance with the comedy used as a relaxation device to put you in the mood for love.
Several couples are in the process of forming relationships, and all of the relationships are touchingly genuine, thanks to the meticulous direction and to the delicately effective script by Alexandre Machado and Fernanda Young, based on Sérgio Sant'Anna's novel.
Although some of the lovers are the traditional young twentysomethings, popular in the cinema, the leads (Irving and Antônio Fagundes) are both around 50. Most motion pictures believe that significant love stops around 35 and isn't reborn, except for some patronizing films about senior citizen romances.
The film is set in Rio, which is shown so gorgeously, particularly in the scenes set at dusk, that you may feel compelled to consult your travel agent after the picture is over.
With a twinkle in her eye, Irving plays an English language teacher named Mary Ann. A widow, Mary Ann hasn't dated in over 2 years, and she isn't on the prowl now, even if, subconsciously, she's receptive to the right gestures. One day, a dashingly handsome lawyer, Pedro Paulo (Fagundes), sees her and is instantly smitten. Pedro is on the rebound, having recently separated from his wife. You can tell by the way he ignores his beautiful legal assistant, Sharon (Giovanna Antonelli), that he hasn't been exactly knocking doors down to find another woman. But Mary Ann is something different, so he enrolls in her language class in the hopes of sparking her interest in him.
Barreto's brilliance can be seen in the way he stages the scenes. One of the best has Pedro behind Mary Ann in a crowded elevator. He opens his palm and sneaks it toward her rear. We, of course, think he is going to do some Latin, macho thing and secretly fondle her before she knows who touched her. But his hand never quite comes in contact with her body. He quickly moves his hand all over her backside, measuring her for a blouse that he is going to make. You see, he comes from a long line of tailors.
In another scene, we meet Pedro's father, Juan (Alberto de Mendoza), a tailor of the old school. He literally listens to the fabric to grade it and to determine how best to use the material. Also at the tailor shop is Pedro's brother, Roberto (Pedro Cardoso), who falls for Sharon, as does soccer star Acácio (Alexandre Borges).
Acácio, one of Mary Ann's private pupils, also has eyes for her. But she's more flattered than interested. Since he is about to move to England, he needs her to teach him how to cuss in English as well as he can in Portuguese so that he can intimidate the players in his new country. The profanity lesson is the movie's funniest episode since it's done so sweetly. It's also one of the few fast paced scenes in the picture, which usually takes its time.
There are many other key characters, and they are all linked together in various ways, many being English language students. Characters are only introduced if the writer has a plan for the character's development. Most movies fail when they become too ambitious in the number of plots and subplots, but BOSSA NOVA never overreaches. Every character is worth caring about, and every romance is worth our attention. The film's dreamy, old-time music invokes memories of the movie romances from the 1940s. There is even a dream sequence in which the two leads take a spin around the dance floor, actually Mary Ann's classroom.
Even the smallest details are carefully designed to reinforce the story's romantic mood. The sheets in the hospital, for example, are a peaceful sea green. The contrasting clothes include some of the best looking, and best tailored, suits that you've ever seen on Pedro and some of the flashiest silk shirts on Acácio.
Not all of the relationships turn out exactly as you might guess and some are left not completely resolved. Nevertheless, the good-spirited story leaves you with a warm glow. A very satisfying film about the possibilities and the joys of love, BOSSA NOVA shows what can happen when romantic comedies tone down the comedy and accentuate the romance. The result can be splendid.
BOSSA NOVA runs 1:35. The film is in English and in Portuguese with English subtitles. It is rated R for language and some sexual content and would be fine for teenagers.
Email<EMAIL_ADDRESS>Web: http://www.InternetReviews.com
The review above was posted to the
rec.arts.movies.reviews newsgroup (de.rec.film.kritiken for German reviews).
The Internet Movie Database accepts no responsibility for the contents of the
review and has no editorial control. Unless stated otherwise, the copyright
belongs to the author.
Please direct comments/criticisms of the review to relevant newsgroups.
Broken URLs inthe reviews are the responsibility of the author.
The formatting of the review is likely to differ from the original due
to ASCII to HTML conversion.
Related links: index of all rec.arts.movies.reviews reviews


This afternoon, whim dictates that I share with readers some famous last words.
“Reynolds! Reynolds! … Reynolds!” — Edgar Allan Poe *
“I suppose I am now becoming a god” — Emperor Vespasian
“All this buttoning and unbuttoning” — Anonymous 17th century suicide
“It was I who discovered leeches have red blood.” Georges Cuvier
* NOTE : Poe was yelling out for Jeremiah Reynolds—not present at his deathbed—an enthusiastic supporter of the hollow earth theories of John Cleve Symmes. Symmes' idea that there were entrances to subterranean worlds at both the Poles was one of the inspirations for Poe's magnificent The Narrative Of Arthur Gordon Pym Of Nantucket.


--- layout: page title: About header-img: "img/about-bg.png" ---
Pursuing a role as a Software Engineer. I currently specialize in using JavaScript as the frontend and Ruby as the backend. Experienced in using JavaScript libraries such as: React and Redux as well as using Ruby on Rails which utilizes Active Record. Some experience using C#. Looking for a job that brings structure like a typical "9-5." Open to learning new languages and technologies.
To learn more about Allan Farca, find me on LinkedIn.


Spry supports the notion of region states. That is, at any given time, a region is either loading data, ready to display the data, or in an error state because one or more of the data sets it is bound to failed to load its data. You can place a spry:state attribute, with a value of "loading", "error", or "ready" on elements inside a region container to associate it with a specific region state. Doing so can be quite useful for displaying a loading message as the data for a region loads, or notifying the user that the region failed to get its data. As the region changes states, it automatically regenerates its code and displays any elements with a spry:state attribute that matches the current state.
The following example uses the spry:state attribute to display loading and error messages:

Loading employee data ...

Failed to load employee data!

{firstname} {lastname}

Any content that does not have a spry:state attribute on it, or is not a child or descendent of an element that has a spry:state attribute on it, is always included in the output when the code is regenerated. Also, children or descendents of an element with a spry:state attribute cannot have spry:state attributes. That is, nesting elements with spry:state attributes is not supported.


Legacies: Landon and Josie Confront Professor Vardemus in New Photos
by Sam StoneProfessor Vardemus and his less-than-altruistic agenda begin to surface in new official stills from Legacies Season 2.
The CW has released photos from the season's seventh episode, ominously titled "It Will All Be Painfully Clear Soon Enough," that show Landon and his girlfriend Josie confronting the Salvatore Boarding School for the Young & Gifted's new headmaster. Meanwhile, Josie and her fraternal twin sister Lizzie commiserate with Hope as she contemplates leaving town.
It Will All Be Painfully Clear Soon Enough (Ep# 207)THE RACE TO CLOSE THE MALIVORE PORTAL -- After deciding that leaving town would be for the best, Hope (Danielle Rose Russell) gets pulled back in after Josie (Kaylee Bryant) comes up with a risky plan to close the Malivore portal. Elsewhere, Alaric (Matthew Davis) and Dorian (guest star Demetrius Bridges) make an alarming discovery about Professor Vardemus (guest star Alexis Denisof), while Rafael (Peyton Alex Smith) learns some upsetting news about Landon's (Aria Shahghasemi) future. Jenny Boyd also stars. Lauren Petzke directed the episode written by Jimmy Mosqueda & Cynthia Adarkwa (#207). Original airdate 12/5/2019.
Click the button below to start this article in quick view.
The Malivore Portal was a gateway into a hellish dimension introduced in The Vampire Diaries. With one opening near the town of Mystic Falls, supernatural mayhem is sure to follow.
Vardemus arrived to helm the Salvatore School after its previous headmaster, Alaric Saltzman, was voted out. However, while Vardemus has attempted to grow closer to Josie after witnessing her power, Alaric has since become the Principal of Mystic Falls High School.
Airing Thursdays at 9 pm ET on The CW, Legacies stars Danielle Rose Russell as Hope Mikaelson, Jenny Boyd as Lizzie Saltzman, Kaylee Bryant as Josie Saltzman, Quincy Fouse as Milton Greasley/MG, Aria Shahghasemi as Landon Kirby, Peyton Alex Smith as Rafael Waithe and Matt Davis as Alaric Saltzman.
https://schema.orgBreadcrumbListListItem1Homehttps://www.cbr.com/ListItem2TVhttps://www.cbr.com/category/tv/ListItem3TV Newshttps://www.cbr.com/category/tv/news-tv/ListItem4Legacies: Landon and Josie Confront Professor Vardemus in New Photoshttps://www.cbr.com/legacies-landon-josie-vardemus-photos/


Visual Studio is a complete set of development tools for building ASP.NET Web applications, XML Web Services, desktop applications, and mobile applications. It supports nearly every language with the right plugins (more on that later) but has the support for the following right after install:
One word: IntelliSense (Wait, maybe 2 words?). IntelliSense is Microsoft's code completion and it can save time and keystrokes. Much like spell check in Office, it also applies a squiggly underlines to code that it doesn't believe is correct.
Newer versions support 'Peek to definition', 'Navigate To' and 'Quick Find' that help you see what's going on with the code you are looking at. This comes in handy especially in huge files with lines and lines of code and it can even display the complete code and where you are in relation to the start and end of it.
Great for debugging the inevitable errors. No matter what you make, whether a Windows program or IOS app, Visual Studio can fix it if it breaks. You can pause the code and check on the value of your variables to make sure everything is moving smoothly. It even lets you move from human readable 'high level' code to 'low level' machine code for particularly pesky issues.
Does have versioning tools and change-highlighting for collabrative work. Visual Studio is available on all major operating systems and can integrate with other popular IDEs like IntelliJ and Eclipse, which allows teams coming from different preferences to stay productive.
The IDE also allows you to add in additional languages through extensions. Take a look at this open-sourced Python extension here.


Highcharts 6.0.7 (2018-02-16)
- Fixed #150, grid lines did not always align to plot border and to other axis' grid lines.
- Fixed #1813, graphs and areas were not clipped when exceeding perimeter in polar charts.
- Fixed #7191, level options was applied to wrong level in treemap when
levelIsConstant
is false.
- Fixed #7729,
highcharts-more.js
couldn't be included multiple times without errors.
- Fixed #7787, a regression causing incorrect title alignment when useHTML was enabled in v6.0.5.
- Fixed #7800, error on hovering points in IE11 + compatibility mode.
- Fixed #7806, API reference had a wrong extend for bullet's targetOptions.
- Fixed #7812, a regression causing wrong initial position of text with
useHTML
.
- Fixed #7814, multiline axis title didn't reflow to chart resize.
- Fixed #7817, regression with categories in drilldown. Point names were not properly purged from Axis.names array.
- Fixed #7825, histogram threw error if the base series had equaled values.
- Fixed #7826, annotations were hidden if the points had disabled markers.
reference description for chart.options3d.frame.bottom.
- Fixed #7850, legacy IE event for
onContainerMouseDown
wasn't provided properly.
- Fixed #7854, accessibility of datetime charts.


Directives are the AngularJS facility that allow for the easy extension of the display capabilities and behavoir of HTML pages.
Triangular uses this facility in several places. The templates along with the macro facility is the most complex use of directives. The blurEvent, focusClear and autotab directives are more simple examples.
Nothing in the design of Triangular prohibits the addition of custom directives to an application. The
oApp.directive('directive name', function(...) {
format should be used since oApp
is a global variable in which all directives are registered.


Our address is:
600 First Ave, Unit 605
Seattle WA 98104
After business hours, you can enter the building on the James Street side; look for the "Office Space" sign, and dial "Attic" on the intercom.
The building is wheelchair accessible, including the bathrooms.
We hold a weekly open house on Tuesday evenings from 6:30-9PM.
Need to figure out parking? Check out SDOT's Seattle Parking Map.


