Program Version:EnergyPlus, Version 9.1.0-08d2e308bb, YMD=2021.07.16 12:27
Tabular Output Report in Format: HTML
Building: Ref Bldg Medium Office New2004_v1.3_5.0
Environment: PHILADELPHIA 2014 ** PHILADELPHIA - USA Custom-720304 WMO#=720304
Simulation Timestamp: 2021-07-16 12:27:56
Report: Annual Building Utility Performance Summary
For: Entire Facility
Timestamp: 2021-07-16 12:27:56
Values gathered over 8760.00 hours| Total Energy [GJ] | Energy Per Total Building Area [MJ/m2] | Energy Per Conditioned Building Area [MJ/m2] | |
| Total Site Energy | 1715.43 | 344.31 | 344.31 |
| Net Site Energy | 1715.43 | 344.31 | 344.31 |
| Total Source Energy | 5751.96 | 1154.51 | 1154.51 |
| Net Source Energy | 5751.96 | 1154.51 | 1154.51 |
| Site=>Source Conversion Factor | |
| Electricity | 3.546 |
| Natural Gas | 1.092 |
| District Cooling | 0.848 |
| District Heating | 1.647 |
| Steam | 0.585 |
| Gasoline | 1.050 |
| Diesel | 1.050 |
| Coal | 1.050 |
| Fuel Oil #1 | 1.050 |
| Fuel Oil #2 | 1.050 |
| Propane | 1.050 |
| Other Fuel 1 | 1.000 |
| Other Fuel 2 | 1.000 |
| Area [m2] | |
| Total Building Area | 4982.19 |
| Net Conditioned Building Area | 4982.19 |
| Unconditioned Building Area | 0.00 |
| Electricity [GJ] | Natural Gas [GJ] | Additional Fuel [GJ] | District Cooling [GJ] | District Heating [GJ] | Water [m3] | |
| Heating | 226.55 | 98.74 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | 253.92 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 210.48 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 232.69 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 594.08 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 62.58 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 0.27 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 36.13 | 0.00 | 0.00 | 0.00 | 174.75 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total End Uses | 1580.57 | 134.86 | 0.00 | 0.00 | 0.00 | 174.75 |
| Subcategory | Electricity [GJ] | Natural Gas [GJ] | Additional Fuel [GJ] | District Cooling [GJ] | District Heating [GJ] | Water [m3] | |
| Heating | General | 226.55 | 98.74 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | General | 253.92 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | General | 210.48 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | Exterior Facade Lighting | 232.69 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | General | 429.16 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Elevators | 164.92 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Exterior Equipment | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | Fan Energy | 62.58 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | General | 0.27 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | Water Heater | 0.00 | 36.13 | 0.00 | 0.00 | 0.00 | 0.00 |
| General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 174.75 | |
| Refrigeration | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Electricity Intensity [MJ/m2] | Natural Gas Intensity [MJ/m2] | Additional Fuel Intensity [MJ/m2] | District Cooling Intensity [MJ/m2] | District Heating Intensity [MJ/m2] | Water Intensity [m3/m2] | |
| Lighting | 88.95 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| HVAC | 109.05 | 27.07 | 0.00 | 0.00 | 0.00 | 0.04 |
| Other | 119.24 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total | 317.24 | 27.07 | 0.00 | 0.00 | 0.00 | 0.04 |
| Electricity Intensity [MJ/m2] | Natural Gas Intensity [MJ/m2] | Additional Fuel Intensity [MJ/m2] | District Cooling Intensity [MJ/m2] | District Heating Intensity [MJ/m2] | Water Intensity [m3/m2] | |
| Lighting | 88.95 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| HVAC | 109.05 | 27.07 | 0.00 | 0.00 | 0.00 | 0.04 |
| Other | 119.24 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total | 317.24 | 27.07 | 0.00 | 0.00 | 0.00 | 0.04 |
| Electricity [GJ] | Percent Electricity [%] | |
| Fuel-Fired Power Generation | 0.000 | 0.00 |
| High Temperature Geothermal* | 0.000 | 0.00 |
| Photovoltaic Power | 0.000 | 0.00 |
| Wind Power | 0.000 | 0.00 |
| Power Conversion | 0.000 | 0.00 |
| Net Decrease in On-Site Storage | 0.000 | 0.00 |
| Total On-Site Electric Sources | 0.000 | 0.00 |
| Electricity Coming From Utility | 1580.568 | 100.00 |
| Surplus Electricity Going To Utility | 0.000 | 0.00 |
| Net Electricity From Utility | 1580.568 | 100.00 |
| Total On-Site and Utility Electric Sources | 1580.568 | 100.00 |
| Total Electricity End Uses | 1580.568 | 100.00 |
| Heat [GJ] | Percent Heat [%] | |
| Water-Side Heat Recovery | 0.00 | |
| Air to Air Heat Recovery for Cooling | 0.00 | |
| Air to Air Heat Recovery for Heating | 0.00 | |
| High-Temperature Geothermal* | 0.00 | |
| Solar Water Thermal | 0.00 | |
| Solar Air Thermal | 0.00 | |
| Total On-Site Thermal Sources | 0.00 |
| Water [m3] | Percent Water [%] | |
| Rainwater Collection | 0.00 | 0.00 |
| Condensate Collection | 0.00 | 0.00 |
| Groundwater Well | 0.00 | 0.00 |
| Total On Site Water Sources | 0.00 | 0.00 |
| - | - | - |
| Initial Storage | 0.00 | 0.00 |
| Final Storage | 0.00 | 0.00 |
| Change in Storage | 0.00 | 0.00 |
| - | - | - |
| Water Supplied by Utility | 174.75 | 100.00 |
| - | - | - |
| Total On Site, Change in Storage, and Utility Water Sources | 174.75 | 100.00 |
| Total Water End Uses | 174.75 | 100.00 |
| Degrees [deltaC] | |
| Tolerance for Zone Heating Setpoint Not Met Time | 0.56 |
| Tolerance for Zone Cooling Setpoint Not Met Time | 0.56 |
| Facility [Hours] | |
| Time Setpoint Not Met During Occupied Heating | 9.50 |
| Time Setpoint Not Met During Occupied Cooling | 6.00 |
| Time Not Comfortable Based on Simple ASHRAE 55-2004 | 3004.33 |
Table of Contents
TopEMISSIONS DATA SUMMARY
| Meter |COMPONENTS OF PEAK ELECTRICAL DEMAND
| Meter |HEATING PART LOAD PERFORMANCE
| VAV_1_HEATC | VAV_2_HEATC | VAV_3_HEATC |COOLING PART LOAD PERFORMANCE
| VAV_1_COOLC DXCOIL | VAV_2_COOLC DXCOIL | VAV_3_COOLC DXCOIL |FAN PART LOAD PERFORMANCE
| VAV_1_FAN | VAV_2_FAN | VAV_3_FAN |Report: Input Verification and Results Summary
For: Entire Facility
Timestamp: 2021-07-16 12:27:56
General| Value | |
| Program Version and Build | EnergyPlus, Version 9.1.0-08d2e308bb, YMD=2021.07.16 12:27 |
| RunPeriod | PHILADELPHIA 2014 |
| Weather File | PHILADELPHIA - USA Custom-720304 WMO#=720304 |
| Latitude [deg] | 40.14 |
| Longitude [deg] | -75.3 |
| Elevation [m] | 92.00 |
| Time Zone | -5.0 |
| North Axis Angle [deg] | 0.00 |
| Rotation for Appendix G [deg] | 0.00 |
| Hours Simulated [hrs] | 8760.00 |
| Total | North (315 to 45 deg) | East (45 to 135 deg) | South (135 to 225 deg) | West (225 to 315 deg) | |
| Gross Wall Area [m2] | 1977.67 | 593.30 | 395.53 | 593.30 | 395.53 |
| Above Ground Wall Area [m2] | 1977.67 | 593.30 | 395.53 | 593.30 | 395.53 |
| Window Opening Area [m2] | 652.83 | 195.85 | 130.57 | 195.85 | 130.57 |
| Gross Window-Wall Ratio [%] | 33.01 | 33.01 | 33.01 | 33.01 | 33.01 |
| Above Ground Window-Wall Ratio [%] | 33.01 | 33.01 | 33.01 | 33.01 | 33.01 |
| Total | North (315 to 45 deg) | East (45 to 135 deg) | South (135 to 225 deg) | West (225 to 315 deg) | |
| Gross Wall Area [m2] | 1977.67 | 593.30 | 395.53 | 593.30 | 395.53 |
| Above Ground Wall Area [m2] | 1977.67 | 593.30 | 395.53 | 593.30 | 395.53 |
| Window Opening Area [m2] | 652.83 | 195.85 | 130.57 | 195.85 | 130.57 |
| Gross Window-Wall Ratio [%] | 33.01 | 33.01 | 33.01 | 33.01 | 33.01 |
| Above Ground Window-Wall Ratio [%] | 33.01 | 33.01 | 33.01 | 33.01 | 33.01 |
| Total | |
| Gross Roof Area [m2] | 1660.73 |
| Skylight Area [m2] | 0.00 |
| Skylight-Roof Ratio [%] | 0.00 |
| Area [m2] | Conditioned (Y/N) | Part of Total Floor Area (Y/N) | Volume [m3] | Multipliers | Above Ground Gross Wall Area [m2] | Underground Gross Wall Area [m2] | Window Glass Area [m2] | Opening Area [m2] | Lighting [W/m2] | People [m2 per person] | Plug and Process [W/m2] | |
| CORE_BOTTOM | 983.54 | Yes | Yes | 2698.04 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 3.7320 | 22.58 | 37.7664 |
| CORE_MID | 983.54 | Yes | Yes | 2698.04 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 3.7320 | 22.58 | 5.1190 |
| CORE_TOP | 983.54 | Yes | Yes | 2698.04 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 3.7320 | 22.58 | 5.1190 |
| FIRSTFLOOR_PLENUM | 1660.73 | Yes | No | 2024.76 | 1.00 | 202.84 | 0.00 | 0.00 | 0.00 | 0.0000 | 0.0000 | |
| MIDFLOOR_PLENUM | 1660.73 | Yes | No | 2024.76 | 1.00 | 202.84 | 0.00 | 0.00 | 0.00 | 0.0000 | 0.0000 | |
| PERIMETER_BOT_ZN_1 | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 3.7320 | 22.58 | 5.1190 |
| PERIMETER_BOT_ZN_2 | 131.26 | Yes | Yes | 360.08 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 3.7320 | 22.58 | 5.1190 |
| PERIMETER_BOT_ZN_3 | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 3.7320 | 22.58 | 5.1190 |
| PERIMETER_BOT_ZN_4 | 131.25 | Yes | Yes | 360.05 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 3.7320 | 22.58 | 5.1190 |
| PERIMETER_MID_ZN_1 | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 3.7320 | 22.58 | 5.1190 |
| PERIMETER_MID_ZN_2 | 131.26 | Yes | Yes | 360.08 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 3.7320 | 22.58 | 5.1190 |
| PERIMETER_MID_ZN_3 | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 3.7320 | 22.58 | 5.1190 |
| PERIMETER_MID_ZN_4 | 131.25 | Yes | Yes | 360.05 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 3.7320 | 22.58 | 5.1190 |
| PERIMETER_TOP_ZN_1 | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 3.7320 | 22.58 | 5.1190 |
| PERIMETER_TOP_ZN_2 | 131.26 | Yes | Yes | 360.08 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 3.7320 | 22.58 | 5.1190 |
| PERIMETER_TOP_ZN_3 | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 3.7320 | 22.58 | 5.1190 |
| PERIMETER_TOP_ZN_4 | 131.25 | Yes | Yes | 360.05 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 3.7320 | 22.58 | 5.1190 |
| TOPFLOOR_PLENUM | 1660.73 | Yes | No | 2024.76 | 1.00 | 202.84 | 0.00 | 0.00 | 0.00 | 0.0000 | 0.0000 | |
| Total | 4982.19 | 13667.13 | 1369.16 | 0.00 | 652.83 | 652.83 | 3.7320 | 22.58 | 11.5639 | |||
| Conditioned Total | 4982.19 | 13667.13 | 1369.16 | 0.00 | 652.83 | 652.83 | 3.7320 | 22.58 | 11.5639 | |||
| Unconditioned Total | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | ||||||
| Not Part of Total | 4982.19 | 6074.28 | 608.51 | 0.00 | 0.00 | 0.00 | 0.0000 | 0.0000 |
Report: Component Sizing Summary
For: Entire Facility
Timestamp: 2021-07-16 12:27:56
AirTerminal:SingleDuct:VAV:Reheat| Design Size Maximum Air Flow Rate [m3/s] | Design Size Constant Minimum Air Flow Fraction | User-Specified Constant Minimum Air Flow Fraction | Design Size Minimum Air Flow Rate [m3/s] | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | Design Size Maximum Flow Fraction during Reheat [] | |
| CORE_BOTTOM VAV BOX COMPONENT | 2.54 | 0.295284 | 0.300000 | 0.761424 | 0.000774 | 0.300000 |
| CORE_MID VAV BOX COMPONENT | 2.22 | 0.338270 | 0.300000 | 0.664666 | 0.000676 | 0.300000 |
| CORE_TOP VAV BOX COMPONENT | 2.28 | 0.329017 | 0.300000 | 0.683358 | 0.000695 | 0.300000 |
| PERIMETER_BOT_ZN_1 VAV BOX COMPONENT | 0.804155 | 0.200000 | 0.300000 | 0.241247 | 0.001164 | 0.300000 |
| PERIMETER_BOT_ZN_2 VAV BOX COMPONENT | 1.09 | 0.200000 | 0.300000 | 0.326562 | 0.002488 | 0.300000 |
| PERIMETER_BOT_ZN_3 VAV BOX COMPONENT | 0.500794 | 0.315482 | 0.300000 | 0.150238 | 0.000725 | 0.300000 |
| PERIMETER_BOT_ZN_4 VAV BOX COMPONENT | 1.20 | 0.200000 | 0.300000 | 0.361343 | 0.002753 | 0.300000 |
| PERIMETER_MID_ZN_1 VAV BOX COMPONENT | 0.967530 | 0.200000 | 0.300000 | 0.290259 | 0.001400 | 0.300000 |
| PERIMETER_MID_ZN_2 VAV BOX COMPONENT | 1.21 | 0.200000 | 0.300000 | 0.364122 | 0.002774 | 0.300000 |
| PERIMETER_MID_ZN_3 VAV BOX COMPONENT | 0.653587 | 0.241730 | 0.300000 | 0.196076 | 0.000946 | 0.300000 |
| PERIMETER_MID_ZN_4 VAV BOX COMPONENT | 1.31 | 0.200000 | 0.300000 | 0.391758 | 0.002985 | 0.300000 |
| PERIMETER_TOP_ZN_1 VAV BOX COMPONENT | 1.02 | 0.200000 | 0.300000 | 0.304716 | 0.001470 | 0.300000 |
| PERIMETER_TOP_ZN_2 VAV BOX COMPONENT | 1.22 | 0.200000 | 0.300000 | 0.364534 | 0.002777 | 0.300000 |
| PERIMETER_TOP_ZN_3 VAV BOX COMPONENT | 0.741901 | 0.212955 | 0.300000 | 0.222570 | 0.001073 | 0.300000 |
| PERIMETER_TOP_ZN_4 VAV BOX COMPONENT | 1.38 | 0.200000 | 0.300000 | 0.413481 | 0.003150 | 0.300000 |
| Design Size Nominal Capacity [W] | |
| CORE_BOTTOM VAV BOX REHEAT COIL | 30799.51 |
| CORE_MID VAV BOX REHEAT COIL | 26885.69 |
| CORE_TOP VAV BOX REHEAT COIL | 27641.74 |
| PERIMETER_BOT_ZN_1 VAV BOX REHEAT COIL | 9758.40 |
| PERIMETER_BOT_ZN_2 VAV BOX REHEAT COIL | 13209.38 |
| PERIMETER_BOT_ZN_3 VAV BOX REHEAT COIL | 9502.31 |
| PERIMETER_BOT_ZN_4 VAV BOX REHEAT COIL | 14616.28 |
| PERIMETER_MID_ZN_1 VAV BOX REHEAT COIL | 11740.94 |
| PERIMETER_MID_ZN_2 VAV BOX REHEAT COIL | 14728.71 |
| PERIMETER_MID_ZN_3 VAV BOX REHEAT COIL | 11384.79 |
| PERIMETER_MID_ZN_4 VAV BOX REHEAT COIL | 15846.56 |
| PERIMETER_TOP_ZN_1 VAV BOX REHEAT COIL | 15296.69 |
| PERIMETER_TOP_ZN_2 VAV BOX REHEAT COIL | 14745.36 |
| PERIMETER_TOP_ZN_3 VAV BOX REHEAT COIL | 15133.13 |
| PERIMETER_TOP_ZN_4 VAV BOX REHEAT COIL | 16725.25 |
| Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | Sum of Air Terminal Maximum Flow Rates [m3/s] | Adjusted Heating Design Air Flow Rate [m3/s] | Adjusted Cooling Design Air Flow Rate [m3/s] | Adjusted Main Design Air Flow Rate [m3/s] | User Heating Air Flow Ratio [] | Calculated Heating Air Flow Ratio [] | Design Supply Air Flow Rate [m3/s] | |
| VAV_1 | 1.84 | 1.84 | 6.14 | 1.84 | 6.14 | 6.14 | 0.300000 | 0.300000 | 6.14 |
| VAV_2 | 1.91 | 1.91 | 6.36 | 1.91 | 6.36 | 6.36 | 0.300000 | 0.300000 | 6.36 |
| VAV_3 | 1.99 | 1.99 | 6.63 | 1.99 | 6.63 | 6.63 | 0.300000 | 0.300000 | 6.63 |
| Maximum Outdoor Air Flow Rate [m3/s] | Minimum Outdoor Air Flow Rate [m3/s] | |
| VAV_1_OA_CONTROLLER | 6.14 | 0.919521 |
| VAV_2_OA_CONTROLLER | 6.36 | 0.919521 |
| VAV_3_OA_CONTROLLER | 6.63 | 0.919521 |
| Design Size High Speed Rated Air Flow Rate [m3/s] | Design Size High Speed Gross Rated Total Cooling Capacity [W] | Design Size High Speed Rated Sensible Heat Ratio | Design Size Low Speed Rated Air Flow Rate [m3/s] | Design Size Low Speed Gross Rated Total Cooling Capacity [W] | Design Size Low Speed Gross Rated Sensible Heat Ratio | |
| VAV_1_COOLC DXCOIL | 6.14 | 125832.08 | 0.762776 | 2.05 | 41939.83 | 0.762776 |
| VAV_2_COOLC DXCOIL | 6.36 | 126066.54 | 0.775856 | 2.12 | 42017.98 | 0.775856 |
| VAV_3_COOLC DXCOIL | 6.63 | 130132.25 | 0.780017 | 2.21 | 43373.08 | 0.780017 |
| Design Size Design Maximum Air Flow Rate [m3/s] | Design Electric Power Consumption [W] | |
| VAV_1_FAN | 6.14 | 11511.16 |
| Design Size Nominal Capacity [W] | |
| VAV_1_HEATC | 38367.98 |
| VAV_2_HEATC | 38175.23 |
| VAV_3_HEATC | 37936.68 |
| Design Size Maximum Flow Rate [m3/s] | |
| VAV_2_FAN | 6.36 |
| VAV_3_FAN | 6.63 |
| Maximum Loop Flow Rate [m3/s] | Plant Loop Volume [m3] | |
| SWHSYS1 | 0.000031 | 0.003744 |
| Design Flow Rate [m3/s] | Design Power Consumption [W] | |
| SWHSYS1 PUMP | 0.000031 | 8.44 |
| Use Side Design Flow Rate [m3/s] | |
| SWHSYS1 WATER HEATER | 0.000031 |
Report: Climatic Data Summary
For: Entire Facility
Timestamp: 2021-07-16 12:27:56
SizingPeriod:DesignDay| Maximum Dry Bulb [C] | Daily Temperature Range [deltaC] | Humidity Value | Humidity Type | Wind Speed [m/s] | Wind Direction | |
| CHICAGO ANN HTG 99.6% CONDNS DB | -20.60 | 0.00 | -20.60 | Wetbulb [C] | 4.90 | 270.00 |
| CHICAGO ANN CLG .4% CONDNS WB=>MDB | 31.20 | 10.70 | 25.50 | Wetbulb [C] | 5.30 | 230.00 |
| Value | |
| None |
Report: Envelope Summary
For: Entire Facility
Timestamp: 2021-07-16 12:27:56