Transaction
The transaction object is used to identify a running transaction. It is created by calling Sequelize.transaction()
.
To run a query under a transaction, you should pass the transaction in the options object..
Static Member Summary
| Static Public Members | ||
| public static get |
ISOLATION_LEVELS: {"READ_UNCOMMITTED": string, "READ_COMMITTED": string, "REPEATABLE_READ": string, "SERIALIZABLE": string} Isolations levels can be set per-transaction by passing |
|
| public static get |
LOCK: Object: {"UPDATE": string, "SHARE": string, "KEY_SHARE": string, "NO_KEY_UPDATE": string} Possible options for row locking. |
|
| public static get |
TYPES: {"DEFERRED": string, "IMMEDIATE": string, "EXCLUSIVE": string} Types can be set per-transaction by passing |
Constructor Summary
| Public Constructor | ||
| public |
constructor(sequelize: Sequelize, options: Object) |
Member Summary
| Public Members | ||
| public get |
LOCK: * |
Method Summary
| Public Methods | ||
| public |
commit(): Promise Commit the transaction |
|
| public |
rollback(): Promise Rollback (abort) the transaction |
Static Public Members
public static get ISOLATION_LEVELS: {"READ_UNCOMMITTED": string, "READ_COMMITTED": string, "REPEATABLE_READ": string, "SERIALIZABLE": string} source
Isolations levels can be set per-transaction by passing options.isolationLevel
to sequelize.transaction
.
Default to REPEATABLE_READ
but you can override the default isolation level by passing options.isolationLevel
in new Sequelize
.
Pass in the desired level as the first argument:
return sequelize.transaction({isolationLevel: Sequelize.Transaction.ISOLATION_LEVELS.SERIALIZABLE}, transaction => {
// your transactions
}).then(result => {
// transaction has been committed. Do something after the commit if required.
}).catch(err => {
// do something with the err.
});
Properties:
| Name | Type | Attribute | Description |
| READ_UNCOMMITTED | * | ||
| READ_COMMITTED | * | ||
| REPEATABLE_READ | * | ||
| SERIALIZABLE | * |
public static get LOCK: Object: {"UPDATE": string, "SHARE": string, "KEY_SHARE": string, "NO_KEY_UPDATE": string} source
Possible options for row locking. Used in conjunction with find
calls:
t1 // is a transaction
Model.findAll({
where: ...,
transaction: t1,
lock: t1.LOCK...
});
Postgres also supports specific locks while eager loading by using OF:
UserModel.findAll({
where: ...,
include: [TaskModel, ...],
transaction: t1,
lock: {
level: t1.LOCK...,
of: UserModel
}
});
UserModel will be locked but TaskModel won't!
Properties:
| Name | Type | Attribute | Description |
| UPDATE | * | ||
| SHARE | * | ||
| KEY_SHARE | * | Postgres 9.3+ only |
|
| NO_KEY_UPDATE | * | Postgres 9.3+ only |
Return:
| Object |
Return Properties:
| Name | Type | Attribute | Description |
| UPDATE | * | ||
| SHARE | * | ||
| KEY_SHARE | * | Postgres 9.3+ only |
|
| NO_KEY_UPDATE | * | Postgres 9.3+ only |
public static get TYPES: {"DEFERRED": string, "IMMEDIATE": string, "EXCLUSIVE": string} source
Types can be set per-transaction by passing options.type
to sequelize.transaction
.
Default to DEFERRED
but you can override the default type by passing options.transactionType
in new Sequelize
.
Sqlite only.
Pass in the desired level as the first argument:
return sequelize.transaction({type: Sequelize.Transaction.TYPES.EXCLUSIVE}, transaction => {
// your transactions
}).then(result => {
// transaction has been committed. Do something after the commit if required.
}).catch(err => {
// do something with the err.
});
Properties:
| Name | Type | Attribute | Description |
| DEFERRED | * | ||
| IMMEDIATE | * | ||
| EXCLUSIVE | * |
Public Constructors
public constructor(sequelize: Sequelize, options: Object) source
Params:
| Name | Type | Attribute | Description |
| sequelize | Sequelize | A configured sequelize Instance |
|
| options | Object | An object with options |
|
| options.autocommit | Boolean | Sets the autocommit property of the transaction. |
|
| options.type | String |
|
Sets the type of the transaction. |
| options.isolationLevel | String |
|
Sets the isolation level of the transaction. |
| options.deferrable | String | Sets the constraints to be deferred or immediately checked. |


Occupation |
Image |
This is Siddhesh.
He is a Mechanic.
He uses a spanner.
He uses a screw-driver.
He repairs machines.
|
Mechanic |
This is Abdul.
He is a Carpenter.
He uses a saw.
He uses a tape-measure.
He makes things from wood.
|
Carpenter |
This is Pranali.
She is a Manager.
She uses a computer.
She uses a projector.
She works in an office.
|
Manager |
This is Kishor.
He is a Traffic-police.
He uses a whistle.
He uses a baton.
He directs traffic.
|
Traffic-police |
This is Siya.
She is a Chef.
She works in the kitchen.
She uses pots, pans, knives and spoons.
She cooks tasty food.
|
Chef |
This is Varsha.
She is a Singer.
She uses tanpura to practise.
She uses tabla for rhythm.
She sings sweet songs.
|
Singer |


|
JavaTM 2 Platform Standard Ed. 5.0 |
|||||||||
| PREV PACKAGE NEXT PACKAGE | FRAMES NO FRAMES |
See:
Description
| Interface Summary | |
|---|---|
| CertPathBuilderResult | A specification of the result of a certification path builder algorithm. |
| CertPathParameters | A specification of certification path algorithm parameters. |
| CertPathValidatorResult | A specification of the result of a certification path validator algorithm. |
| CertSelector | A selector that defines a set of criteria for selecting
Certificate s. |
| CertStoreParameters | A specification of CertStore parameters. |
| CRLSelector | A selector that defines a set of criteria for selecting CRL s. |
| PolicyNode | An immutable valid policy tree node as defined by the PKIX certification path validation algorithm. |
| X509Extension | Interface for an X.509 extension. |
| Class Summary | |
|---|---|
| Certificate | Abstract class for managing a variety of identity certificates. |
| Certificate.CertificateRep | Alternate Certificate class for serialization. |
| CertificateFactory | This class defines the functionality of a certificate factory, which is
used to generate certificate, certification path (CertPath )
and certificate revocation list (CRL) objects from their encodings. |
| CertificateFactorySpi | This class defines the Service Provider Interface (SPI)
for the CertificateFactory class. |
| CertPath | An immutable sequence of certificates (a certification path). |
| CertPath.CertPathRep | Alternate CertPath class for serialization. |
| CertPathBuilder | A class for building certification paths (also known as certificate chains). |
| CertPathBuilderSpi | The Service Provider Interface (SPI)
for the CertPathBuilder class. |
| CertPathValidator | A class for validating certification paths (also known as certificate chains). |
| CertPathValidatorSpi | The Service Provider Interface (SPI)
for the CertPathValidator class. |
| CertStore | A class for retrieving Certificate s and CRL s
from a repository. |
| CertStoreSpi | The Service Provider Interface (SPI)
for the CertStore class. |
| CollectionCertStoreParameters | Parameters used as input for the Collection CertStore
algorithm. |
| CRL | This class is an abstraction of certificate revocation lists (CRLs) that have different formats but important common uses. |
| LDAPCertStoreParameters | Parameters used as input for the LDAP CertStore algorithm. |
| PKIXBuilderParameters | Parameters used as input for the PKIX CertPathBuilder
algorithm. |
| PKIXCertPathBuilderResult | This class represents the successful result of the PKIX certification path builder algorithm. |
| PKIXCertPathChecker | An abstract class that performs one or more checks on an
X509Certificate . |
| PKIXCertPathValidatorResult | This class represents the successful result of the PKIX certification path validation algorithm. |
| PKIXParameters | Parameters used as input for the PKIX CertPathValidator
algorithm. |
| PolicyQualifierInfo | An immutable policy qualifier represented by the ASN.1 PolicyQualifierInfo structure. |
| TrustAnchor | A trust anchor or most-trusted Certification Authority (CA). |
| X509Certificate | Abstract class for X.509 certificates. |
| X509CertSelector | A CertSelector that selects X509Certificates that
match all specified criteria. |
| X509CRL | Abstract class for an X.509 Certificate Revocation List (CRL). |
| X509CRLEntry | Abstract class for a revoked certificate in a CRL (Certificate Revocation List). |
| X509CRLSelector | A CRLSelector that selects X509CRLs that
match all specified criteria. |
| Exception Summary | |
|---|---|
| CertificateEncodingException | Certificate Encoding Exception. |
| CertificateException | This exception indicates one of a variety of certificate problems. |
| CertificateExpiredException | Certificate Expired Exception. |
| CertificateNotYetValidException | Certificate is not yet valid exception. |
| CertificateParsingException | Certificate Parsing Exception. |
| CertPathBuilderException | An exception indicating one of a variety of problems encountered when
building a certification path with a CertPathBuilder . |
| CertPathValidatorException | An exception indicating one of a variety of problems encountered when validating a certification path. |
| CertStoreException | An exception indicating one of a variety of problems retrieving
certificates and CRLs from a CertStore . |
| CRLException | CRL (Certificate Revocation List) Exception. |
Provides classes and interfaces for parsing and managing certificates, certificate revocation lists (CRLs), and certification paths. It contains support for X.509 v3 certificates and X.509 v2 CRLs.
|
JavaTM 2 Platform Standard Ed. 5.0 |
|||||||||
| PREV PACKAGE NEXT PACKAGE | FRAMES NO FRAMES |
Copyright © 2004, 2010 Oracle and/or its affiliates. All rights reserved. Use is subject to license terms. Also see the documentation redistribution policy.


Data successfully saved. Please copy your SSL certificate in the folder {{folder}} and name it server.js. Then click ready.
server.js


Psalm 39
For the chief musician, for Jeduthun. A psalm of David.
1 I decided, "I will watch what I say
so that I do not sin with my tongue.

2 I kept silent; I kept back my words even from saying anything good,
and my pain grew worse.
3 My heart became hot;
when I thought about these things, it burned like a fire.
Then finally I spoke.
4 "Yahweh, make me know when will be the end of my life
and the extent of my days.
Show me how transient I am.
5 See, you have made my days only the width of my hand,
and my lifetime is like nothing before you.
Surely every man is a single breath.
Selah
6 Surely every man walks about like a shadow.
Surely everyone hurries about
to accumulate riches although they do not know who will receive them.
7 Now, Lord, for what am I waiting?

Selah
12 Hear my prayer, Yahweh, and listen to me;
listen to my weeping!


Ghost of Wigoth:
I already gathered three goblets. You did good too.
"Do you know them?"


I leave my closet door open all night I know the CIA would say What you hear is all here say Wish someone would tell me what was right Up all night long and there's something very wrong And I know it must be late, been gone since yesterday I'm not like you guys, I'm not like you I'm still a skeptic, yes you know me Been best friends and will be until we die I got an injection, a fear from the abduction My best friend thinks I'm just telling lies Alright Up all night long and there's something very wrong And I know it must be late, been gone since yesterday I'm not like you guys, I'm not like you Dark and scary, ordinary, explanation, information Nice to know ya', paranoia Where's my mother? By my father Up all night long and there's something very wrong And I know it must be late, been gone since yesterday I'm not like you guys, Swell majestic lies |


The Chat example shows how to use stomp.js to send and receive STOMP messages directly from the Web browser.
stomp.js
The WebWorker example uses a WebWorker instead to send and receive STOMP messages from the broker.


COOL, NORMAL, ETC: Melbourne Might Cop Its Hottest November Day In 22 Years Tomorrow
by By Cam TyesonFun as it may be to think of a world where the greedy corporate fat cats atop the oven and stovetop industries are sent to the poor house because people can cook shit by putting it outside, the various on-going weather crises in Australia look set to settle in for a particularly brutal summer. And tomorrow, Melbourne is staring straight down the barrel of copping its hottest November day in over two decades as a result.
The Bureau of Meteorology currently has the Victorian capital braced for a high of an eye-watering 39 degrees tomorrow, but there are fears the mercury could rise up over the 40 mark, which would make it the first time Melbourne has hit 40 or above in November since 1997.
A furnace-like northerly is the culprit for this latest bout of high temperatures, which will arrive at some point this evening and push today’s temperature up above 30.
This comes after a day where vast tracks of South Australia, including Adelaide, are nudging up over 40 degrees, with some areas tipped to go as high as 45.
That’s 45 degrees celsius.
In November.
Large portions of South Australia, including Port Lincoln and the Adelaide Hills, are under Catastrophic level fire warnings today.
Victoria’s Mallee and Northern Country regions have been given Severe danger ratings for tomorrow.
Image: Getty Images / Scott Barbour


Packages¶
Packages is the means to provide inversion of control. The basic package simply has:
- A name
- A list of names to import
- The list of objects to export
For example:
new function() {
base2.package(this, {
name: "zoo",
imports: "miruken",
exports: "Animal,Eagle,Mouse"
});
eval(imports);
const Animal = Base.extend({
});
const Eagle = Animal.extend({
shriek: function(){
// make a sound
}
});
const Mouse = Animal.extend({
squeak: function(){
// make a sound
}
});
eval(exports);
};
Imports¶
Using imports states that names of package(s) to be available in your closure. This is in essence makes classes defined in packages available in the closure. To start, you will need to bring in miruken. You will also need to run the eval function to actually import those classes.
For example:
new function() {
base2.package(this, {
name: "logging",
imports: "miruken"
});
eval(this.imports);
}
If you need to import multiple names under the imports property, just separate them with a comma. Order does not matter.
Exports¶
Using exports states that classes defined in the closure to be available for other closures. Similar to imports, you need to call the eval to actually export the classes.
For example:
new function() {
base2.package(this, {
name: "logging",
imports: "miruken"
});
eval(this.imports);
const loggingProtocol = Protocol.extend({
debug(){},
error(){}
});
const NullLogger = Base.extend(loggingProtocol, {
debug(){},
error(){}
});
let nullLogger = new NullLogger();
const Logger = Base.extend(loggingProtocol, {
debug(message){
console.log(`DEBUG: ${message}`);
},
error(message){
console.log(`ERROR: ${message}`);
}
}, {
get NullLogger(){
return nullLogger
}
});
eval(this.exports);
}
When you list your objects under the exports property, just separate them with a comma. Order does not matter.
Naming¶
The name is similar to namespace, meaning how would you organize or categorize your objects. The name is used during import to get a collection of objects for a given namespace and make them available for the particular closure.
For example:
name: company.security name: company.http name: company.accounting name: company.security.cookies
Once you create the name, you can import as shown above.
new function() {
base2.package(this, {
name : "company.security.cookies",
imports : "miruken,company.security,company.http"
});
eval(this.imports);
});
File Separation¶
A file can have one object defined for a package or group objects. It is often best practice to keep objects in separate files. If you choose to use separate files for your objects, the name of the package is the same. When you call eval, it searches for all the files for a given package name.
Person.js
new function() {
base2.package(this, {
name : "person",
exports: "Person"
});
eval(this.imports);
const Person = Base.extend({
$properties: {
firstName: null,
lastName : null,
gender : null
},
get fullName(){
return `${this.firstName} ${this.lastName}`
}
}, {
male : "MALE",
female : "FEMALE",
itsComplicated: "ITSCOMPLICATED"
});
eval(this.exports);
};
Patient.js
new function() {
base2.package(this, {
name : "person",
imports : "person",
exports : "Patient"
});
eval(this.imports);
const Patient = Person.extend({
$properties: {
exams: []
}
});
eval(this.exports);
};
Student.js
new function() {
base2.package(this, {
name : "person",
imports : "person",
exports : "Student"
});
eval(this.imports);
const Student = Person.extend({
$properties: {
grade: 0
}
});S
eval(this.exports);
};


Naked CSS
The responsive front-end & back-end Framework
you've been waiting for.
Explore
Download Latest Version


Meet the team - our office rats:
Flinder is a service that provides aspiring students with suggestions for colleges and majors that fit their person interests. Flinder utilizes data from hundreds of colleges and universites nationwide in order to match future students with the perfect institution for them. We believe that if students are going to pay for a higher education, they should first understand which institutions suits them best. Whatever your personal preferences are, Flinder can match you with a major that best fits your interests and aspirations.
350 Spelman Lane
Atlanta, Georgia
830 Westview Drive
Atlanta, Georgia
Find the Major or College that Fits You Here At Flinder.
Flinder Funnies
College Search
Flinder Funnies
Say How You Feel
<EMAIL_ADDRESS><EMAIL_ADDRESS><EMAIL_ADDRESS><EMAIL_ADDRESS>Leave a review!
~ User Reviews ~


Bong Tan passes away at 53
Lucio “Bong” Tan Jr., the newly-appointed President of PAL Holdings Inc. and the son of taipan Lucio Tan, has passed away at the age of 53 after being hospitalized when he fell unconscious during a basketball game last Saturday.
In a statement, his sister Vivienne K. Tan said: “It is with deep sorrow that I announce the passing of my brother, Lucio “Bong” Tan, Jr. this morning, November 11, 2019. He was 53.”
“His untimely passing leaves a big void in our hearts and our Group’s management team which would be very hard to fill. Bong was a son, husband, father, friend and, most importantly, our elder brother whom we all relied on for advice, counsel and leadership,” she added.
He is survived by his wife Julie and sons Hun hun (Lucio Tan III) and Kyle Tan.
“Our sincerest thanks to all who offered prayers and shared words of comfort during this hour of grief. Our family continues to request everyone to respect our wish for privacy as we go through this very difficult time. We ask for your prayers for the eternal repose of his soul. Wake details will be announced soon,” she said. (James A. Loyola)


CruiseControl.NET
Search
Home
Projects
All Projects
?
Register
Sign in
Login
Password
Stay logged in
Lost password
|
Register
CruiseControl.NET
Overview
Activity
Roadmap
1.9
1.8
Issues
New issue
View all open issues
New saved query
Issue summary
Time entries
New time entry
Time entry report
Gantt
Calendar
News
Add news
Documents
New document
Wiki
Index by title
Index by date
Forums
New forum
General Discussion
Help
Coding
Files
New file
Repository
Wiki
Start page
Index by title
Index by date
History
Wiki
»
Configuration
»
ConfiguringTheServer
»
Security
»
Security Configuration
»
Server Level Security
¶
The following elements are defined at the server level for security:
Channel Security
Encrypted Messages Channel
External File Server Security
Internal Server Security
Null Server Security
Security Audit Loggers
XML File Audit Logger
Security Audit Readers
XML File Audit Reader
Security Caches
File Based Security Cache
In Memory Security Cache
Security Users
LDAP User Authentication
User Name Authentication
User Password Authentication
Loading...


Querying is a way of selecting or filtering data, and is a very powerful capability of GIS.
If you’ve searched on the Internet then you are familiar with text searches. You can do the same type of query in a GIS. These are known as attribute queries and give you the same power as working in a conventional spreadsheet or database.
What makes GIS especially powerful is the ability to perform spatial queries, or queries based on location.
Some spatial relationships you can use in queries:
Study the image below illustrating using a buffer and select features within a distance of another feature. This uses the ‘within’ relationship to perform a ‘within a distance of’ query. The ‘distance’ part was done when we created the buffer. Here we have done a spatial query to see which restaurants are within the 1 km buffer of Aster Palms Guest House.


Hello
FirstName
, welcome to Yottr.
Your username is
UserBob
which you will need to log in.
Happy sailing!
Log in


Home
Updates
About
Projects
Contact
MineToUnlock
PrivateGER's Projects
MTU (MineToUnlock)
Check it out!


{% extends "base_site.html" %} {% block content %}
We couldn't find the page you requested. If you believe this is in error, please contact pbs_support@dpaw.wa.gov.au".


get from keythereum.recover(password, JSON.parse(fs.readFileSync(keyStorePath, 'utf8'))),
Customize the transaction with the user data
Calculate the user nonce. It is async to ask Web3 bust it is sync to set it manually TODO: review the promise @param {object} endPoint @param {string} type web3, selfManaged or others.. @param {address} address user
Sign the payload data
transaction to be signed
tx hash
Generated using TypeDoc


Borrower's Information
Item Information
Included Items
Laptop bag
Power cable
VGA adaptor
DVI adaptor
Date Out
  COUNTRY
  LOCATION
  BALANCE
  DATE


List of Employees
Employees...
Link
Employee ID
First Name
Last Name
Hire Date
Department
Salary
DELETE
Bob
ID
First Name
Last Name
Hire Date
Department
Salary