Opaque Exterior| Construction | Reflectance | U-Factor with Film [W/m2-K] | U-Factor no Film [W/m2-K] | Gross Area [m2] | Net Area [m2] | Azimuth [deg] | Tilt [deg] | Cardinal Direction | |
| CORE_BOT_ZN_5_FLOOR | EXT-SLAB | 0.30 | 2.193 | 3.401 | 983.54 | 983.54 | 0.00 | 180.00 | |
| PERIMETER_BOT_PLENUM_WALL_EAST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 40.57 | 40.57 | 90.00 | 90.00 | E |
| PERIMETER_BOT_PLENUM_WALL_NORTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 60.85 | 60.85 | 0.00 | 90.00 | N |
| PERIMETER_BOT_PLENUM_WALL_SOUTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 60.85 | 60.85 | 180.00 | 90.00 | S |
| PERIMETER_BOT_PLENUM_WALL_WEST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 40.57 | 40.57 | 270.00 | 90.00 | W |
| PERIMETER_MID_PLENUM_WALL_EAST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 40.57 | 40.57 | 90.00 | 90.00 | E |
| PERIMETER_MID_PLENUM_WALL_NORTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 60.85 | 60.85 | 0.00 | 90.00 | N |
| PERIMETER_MID_PLENUM_WALL_SOUTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 60.85 | 60.85 | 180.00 | 90.00 | S |
| PERIMETER_MID_PLENUM_WALL_WEST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 40.57 | 40.57 | 270.00 | 90.00 | W |
| PERIMETER_BOT_ZN_1_WALL_SOUTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 136.92 | 71.63 | 180.00 | 90.00 | S |
| PERIMETER_BOT_ZN_1_FLOOR | EXT-SLAB | 0.30 | 2.193 | 3.401 | 207.34 | 207.34 | 180.00 | 180.00 | |
| PERIMETER_BOT_ZN_2_WALL_EAST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 91.28 | 47.75 | 90.00 | 90.00 | E |
| PERIMETER_BOT_ZN_2_FLOOR | EXT-SLAB | 0.30 | 2.193 | 3.401 | 131.26 | 131.26 | 90.00 | 180.00 | |
| PERIMETER_BOT_ZN_3_WALL_NORTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 136.92 | 71.63 | 0.00 | 90.00 | N |
| PERIMETER_BOT_ZN_3_FLOOR | EXT-SLAB | 0.30 | 2.193 | 3.401 | 207.34 | 207.34 | 0.00 | 180.00 | |
| PERIMETER_BOT_ZN_4_WALL_WEST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 91.28 | 47.75 | 270.00 | 90.00 | W |
| PERIMETER_BOT_ZN_4_FLOOR | EXT-SLAB | 0.30 | 2.193 | 3.401 | 131.25 | 131.25 | 270.00 | 180.00 | |
| PERIMETER_MID_ZN_1_WALL_SOUTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 136.92 | 71.63 | 180.00 | 90.00 | S |
| PERIMETER_MID_ZN_2_WALL_EAST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 91.28 | 47.75 | 90.00 | 90.00 | E |
| PERIMETER_MID_ZN_3_WALL_NORTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 136.92 | 71.63 | 0.00 | 90.00 | N |
| PERIMETER_MID_ZN_4_WALL_WEST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 91.28 | 47.75 | 270.00 | 90.00 | W |
| PERIMETER_TOP_ZN_1_WALL_SOUTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 136.92 | 71.63 | 180.00 | 90.00 | S |
| PERIMETER_TOP_ZN_2_WALL_EAST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 91.28 | 47.75 | 90.00 | 90.00 | E |
| PERIMETER_TOP_ZN_3_WALL_NORTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 136.92 | 71.63 | 0.00 | 90.00 | N |
| PERIMETER_TOP_ZN_4_WALL_WEST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 91.28 | 47.75 | 270.00 | 90.00 | W |
| PERIMETER_TOP_PLENUM_WALL_EAST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 40.57 | 40.57 | 90.00 | 90.00 | E |
| PERIMETER_TOP_PLENUM_WALL_NORTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 60.85 | 60.85 | 0.00 | 90.00 | N |
| PERIMETER_TOP_PLENUM_WALL_SOUTH | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 60.85 | 60.85 | 180.00 | 90.00 | S |
| PERIMETER_TOP_PLENUM_WALL_WEST | STEEL FRAME NON-RES EXT WALL | 0.22 | 0.342 | 0.361 | 40.57 | 40.57 | 270.00 | 90.00 | W |
| BUILDING_ROOF | IEAD NON-RES ROOF | 0.30 | 0.358 | 0.376 | 1660.73 | 1660.73 | 0.00 | 0.00 |
| Construction | Glass Area [m2] | Frame Area [m2] | Divider Area [m2] | Area of One Opening [m2] | Area of Multiplied Openings [m2] | Glass U-Factor [W/m2-K] | Glass SHGC | Glass Visible Transmittance | Frame Conductance [W/m2-K] | Divider Conductance [W/m2-K] | Shade Control | Parent Surface | Azimuth [deg] | Tilt [deg] | Cardinal Direction | |
| PERIMETER_BOT_ZN_1_WALL_SOUTH_WINDOW | WINDOW NON-RES FIXED | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 3.940 | 0.519 | 0.398 | No | PERIMETER_BOT_ZN_1_WALL_SOUTH | 180.00 | 90.00 | S | ||
| PERIMETER_BOT_ZN_2_WALL_EAST_WINDOW | WINDOW NON-RES FIXED | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 3.940 | 0.519 | 0.398 | No | PERIMETER_BOT_ZN_2_WALL_EAST | 90.00 | 90.00 | E | ||
| PERIMETER_BOT_ZN_3_WALL_NORTH_WINDOW | WINDOW NON-RES FIXED | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 3.940 | 0.519 | 0.398 | No | PERIMETER_BOT_ZN_3_WALL_NORTH | 0.00 | 90.00 | N | ||
| PERIMETER_BOT_ZN_4_WALL_WEST_WINDOW | WINDOW NON-RES FIXED | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 3.940 | 0.519 | 0.398 | No | PERIMETER_BOT_ZN_4_WALL_WEST | 270.00 | 90.00 | W | ||
| PERIMETER_MID_ZN_1_WALL_SOUTH_WINDOW | WINDOW NON-RES FIXED | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 3.940 | 0.519 | 0.398 | No | PERIMETER_MID_ZN_1_WALL_SOUTH | 180.00 | 90.00 | S | ||
| PERIMETER_MID_ZN_2_WALL_EAST_WINDOW | WINDOW NON-RES FIXED | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 3.940 | 0.519 | 0.398 | No | PERIMETER_MID_ZN_2_WALL_EAST | 90.00 | 90.00 | E | ||
| PERIMETER_MID_ZN_3_WALL_NORTH_WINDOW | WINDOW NON-RES FIXED | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 3.940 | 0.519 | 0.398 | No | PERIMETER_MID_ZN_3_WALL_NORTH | 0.00 | 90.00 | N | ||
| PERIMETER_MID_ZN_4_WALL_WEST_WINDOW | WINDOW NON-RES FIXED | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 3.940 | 0.519 | 0.398 | No | PERIMETER_MID_ZN_4_WALL_WEST | 270.00 | 90.00 | W | ||
| PERIMETER_TOP_ZN_1_WALL_SOUTH_WINDOW | WINDOW NON-RES FIXED | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 3.940 | 0.519 | 0.398 | No | PERIMETER_TOP_ZN_1_WALL_SOUTH | 180.00 | 90.00 | S | ||
| PERIMETER_TOP_ZN_2_WALL_EAST_WINDOW | WINDOW NON-RES FIXED | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 3.940 | 0.519 | 0.398 | No | PERIMETER_TOP_ZN_2_WALL_EAST | 90.00 | 90.00 | E | ||
| PERIMETER_TOP_ZN_3_WALL_NORTH_WINDOW | WINDOW NON-RES FIXED | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 3.940 | 0.519 | 0.398 | No | PERIMETER_TOP_ZN_3_WALL_NORTH | 0.00 | 90.00 | N | ||
| PERIMETER_TOP_ZN_4_WALL_WEST_WINDOW | WINDOW NON-RES FIXED | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 3.940 | 0.519 | 0.398 | No | PERIMETER_TOP_ZN_4_WALL_WEST | 270.00 | 90.00 | W | ||
| Total or Average | 652.83 | 3.940 | 0.519 | 0.398 | ||||||||||||
| North Total or Average | 195.85 | 3.940 | 0.519 | 0.398 | ||||||||||||
| Non-North Total or Average | 456.98 | 3.940 | 0.519 | 0.398 |
| Construction | Area of One Opening [m2] | Area of Openings [m2] | Glass U-Factor [W/m2-K] | Glass SHGC | Glass Visible Transmittance | Parent Surface | |
| Total or Average | 0.00 | - | - | - |
| Construction | U-Factor with Film [W/m2-K] | U-Factor no Film [W/m2-K] | Gross Area [m2] | Parent Surface | |
| None |
Report: Equipment Summary
For: Entire Facility
Timestamp: 2021-07-16 12:27:56
Central Plant| Type | Nominal Capacity [W] | Nominal Efficiency [W/W] | IPLV in SI Units [W/W] | IPLV in IP Units [Btu/W-h] | |
| None |
| Type | Design Coil Load [W] | Nominal Total Capacity [W] | Nominal Sensible Capacity [W] | Nominal Latent Capacity [W] | Nominal Sensible Heat Ratio | Nominal Efficiency [W/W] | Nominal Coil UA Value [W/C] | Nominal Coil Surface Area [m2] | |
| VAV_1_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | 125832.08 | 95981.71 | 29850.37 | 0.76 | 3.23 | |||
| VAV_2_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | 126066.54 | 97809.48 | 28257.06 | 0.78 | 3.23 | |||
| VAV_3_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | 130132.25 | 101505.42 | 28626.84 | 0.78 | 3.23 |