Program Version:EnergyPlus, Version 9.1.0-08d2e308bb, YMD=2021.07.16 12:27
Tabular Output Report in Format: HTML
Building: Ref Bldg Medium Office New2004_v1.3_5.0
Environment: PHILADELPHIA 2014 ** PHILADELPHIA - USA Custom-720304 WMO#=720304
Simulation Timestamp: 2021-07-16 12:27:07
Report: Annual Building Utility Performance Summary
For: Entire Facility
Timestamp: 2021-07-16 12:27:07
Values gathered over 8760.00 hours| Total Energy [GJ] | Energy Per Total Building Area [MJ/m2] | Energy Per Conditioned Building Area [MJ/m2] | |
| Total Site Energy | 2604.43 | 522.75 | 522.75 |
| Net Site Energy | 2604.43 | 522.75 | 522.75 |
| Total Source Energy | 8504.63 | 1707.01 | 1707.01 |
| Net Source Energy | 8504.63 | 1707.01 | 1707.01 |
| Site=>Source Conversion Factor | |
| Electricity | 3.546 |
| Natural Gas | 1.092 |
| District Cooling | 0.848 |
| District Heating | 1.647 |
| Steam | 0.585 |
| Gasoline | 1.050 |
| Diesel | 1.050 |
| Coal | 1.050 |
| Fuel Oil #1 | 1.050 |
| Fuel Oil #2 | 1.050 |
| Propane | 1.050 |
| Other Fuel 1 | 1.000 |
| Other Fuel 2 | 1.000 |
| Area [m2] | |
| Total Building Area | 4982.19 |
| Net Conditioned Building Area | 4982.19 |
| Unconditioned Building Area | 0.00 |
| Electricity [GJ] | Natural Gas [GJ] | Additional Fuel [GJ] | District Cooling [GJ] | District Heating [GJ] | Water [m3] | |
| Heating | 244.08 | 261.62 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | 308.19 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 566.57 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 232.69 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 879.79 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 75.09 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 0.27 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 36.13 | 0.00 | 0.00 | 0.00 | 174.75 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total End Uses | 2306.68 | 297.75 | 0.00 | 0.00 | 0.00 | 174.75 |
| Subcategory | Electricity [GJ] | Natural Gas [GJ] | Additional Fuel [GJ] | District Cooling [GJ] | District Heating [GJ] | Water [m3] | |
| Heating | General | 244.08 | 261.62 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | General | 308.19 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | General | 566.57 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | Exterior Facade Lighting | 232.69 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | General | 714.87 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Elevators | 164.92 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Exterior Equipment | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | Fan Energy | 75.09 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | General | 0.27 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | Water Heater | 0.00 | 36.13 | 0.00 | 0.00 | 0.00 | 0.00 |
| General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 174.75 | |
| Refrigeration | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Electricity Intensity [MJ/m2] | Natural Gas Intensity [MJ/m2] | Additional Fuel Intensity [MJ/m2] | District Cooling Intensity [MJ/m2] | District Heating Intensity [MJ/m2] | Water Intensity [m3/m2] | |
| Lighting | 160.42 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| HVAC | 125.97 | 59.76 | 0.00 | 0.00 | 0.00 | 0.04 |
| Other | 176.59 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total | 462.99 | 59.76 | 0.00 | 0.00 | 0.00 | 0.04 |
| Electricity Intensity [MJ/m2] | Natural Gas Intensity [MJ/m2] | Additional Fuel Intensity [MJ/m2] | District Cooling Intensity [MJ/m2] | District Heating Intensity [MJ/m2] | Water Intensity [m3/m2] | |
| Lighting | 160.42 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| HVAC | 125.97 | 59.76 | 0.00 | 0.00 | 0.00 | 0.04 |
| Other | 176.59 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total | 462.99 | 59.76 | 0.00 | 0.00 | 0.00 | 0.04 |
| Electricity [GJ] | Percent Electricity [%] | |
| Fuel-Fired Power Generation | 0.000 | 0.00 |
| High Temperature Geothermal* | 0.000 | 0.00 |
| Photovoltaic Power | 0.000 | 0.00 |
| Wind Power | 0.000 | 0.00 |
| Power Conversion | 0.000 | 0.00 |
| Net Decrease in On-Site Storage | 0.000 | 0.00 |
| Total On-Site Electric Sources | 0.000 | 0.00 |
| Electricity Coming From Utility | 2306.680 | 100.00 |
| Surplus Electricity Going To Utility | 0.000 | 0.00 |
| Net Electricity From Utility | 2306.680 | 100.00 |
| Total On-Site and Utility Electric Sources | 2306.680 | 100.00 |
| Total Electricity End Uses | 2306.680 | 100.00 |
| Heat [GJ] | Percent Heat [%] | |
| Water-Side Heat Recovery | 0.00 | |
| Air to Air Heat Recovery for Cooling | 0.00 | |
| Air to Air Heat Recovery for Heating | 0.00 | |
| High-Temperature Geothermal* | 0.00 | |
| Solar Water Thermal | 0.00 | |
| Solar Air Thermal | 0.00 | |
| Total On-Site Thermal Sources | 0.00 |
| Water [m3] | Percent Water [%] | |
| Rainwater Collection | 0.00 | 0.00 |
| Condensate Collection | 0.00 | 0.00 |
| Groundwater Well | 0.00 | 0.00 |
| Total On Site Water Sources | 0.00 | 0.00 |
| - | - | - |
| Initial Storage | 0.00 | 0.00 |
| Final Storage | 0.00 | 0.00 |
| Change in Storage | 0.00 | 0.00 |
| - | - | - |
| Water Supplied by Utility | 174.75 | 100.00 |
| - | - | - |
| Total On Site, Change in Storage, and Utility Water Sources | 174.75 | 100.00 |
| Total Water End Uses | 174.75 | 100.00 |
| Degrees [deltaC] | |
| Tolerance for Zone Heating Setpoint Not Met Time | 0.56 |
| Tolerance for Zone Cooling Setpoint Not Met Time | 0.56 |
| Facility [Hours] | |
| Time Setpoint Not Met During Occupied Heating | 7.83 |
| Time Setpoint Not Met During Occupied Cooling | 0.17 |
| Time Not Comfortable Based on Simple ASHRAE 55-2004 | 2987.17 |
Table of Contents
TopEMISSIONS DATA SUMMARY
| Meter |COMPONENTS OF PEAK ELECTRICAL DEMAND
| Meter |HEATING PART LOAD PERFORMANCE
| VAV_1_HEATC | VAV_2_HEATC | VAV_3_HEATC |COOLING PART LOAD PERFORMANCE
| VAV_1_COOLC DXCOIL | VAV_2_COOLC DXCOIL | VAV_3_COOLC DXCOIL |FAN PART LOAD PERFORMANCE
| VAV_1_FAN | VAV_2_FAN | VAV_3_FAN |Report: Input Verification and Results Summary
For: Entire Facility
Timestamp: 2021-07-16 12:27:07
General| Value | |
| Program Version and Build | EnergyPlus, Version 9.1.0-08d2e308bb, YMD=2021.07.16 12:27 |
| RunPeriod | PHILADELPHIA 2014 |
| Weather File | PHILADELPHIA - USA Custom-720304 WMO#=720304 |
| Latitude [deg] | 40.14 |
| Longitude [deg] | -75.3 |
| Elevation [m] | 92.00 |
| Time Zone | -5.0 |
| North Axis Angle [deg] | 0.00 |
| Rotation for Appendix G [deg] | 0.00 |
| Hours Simulated [hrs] | 8760.00 |
| Total | North (315 to 45 deg) | East (45 to 135 deg) | South (135 to 225 deg) | West (225 to 315 deg) | |
| Gross Wall Area [m2] | 1977.67 | 593.30 | 395.53 | 593.30 | 395.53 |
| Above Ground Wall Area [m2] | 1977.67 | 593.30 | 395.53 | 593.30 | 395.53 |
| Window Opening Area [m2] | 652.83 | 195.85 | 130.57 | 195.85 | 130.57 |
| Gross Window-Wall Ratio [%] | 33.01 | 33.01 | 33.01 | 33.01 | 33.01 |
| Above Ground Window-Wall Ratio [%] | 33.01 | 33.01 | 33.01 | 33.01 | 33.01 |
| Total | North (315 to 45 deg) | East (45 to 135 deg) | South (135 to 225 deg) | West (225 to 315 deg) | |
| Gross Wall Area [m2] | 1977.67 | 593.30 | 395.53 | 593.30 | 395.53 |
| Above Ground Wall Area [m2] | 1977.67 | 593.30 | 395.53 | 593.30 | 395.53 |
| Window Opening Area [m2] | 652.83 | 195.85 | 130.57 | 195.85 | 130.57 |
| Gross Window-Wall Ratio [%] | 33.01 | 33.01 | 33.01 | 33.01 | 33.01 |
| Above Ground Window-Wall Ratio [%] | 33.01 | 33.01 | 33.01 | 33.01 | 33.01 |
| Total | |
| Gross Roof Area [m2] | 1660.73 |
| Skylight Area [m2] | 0.00 |
| Skylight-Roof Ratio [%] | 0.00 |
| Area [m2] | Conditioned (Y/N) | Part of Total Floor Area (Y/N) | Volume [m3] | Multipliers | Above Ground Gross Wall Area [m2] | Underground Gross Wall Area [m2] | Window Glass Area [m2] | Opening Area [m2] | Lighting [W/m2] | People [m2 per person] | Plug and Process [W/m2] | |
| CORE_BOTTOM | 983.54 | Yes | Yes | 2698.04 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 10.0460 | 14.09 | 41.1744 |
| CORE_MID | 983.54 | Yes | Yes | 2698.04 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 10.0460 | 14.09 | 8.5270 |
| CORE_TOP | 983.54 | Yes | Yes | 2698.04 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 10.0460 | 14.09 | 8.5270 |
| FIRSTFLOOR_PLENUM | 1660.73 | Yes | No | 2024.76 | 1.00 | 202.84 | 0.00 | 0.00 | 0.00 | 0.0000 | 0.0000 | |
| MIDFLOOR_PLENUM | 1660.73 | Yes | No | 2024.76 | 1.00 | 202.84 | 0.00 | 0.00 | 0.00 | 0.0000 | 0.0000 | |
| PERIMETER_BOT_ZN_1 | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 10.0460 | 14.09 | 8.5270 |
| PERIMETER_BOT_ZN_2 | 131.26 | Yes | Yes | 360.08 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 10.0460 | 14.09 | 8.5270 |
| PERIMETER_BOT_ZN_3 | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 10.0460 | 14.09 | 8.5270 |
| PERIMETER_BOT_ZN_4 | 131.25 | Yes | Yes | 360.05 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 10.0460 | 14.09 | 8.5270 |
| PERIMETER_MID_ZN_1 | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 10.0460 | 14.09 | 8.5270 |
| PERIMETER_MID_ZN_2 | 131.26 | Yes | Yes | 360.08 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 10.0460 | 14.09 | 8.5270 |
| PERIMETER_MID_ZN_3 | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 10.0460 | 14.09 | 8.5270 |
| PERIMETER_MID_ZN_4 | 131.25 | Yes | Yes | 360.05 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 10.0460 | 14.09 | 8.5270 |
| PERIMETER_TOP_ZN_1 | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 10.0460 | 14.09 | 8.5270 |
| PERIMETER_TOP_ZN_2 | 131.26 | Yes | Yes | 360.08 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 10.0460 | 14.09 | 8.5270 |
| PERIMETER_TOP_ZN_3 | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 10.0460 | 14.09 | 8.5270 |
| PERIMETER_TOP_ZN_4 | 131.25 | Yes | Yes | 360.05 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 10.0460 | 14.09 | 8.5270 |
| TOPFLOOR_PLENUM | 1660.73 | Yes | No | 2024.76 | 1.00 | 202.84 | 0.00 | 0.00 | 0.00 | 0.0000 | 0.0000 | |
| Total | 4982.19 | 13667.13 | 1369.16 | 0.00 | 652.83 | 652.83 | 10.0460 | 14.09 | 14.9719 | |||
| Conditioned Total | 4982.19 | 13667.13 | 1369.16 | 0.00 | 652.83 | 652.83 | 10.0460 | 14.09 | 14.9719 | |||
| Unconditioned Total | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | ||||||
| Not Part of Total | 4982.19 | 6074.28 | 608.51 | 0.00 | 0.00 | 0.00 | 0.0000 | 0.0000 |
Report: Component Sizing Summary
For: Entire Facility
Timestamp: 2021-07-16 12:27:07
AirTerminal:SingleDuct:VAV:Reheat| Design Size Maximum Air Flow Rate [m3/s] | Design Size Constant Minimum Air Flow Fraction | User-Specified Constant Minimum Air Flow Fraction | Design Size Minimum Air Flow Rate [m3/s] | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | Design Size Maximum Flow Fraction during Reheat [] | |
| CORE_BOTTOM VAV BOX COMPONENT | 3.97 | 0.200000 | 0.300000 | 1.19 | 0.001212 | 0.300000 |
| CORE_MID VAV BOX COMPONENT | 3.64 | 0.205705 | 0.300000 | 1.09 | 0.001111 | 0.300000 |
| CORE_TOP VAV BOX COMPONENT | 3.87 | 0.200000 | 0.300000 | 1.16 | 0.001179 | 0.300000 |
| PERIMETER_BOT_ZN_1 VAV BOX COMPONENT | 0.934218 | 0.200000 | 0.300000 | 0.280266 | 0.001352 | 0.300000 |
| PERIMETER_BOT_ZN_2 VAV BOX COMPONENT | 0.896837 | 0.200000 | 0.300000 | 0.269051 | 0.002050 | 0.300000 |
| PERIMETER_BOT_ZN_3 VAV BOX COMPONENT | 0.708460 | 0.223007 | 0.300000 | 0.212538 | 0.001025 | 0.300000 |
| PERIMETER_BOT_ZN_4 VAV BOX COMPONENT | 0.987145 | 0.200000 | 0.300000 | 0.296144 | 0.002256 | 0.300000 |
| PERIMETER_MID_ZN_1 VAV BOX COMPONENT | 1.08 | 0.200000 | 0.300000 | 0.323004 | 0.001558 | 0.300000 |
| PERIMETER_MID_ZN_2 VAV BOX COMPONENT | 0.997289 | 0.200000 | 0.300000 | 0.299187 | 0.002279 | 0.300000 |
| PERIMETER_MID_ZN_3 VAV BOX COMPONENT | 0.837425 | 0.200000 | 0.300000 | 0.251227 | 0.001212 | 0.300000 |
| PERIMETER_MID_ZN_4 VAV BOX COMPONENT | 1.06 | 0.200000 | 0.300000 | 0.319436 | 0.002434 | 0.300000 |
| PERIMETER_TOP_ZN_1 VAV BOX COMPONENT | 1.12 | 0.200000 | 0.300000 | 0.335919 | 0.001620 | 0.300000 |
| PERIMETER_TOP_ZN_2 VAV BOX COMPONENT | 0.994386 | 0.200000 | 0.300000 | 0.298316 | 0.002273 | 0.300000 |
| PERIMETER_TOP_ZN_3 VAV BOX COMPONENT | 0.933102 | 0.200000 | 0.300000 | 0.279931 | 0.001350 | 0.300000 |
| PERIMETER_TOP_ZN_4 VAV BOX COMPONENT | 1.13 | 0.200000 | 0.300000 | 0.339114 | 0.002584 | 0.300000 |
| Design Size Nominal Capacity [W] | |
| CORE_BOTTOM VAV BOX REHEAT COIL | 48225.57 |
| CORE_MID VAV BOX REHEAT COIL | 44211.95 |
| CORE_TOP VAV BOX REHEAT COIL | 46916.43 |
| PERIMETER_BOT_ZN_1 VAV BOX REHEAT COIL | 11336.71 |
| PERIMETER_BOT_ZN_2 VAV BOX REHEAT COIL | 10883.08 |
| PERIMETER_BOT_ZN_3 VAV BOX REHEAT COIL | 10626.26 |
| PERIMETER_BOT_ZN_4 VAV BOX REHEAT COIL | 11978.98 |
| PERIMETER_MID_ZN_1 VAV BOX REHEAT COIL | 13065.47 |
| PERIMETER_MID_ZN_2 VAV BOX REHEAT COIL | 12102.07 |
| PERIMETER_MID_ZN_3 VAV BOX REHEAT COIL | 12732.00 |
| PERIMETER_MID_ZN_4 VAV BOX REHEAT COIL | 12921.15 |
| PERIMETER_TOP_ZN_1 VAV BOX REHEAT COIL | 16694.81 |
| PERIMETER_TOP_ZN_2 VAV BOX REHEAT COIL | 12066.84 |
| PERIMETER_TOP_ZN_3 VAV BOX REHEAT COIL | 16509.11 |
| PERIMETER_TOP_ZN_4 VAV BOX REHEAT COIL | 13717.15 |
| Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | Sum of Air Terminal Maximum Flow Rates [m3/s] | Adjusted Heating Design Air Flow Rate [m3/s] | Adjusted Cooling Design Air Flow Rate [m3/s] | Adjusted Main Design Air Flow Rate [m3/s] | User Heating Air Flow Ratio [] | Calculated Heating Air Flow Ratio [] | Design Supply Air Flow Rate [m3/s] | |
| VAV_1 | 2.25 | 2.25 | 7.50 | 2.25 | 7.50 | 7.50 | 0.300000 | 0.300000 | 7.50 |
| VAV_2 | 2.29 | 2.29 | 7.62 | 2.29 | 7.62 | 7.62 | 0.300000 | 0.300000 | 7.62 |
| VAV_3 | 2.41 | 2.41 | 8.04 | 2.41 | 8.04 | 8.04 | 0.300000 | 0.300000 | 8.04 |
| Maximum Outdoor Air Flow Rate [m3/s] | Minimum Outdoor Air Flow Rate [m3/s] | |
| VAV_1_OA_CONTROLLER | 7.50 | 1.47 |
| VAV_2_OA_CONTROLLER | 7.62 | 1.47 |
| VAV_3_OA_CONTROLLER | 8.04 | 1.47 |
| Design Size High Speed Rated Air Flow Rate [m3/s] | Design Size High Speed Gross Rated Total Cooling Capacity [W] | Design Size High Speed Rated Sensible Heat Ratio | Design Size Low Speed Rated Air Flow Rate [m3/s] | Design Size Low Speed Gross Rated Total Cooling Capacity [W] | Design Size Low Speed Gross Rated Sensible Heat Ratio | |
| VAV_1_COOLC DXCOIL | 7.50 | 158500.57 | 0.752009 | 2.50 | 52828.24 | 0.752009 |
| VAV_2_COOLC DXCOIL | 7.62 | 152777.40 | 0.771530 | 2.54 | 50920.71 | 0.771530 |
| VAV_3_COOLC DXCOIL | 8.04 | 162141.40 | 0.768926 | 2.68 | 54041.73 | 0.768926 |
| Design Size Design Maximum Air Flow Rate [m3/s] | Design Electric Power Consumption [W] | |
| VAV_1_FAN | 7.50 | 14071.35 |
| Design Size Nominal Capacity [W] | |
| VAV_1_HEATC | 63637.85 |
| VAV_2_HEATC | 63538.58 |
| VAV_3_HEATC | 63184.03 |
| Design Size Maximum Flow Rate [m3/s] | |
| VAV_2_FAN | 7.62 |
| VAV_3_FAN | 8.04 |
| Maximum Loop Flow Rate [m3/s] | Plant Loop Volume [m3] | |
| SWHSYS1 | 0.000031 | 0.003744 |
| Design Flow Rate [m3/s] | Design Power Consumption [W] | |
| SWHSYS1 PUMP | 0.000031 | 8.44 |
| Use Side Design Flow Rate [m3/s] | |
| SWHSYS1 WATER HEATER | 0.000031 |
Report: Climatic Data Summary
For: Entire Facility
Timestamp: 2021-07-16 12:27:07
SizingPeriod:DesignDay| Maximum Dry Bulb [C] | Daily Temperature Range [deltaC] | Humidity Value | Humidity Type | Wind Speed [m/s] | Wind Direction | |
| CHICAGO ANN HTG 99.6% CONDNS DB | -20.60 | 0.00 | -20.60 | Wetbulb [C] | 4.90 | 270.00 |
| CHICAGO ANN CLG .4% CONDNS WB=>MDB | 31.20 | 10.70 | 25.50 | Wetbulb [C] | 5.30 | 230.00 |
| Value | |
| None |
Report: Envelope Summary
For: Entire Facility
Timestamp: 2021-07-16 12:27:07
Opaque Exterior| Construction | Reflectance | U-Factor with Film [W/m2-K] | U-Factor no Film [W/m2-K] | Gross Area [m2] | Net Area [m2] | Azimuth [deg] | Tilt [deg] | Cardinal Direction | |
| CORE_BOT_ZN_5_FLOOR | EXT-SLAB | 0.30 | 2.193 | 3.401 | 983.54 | 983.54 | 0.00 | 180.00 | |
| PERIMETER_BOT_PLENUM_WALL_EAST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 40.57 | 40.57 | 90.00 | 90.00 | E |
| PERIMETER_BOT_PLENUM_WALL_NORTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 60.85 | 60.85 | 0.00 | 90.00 | N |
| PERIMETER_BOT_PLENUM_WALL_SOUTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 60.85 | 60.85 | 180.00 | 90.00 | S |
| PERIMETER_BOT_PLENUM_WALL_WEST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 40.57 | 40.57 | 270.00 | 90.00 | W |
| PERIMETER_MID_PLENUM_WALL_EAST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 40.57 | 40.57 | 90.00 | 90.00 | E |
| PERIMETER_MID_PLENUM_WALL_NORTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 60.85 | 60.85 | 0.00 | 90.00 | N |
| PERIMETER_MID_PLENUM_WALL_SOUTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 60.85 | 60.85 | 180.00 | 90.00 | S |
| PERIMETER_MID_PLENUM_WALL_WEST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 40.57 | 40.57 | 270.00 | 90.00 | W |
| PERIMETER_BOT_ZN_1_WALL_SOUTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 136.92 | 71.63 | 180.00 | 90.00 | S |
| PERIMETER_BOT_ZN_1_FLOOR | EXT-SLAB | 0.30 | 2.193 | 3.401 | 207.34 | 207.34 | 180.00 | 180.00 | |
| PERIMETER_BOT_ZN_2_WALL_EAST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 91.28 | 47.75 | 90.00 | 90.00 | E |
| PERIMETER_BOT_ZN_2_FLOOR | EXT-SLAB | 0.30 | 2.193 | 3.401 | 131.26 | 131.26 | 90.00 | 180.00 | |
| PERIMETER_BOT_ZN_3_WALL_NORTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 136.92 | 71.63 | 0.00 | 90.00 | N |
| PERIMETER_BOT_ZN_3_FLOOR | EXT-SLAB | 0.30 | 2.193 | 3.401 | 207.34 | 207.34 | 0.00 | 180.00 | |
| PERIMETER_BOT_ZN_4_WALL_WEST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 91.28 | 47.75 | 270.00 | 90.00 | W |
| PERIMETER_BOT_ZN_4_FLOOR | EXT-SLAB | 0.30 | 2.193 | 3.401 | 131.25 | 131.25 | 270.00 | 180.00 | |
| PERIMETER_MID_ZN_1_WALL_SOUTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 136.92 | 71.63 | 180.00 | 90.00 | S |
| PERIMETER_MID_ZN_2_WALL_EAST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 91.28 | 47.75 | 90.00 | 90.00 | E |
| PERIMETER_MID_ZN_3_WALL_NORTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 136.92 | 71.63 | 0.00 | 90.00 | N |
| PERIMETER_MID_ZN_4_WALL_WEST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 91.28 | 47.75 | 270.00 | 90.00 | W |
| PERIMETER_TOP_ZN_1_WALL_SOUTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 136.92 | 71.63 | 180.00 | 90.00 | S |
| PERIMETER_TOP_ZN_2_WALL_EAST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 91.28 | 47.75 | 90.00 | 90.00 | E |
| PERIMETER_TOP_ZN_3_WALL_NORTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 136.92 | 71.63 | 0.00 | 90.00 | N |
| PERIMETER_TOP_ZN_4_WALL_WEST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 91.28 | 47.75 | 270.00 | 90.00 | W |
| PERIMETER_TOP_PLENUM_WALL_EAST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 40.57 | 40.57 | 90.00 | 90.00 | E |
| PERIMETER_TOP_PLENUM_WALL_NORTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 60.85 | 60.85 | 0.00 | 90.00 | N |
| PERIMETER_TOP_PLENUM_WALL_SOUTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 60.85 | 60.85 | 180.00 | 90.00 | S |
| PERIMETER_TOP_PLENUM_WALL_WEST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 40.57 | 40.57 | 270.00 | 90.00 | W |
| BUILDING_ROOF | IEAD NON-RES ROOF | 0.30 | 0.358 | 0.376 | 1660.73 | 1660.73 | 0.00 | 0.00 |
| Construction | Glass Area [m2] | Frame Area [m2] | Divider Area [m2] | Area of One Opening [m2] | Area of Multiplied Openings [m2] | Glass U-Factor [W/m2-K] | Glass SHGC | Glass Visible Transmittance | Frame Conductance [W/m2-K] | Divider Conductance [W/m2-K] | Shade Control | Parent Surface | Azimuth [deg] | Tilt [deg] | Cardinal Direction | |
| PERIMETER_BOT_ZN_1_WALL_SOUTH_WINDOW | WINDOW NON-RES FIXED | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 4.717 | 0.228 | 0.094 | No | PERIMETER_BOT_ZN_1_WALL_SOUTH | 180.00 | 90.00 | S | ||
| PERIMETER_BOT_ZN_2_WALL_EAST_WINDOW | WINDOW NON-RES FIXED | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 4.717 | 0.228 | 0.094 | No | PERIMETER_BOT_ZN_2_WALL_EAST | 90.00 | 90.00 | E | ||
| PERIMETER_BOT_ZN_3_WALL_NORTH_WINDOW | WINDOW NON-RES FIXED | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 4.717 | 0.228 | 0.094 | No | PERIMETER_BOT_ZN_3_WALL_NORTH | 0.00 | 90.00 | N | ||
| PERIMETER_BOT_ZN_4_WALL_WEST_WINDOW | WINDOW NON-RES FIXED | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 4.717 | 0.228 | 0.094 | No | PERIMETER_BOT_ZN_4_WALL_WEST | 270.00 | 90.00 | W | ||
| PERIMETER_MID_ZN_1_WALL_SOUTH_WINDOW | WINDOW NON-RES FIXED | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 4.717 | 0.228 | 0.094 | No | PERIMETER_MID_ZN_1_WALL_SOUTH | 180.00 | 90.00 | S | ||
| PERIMETER_MID_ZN_2_WALL_EAST_WINDOW | WINDOW NON-RES FIXED | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 4.717 | 0.228 | 0.094 | No | PERIMETER_MID_ZN_2_WALL_EAST | 90.00 | 90.00 | E | ||
| PERIMETER_MID_ZN_3_WALL_NORTH_WINDOW | WINDOW NON-RES FIXED | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 4.717 | 0.228 | 0.094 | No | PERIMETER_MID_ZN_3_WALL_NORTH | 0.00 | 90.00 | N | ||
| PERIMETER_MID_ZN_4_WALL_WEST_WINDOW | WINDOW NON-RES FIXED | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 4.717 | 0.228 | 0.094 | No | PERIMETER_MID_ZN_4_WALL_WEST | 270.00 | 90.00 | W | ||
| PERIMETER_TOP_ZN_1_WALL_SOUTH_WINDOW | WINDOW NON-RES FIXED | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 4.717 | 0.228 | 0.094 | No | PERIMETER_TOP_ZN_1_WALL_SOUTH | 180.00 | 90.00 | S | ||
| PERIMETER_TOP_ZN_2_WALL_EAST_WINDOW | WINDOW NON-RES FIXED | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 4.717 | 0.228 | 0.094 | No | PERIMETER_TOP_ZN_2_WALL_EAST | 90.00 | 90.00 | E | ||
| PERIMETER_TOP_ZN_3_WALL_NORTH_WINDOW | WINDOW NON-RES FIXED | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 4.717 | 0.228 | 0.094 | No | PERIMETER_TOP_ZN_3_WALL_NORTH | 0.00 | 90.00 | N | ||
| PERIMETER_TOP_ZN_4_WALL_WEST_WINDOW | WINDOW NON-RES FIXED | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 4.717 | 0.228 | 0.094 | No | PERIMETER_TOP_ZN_4_WALL_WEST | 270.00 | 90.00 | W | ||
| Total or Average | 652.83 | 4.717 | 0.228 | 0.094 | ||||||||||||
| North Total or Average | 195.85 | 4.717 | 0.228 | 0.094 | ||||||||||||
| Non-North Total or Average | 456.98 | 4.717 | 0.228 | 0.094 |
| Construction | Area of One Opening [m2] | Area of Openings [m2] | Glass U-Factor [W/m2-K] | Glass SHGC | Glass Visible Transmittance | Parent Surface | |
| Total or Average | 0.00 | - | - | - |
| Construction | U-Factor with Film [W/m2-K] | U-Factor no Film [W/m2-K] | Gross Area [m2] | Parent Surface | |
| None |
Report: Equipment Summary
For: Entire Facility
Timestamp: 2021-07-16 12:27:07
Central Plant| Type | Nominal Capacity [W] | Nominal Efficiency [W/W] | IPLV in SI Units [W/W] | IPLV in IP Units [Btu/W-h] | |
| None |
| Type | Design Coil Load [W] | Nominal Total Capacity [W] | Nominal Sensible Capacity [W] | Nominal Latent Capacity [W] | Nominal Sensible Heat Ratio | Nominal Efficiency [W/W] | Nominal Coil UA Value [W/C] | Nominal Coil Surface Area [m2] | |
| VAV_1_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | 158500.57 | 119193.88 | 39306.68 | 0.75 | 3.23 | |||
| VAV_2_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | 152777.40 | 117872.29 | 34905.11 | 0.77 | 3.23 | |||
| VAV_3_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | 162141.40 | 124674.71 | 37466.69 | 0.77 | 3.23 |
| DX Cooling Coil Type | Standard Rated Net Cooling Capacity [W] | Standard Rated Net COP [W/W] | EER [Btu/W-h] | SEER [Btu/W-h] | IEER [Btu/W-h] | |
| VAV_1_COOLC DXCOIL | 157419.1 | 2.80 | 9.54 | N/A | 12.68 | |
| VAV_2_COOLC DXCOIL | 151704.4 | 2.78 | 9.48 | N/A | 12.62 | |
| VAV_3_COOLC DXCOIL | 161054.5 | 2.78 | 9.48 | N/A | 12.63 |
| DX Cooling Coil Type | Rated Net Cooling Capacity Test A [W] | Rated Electric Power Test A [W] | Rated Net Cooling Capacity Test B [W] | Rated Electric Power Test B [W] | Rated Net Cooling Capacity Test C [W] | Rated Electric Power Test C [W] | Rated Net Cooling Capacity Test D [W] | Rated Electric Power Test D [W] | |