| DX Cooling Coil Type | Standard Rated Net Cooling Capacity [W] | Standard Rated Net COP [W/W] | EER [Btu/W-h] | SEER [Btu/W-h] | IEER [Btu/W-h] | |
| VAV_1_COOLC DXCOIL | 124838.8 | 2.80 | 9.55 | N/A | 12.67 | |
| VAV_2_COOLC DXCOIL | 125073.0 | 2.79 | 9.51 | N/A | 12.63 | |
| VAV_3_COOLC DXCOIL | 129132.6 | 2.78 | 9.50 | N/A | 12.62 |
| DX Cooling Coil Type | Rated Net Cooling Capacity Test A [W] | Rated Electric Power Test A [W] | Rated Net Cooling Capacity Test B [W] | Rated Electric Power Test B [W] | Rated Net Cooling Capacity Test C [W] | Rated Electric Power Test C [W] | Rated Net Cooling Capacity Test D [W] | Rated Electric Power Test D [W] | |
| VAV_1_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | ||||||||
| VAV_2_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | ||||||||
| VAV_3_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed |
| DX Heating Coil Type | High Temperature Heating (net) Rating Capacity [W] | Low Temperature Heating (net) Rating Capacity [W] | HSPF [Btu/W-h] | Region Number | |
| None |
| Type | Design Coil Load [W] | Nominal Total Capacity [W] | Nominal Efficiency [W/W] | |
| CORE_BOTTOM VAV BOX REHEAT COIL | Coil:Heating:Electric | 30799.51 | 1.00 | |
| CORE_MID VAV BOX REHEAT COIL | Coil:Heating:Electric | 26885.69 | 1.00 | |
| CORE_TOP VAV BOX REHEAT COIL | Coil:Heating:Electric | 27641.74 | 1.00 | |
| PERIMETER_BOT_ZN_1 VAV BOX REHEAT COIL | Coil:Heating:Electric | 9758.40 | 1.00 | |
| PERIMETER_BOT_ZN_2 VAV BOX REHEAT COIL | Coil:Heating:Electric | 13209.38 | 1.00 | |
| PERIMETER_BOT_ZN_3 VAV BOX REHEAT COIL | Coil:Heating:Electric | 9502.31 | 1.00 | |
| PERIMETER_BOT_ZN_4 VAV BOX REHEAT COIL | Coil:Heating:Electric | 14616.28 | 1.00 | |
| PERIMETER_MID_ZN_1 VAV BOX REHEAT COIL | Coil:Heating:Electric | 11740.94 | 1.00 | |
| PERIMETER_MID_ZN_2 VAV BOX REHEAT COIL | Coil:Heating:Electric | 14728.71 | 1.00 | |
| PERIMETER_MID_ZN_3 VAV BOX REHEAT COIL | Coil:Heating:Electric | 11384.79 | 1.00 | |
| PERIMETER_MID_ZN_4 VAV BOX REHEAT COIL | Coil:Heating:Electric | 15846.56 | 1.00 | |
| PERIMETER_TOP_ZN_1 VAV BOX REHEAT COIL | Coil:Heating:Electric | 15296.69 | 1.00 | |
| PERIMETER_TOP_ZN_2 VAV BOX REHEAT COIL | Coil:Heating:Electric | 14745.36 | 1.00 | |
| PERIMETER_TOP_ZN_3 VAV BOX REHEAT COIL | Coil:Heating:Electric | 15133.13 | 1.00 | |
| PERIMETER_TOP_ZN_4 VAV BOX REHEAT COIL | Coil:Heating:Electric | 16725.25 | 1.00 | |
| VAV_1_HEATC | Coil:Heating:Fuel | 38367.98 | 0.80 | |
| VAV_2_HEATC | Coil:Heating:Fuel | 38175.23 | 0.80 | |
| VAV_3_HEATC | Coil:Heating:Fuel | 37936.68 | 0.80 |
| Type | Total Efficiency [W/W] | Delta Pressure [pa] | Max Air Flow Rate [m3/s] | Rated Electric Power [W] | Rated Power Per Max Air Flow Rate [W-s/m3] | Motor Heat In Air Fraction | Fan Energy Index | End Use Subcategory | Design Day Name for Fan Sizing Peak | Date/Time for Fan Sizing Peak | |
| VAV_1_FAN | Fan:SystemModel | 0.59 | 1109.65 | 6.14 | 11511.16 | 1875.99 | 1.00 | 1.13 | Fan Energy | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 18:00:00 |
| VAV_2_FAN | Fan:VariableVolume | 0.59 | 1109.65 | 6.36 | 11924.30 | 1875.99 | 1.00 | 1.12 | Fan Energy | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 16:30:00 |
| VAV_3_FAN | Fan:VariableVolume | 0.59 | 1109.65 | 6.63 | 12435.68 | 1875.99 | 1.00 | 1.12 | Fan Energy | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 16:50:00 |
| Type | Control | Head [pa] | Water Flow [m3/s] | Electric Power [W] | Power Per Water Flow Rate [W-s/m3] | Motor Efficiency [W/W] | End Use Subcategory | |
| SWHSYS1 PUMP | Pump:ConstantSpeed | Intermittent | 179352.00 | 0.000031 | 8.44 | 270515.84 | 0.85 | General |
| Type | Storage Volume [m3] | Input [W] | Thermal Efficiency [W/W] | Recovery Efficiency [W/W] | Energy Factor | |
| SWHSYS1 WATER HEATER | WaterHeater:Mixed | 0.38 | 845000.00 | 0.80 | 1.83 | 0.57 |
| DX Cooling Coil Type | Assocated Fan | Net Cooling Capacity [W] | COP [W/W] | EER [Btu/W-h] | IEER [Btu/W-h] | Supply Air Flow 100% [kg/s] | COP 75% Capacity [W/W] | EER 75% Capacity [Btu/W-h] | Supply Air Flow 75% [kg/s] | COP 50% Capacity [W/W] | EER 50% Capacity [Btu/W-h] | Supply Air Flow 50% [kg/s] | COP 25% Capacity [W/W] | EER 25% Capacity [Btu/W-h] | Supply Air Flow 25% [kg/s] | |
| VAV_1_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | VAV_1_FAN | 124838.84 | 2.80 | 9.55 | 12.67 | 7.0201 | 3.46 | 11.80 | 5.6672 | 4.16 | 14.18 | 3.8013 | 4.28 | 14.60 | 1.5479 |
| VAV_2_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | VAV_2_FAN | 125072.95 | 2.79 | 9.51 | 12.63 | 7.2720 | 3.44 | 11.75 | 5.8804 | 4.15 | 14.15 | 3.9459 | 4.27 | 14.58 | 1.5874 |
| VAV_3_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | VAV_3_FAN | 129132.62 | 2.78 | 9.50 | 12.62 | 7.5839 | 3.44 | 11.74 | 6.1349 | 4.14 | 14.14 | 4.1172 | 4.27 | 14.58 | 1.6503 |
Report: HVAC Sizing Summary
For: Entire Facility
Timestamp: 2021-07-16 12:27:56
Zone Sensible Cooling| Calculated Design Load [W] | User Design Load [W] | User Design Load per Area [W/m2] | Calculated Design Air Flow [m3/s] | User Design Air Flow [m3/s] | Design Day Name | Date/Time Of Peak {TIMESTAMP} | Thermostat Setpoint Temperature at Peak Load [C] | Indoor Temperature at Peak Load [C] | Indoor Humidity Ratio at Peak Load [kgWater/kgAir] | Outdoor Temperature at Peak Load [C] | Outdoor Humidity Ratio at Peak Load [kgWater/kgAir] | Minimum Outdoor Air Flow Rate [m3/s] | Heat Gain Rate from DOAS [W] | |
| CORE_BOTTOM | 24850.72 | 33051.46 | 33.60 | 1.908 | 2.538 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 09:00:00 | 23.51 | 23.51 | 0.00888 | 25.31 | 0.01878 | 0.545 | 0.00 |
| CORE_MID | 22425.08 | 29825.36 | 30.32 | 1.666 | 2.216 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 07:00:00 | 23.51 | 23.51 | 0.00895 | 21.46 | 0.01650 | 0.545 | 0.00 |
| CORE_TOP | 23025.71 | 30624.19 | 31.14 | 1.713 | 2.278 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 07:00:00 | 23.51 | 23.51 | 0.00889 | 21.46 | 0.01650 | 0.545 | 0.00 |
| PERIMETER_BOT_ZN_1 | 7874.25 | 10472.75 | 50.51 | 0.605 | 0.804 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 13:10:00 | 23.51 | 23.51 | 0.00874 | 30.75 | 0.01878 | 0.115 | 0.00 |
| PERIMETER_BOT_ZN_2 | 10659.12 | 14176.63 | 108.00 | 0.818 | 1.089 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 08:40:00 | 23.51 | 23.51 | 0.00861 | 24.64 | 0.01878 | 0.073 | 0.00 |
| PERIMETER_BOT_ZN_3 | 4903.69 | 6521.91 | 31.46 | 0.377 | 0.501 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 15:00:00 | 23.51 | 23.51 | 0.00889 | 31.20 | 0.01878 | 0.115 | 0.00 |
| PERIMETER_BOT_ZN_4 | 11794.42 | 15686.58 | 119.51 | 0.906 | 1.204 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 17:10:00 | 23.51 | 23.51 | 0.00860 | 29.52 | 0.01878 | 0.073 | 0.00 |
| PERIMETER_MID_ZN_1 | 9474.05 | 12600.49 | 60.77 | 0.727 | 0.968 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 13:00:00 | 23.51 | 23.51 | 0.00870 | 30.66 | 0.01878 | 0.115 | 0.00 |
| PERIMETER_MID_ZN_2 | 11885.15 | 15807.25 | 120.43 | 0.913 | 1.214 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 08:40:00 | 23.51 | 23.51 | 0.00860 | 24.64 | 0.01878 | 0.073 | 0.00 |
| PERIMETER_MID_ZN_3 | 6399.87 | 8511.83 | 41.05 | 0.491 | 0.654 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 15:00:00 | 23.51 | 23.51 | 0.00880 | 31.20 | 0.01878 | 0.115 | 0.00 |
| PERIMETER_MID_ZN_4 | 12787.19 | 17006.97 | 129.57 | 0.982 | 1.306 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 17:00:00 | 23.51 | 23.51 | 0.00859 | 29.70 | 0.01878 | 0.073 | 0.00 |
| PERIMETER_TOP_ZN_1 | 9945.96 | 13228.13 | 63.80 | 0.764 | 1.016 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 13:20:00 | 23.51 | 23.51 | 0.00869 | 30.84 | 0.01878 | 0.115 | 0.00 |
| PERIMETER_TOP_ZN_2 | 11898.59 | 15825.12 | 120.56 | 0.914 | 1.215 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 08:30:00 | 23.51 | 23.51 | 0.00860 | 24.30 | 0.01878 | 0.073 | 0.00 |