| VAV_1_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | ||||||||
| VAV_2_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | ||||||||
| VAV_3_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed |
| DX Heating Coil Type | High Temperature Heating (net) Rating Capacity [W] | Low Temperature Heating (net) Rating Capacity [W] | HSPF [Btu/W-h] | Region Number | |
| None |
| Type | Design Coil Load [W] | Nominal Total Capacity [W] | Nominal Efficiency [W/W] | |
| CORE_BOTTOM VAV BOX REHEAT COIL | Coil:Heating:Electric | 48225.57 | 1.00 | |
| CORE_MID VAV BOX REHEAT COIL | Coil:Heating:Electric | 44211.95 | 1.00 | |
| CORE_TOP VAV BOX REHEAT COIL | Coil:Heating:Electric | 46916.43 | 1.00 | |
| PERIMETER_BOT_ZN_1 VAV BOX REHEAT COIL | Coil:Heating:Electric | 11336.71 | 1.00 | |
| PERIMETER_BOT_ZN_2 VAV BOX REHEAT COIL | Coil:Heating:Electric | 10883.08 | 1.00 | |
| PERIMETER_BOT_ZN_3 VAV BOX REHEAT COIL | Coil:Heating:Electric | 10626.26 | 1.00 | |
| PERIMETER_BOT_ZN_4 VAV BOX REHEAT COIL | Coil:Heating:Electric | 11978.98 | 1.00 | |
| PERIMETER_MID_ZN_1 VAV BOX REHEAT COIL | Coil:Heating:Electric | 13065.47 | 1.00 | |
| PERIMETER_MID_ZN_2 VAV BOX REHEAT COIL | Coil:Heating:Electric | 12102.07 | 1.00 | |
| PERIMETER_MID_ZN_3 VAV BOX REHEAT COIL | Coil:Heating:Electric | 12732.00 | 1.00 | |
| PERIMETER_MID_ZN_4 VAV BOX REHEAT COIL | Coil:Heating:Electric | 12921.15 | 1.00 | |
| PERIMETER_TOP_ZN_1 VAV BOX REHEAT COIL | Coil:Heating:Electric | 16694.81 | 1.00 | |
| PERIMETER_TOP_ZN_2 VAV BOX REHEAT COIL | Coil:Heating:Electric | 12066.84 | 1.00 | |
| PERIMETER_TOP_ZN_3 VAV BOX REHEAT COIL | Coil:Heating:Electric | 16509.11 | 1.00 | |
| PERIMETER_TOP_ZN_4 VAV BOX REHEAT COIL | Coil:Heating:Electric | 13717.15 | 1.00 | |
| VAV_1_HEATC | Coil:Heating:Fuel | 63637.85 | 0.80 | |
| VAV_2_HEATC | Coil:Heating:Fuel | 63538.58 | 0.80 | |
| VAV_3_HEATC | Coil:Heating:Fuel | 63184.03 | 0.80 |
| Type | Total Efficiency [W/W] | Delta Pressure [pa] | Max Air Flow Rate [m3/s] | Rated Electric Power [W] | Rated Power Per Max Air Flow Rate [W-s/m3] | Motor Heat In Air Fraction | Fan Energy Index | End Use Subcategory | Design Day Name for Fan Sizing Peak | Date/Time for Fan Sizing Peak | |
| VAV_1_FAN | Fan:SystemModel | 0.59 | 1109.65 | 7.50 | 14071.35 | 1875.99 | 1.00 | 1.12 | Fan Energy | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 09:00:00 |
| VAV_2_FAN | Fan:VariableVolume | 0.59 | 1109.65 | 7.62 | 14294.16 | 1875.99 | 1.00 | 1.11 | Fan Energy | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 07:00:00 |
| VAV_3_FAN | Fan:VariableVolume | 0.59 | 1109.65 | 8.04 | 15090.12 | 1875.99 | 1.00 | 1.11 | Fan Energy | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 07:00:00 |
| Type | Control | Head [pa] | Water Flow [m3/s] | Electric Power [W] | Power Per Water Flow Rate [W-s/m3] | Motor Efficiency [W/W] | End Use Subcategory | |
| SWHSYS1 PUMP | Pump:ConstantSpeed | Intermittent | 179352.00 | 0.000031 | 8.44 | 270515.84 | 0.85 | General |
| Type | Storage Volume [m3] | Input [W] | Thermal Efficiency [W/W] | Recovery Efficiency [W/W] | Energy Factor | |
| SWHSYS1 WATER HEATER | WaterHeater:Mixed | 0.38 | 845000.00 | 0.80 | 1.83 | 0.57 |
| DX Cooling Coil Type | Assocated Fan | Net Cooling Capacity [W] | COP [W/W] | EER [Btu/W-h] | IEER [Btu/W-h] | Supply Air Flow 100% [kg/s] | COP 75% Capacity [W/W] | EER 75% Capacity [Btu/W-h] | Supply Air Flow 75% [kg/s] | COP 50% Capacity [W/W] | EER 50% Capacity [Btu/W-h] | Supply Air Flow 50% [kg/s] | COP 25% Capacity [W/W] | EER 25% Capacity [Btu/W-h] | Supply Air Flow 25% [kg/s] | |
| VAV_1_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | VAV_1_FAN | 157419.07 | 2.80 | 9.54 | 12.68 | 8.5814 | 3.46 | 11.80 | 6.9277 | 4.16 | 14.21 | 4.6490 | 4.29 | 14.63 | 1.9068 |
| VAV_2_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | VAV_2_FAN | 151704.42 | 2.78 | 9.48 | 12.62 | 8.7173 | 3.44 | 11.73 | 7.0460 | 4.15 | 14.15 | 4.7282 | 4.28 | 14.60 | 1.9091 |
| VAV_3_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | VAV_3_FAN | 161054.48 | 2.78 | 9.48 | 12.63 | 9.2027 | 3.44 | 11.74 | 7.4311 | 4.15 | 14.16 | 4.9840 | 4.28 | 14.61 | 2.0204 |
Report: HVAC Sizing Summary
For: Entire Facility
Timestamp: 2021-07-16 12:27:07
Zone Sensible Cooling| Calculated Design Load [W] | User Design Load [W] | User Design Load per Area [W/m2] | Calculated Design Air Flow [m3/s] | User Design Air Flow [m3/s] | Design Day Name | Date/Time Of Peak {TIMESTAMP} | Thermostat Setpoint Temperature at Peak Load [C] | Indoor Temperature at Peak Load [C] | Indoor Humidity Ratio at Peak Load [kgWater/kgAir] | Outdoor Temperature at Peak Load [C] | Outdoor Humidity Ratio at Peak Load [kgWater/kgAir] | Minimum Outdoor Air Flow Rate [m3/s] | Heat Gain Rate from DOAS [W] | |
| CORE_BOTTOM | 35720.59 | 47508.38 | 48.30 | 2.988 | 3.974 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 09:00:00 | 22.64 | 22.63 | 0.00884 | 25.31 | 0.01878 | 0.873 | 0.00 |
| CORE_MID | 33974.52 | 45186.11 | 45.94 | 2.739 | 3.643 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 07:00:00 | 22.64 | 22.63 | 0.00888 | 21.46 | 0.01650 | 0.873 | 0.00 |
| CORE_TOP | 36024.43 | 47912.49 | 48.71 | 2.907 | 3.866 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 07:00:00 | 22.64 | 22.63 | 0.00886 | 21.46 | 0.01650 | 0.873 | 0.00 |
| PERIMETER_BOT_ZN_1 | 8397.54 | 11168.73 | 53.87 | 0.702 | 0.934 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 13:10:00 | 22.64 | 22.63 | 0.00881 | 30.75 | 0.01878 | 0.184 | 0.00 |
| PERIMETER_BOT_ZN_2 | 8061.66 | 10722.01 | 81.68 | 0.674 | 0.897 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 08:50:00 | 22.64 | 22.63 | 0.00870 | 24.98 | 0.01878 | 0.116 | 0.00 |
| PERIMETER_BOT_ZN_3 | 6630.38 | 8818.41 | 42.53 | 0.533 | 0.708 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 07:00:00 | 22.64 | 22.63 | 0.00897 | 21.46 | 0.01650 | 0.184 | 0.00 |
| PERIMETER_BOT_ZN_4 | 8873.45 | 11801.69 | 89.92 | 0.742 | 0.987 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 17:00:00 | 22.64 | 22.63 | 0.00868 | 29.70 | 0.01878 | 0.116 | 0.00 |
| PERIMETER_MID_ZN_1 | 9678.17 | 12871.97 | 62.08 | 0.810 | 1.077 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 13:10:00 | 22.64 | 22.63 | 0.00877 | 30.75 | 0.01878 | 0.184 | 0.00 |
| PERIMETER_MID_ZN_2 | 8964.68 | 11923.02 | 90.83 | 0.750 | 0.997 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 08:40:00 | 22.64 | 22.63 | 0.00868 | 24.64 | 0.01878 | 0.116 | 0.00 |
| PERIMETER_MID_ZN_3 | 7785.77 | 10355.08 | 49.94 | 0.630 | 0.837 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 07:00:00 | 22.64 | 22.63 | 0.00885 | 21.46 | 0.01650 | 0.184 | 0.00 |
| PERIMETER_MID_ZN_4 | 9571.41 | 12729.98 | 96.99 | 0.801 | 1.065 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 17:00:00 | 22.64 | 22.63 | 0.00867 | 29.70 | 0.01878 | 0.116 | 0.00 |
| PERIMETER_TOP_ZN_1 | 10065.18 | 13386.69 | 64.56 | 0.842 | 1.120 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 13:30:00 | 22.64 | 22.63 | 0.00876 | 30.93 | 0.01878 | 0.184 | 0.00 |
| PERIMETER_TOP_ZN_2 | 8938.57 | 11888.30 | 90.57 | 0.748 | 0.994 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 08:30:00 | 22.64 | 22.63 | 0.00868 | 24.30 | 0.01878 | 0.116 | 0.00 |
| PERIMETER_TOP_ZN_3 | 8387.55 | 11155.44 | 53.80 | 0.702 | 0.933 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 15:40:00 | 22.64 | 22.63 | 0.00881 | 30.77 | 0.01878 | 0.184 | 0.00 |
| PERIMETER_TOP_ZN_4 | 10161.09 | 13514.24 | 102.96 | 0.850 | 1.130 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 17:10:00 | 22.64 | 22.63 | 0.00866 | 29.52 | 0.01878 | 0.116 | 0.00 |
| Calculated Design Load [W] | User Design Load [W] | User Design Load per Area [W/m2] | Calculated Design Air Flow [m3/s] | User Design Air Flow [m3/s] | Design Day Name | Date/Time Of Peak {TIMESTAMP} | Thermostat Setpoint Temperature at Peak Load [C] | Indoor Temperature at Peak Load [C] | Indoor Humidity Ratio at Peak Load [kgWater/kgAir] | Outdoor Temperature at Peak Load [C] | Outdoor Humidity Ratio at Peak Load [kgWater/kgAir] | Minimum Outdoor Air Flow Rate [m3/s] | Heat Gain Rate from DOAS [W] | |
| CORE_BOTTOM | 2376.70 | 3161.01 | 3.21 | 0.063 | 0.873 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | 19.03 | 19.03 | 0.00794 | -20.60 | 0.00061 | 0.873 | 0.00 |
| CORE_MID | 6216.03 | 8267.32 | 8.41 | 0.165 | 0.873 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:10:00 | 19.03 | 19.03 | 0.00800 | -20.60 | 0.00061 | 0.873 | 0.00 |
| CORE_TOP | 17031.41 | 22651.77 | 23.03 | 0.453 | 0.873 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 19.03 | 19.03 | 0.00800 | -20.60 | 0.00061 | 0.873 | 0.00 |
| PERIMETER_BOT_ZN_1 | 7603.47 | 10112.61 | 48.77 | 0.202 | 0.269 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | 19.03 | 19.03 | 0.00800 | -20.60 | 0.00061 | 0.184 | 0.00 |
| PERIMETER_BOT_ZN_2 | 5081.13 | 6757.90 | 51.48 | 0.135 | 0.180 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | 19.03 | 19.03 | 0.00800 | -20.60 | 0.00061 | 0.116 | 0.00 |
| PERIMETER_BOT_ZN_3 | 7431.35 | 9883.70 | 47.67 | 0.198 | 0.263 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | 19.03 | 19.03 | 0.00800 | -20.60 | 0.00061 | 0.184 | 0.00 |
| PERIMETER_BOT_ZN_4 | 5064.39 | 6735.64 | 51.32 | 0.135 | 0.179 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | 19.03 | 19.03 | 0.00800 | -20.60 | 0.00061 | 0.116 | 0.00 |
| PERIMETER_MID_ZN_1 | 9050.92 | 12037.72 | 58.06 | 0.241 | 0.320 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:10:00 | 19.03 | 19.03 | 0.00800 | -20.60 | 0.00061 | 0.184 | 0.00 |
| PERIMETER_MID_ZN_2 | 5949.47 | 7912.80 | 60.28 | 0.158 | 0.210 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:10:00 | 19.03 | 19.03 | 0.00800 | -20.60 | 0.00061 | 0.116 | 0.00 |
| PERIMETER_MID_ZN_3 | 8903.98 | 11842.29 | 57.12 | 0.237 | 0.315 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:10:00 | 19.03 | 19.03 | 0.00800 | -20.60 | 0.00061 | 0.184 | 0.00 |
| PERIMETER_MID_ZN_4 | 6005.63 | 7987.49 | 60.86 | 0.160 | 0.212 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:10:00 | 19.03 | 19.03 | 0.00800 | -20.60 | 0.00061 | 0.116 | 0.00 |
| PERIMETER_TOP_ZN_1 | 11675.32 | 15528.18 | 74.89 | 0.310 | 0.413 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 19.03 | 19.03 | 0.00800 | -20.60 | 0.00061 | 0.184 | 0.00 |
| PERIMETER_TOP_ZN_2 | 7573.00 | 10072.08 | 76.73 | 0.201 | 0.268 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 19.03 | 19.03 | 0.00800 | -20.60 | 0.00061 | 0.116 | 0.00 |
| PERIMETER_TOP_ZN_3 | 11545.45 | 15355.45 | 74.06 | 0.307 | 0.408 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 19.03 | 19.03 | 0.00800 | -20.60 | 0.00061 | 0.184 | 0.00 |
| PERIMETER_TOP_ZN_4 | 7671.76 | 10203.45 | 77.74 | 0.204 | 0.271 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 19.03 | 19.03 | 0.00800 | -20.60 | 0.00061 | 0.116 | 0.00 |
| Calculated cooling [m3/s] | User cooling [m3/s] | Calculated heating [m3/s] | User heating [m3/s] | Adjusted cooling [m3/s] | Adjusted heating [m3/s] | Adjusted main [m3/s] | Calculated Heating Air Flow Ratio [] | User Heating Air Flow Ratio [] | |
| VAV_1 | 7.50 | 7.50 | 1.76 | 1.76 | 7.5008 | 2.2502 | 7.5008 | 0.3000 | 0.3000 |
| VAV_2 | 7.62 | 7.62 | 1.93 | 1.93 | 7.6195 | 2.2859 | 7.6195 | 0.3000 | 0.3000 |
| VAV_3 | 8.04 | 8.04 | 2.23 | 2.23 | 8.0438 | 2.4131 | 8.0438 | 0.3000 | 0.3000 |
| Previous Design Volume Flow Rate [m3/s] | Algorithm Volume Flow Rate [m3/s] | Coincident Design Volume Flow Rate [m3/s] | Coincident Size Adjusted | Peak Sizing Period Name | Peak Day into Period {TIMESTAMP}[day] | Peak Hour Of Day {TIMESTAMP}[hr] | Peak Step Start Minute {TIMESTAMP}[min] | |
| None |
| Coil Type | HVAC Type | HVAC Name | Coil Final Gross Total Capacity [W] | Coil Final Gross Sensible Capacity [W] | Coil Final Reference Air Volume Flow Rate [m3/s] | Coil Final Reference Plant Fluid Volume Flow Rate [m3/s] | Coil U-value Times Area Value [W/K] | Design Day Name at Sensible Ideal Loads Peak | Date/Time at Sensible Ideal Loads Peak | Design Day Name at Air Flow Ideal Loads Peak | Date/Time at Air Flow Ideal Loads Peak | Coil Total Capacity at Ideal Loads Peak [W] | Coil Sensible Capacity at Ideal Loads Peak [W] | Coil Air Volume Flow Rate at Ideal Loads Peak [m3/s] | Coil Entering Air Drybulb at Ideal Loads Peak [C] | Coil Entering Air Wetbulb at Ideal Loads Peak [C] | Coil Entering Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Coil Leaving Air Drybulb at Ideal Loads Peak [C] | Coil Leaving Air Wetbulb at Ideal Loads Peak [C] | Coil Leaving Air Humidity Ratio at Ideal Loads Peak [C] | Outdoor Air Drybulb at Ideal Loads Peak [C] | Outdoor Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Outdoor Air Wetbulb at Ideal Loads Peak [C] | Outdoor Air Flow Percentage at Ideal Loads Peak [%] | Zone Air Drybulb at Ideal Loads Peak [C] | Zone Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Zone Air Relative Humidity at Ideal Loads Peak [%] | Zone Sensible Heat Gain at Ideal Loads Peak [W] | Zone Latent Heat Gain at Ideal Loads Peak [W] | Coil Total Capacity at Rating Conditions [W] | Coil Sensible Capacity at Rating Conditions [W] | |
| CORE_BOTTOM VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | CORE_BOTTOM VAV BOX | 48225.567 | 48225.567 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | 48225.57 | 35304.51 | 0.872796 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.03 | 0.00793875 | 57.3751 | 3161.01 | 0.00 | -999.00 | -999.00 |
| CORE_MID VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | CORE_MID VAV BOX | 44211.954 | 44211.954 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:10:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:10:00 | 44211.95 | 35304.51 | 0.872796 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.03 | 0.00800000 | 57.8121 | 8267.32 | 0.00 | -999.00 | -999.00 |
| CORE_TOP VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | CORE_TOP VAV BOX | 46916.430 | 46916.430 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 46916.43 | 35304.51 | 0.872796 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.03 | 0.00800000 | 57.8121 | 22651.77 | 0.00 | -999.00 | -999.00 |
| PERIMETER_BOT_ZN_1 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_BOT_ZN_1 VAV BOX | 11336.711 | 11336.711 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | 11336.71 | 10872.37 | 0.268786 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.03 | 0.00800000 | 57.8121 | 10112.61 | 0.00 | -999.00 | -999.00 |
| PERIMETER_BOT_ZN_2 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_BOT_ZN_2 VAV BOX | 10883.083 | 10883.083 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | 10883.08 | 7265.62 | 0.179620 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.03 | 0.00800000 | 57.8121 | 6757.90 | 0.00 | -999.00 | -999.00 |
| PERIMETER_BOT_ZN_3 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_BOT_ZN_3 VAV BOX | 10626.259 | 10626.259 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | 10626.26 | 10626.26 | 0.262702 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.03 | 0.00800000 | 57.8121 | 9883.70 | 0.00 | -999.00 | -999.00 |
| PERIMETER_BOT_ZN_4 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_BOT_ZN_4 VAV BOX | 11978.978 | 11978.978 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | 11978.98 | 7241.69 | 0.179029 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.03 | 0.00800000 | 57.8121 | 6735.64 | 0.00 | -999.00 | -999.00 |
| PERIMETER_MID_ZN_1 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_MID_ZN_1 VAV BOX | 13065.466 | 13065.466 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:10:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:10:00 | 13065.47 | 12942.11 | 0.319954 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.03 | 0.00800000 | 57.8121 | 12037.72 | 0.00 | -999.00 | -999.00 |
| PERIMETER_MID_ZN_2 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_MID_ZN_2 VAV BOX | 12102.074 | 12102.074 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:10:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:10:00 | 12102.07 | 8507.29 | 0.210317 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.03 | 0.00800000 | 57.8121 | 7912.80 | 0.00 | -999.00 | -999.00 |
| PERIMETER_MID_ZN_3 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_MID_ZN_3 VAV BOX | 12732.001 | 12732.001 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:10:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:10:00 | 12732.00 | 12732.00 | 0.314760 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.03 | 0.00800000 | 57.8121 | 11842.29 | 0.00 | -999.00 | -999.00 |
| PERIMETER_MID_ZN_4 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_MID_ZN_4 VAV BOX | 12921.148 | 12921.148 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:10:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:10:00 | 12921.15 | 8587.59 | 0.212302 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.03 | 0.00800000 | 57.8121 | 7987.49 | 0.00 | -999.00 | -999.00 |
| PERIMETER_TOP_ZN_1 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_TOP_ZN_1 VAV BOX | 16694.811 | 16694.811 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 16694.81 | 16694.81 | 0.412728 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.03 | 0.00800000 | 57.8121 | 15528.18 | 0.00 | -999.00 | -999.00 |
| PERIMETER_TOP_ZN_2 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_TOP_ZN_2 VAV BOX | 12066.840 | 12066.840 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 12066.84 | 10828.80 | 0.267709 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.03 | 0.00800000 | 57.8121 | 10072.08 | 0.00 | -999.00 | -999.00 |
| PERIMETER_TOP_ZN_3 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_TOP_ZN_3 VAV BOX | 16509.107 | 16509.107 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 16509.11 | 16509.11 | 0.408137 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.03 | 0.00800000 | 57.8121 | 15355.45 | 0.00 | -999.00 | -999.00 |
| PERIMETER_TOP_ZN_4 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_TOP_ZN_4 VAV BOX | 13717.146 | 13717.146 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 13717.15 | 10970.03 | 0.271200 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.03 | 0.00800000 | 57.8121 | 10203.45 | 0.00 | -999.00 | -999.00 |
| VAV_1_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | AirLoopHVAC | VAV_1 | 158500.566 | 119193.882 | 7.500759 | -999.0 | -999.000 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 13:00:00 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 09:00:00 | 153805.57 | 106956.00 | 7.500759 | 24.13 | 18.15 | 0.01072855 | 11.26 | 11.26 | 0.00850000 | 26.17 | 0.01856681 | 24.24 | 19.6479 | 22.63 | 0.00881192 | 50.9389 | 90019.21 | 0.00 | 158485.11 | 119093.30 |
| VAV_1_HEATC | Coil:Heating:Fuel | AirLoopHVAC | VAV_1 | 63637.852 | 63637.852 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 13:20:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | 63637.85 | 63637.85 | 2.250228 | -14.10 | -14.10 | 0.00181944 | 16.70 | 13.08 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 65.4929 | 19.03 | 0.00796968 | 57.5958 | 36650.86 | 0.00 | -999.00 | -999.00 |
| VAV_2_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | AirLoopHVAC | VAV_2 | 152777.398 | 117872.286 | 7.619531 | -999.0 | -999.000 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 15:00:00 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 07:00:00 | 147793.78 | 105829.51 | 7.619531 | 23.85 | 17.85 | 0.01047398 | 11.26 | 11.26 | 0.00850000 | 24.34 | 0.01743769 | 23.04 | 19.3416 | 22.63 | 0.00880410 | 50.8937 | 93066.16 | 0.00 | 152762.50 | 117772.12 |
| VAV_2_HEATC | Coil:Heating:Fuel | AirLoopHVAC | VAV_2 | 63538.585 | 63538.585 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 17:10:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:10:00 | 63538.58 | 63538.58 | 2.285859 | -11.23 | -11.23 | 0.00235937 | 16.70 | 13.08 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 64.4721 | 19.03 | 0.00800000 | 57.8121 | 48047.62 | 0.00 | -999.00 | -999.00 |
| VAV_3_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | AirLoopHVAC | VAV_3 | 162141.398 | 124674.710 | 8.043818 | -999.0 | -999.000 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 16:00:00 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 07:00:00 | 158022.85 | 114319.72 | 8.043818 | 23.95 | 17.84 | 0.01041886 | 11.26 | 11.26 | 0.00850000 | 25.34 | 0.01768341 | 23.47 | 18.3214 | 22.63 | 0.00878934 | 50.8095 | 97857.17 | 0.00 | 162125.58 | 124558.12 |
| VAV_3_HEATC | Coil:Heating:Fuel | AirLoopHVAC | VAV_3 | 63184.034 | 63184.034 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 01:00:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 63184.03 | 63184.03 | 2.413145 | -7.13 | -7.13 | 0.00312349 | 16.70 | 13.08 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 61.0713 | 19.03 | 0.00800000 | 57.8121 | 73810.93 | 0.00 | -999.00 | -999.00 |
Report: System Summary
For: Entire Facility
Timestamp: 2021-07-16 12:27:07
Economizer| High Limit Shutoff Control | Minimum Outdoor Air [m3/s] | Maximum Outdoor Air [m3/s] | Return Air Temp Limit | Return Air Enthalpy Limit | Outdoor Air Temperature Limit [C] | Outdoor Air Enthalpy Limit [C] | |
| VAV_1_OA_CONTROLLER | DifferentialDryBulb | 1.47 | 7.50 | - | |||
| VAV_2_OA_CONTROLLER | DifferentialDryBulb | 1.47 | 7.62 | - | |||
| VAV_3_OA_CONTROLLER | DifferentialDryBulb | 1.47 | 8.04 | - |
| Controller:MechanicalVentilation Name | Outdoor Air Per Person [m3/s-person] | Outdoor Air Per Area [m3/s-m2] | Outdoor Air Per Zone [m3/s] | Outdoor Air ACH [ach] | Outdoor Air Method | Outdoor Air Schedule Name | Air Distribution Effectiveness in Cooling Mode | Air Distribution Effectiveness in Heating Mode | Air Distribution Effectiveness Schedule Name | |
| None |
| Winter Clothes [hr] | Summer Clothes [hr] | Summer or Winter Clothes [hr] | |
| CORE_BOTTOM | 1035.83 | 5099.50 | 1035.83 |
| CORE_MID | 1823.67 | 4992.33 | 1783.50 |
| CORE_TOP | 2289.33 | 4950.67 | 2184.83 |
| PERIMETER_BOT_ZN_1 | 1840.00 | 4938.00 | 1838.33 |
| PERIMETER_BOT_ZN_2 | 2585.17 | 4894.83 | 2564.33 |
| PERIMETER_BOT_ZN_3 | 2569.67 | 5100.33 | 2569.50 |
| PERIMETER_BOT_ZN_4 | 2757.17 | 4798.00 | 2694.83 |
| PERIMETER_MID_ZN_1 | 1913.67 | 4730.83 | 1881.00 |
| PERIMETER_MID_ZN_2 | 2560.33 | 4694.50 | 2484.83 |
| PERIMETER_MID_ZN_3 | 2500.17 | 5023.67 | 2483.17 |
| PERIMETER_MID_ZN_4 | 2704.83 | 4651.17 | 2570.17 |
| PERIMETER_TOP_ZN_1 | 2217.17 | 4593.67 | 2143.83 |
| PERIMETER_TOP_ZN_2 | 2666.33 | 4540.00 | 2562.00 |
| PERIMETER_TOP_ZN_3 | 2685.83 | 4870.83 | 2639.67 |
| PERIMETER_TOP_ZN_4 | 2926.33 | 4550.50 | 2700.33 |
| FIRSTFLOOR_PLENUM | 0.00 | 0.00 | 0.00 |
| MIDFLOOR_PLENUM | 0.00 | 0.00 | 0.00 |
| TOPFLOOR_PLENUM | 0.00 | 0.00 | 0.00 |
| Facility | 3366.83 | 5105.83 | 2987.17 |
| During Heating [hr] | During Cooling [hr] | During Occupied Heating [hr] | During Occupied Cooling [hr] | |
| CORE_BOTTOM | 0.00 | 0.00 | 0.00 | 0.00 |
| CORE_MID | 0.00 | 0.00 | 0.00 | 0.00 |
| CORE_TOP | 0.50 | 0.17 | 0.50 | 0.17 |
| PERIMETER_BOT_ZN_1 | 3.67 | 0.00 | 1.83 | 0.00 |
| PERIMETER_BOT_ZN_2 | 5.83 | 0.50 | 0.00 | 0.00 |
| PERIMETER_BOT_ZN_3 | 6.50 | 0.00 | 3.50 | 0.00 |
| PERIMETER_BOT_ZN_4 | 5.67 | 0.33 | 0.00 | 0.00 |
| PERIMETER_MID_ZN_1 | 18.33 | 0.67 | 1.67 | 0.00 |
| PERIMETER_MID_ZN_2 | 37.67 | 0.50 | 0.33 | 0.00 |
| PERIMETER_MID_ZN_3 | 34.33 | 0.00 | 1.83 | 0.00 |
| PERIMETER_MID_ZN_4 | 34.00 | 0.33 | 0.33 | 0.00 |
| PERIMETER_TOP_ZN_1 | 69.33 | 0.83 | 1.83 | 0.00 |
| PERIMETER_TOP_ZN_2 | 114.50 | 1.00 | 4.33 | 0.00 |
| PERIMETER_TOP_ZN_3 | 113.67 | 0.00 | 2.50 | 0.00 |
| PERIMETER_TOP_ZN_4 | 108.50 | 1.83 | 1.67 | 0.00 |
| FIRSTFLOOR_PLENUM | 0.00 | 0.00 | 0.00 | 0.00 |
| MIDFLOOR_PLENUM | 0.00 | 0.00 | 0.00 | 0.00 |
| TOPFLOOR_PLENUM | 0.00 | 0.00 | 0.00 | 0.00 |
| Facility | 163.83 | 5.67 | 7.83 | 0.17 |
Report: EMISSIONS DATA SUMMARY
For: Meter
Timestamp: 2021-07-16 12:27:07
Custom Monthly Report| CO2:FACILITY [kg] | NOX:FACILITY [kg] | SO2:FACILITY [kg] | PM:FACILITY [kg] | HG:FACILITY [kg] | WATERENVIRONMENTALFACTORS:FACILITY [L] | CARBON EQUIVALENT:FACILITY [kg] | |