| PERIMETER_TOP_ZN_3 | 7264.65 | 9661.99 | 46.60 | 0.558 | 0.742 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 15:40:00 | 23.51 | 23.51 | 0.00876 | 30.77 | 0.01878 | 0.115 | 0.00 |
| PERIMETER_TOP_ZN_4 | 13496.27 | 17950.04 | 136.76 | 1.036 | 1.378 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 17:10:00 | 23.51 | 23.51 | 0.00859 | 29.52 | 0.01878 | 0.073 | 0.00 |
| Calculated Design Load [W] | User Design Load [W] | User Design Load per Area [W/m2] | Calculated Design Air Flow [m3/s] | User Design Air Flow [m3/s] | Design Day Name | Date/Time Of Peak {TIMESTAMP} | Thermostat Setpoint Temperature at Peak Load [C] | Indoor Temperature at Peak Load [C] | Indoor Humidity Ratio at Peak Load [kgWater/kgAir] | Outdoor Temperature at Peak Load [C] | Outdoor Humidity Ratio at Peak Load [kgWater/kgAir] | Minimum Outdoor Air Flow Rate [m3/s] | Heat Gain Rate from DOAS [W] | |
| CORE_BOTTOM | 2318.15 | 3083.14 | 3.13 | 0.062 | 0.545 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | 19.14 | 19.14 | 0.00793 | -20.60 | 0.00061 | 0.545 | 0.00 |
| CORE_MID | 5886.65 | 7829.24 | 7.96 | 0.157 | 0.545 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:10:00 | 19.14 | 19.14 | 0.00800 | -20.60 | 0.00061 | 0.545 | 0.00 |
| CORE_TOP | 16733.71 | 22255.83 | 22.63 | 0.446 | 0.594 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 19.14 | 19.14 | 0.00800 | -20.60 | 0.00061 | 0.545 | 0.00 |
| PERIMETER_BOT_ZN_1 | 6779.22 | 9016.37 | 43.49 | 0.181 | 0.241 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | 19.14 | 19.14 | 0.00800 | -20.60 | 0.00061 | 0.115 | 0.00 |
| PERIMETER_BOT_ZN_2 | 4527.09 | 6021.03 | 45.87 | 0.121 | 0.161 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | 19.14 | 19.14 | 0.00800 | -20.60 | 0.00061 | 0.073 | 0.00 |
| PERIMETER_BOT_ZN_3 | 6621.73 | 8806.90 | 42.48 | 0.177 | 0.235 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | 19.14 | 19.14 | 0.00800 | -20.60 | 0.00061 | 0.115 | 0.00 |
| PERIMETER_BOT_ZN_4 | 4514.04 | 6003.67 | 45.74 | 0.120 | 0.160 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | 19.14 | 19.14 | 0.00800 | -20.60 | 0.00061 | 0.073 | 0.00 |
| PERIMETER_MID_ZN_1 | 8066.90 | 10728.98 | 51.75 | 0.215 | 0.286 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:10:00 | 19.14 | 19.14 | 0.00800 | -20.60 | 0.00061 | 0.115 | 0.00 |
| PERIMETER_MID_ZN_2 | 5307.83 | 7059.41 | 53.78 | 0.142 | 0.188 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:10:00 | 19.14 | 19.14 | 0.00800 | -20.60 | 0.00061 | 0.073 | 0.00 |
| PERIMETER_MID_ZN_3 | 7933.54 | 10551.61 | 50.89 | 0.212 | 0.281 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:10:00 | 19.14 | 19.14 | 0.00800 | -20.60 | 0.00061 | 0.115 | 0.00 |
| PERIMETER_MID_ZN_4 | 5350.87 | 7116.66 | 54.22 | 0.143 | 0.190 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:10:00 | 19.14 | 19.14 | 0.00800 | -20.60 | 0.00061 | 0.073 | 0.00 |
| PERIMETER_TOP_ZN_1 | 10659.57 | 14177.23 | 68.38 | 0.284 | 0.378 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 19.14 | 19.14 | 0.00800 | -20.60 | 0.00061 | 0.115 | 0.00 |
| PERIMETER_TOP_ZN_2 | 6921.25 | 9205.27 | 70.13 | 0.185 | 0.246 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 19.14 | 19.14 | 0.00800 | -20.60 | 0.00061 | 0.073 | 0.00 |
| PERIMETER_TOP_ZN_3 | 10545.59 | 14025.64 | 67.65 | 0.281 | 0.374 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 19.14 | 19.14 | 0.00800 | -20.60 | 0.00061 | 0.115 | 0.00 |
| PERIMETER_TOP_ZN_4 | 6996.29 | 9305.07 | 70.89 | 0.187 | 0.248 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 19.14 | 19.14 | 0.00800 | -20.60 | 0.00061 | 0.073 | 0.00 |
| Calculated cooling [m3/s] | User cooling [m3/s] | Calculated heating [m3/s] | User heating [m3/s] | Adjusted cooling [m3/s] | Adjusted heating [m3/s] | Adjusted main [m3/s] | Calculated Heating Air Flow Ratio [] | User Heating Air Flow Ratio [] | |
| VAV_1 | 6.14 | 6.14 | 1.34 | 1.34 | 6.1360 | 1.8408 | 6.1360 | 0.3000 | 0.3000 |
| VAV_2 | 6.36 | 6.36 | 1.49 | 1.49 | 6.3563 | 1.9069 | 6.3563 | 0.3000 | 0.3000 |
| VAV_3 | 6.63 | 6.63 | 1.84 | 1.84 | 6.6289 | 1.9887 | 6.6289 | 0.3000 | 0.3000 |
| Previous Design Volume Flow Rate [m3/s] | Algorithm Volume Flow Rate [m3/s] | Coincident Design Volume Flow Rate [m3/s] | Coincident Size Adjusted | Peak Sizing Period Name | Peak Day into Period {TIMESTAMP}[day] | Peak Hour Of Day {TIMESTAMP}[hr] | Peak Step Start Minute {TIMESTAMP}[min] | |
| None |
| Coil Type | HVAC Type | HVAC Name | Coil Final Gross Total Capacity [W] | Coil Final Gross Sensible Capacity [W] | Coil Final Reference Air Volume Flow Rate [m3/s] | Coil Final Reference Plant Fluid Volume Flow Rate [m3/s] | Coil U-value Times Area Value [W/K] | Design Day Name at Sensible Ideal Loads Peak | Date/Time at Sensible Ideal Loads Peak | Design Day Name at Air Flow Ideal Loads Peak | Date/Time at Air Flow Ideal Loads Peak | Coil Total Capacity at Ideal Loads Peak [W] | Coil Sensible Capacity at Ideal Loads Peak [W] | Coil Air Volume Flow Rate at Ideal Loads Peak [m3/s] | Coil Entering Air Drybulb at Ideal Loads Peak [C] | Coil Entering Air Wetbulb at Ideal Loads Peak [C] | Coil Entering Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Coil Leaving Air Drybulb at Ideal Loads Peak [C] | Coil Leaving Air Wetbulb at Ideal Loads Peak [C] | Coil Leaving Air Humidity Ratio at Ideal Loads Peak [C] | Outdoor Air Drybulb at Ideal Loads Peak [C] | Outdoor Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Outdoor Air Wetbulb at Ideal Loads Peak [C] | Outdoor Air Flow Percentage at Ideal Loads Peak [%] | Zone Air Drybulb at Ideal Loads Peak [C] | Zone Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Zone Air Relative Humidity at Ideal Loads Peak [%] | Zone Sensible Heat Gain at Ideal Loads Peak [W] | Zone Latent Heat Gain at Ideal Loads Peak [W] | Coil Total Capacity at Rating Conditions [W] | Coil Sensible Capacity at Rating Conditions [W] | |
| CORE_BOTTOM VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | CORE_BOTTOM VAV BOX | 30799.508 | 30799.508 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:00:00 | 30799.51 | 22027.79 | 0.544570 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.14 | 0.00792931 | 56.9159 | 3083.14 | 0.00 | -999.00 | -999.00 |
| CORE_MID VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | CORE_MID VAV BOX | 26885.688 | 26885.688 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:10:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:10:00 | 26885.69 | 22027.79 | 0.544570 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.14 | 0.00800000 | 57.4167 | 7829.24 | 0.00 | -999.00 | -999.00 |
| CORE_TOP VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | CORE_TOP VAV BOX | 27641.743 | 27641.743 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 27641.74 | 24013.19 | 0.593653 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.14 | 0.00800000 | 57.4167 | 22255.83 | 0.00 | -999.00 | -999.00 |
| PERIMETER_BOT_ZN_1 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_BOT_ZN_1 VAV BOX | 9758.397 | 9758.397 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | 9758.40 | 9728.32 | 0.240503 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.14 | 0.00800000 | 57.4167 | 9016.37 | 0.00 | -999.00 | -999.00 |
| PERIMETER_BOT_ZN_2 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_BOT_ZN_2 VAV BOX | 13209.382 | 13209.382 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | 13209.38 | 6496.47 | 0.160605 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.14 | 0.00800000 | 57.4167 | 6021.03 | 0.00 | -999.00 | -999.00 |
| PERIMETER_BOT_ZN_3 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_BOT_ZN_3 VAV BOX | 9502.308 | 9502.308 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | 9502.31 | 9502.31 | 0.234916 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.14 | 0.00800000 | 57.4167 | 8806.90 | 0.00 | -999.00 | -999.00 |
| PERIMETER_BOT_ZN_4 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_BOT_ZN_4 VAV BOX | 14616.282 | 14616.282 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | 14616.28 | 6477.73 | 0.160142 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.14 | 0.00800000 | 57.4167 | 6003.67 | 0.00 | -999.00 | -999.00 |
| PERIMETER_MID_ZN_1 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_MID_ZN_1 VAV BOX | 11740.942 | 11740.942 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:10:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:10:00 | 11740.94 | 11576.16 | 0.286185 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.14 | 0.00800000 | 57.4167 | 10728.98 | 0.00 | -999.00 | -999.00 |
| PERIMETER_MID_ZN_2 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_MID_ZN_2 VAV BOX | 14728.706 | 14728.706 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:10:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:10:00 | 14728.71 | 7616.84 | 0.188303 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.14 | 0.00800000 | 57.4167 | 7059.41 | 0.00 | -999.00 | -999.00 |
| PERIMETER_MID_ZN_3 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_MID_ZN_3 VAV BOX | 11384.786 | 11384.786 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:10:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:10:00 | 11384.79 | 11384.79 | 0.281454 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.14 | 0.00800000 | 57.4167 | 10551.61 | 0.00 | -999.00 | -999.00 |
| PERIMETER_MID_ZN_4 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_MID_ZN_4 VAV BOX | 15846.560 | 15846.560 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:10:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:10:00 | 15846.56 | 7678.60 | 0.189830 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.14 | 0.00800000 | 57.4167 | 7116.66 | 0.00 | -999.00 | -999.00 |
| PERIMETER_TOP_ZN_1 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_TOP_ZN_1 VAV BOX | 15296.693 | 15296.693 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 15296.69 | 15296.69 | 0.378164 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.14 | 0.00800000 | 57.4167 | 14177.23 | 0.00 | -999.00 | -999.00 |
| PERIMETER_TOP_ZN_2 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_TOP_ZN_2 VAV BOX | 14745.361 | 14745.361 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 14745.36 | 9932.13 | 0.245542 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.14 | 0.00800000 | 57.4167 | 9205.27 | 0.00 | -999.00 | -999.00 |
| PERIMETER_TOP_ZN_3 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_TOP_ZN_3 VAV BOX | 15133.128 | 15133.128 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 15133.13 | 15133.13 | 0.374120 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.14 | 0.00800000 | 57.4167 | 14025.64 | 0.00 | -999.00 | -999.00 |
| PERIMETER_TOP_ZN_4 VAV BOX REHEAT COIL | Coil:Heating:Electric | ZONEHVAC:AIRDISTRIBUTIONUNIT | PERIMETER_TOP_ZN_4 VAV BOX | 16725.250 | 16725.250 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 16725.25 | 10039.82 | 0.248204 | 16.70 | 13.08 | 0.00800000 | 50.00 | 23.81 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 0.0000 | 19.14 | 0.00800000 | 57.4167 | 9305.07 | 0.00 | -999.00 | -999.00 |
| VAV_1_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | AirLoopHVAC | VAV_1 | 125832.077 | 95981.709 | 6.136044 | -999.0 | -999.000 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 18:00:00 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 18:00:00 | 124203.43 | 92812.36 | 6.136044 | 24.44 | 17.88 | 0.01026322 | 11.26 | 11.26 | 0.00850000 | 27.21 | 0.01878287 | 24.64 | 14.9856 | 23.51 | 0.00876146 | 48.0295 | 79909.32 | 0.00 | 125819.80 | 95877.54 |
| VAV_1_HEATC | Coil:Heating:Fuel | AirLoopHVAC | VAV_1 | 38367.979 | 38367.979 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 13:20:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 07:10:00 | 38367.98 | 38367.98 | 1.840813 | -8.12 | -8.12 | 0.00292444 | 16.70 | 13.08 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 49.9519 | 19.14 | 0.00797129 | 57.2133 | 32931.11 | 0.00 | -999.00 | -999.00 |
| VAV_2_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | AirLoopHVAC | VAV_2 | 126066.538 | 97809.475 | 6.356272 | -999.0 | -999.000 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 16:00:00 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 16:30:00 | 124224.17 | 94964.91 | 6.356272 | 24.31 | 17.70 | 0.01009037 | 11.26 | 11.26 | 0.00850000 | 26.16 | 0.01798554 | 23.88 | 14.4664 | 23.51 | 0.00875505 | 47.9943 | 83751.90 | 0.00 | 126054.24 | 97720.82 |
| VAV_2_HEATC | Coil:Heating:Fuel | AirLoopHVAC | VAV_2 | 38175.231 | 38175.231 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 17:20:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 09:10:00 | 38175.23 | 38175.23 | 1.906882 | -5.38 | -5.38 | 0.00344206 | 16.70 | 13.08 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 48.2212 | 19.14 | 0.00800000 | 57.4167 | 43285.90 | 0.00 | -999.00 | -999.00 |
| VAV_3_COOLC DXCOIL | Coil:Cooling:DX:TwoSpeed | AirLoopHVAC | VAV_3 | 130132.255 | 101505.419 | 6.628863 | -999.0 | -999.000 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 16:40:00 | CHICAGO ANN CLG .4% CONDNS WB=>MDB | 7/21 16:50:00 | 128515.21 | 99291.94 | 6.628863 | 24.28 | 17.63 | 0.01001583 | 11.26 | 11.26 | 0.00850000 | 26.14 | 0.01799683 | 23.88 | 13.8715 | 23.51 | 0.00873045 | 47.8610 | 87289.48 | 0.00 | 130119.56 | 101406.24 |
| VAV_3_HEATC | Coil:Heating:Fuel | AirLoopHVAC | VAV_3 | 37936.675 | 37936.675 | -999.0 | -999.0 | -999.000 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 01:00:00 | CHICAGO ANN HTG 99.6% CONDNS DB | 1/21 24:00:00 | 37936.68 | 37936.68 | 1.988659 | -0.72 | -0.72 | 0.00430757 | 16.70 | 13.08 | 0.00800000 | -20.60 | 0.00061258 | -20.60 | 46.2383 | 19.14 | 0.00800000 | 57.4167 | 68969.04 | 0.00 | -999.00 | -999.00 |
Report: System Summary
For: Entire Facility
Timestamp: 2021-07-16 12:27:56
Economizer| High Limit Shutoff Control | Minimum Outdoor Air [m3/s] | Maximum Outdoor Air [m3/s] | Return Air Temp Limit | Return Air Enthalpy Limit | Outdoor Air Temperature Limit [C] | Outdoor Air Enthalpy Limit [C] | |
| VAV_1_OA_CONTROLLER | DifferentialDryBulb | 0.92 | 6.14 | - | |||
| VAV_2_OA_CONTROLLER | DifferentialDryBulb | 0.92 | 6.36 | - | |||
| VAV_3_OA_CONTROLLER | DifferentialDryBulb | 0.92 | 6.63 | - |
| Controller:MechanicalVentilation Name | Outdoor Air Per Person [m3/s-person] | Outdoor Air Per Area [m3/s-m2] | Outdoor Air Per Zone [m3/s] | Outdoor Air ACH [ach] | Outdoor Air Method | Outdoor Air Schedule Name | Air Distribution Effectiveness in Cooling Mode | Air Distribution Effectiveness in Heating Mode | Air Distribution Effectiveness Schedule Name | |
| None |
| Winter Clothes [hr] | Summer Clothes [hr] | Summer or Winter Clothes [hr] | |
| CORE_BOTTOM | 941.50 | 4669.00 | 941.50 |
| CORE_MID | 1848.67 | 4354.00 | 1781.17 |
| CORE_TOP | 2445.67 | 4063.67 | 2191.67 |
| PERIMETER_BOT_ZN_1 | 2153.67 | 3720.33 | 1398.00 |
| PERIMETER_BOT_ZN_2 | 2841.83 | 4410.83 | 2387.83 |
| PERIMETER_BOT_ZN_3 | 2571.83 | 4319.33 | 2418.17 |
| PERIMETER_BOT_ZN_4 | 3001.33 | 4479.17 | 2527.17 |
| PERIMETER_MID_ZN_1 | 2329.83 | 3493.83 | 1328.17 |
| PERIMETER_MID_ZN_2 | 2928.67 | 4197.83 | 2316.67 |
| PERIMETER_MID_ZN_3 | 2872.00 | 4000.00 | 2371.67 |
| PERIMETER_MID_ZN_4 | 2982.83 | 4340.33 | 2408.00 |
| PERIMETER_TOP_ZN_1 | 2613.33 | 3509.83 | 1532.17 |
| PERIMETER_TOP_ZN_2 | 3162.00 | 4095.33 | 2444.00 |
| PERIMETER_TOP_ZN_3 | 3211.33 | 3958.17 | 2551.50 |
| PERIMETER_TOP_ZN_4 | 3194.50 | 4298.17 | 2560.83 |
| FIRSTFLOOR_PLENUM | 0.00 | 0.00 | 0.00 |
| MIDFLOOR_PLENUM | 0.00 | 0.00 | 0.00 |
| TOPFLOOR_PLENUM | 0.00 | 0.00 | 0.00 |
| Facility | 4509.50 | 5039.00 | 3004.33 |
| During Heating [hr] | During Cooling [hr] | During Occupied Heating [hr] | During Occupied Cooling [hr] | |
| CORE_BOTTOM | 0.00 | 0.00 | 0.00 | 0.00 |
| CORE_MID | 0.17 | 0.00 | 0.17 | 0.00 |
| CORE_TOP | 7.17 | 0.00 | 7.17 | 0.00 |
| PERIMETER_BOT_ZN_1 | 2.67 | 15.83 | 2.67 | 6.00 |
| PERIMETER_BOT_ZN_2 | 1.00 | 4.83 | 0.00 | 0.00 |
| PERIMETER_BOT_ZN_3 | 4.00 | 0.00 | 3.67 | 0.00 |
| PERIMETER_BOT_ZN_4 | 1.17 | 9.67 | 0.00 | 0.00 |
| PERIMETER_MID_ZN_1 | 3.00 | 15.17 | 2.00 | 1.50 |
| PERIMETER_MID_ZN_2 | 10.33 | 9.33 | 0.00 | 0.00 |
| PERIMETER_MID_ZN_3 | 12.67 | 0.00 | 4.33 | 0.00 |
| PERIMETER_MID_ZN_4 | 8.50 | 13.33 | 0.00 | 0.00 |
| PERIMETER_TOP_ZN_1 | 33.83 | 11.17 | 1.67 | 0.00 |
| PERIMETER_TOP_ZN_2 | 79.00 | 9.17 | 1.83 | 0.00 |
| PERIMETER_TOP_ZN_3 | 90.17 | 0.00 | 3.17 | 0.00 |
| PERIMETER_TOP_ZN_4 | 71.50 | 18.00 | 0.50 | 0.00 |
| FIRSTFLOOR_PLENUM | 0.00 | 0.00 | 0.00 | 0.00 |
| MIDFLOOR_PLENUM | 0.00 | 0.00 | 0.00 | 0.00 |
| TOPFLOOR_PLENUM | 0.00 | 0.00 | 0.00 | 0.00 |
| Facility | 109.50 | 83.67 | 9.50 | 6.00 |
Report: EMISSIONS DATA SUMMARY
For: Meter
Timestamp: 2021-07-16 12:27:56
Custom Monthly Report| CO2:FACILITY [kg] | NOX:FACILITY [kg] | SO2:FACILITY [kg] | PM:FACILITY [kg] | HG:FACILITY [kg] | WATERENVIRONMENTALFACTORS:FACILITY [L] | CARBON EQUIVALENT:FACILITY [kg] | |
| January | 58839.5982 | 105.0986 | 310.1100 | 0.0000 | 0.0009 | 71388.1911 | 16933.2717 |
| February | 45492.1272 | 81.6148 | 241.9049 | 0.0000 | 0.0007 | 55687.6608 | 13097.4600 |
| March | 42238.2745 | 76.1166 | 226.6367 | 0.0000 | 0.0007 | 52173.3048 | 12165.8009 |
| April | 36704.7783 | 66.6635 | 200.0553 | 0.0000 | 0.0006 | 46054.7802 | 10579.8644 |
| May | 41128.0354 | 74.7445 | 224.4484 | 0.0000 | 0.0007 | 51670.3852 | 11855.5534 |
| June | 47474.2709 | 86.3151 | 259.3047 | 0.0000 | 0.0008 | 59694.7178 | 13685.4809 |
| July | 50610.5833 | 92.0342 | 276.5360 | 0.0000 | 0.0008 | 63661.5681 | 14589.8453 |
| August | 49642.4529 | 90.2687 | 271.2161 | 0.0000 | 0.0008 | 62436.8537 | 14310.6799 |
| September | 41822.0483 | 76.0310 | 228.3865 | 0.0000 | 0.0007 | 52577.0089 | 12055.9904 |
| October | 42048.7452 | 76.4024 | 229.3806 | 0.0000 | 0.0007 | 52805.8059 | 12120.7232 |
| November | 41122.9091 | 74.4182 | 222.5197 | 0.0000 | 0.0007 | 51225.9552 | 11849.2683 |
| December | 49982.5312 | 90.1006 | 268.3596 | 0.0000 | 0.0008 | 61778.2407 | 14396.7922 |
| Annual Sum or Average |<PHONE_NUMBER> | 989.8082 | 2958.8588 | 0.0000 | 0.0089 |<PHONE_NUMBER> |<PHONE_NUMBER> |
| Minimum of Months | 36704.7783 | 66.6635 | 200.0553 | 0.0000 | 0.0006 | 46054.7802 | 10579.8644 |
| Maximum of Months | 58839.5982 | 105.0986 | 310.1100 | 0.0000 | 0.0009 | 71388.1911 | 16933.2717 |
Report: COMPONENTS OF PEAK ELECTRICAL DEMAND
For: Meter
Timestamp: 2021-07-16 12:27:56
Custom Monthly Report| ELECTRICITY:FACILITY [J] | ELECTRICITY:FACILITY {Maximum}[W] | ELECTRICITY:FACILITY {TIMESTAMP} | INTERIORLIGHTS:ELECTRICITY {AT MAX/MIN} [W] | INTERIOREQUIPMENT:ELECTRICITY {AT MAX/MIN} [W] | FANS:ELECTRICITY {AT MAX/MIN} [W] | HEATING:ELECTRICITY {AT MAX/MIN} [W] | COOLING:ELECTRICITY {AT MAX/MIN} [W] | EXTERIORLIGHTS:ELECTRICITY {AT MAX/MIN} [W] | PUMPS:ELECTRICITY {AT MAX/MIN} [W] | HEATREJECTION:ELECTRICITY [] | EXTERIOREQUIPMENT:ELECTRICITY [] | HUMIDIFICATION:ELECTRICITY [] | HEATRECOVERY:ELECTRICITY [] | WATERSYSTEMS:ELECTRICITY [] | REFRIGERATION:ELECTRICITY [] | GENERATORS:ELECTRICITY [] | ELECTRICITYPRODUCED:FACILITY [] | |
| January | 0.165651E+12 | 211799.610 | 04-JAN-06:10 | 1859.352 | 10201.524 | 3088.182 | 181838.112 | 0.000 | 14804.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| February | 0.129219E+12 | 196616.284 | 18-FEB-06:10 | 1859.352 | 10201.524 | 3088.182 | 166654.786 | 0.000 | 14804.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| March | 0.121064E+12 | 180514.135 | 01-MAR-06:10 | 1859.352 | 10201.524 | 3088.182 | 150552.637 | 0.000 | 14804.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| April | 0.106867E+12 | 93299.868 | 01-APR-05:10 | 1859.352 | 10201.524 | 3088.182 | 63338.370 | 0.000 | 14804.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| May | 0.119897E+12 | 105817.508 | 02-MAY-12:00 | 16734.166 | 38366.176 | 4479.243 | 0.000 | 46229.483 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| June | 0.138517E+12 | 125970.890 | 17-JUN-15:00 | 16734.166 | 37723.978 | 6797.000 | 0.000 | 64707.306 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| July | 0.147722E+12 | 143497.194 | 02-JUL-15:09 | 16734.166 | 37723.978 | 7056.449 | 0.000 | 81974.161 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| August | 0.144880E+12 | 117595.519 | 22-AUG-12:20 | 16734.166 | 38366.176 | 4781.530 | 0.000 | 57705.207 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| September | 0.122001E+12 | 129918.630 | 11-SEP-12:00 | 16734.166 | 38366.176 | 5849.745 | 0.000 | 68960.103 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| October | 0.122532E+12 | 110817.616 | 07-OCT-11:09 | 16734.166 | 39026.784 | 3997.595 | 0.000 | 51050.631 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| November | 0.118866E+12 | 176881.491 | 25-NOV-06:10 | 1859.352 | 10201.524 | 3088.182 | 146919.993 | 0.000 | 14804.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| December | 0.143352E+12 | 193966.463 | 09-DEC-06:10 | 1859.352 | 10201.524 | 3088.182 | 164004.965 | 0.000 | 14804.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
| Annual Sum or Average | 0.158057E+13 | |||||||||||||||||
| Minimum of Months | 0.106867E+12 | 93299.868 | 1859.352 | 10201.524 | 3088.182 | 0.000 | 0.000 | 0.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | |
| Maximum of Months | 0.165651E+12 | 211799.610 | 16734.166 | 39026.784 | 7056.449 | 181838.112 | 81974.161 | 14804.000 | 8.440 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 |
Report: HEATING PART LOAD PERFORMANCE
For: VAV_1_HEATC
Timestamp: 2021-07-16 12:27:56
Custom Monthly Report| HEATING COIL GAS RATE [W] | HEATING COIL GAS RATE {Maximum}[W] | HEATING COIL GAS RATE {TIMESTAMP} | |
| January | 4318. | 31754. | 04-JAN-07:10 |
| February | 2707. | 27843. | 12-FEB-07:05 |
| March | 1433. | 22148. | 01-MAR-07:10 |
| April | 29. | 5632. | 16-APR-06:03 |
| May | 0. | 0. | 01-MAY-00:10 |
| June | 0. | 0. | 01-JUN-00:10 |
| July | 0. | 0. | 01-JUL-00:10 |
| August | 0. | 0. | 01-AUG-00:10 |
| September | 0. | 0. | 01-SEP-00:10 |
| October | 47. | 7829. | 26-OCT-06:10 |
| November | 698. | 14371. | 25-NOV-07:05 |
| December | 1650. | 18854. | 11-DEC-07:05 |
| Annual Sum or Average | 912. | ||
| Minimum of Months | 0. | 0. | |
| Maximum of Months | 4318. | 31754. |
Report: HEATING PART LOAD PERFORMANCE
For: VAV_2_HEATC
Timestamp: 2021-07-16 12:27:56
Custom Monthly Report| HEATING COIL GAS RATE [W] | HEATING COIL GAS RATE {Maximum}[W] | HEATING COIL GAS RATE {TIMESTAMP} | |
| January | 4626. | 31917. | 04-JAN-07:10 |
| February | 2961. | 27917. | 12-FEB-07:05 |
| March | 1526. | 22152. | 01-MAR-07:10 |
| April | 21. | 5084. | 01-APR-06:03 |
| May | 0. | 0. | 01-MAY-00:10 |
| June | 0. | 0. | 01-JUN-00:10 |
| July | 0. | 0. | 01-JUL-00:10 |
| August | 0. | 0. | 01-AUG-00:10 |
| September | 0. | 0. | 01-SEP-00:10 |
| October | 43. | 7498. | 26-OCT-06:10 |
| November | 796. | 14632. | 25-NOV-07:05 |
| December | 1876. | 18927. | 11-DEC-07:05 |
| Annual Sum or Average | 992. | ||
| Minimum of Months | 0. | 0. | |
| Maximum of Months | 4626. | 31917. |
Report: HEATING PART LOAD PERFORMANCE
For: VAV_3_HEATC
Timestamp: 2021-07-16 12:27:56
Custom Monthly Report| HEATING COIL GAS RATE [W] | HEATING COIL GAS RATE {Maximum}[W] | HEATING COIL GAS RATE {TIMESTAMP} | |
| January | 5317. | 38109. | 04-JAN-07:10 |
| February | 3630. | 33328. | 12-FEB-07:05 |
| March | 1982. | 27777. | 01-MAR-07:10 |
| April | 70. | 7915. | 01-APR-06:03 |
| May | 0. | 0. | 01-MAY-00:10 |
| June | 0. | 0. | 01-JUN-00:10 |
| July | 0. | 0. | 01-JUL-00:10 |
| August | 0. | 0. | 01-AUG-00:10 |
| September | 1. | 1913. | 18-SEP-06:03 |
| October | 102. | 11815. | 26-OCT-06:05 |
| November | 1150. | 19144. | 25-NOV-07:05 |
| December | 2411. | 23468. | 11-DEC-07:05 |
| Annual Sum or Average | 1227. | ||
| Minimum of Months | 0. | 0. | |
| Maximum of Months | 5317. | 38109. |
Report: COOLING PART LOAD PERFORMANCE
For: VAV_1_COOLC DXCOIL
Timestamp: 2021-07-16 12:27:56
Custom Monthly Report| COOLING COIL ELECTRIC POWER [W] | COOLING COIL ELECTRIC POWER {Maximum}[W] | COOLING COIL ELECTRIC POWER {TIMESTAMP} | |
| January | 45. | 5517. | 11-JAN-15:00 |
| February | 0. | 0. | 01-FEB-00:10 |
| March | 151. | 4540. | 22-MAR-15:00 |
| April | 1121. | 9520. | 15-APR-13:00 |
| May | 3519. | 15060. | 02-MAY-14:00 |
| June | 6327. | 20830. | 17-JUN-16:10 |
| July | 7391. | 26461. | 02-JUL-15:10 |
| August | 6549. | 21004. | 29-AUG-11:30 |
| September | 3817. | 22988. | 11-SEP-13:00 |
| October | 1980. | 16789. | 07-OCT-11:10 |
| November | 344. | 8058. | 01-NOV-07:00 |
| December | 113. | 7375. | 22-DEC-13:00 |
| Annual Sum or Average | 2611. | ||
| Minimum of Months | 0. | 0. | |
| Maximum of Months | 7391. | 26461. |
Report: COOLING PART LOAD PERFORMANCE
For: VAV_2_COOLC DXCOIL
Timestamp: 2021-07-16 12:27:56
Custom Monthly Report| COOLING COIL ELECTRIC POWER [W] | COOLING COIL ELECTRIC POWER {Maximum}[W] | COOLING COIL ELECTRIC POWER {TIMESTAMP} | |
| January | 47. | 5722. | 11-JAN-15:00 |
| February | 0. | 0. | 01-FEB-00:10 |
| March | 153. | 4682. | 22-MAR-15:00 |
| April | 1173. | 9822. | 14-APR-15:00 |
| May | 3725. | 15847. | 16-MAY-05:02 |
| June | 6375. | 27972. | 19-JUN-05:02 |
| July | 7392. | 30509. | 14-JUL-05:02 |
| August | 6242. | 25434. | 22-AUG-05:02 |
| September | 3780. | 27177. | 02-SEP-05:02 |
| October | 2052. | 17181. | 07-OCT-11:20 |
| November | 353. | 8311. | 01-NOV-05:10 |
| December | 115. | 7603. | 22-DEC-12:32 |
| Annual Sum or Average | 2615. | ||
| Minimum of Months | 0. | 0. | |
| Maximum of Months | 7392. | 30509. |
Report: COOLING PART LOAD PERFORMANCE
For: VAV_3_COOLC DXCOIL
Timestamp: 2021-07-16 12:27:56
Custom Monthly Report| COOLING COIL ELECTRIC POWER [W] | COOLING COIL ELECTRIC POWER {Maximum}[W] | COOLING COIL ELECTRIC POWER {TIMESTAMP} | |
| January | 50. | 5970. | 11-JAN-15:00 |
| February | 0. | 0. | 01-FEB-00:10 |
| March | 156. | 4726. | 22-MAR-15:00 |
| April | 1220. | 10509. | 14-APR-15:00 |
| May | 4036. | 18778. | 16-MAY-05:02 |
| June | 7136. | 30932. | 19-JUN-05:02 |
| July | 8213. | 31793. | 08-JUL-05:02 |
| August | 6598. | 27231. | 22-AUG-05:02 |
| September | 3949. | 29750. | 02-SEP-05:02 |
| October | 2113. | 17408. | 07-OCT-11:10 |
| November | 348. | 8657. | 01-NOV-05:10 |
| December | 113. | 7909. | 22-DEC-13:00 |
| Annual Sum or Average | 2825. | ||
| Minimum of Months | 0. | 0. | |
| Maximum of Months | 8213. | 31793. |
Report: FAN PART LOAD PERFORMANCE
For: VAV_1_FAN
Timestamp: 2021-07-16 12:27:56
Custom Monthly Report| FAN ELECTRIC POWER [W] | FAN ELECTRIC POWER {Maximum}[W] | FAN ELECTRIC POWER {TIMESTAMP} | |
| January | 527. | 1390. | 13-JAN-13:10 |
| February | 545. | 1302. | 22-FEB-13:10 |
| March | 549. | 1370. | 11-MAR-13:00 |
| April | 592. | 1328. | 14-APR-13:00 |
| May | 617. | 1614. | 06-MAY-16:30 |
| June | 727. | 2314. | 17-JUN-16:10 |
| July | 816. | 2515. | 08-JUL-16:30 |
| August | 774. | 2264. | 21-AUG-16:10 |
| September | 709. | 2146. | 11-SEP-15:10 |
| October | 648. | 1682. | 04-OCT-15:10 |
| November | 552. | 1390. | 14-NOV-11:40 |
| December | 535. | 1390. | 28-DEC-12:00 |
| Annual Sum or Average | 632. | ||
| Minimum of Months | 527. | 1302. | |
| Maximum of Months | 816. | 2515. |
Report: FAN PART LOAD PERFORMANCE
For: VAV_2_FAN
Timestamp: 2021-07-16 12:27:56
Custom Monthly Report| FAN ELECTRIC POWER [W] | FAN ELECTRIC POWER {Maximum}[W] | FAN ELECTRIC POWER {TIMESTAMP} | |
| January | 610. | 1340. | 13-JAN-13:10 |
| February | 588. | 1286. | 22-FEB-13:10 |
| March | 566. | 1373. | 11-MAR-13:00 |
| April | 618. | 1353. | 14-APR-13:00 |
| May | 651. | 2368. | 28-MAY-05:02 |
| June | 712. | 6360. | 18-JUN-05:02 |
| July | 771. | 5499. | 14-JUL-05:02 |
| August | 691. | 3209. | 09-AUG-05:02 |
| September | 680. | 3462. | 02-SEP-05:02 |
| October | 664. | 1735. | 07-OCT-05:02 |
| November | 564. | 1454. | 18-NOV-12:00 |
| December | 556. | 1374. | 28-DEC-12:40 |
| Annual Sum or Average | 639. | ||
| Minimum of Months | 556. | 1286. | |
| Maximum of Months | 771. | 6360. |
Report: FAN PART LOAD PERFORMANCE
For: VAV_3_FAN
Timestamp: 2021-07-16 12:27:56
Custom Monthly Report| FAN ELECTRIC POWER [W] | FAN ELECTRIC POWER {Maximum}[W] | FAN ELECTRIC POWER {TIMESTAMP} | |
| January | 783. | 1275. | 13-JAN-13:10 |
| February | 714. | 1234. | 22-FEB-13:20 |
| March | 603. | 1344. | 11-MAR-13:20 |
| April | 635. | 1447. | 15-APR-05:02 |
| May | 699. | 3262. | 03-MAY-05:02 |
| June | 810. | 7908. | 18-JUN-05:02 |
| July | 883. | 7780. | 14-JUL-05:02 |
| August | 732. | 3692. | 12-AUG-05:02 |
| September | 708. | 4077. | 02-SEP-05:02 |
| October | 676. | 2477. | 07-OCT-05:02 |
| November | 608. | 1443. | 18-NOV-13:05 |
| December | 704. | 1298. | 28-DEC-12:50 |
| Annual Sum or Average | 713. | ||
| Minimum of Months | 603. | 1234. | |
| Maximum of Months | 883. | 7908. |


Use the latest web technology to power your empire.
Staying up with the latest web technology and standards is a tiring proposition - let us sift through the jargon and find the best technology to match your business's needs.
At the end of the day, web statistics can sound great but mean little. With Trellis, we work with you to get real results that matter to you and your business.
 Just fill out the form below and we'll be in contact with you shortly!


{{ innovation.meta.meta_title }}
{% include component/header_xw.html %}
{% include innovation/main_biz_strategy.html %}
{% include innovation/performance.html %}
{% include innovation/article_img_right.html %}
{% include innovation/comm.html %}
{% include innovation/plans.html %}
{% include innovation/article_img_left.html %}
{% include innovation/space_rich.html %}
{% include innovation/article_img_right_2.html %}
{% include innovation/better.html %}
{% include component/back_to_top.html %}
{% include component/footer.html %}
{% lazyScript %}
{% includeScript "../../../src/js/innovation.js" %}


Workout like a pro
Use this gym timer for training with weights,
kettlebells, bodyweight exercises, crossfit, 7 minute workout, WOD, TRX, cardio exercises,
stretching, spinning, calisthenics, tabata, boot camp circuit workout training, or any other high
intensity interval training.


uAdmin Tutorial Part 12 - Introduction to HTML Template¶
In this part, we will discuss about designing a table in HTML and setting up a template file.
Before you proceed, make sure you have at least the basic knowledge of HTML. If you are not familiar with HTML, we advise you to go over W3Schools.
In this tutorial, we will use Bootstrap 5.
First of all, go to your project folder and select templates.
Inside the templates folder, create a new file named todo.html.
Inside the todo.html, create an HTML5 structure following the codes below and change the title from Document to Todo List.
<!DOCTYPE html>

<meta charset="UTF-8">
<meta name="viewport" content="width=device-width, initial-scale=1.0">
<meta http-equiv="X-UA-Compatible" content="ie=edge">

<link<EMAIL_ADDRESS>rel="stylesheet" integrity="sha384-F3w7mX95PdgyTmZZMECAngseQB83DfGTowi0iMjiWaeVhAn4FJkqJByhZMI3AhiU" crossorigin="anonymous">

<title>Todo List</title>

Save the file. Run your application in the browser and see what happens.
The title bar is named as Todo List. Now inside the  tag, create a table header following the code structure below. You