| January | 82574.8926 | 146.0650 | 426.6367 | 0.0000 | 0.0013 | 98211.0256 | 23742.3093 |
| February | 66665.9304 | 118.4016 | 347.3038 | 0.0000 | 0.0011 | 79949.3859 | 19175.3340 |
| March | 64201.9117 | 114.8179 | 339.2179 | 0.0000 | 0.0010 | 78089.1053 | 18478.6160 |
| April | 56348.7978 | 102.3248 | 307.0252 | 0.0000 | 0.0009 | 70680.3075 | 16241.8517 |
| May | 61662.2778 | 112.1353 | 336.9451 | 0.0000 | 0.0010 | 77568.3859 | 17775.8471 |
| June | 70130.7107 | 127.5702 | 383.4278 | 0.0000 | 0.0012 | 88269.2568 | 20217.6322 |
| July | 74533.3436 | 135.5951 | 407.5966 | 0.0000 | 0.0012 | 93833.2029 | 21487.0935 |
| August | 73254.0556 | 133.2629 | 400.5720 | 0.0000 | 0.0012 | 92216.0536 | 21118.2173 |
| September | 61951.9549 | 112.6793 | 338.6316 | 0.0000 | 0.0010 | 77956.6692 | 17859.6166 |
| October | 62174.0286 | 112.9309 | 338.9322 | 0.0000 | 0.0010 | 78025.6761 | 17921.3266 |
| November | 59644.2985 | 107.3285 | 319.1023 | 0.0000 | 0.0010 | 73459.3129 | 17176.8706 |
| December | 70563.2816 | 126.1886 | 372.7939 | 0.0000 | 0.0011 | 85818.3953 | 20309.4590 |
| Annual Sum or Average |<PHONE_NUMBER> | 1449.3001 | 4318.1853 | 0.0000 | 0.0130 |<PHONE_NUMBER> |<PHONE_NUMBER> |
| Minimum of Months | 56348.7978 | 102.3248 | 307.0252 | 0.0000 | 0.0009 | 70680.3075 | 16241.8517 |
| Maximum of Months | 82574.8926 | 146.0650 | 426.6367 | 0.0000 | 0.0013 | 98211.0256 | 23742.3093 |
Report: COMPONENTS OF PEAK ELECTRICAL DEMAND
For: Meter
Timestamp: 2021-07-16 12:27:07
Custom Monthly Report| ELECTRICITY:FACILITY [J] | ELECTRICITY:FACILITY {Maximum}[W] | ELECTRICITY:FACILITY {TIMESTAMP} | INTERIORLIGHTS:ELECTRICITY {AT MAX/MIN} [W] | INTERIOREQUIPMENT:ELECTRICITY {AT MAX/MIN} [W] | FANS:ELECTRICITY {AT MAX/MIN} [W] | HEATING:ELECTRICITY {AT MAX/MIN} [W] | COOLING:ELECTRICITY {AT MAX/MIN} [W] | EXTERIORLIGHTS:ELECTRICITY {AT MAX/MIN} [W] | PUMPS:ELECTRICITY {AT MAX/MIN} [W] | HEATREJECTION:ELECTRICITY [] | EXTERIOREQUIPMENT:ELECTRICITY [] | HUMIDIFICATION:ELECTRICITY [] | HEATRECOVERY:ELECTRICITY [] | WATERSYSTEMS:ELECTRICITY [] | REFRIGERATION:ELECTRICITY [] | GENERATORS:ELECTRICITY [] | ELECTRICITYPRODUCED:FACILITY [] | |
| January | 0.227891E+12 | 240101.018 | 04-JAN-06:10 | 5005.104 | 16993.240 | 3741.139 | 199549.095 | 0.000 | 14804.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| February | 0.185517E+12 | 247294.189 | 18-FEB-06:10 | 5005.104 | 16993.240 | 3741.139 | 206742.266 | 0.000 | 14804.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| March | 0.181200E+12 | 209501.512 | 04-MAR-06:10 | 5005.104 | 16993.240 | 3741.139 | 168949.589 | 0.000 | 14804.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| April | 0.164008E+12 | 141933.362 | 15-APR-07:00 | 45045.936 | 60390.613 | 4012.534 | 0.000 | 32475.839 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| May | 0.179992E+12 | 170833.154 | 02-MAY-13:00 | 45045.936 | 50115.449 | 6569.858 | 0.000 | 69093.472 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| June | 0.204822E+12 | 191826.902 | 17-JUN-15:00 | 45045.936 | 53005.339 | 8816.531 | 0.000 | 84950.657 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| July | 0.217733E+12 | 220230.750 | 02-JUL-15:09 | 45045.936 | 53005.339 | 9527.046 | 0.000 | 112643.990 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| August | 0.213980E+12 | 180002.701 | 09-AUG-15:09 | 45045.936 | 53005.339 | 6995.718 | 0.000 | 74947.268 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| September | 0.180893E+12 | 201782.148 | 11-SEP-12:00 | 45045.936 | 53647.536 | 7853.217 | 0.000 | 95227.018 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| October | 0.181053E+12 | 162920.268 | 04-OCT-12:00 | 45045.936 | 53647.536 | 5690.523 | 0.000 | 58527.833 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| November | 0.170457E+12 | 211557.011 | 25-NOV-06:10 | 5005.104 | 16993.240 | 3741.139 | 171005.088 | 0.000 | 14804.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| December | 0.199135E+12 | 239789.410 | 09-DEC-06:10 | 5005.104 | 16993.240 | 3741.139 | 199237.487 | 0.000 | 14804.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| Annual Sum or Average | 0.230668E+13 | |||||||||||||||||
| Minimum of Months | 0.164008E+12 | 141933.362 | 5005.104 | 16993.240 | 3741.139 | 0.000 | 0.000 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | |
| Maximum of Months | 0.227891E+12 | 247294.189 | 45045.936 | 60390.613 | 9527.046 | 206742.266 | 112643.990 | 14804.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
Report: HEATING PART LOAD PERFORMANCE
For: VAV_1_HEATC
Timestamp: 2021-07-16 12:27:07
Custom Monthly Report| HEATING COIL GAS RATE [W] | HEATING COIL GAS RATE {Maximum}[W] | HEATING COIL GAS RATE {TIMESTAMP} | |
| January | 10188. | 57377. | 04-JAN-07:10 |
| February | 7981. | 51585. | 12-FEB-07:10 |
| March | 4873. | 42680. | 01-MAR-07:10 |
| April | 319. | 17935. | 16-APR-06:03 |
| May | 0. | 0. | 01-MAY-00:10 |
| June | 0. | 0. | 01-JUN-00:10 |
| July | 0. | 0. | 01-JUL-00:10 |
| August | 0. | 0. | 01-AUG-00:10 |
| September | 15. | 8636. | 18-SEP-06:03 |
| October | 346. | 20669. | 26-OCT-06:10 |
| November | 2931. | 30270. | 25-NOV-07:10 |
| December | 5370. | 37050. | 11-DEC-07:05 |
| Annual Sum or Average | 2673. | ||
| Minimum of Months | 0. | 0. | |
| Maximum of Months | 10188. | 57377. |
Report: HEATING PART LOAD PERFORMANCE
For: VAV_2_HEATC
Timestamp: 2021-07-16 12:27:07
Custom Monthly Report| HEATING COIL GAS RATE [W] | HEATING COIL GAS RATE {Maximum}[W] | HEATING COIL GAS RATE {TIMESTAMP} | |
| January | 10496. | 57615. | 04-JAN-07:10 |
| February | 8288. | 51773. | 12-FEB-07:10 |
| March | 5072. | 42789. | 01-MAR-07:10 |
| April | 311. | 16942. | 16-APR-06:03 |
| May | 0. | 0. | 01-MAY-00:10 |
| June | 0. | 0. | 01-JUN-00:10 |
| July | 0. | 0. | 01-JUL-00:10 |
| August | 0. | 0. | 01-AUG-00:10 |
| September | 13. | 8074. | 18-SEP-06:03 |
| October | 357. | 20490. | 26-OCT-06:10 |
| November | 3103. | 30850. | 25-NOV-07:10 |
| December | 5651. | 37211. | 11-DEC-07:05 |
| Annual Sum or Average | 2779. | ||
| Minimum of Months | 0. | 0. | |
| Maximum of Months | 10496. | 57615. |
Report: HEATING PART LOAD PERFORMANCE
For: VAV_3_HEATC
Timestamp: 2021-07-16 12:27:07
Custom Monthly Report| HEATING COIL GAS RATE [W] | HEATING COIL GAS RATE {Maximum}[W] | HEATING COIL GAS RATE {TIMESTAMP} | |
| January | 10709. | 61939. | 04-JAN-07:10 |
| February | 8397. | 55449. | 12-FEB-07:10 |
| March | 5138. | 46663. | 01-MAR-07:10 |
| April | 368. | 19094. | 16-APR-06:03 |
| May | 0. | 0. | 01-MAY-00:10 |
| June | 0. | 0. | 01-JUN-00:10 |
| July | 0. | 0. | 01-JUL-00:10 |
| August | 0. | 0. | 01-AUG-00:10 |
| September | 22. | 9923. | 18-SEP-06:03 |
| October | 410. | 23298. | 26-OCT-06:10 |
| November | 3221. | 33507. | 25-NOV-07:10 |
| December | 5805. | 40301. | 11-DEC-07:05 |
| Annual Sum or Average | 2844. | ||
| Minimum of Months | 0. | 0. | |
| Maximum of Months | 10709. | 61939. |
Report: COOLING PART LOAD PERFORMANCE
For: VAV_1_COOLC DXCOIL
Timestamp: 2021-07-16 12:27:07
Custom Monthly Report| COOLING COIL ELECTRIC POWER [W] | COOLING COIL ELECTRIC POWER {Maximum}[W] | COOLING COIL ELECTRIC POWER {TIMESTAMP} | |
| January | 55. | 6735. | 11-JAN-15:00 |
| February | 0. | 0. | 01-FEB-00:10 |
| March | 177. | 5181. | 22-MAR-15:00 |
| April | 1279. | 12269. | 15-APR-13:00 |
| May | 4233. | 21655. | 02-MAY-14:00 |
| June | 7976. | 32004. | 19-JUN-05:02 |
| July | 9488. | 38724. | 08-JUL-05:02 |
| August | 8218. | 34768. | 22-AUG-05:02 |
| September | 4607. | 31924. | 11-SEP-13:00 |
| October | 2338. | 20308. | 07-OCT-11:20 |
| November | 380. | 9885. | 01-NOV-07:00 |
| December | 108. | 5685. | 21-DEC-15:50 |
| Annual Sum or Average | 3236. | ||
| Minimum of Months | 0. | 0. | |
| Maximum of Months | 9488. | 38724. |
Report: COOLING PART LOAD PERFORMANCE
For: VAV_2_COOLC DXCOIL
Timestamp: 2021-07-16 12:27:07
Custom Monthly Report| COOLING COIL ELECTRIC POWER [W] | COOLING COIL ELECTRIC POWER {Maximum}[W] | COOLING COIL ELECTRIC POWER {TIMESTAMP} | |
| January | 56. | 6857. | 11-JAN-15:00 |
| February | 0. | 0. | 01-FEB-00:10 |
| March | 175. | 5263. | 22-MAR-15:00 |
| April | 1266. | 15215. | 15-APR-05:02 |
| May | 4279. | 28159. | 16-MAY-05:02 |
| June | 7805. | 36963. | 26-JUN-05:02 |
| July | 9266. | 37326. | 08-JUL-05:02 |
| August | 7626. | 36963. | 22-AUG-05:02 |
| September | 4412. | 37076. | 02-SEP-05:02 |
| October | 2297. | 24166. | 07-OCT-05:02 |
| November | 371. | 9976. | 01-NOV-06:50 |
| December | 108. | 5690. | 21-DEC-15:30 |
| Annual Sum or Average | 3135. | ||
| Minimum of Months | 0. | 0. | |
| Maximum of Months | 9266. | 37326. |
Report: COOLING PART LOAD PERFORMANCE
For: VAV_3_COOLC DXCOIL
Timestamp: 2021-07-16 12:27:07
Custom Monthly Report| COOLING COIL ELECTRIC POWER [W] | COOLING COIL ELECTRIC POWER {Maximum}[W] | COOLING COIL ELECTRIC POWER {TIMESTAMP} | |
| January | 62. | 7237. | 11-JAN-15:00 |
| February | 0. | 0. | 01-FEB-00:10 |
| March | 184. | 5556. | 22-MAR-15:00 |
| April | 1349. | 16302. | 15-APR-05:02 |
| May | 4748. | 31314. | 16-MAY-05:02 |
| June | 8669. | 39229. | 26-JUN-05:02 |
| July | 10195. | 40441. | 02-JUL-15:00 |
| August | 8074. | 39229. | 22-AUG-05:02 |
| September | 4663. | 39349. | 02-SEP-05:02 |
| October | 2417. | 26390. | 07-OCT-05:02 |
| November | 388. | 10541. | 01-NOV-07:00 |
| December | 114. | 6019. | 21-DEC-15:30 |
| Annual Sum or Average | 3402. | ||
| Minimum of Months | 0. | 0. | |
| Maximum of Months | 10195. | 40441. |
Report: FAN PART LOAD PERFORMANCE
For: VAV_1_FAN
Timestamp: 2021-07-16 12:27:07
Custom Monthly Report| FAN ELECTRIC POWER [W] | FAN ELECTRIC POWER {Maximum}[W] | FAN ELECTRIC POWER {TIMESTAMP} | |
| January | 675. | 1315. | 13-JAN-13:20 |
| February | 681. | 1324. | 20-FEB-17:40 |
| March | 655. | 1433. | 12-MAR-13:00 |
| April | 700. | 1660. | 14-APR-16:10 |
| May | 731. | 2038. | 02-MAY-13:00 |
| June | 909. | 7685. | 18-JUN-05:02 |
| July | 1035. | 10449. | 14-JUL-05:02 |
| August | 966. | 5552. | 09-AUG-05:02 |
| September | 835. | 2799. | 11-SEP-15:10 |
| October | 749. | 2068. | 04-OCT-15:10 |
| November | 629. | 1589. | 01-NOV-13:00 |
| December | 647. | 1371. | 05-DEC-18:00 |
| Annual Sum or Average | 767. | ||
| Minimum of Months | 629. | 1315. | |
| Maximum of Months | 1035. | 10449. |
Report: FAN PART LOAD PERFORMANCE
For: VAV_2_FAN
Timestamp: 2021-07-16 12:27:07
Custom Monthly Report| FAN ELECTRIC POWER [W] | FAN ELECTRIC POWER {Maximum}[W] | FAN ELECTRIC POWER {TIMESTAMP} | |
| January | 795. | 1254. | 13-JAN-13:20 |
| February | 750. | 1248. | 20-FEB-13:30 |
| March | 669. | 1341. | 11-MAR-13:20 |
| April | 694. | 3885. | 15-APR-05:02 |
| May | 732. | 7987. | 03-MAY-05:02 |
| June | 854. | 12597. | 18-JUN-05:02 |
| July | 940. | 13816. | 14-JUL-05:02 |
| August | 823. | 9725. | 22-AUG-05:02 |
| September | 757. | 10874. | 02-SEP-05:02 |
| October | 725. | 5330. | 07-OCT-05:02 |
| November | 642. | 1398. | 01-NOV-13:00 |
| December | 684. | 1287. | 20-DEC-13:20 |
| Annual Sum or Average | 755. | ||
| Minimum of Months | 642. | 1248. | |
| Maximum of Months | 940. | 13816. |
Report: FAN PART LOAD PERFORMANCE
For: VAV_3_FAN
Timestamp: 2021-07-16 12:27:07
Custom Monthly Report| FAN ELECTRIC POWER [W] | FAN ELECTRIC POWER {Maximum}[W] | FAN ELECTRIC POWER {TIMESTAMP} | |
| January | 985. | 1299. | 01-JAN-00:04 |
| February | 909. | 1299. | 01-FEB-05:03 |
| March | 759. | 1361. | 11-MAR-13:30 |
| April | 733. | 4231. | 15-APR-05:02 |
| May | 812. | 9830. | 03-MAY-05:02 |
| June | 970. | 14010. | 18-JUN-05:02 |
| July | 1069. | 14882. | 14-JUL-05:02 |
| August | 874. | 11568. | 22-AUG-05:02 |
| September | 799. | 12430. | 02-SEP-05:02 |
| October | 759. | 6140. | 07-OCT-05:02 |
| November | 736. | 1435. | 01-NOV-13:00 |
| December | 898. | 1299. | 01-DEC-02:63 |
| Annual Sum or Average | 858. | ||
| Minimum of Months | 733. | 1299. | |
| Maximum of Months | 1069. | 14882. |


Bowling scorecard!
Enter the result from your rolls
Frame
Roll 1
Roll 2
Roll 3: 10th frame bonus
1
2
3
4
5
6
7
8
9
10
Submit
Your score is: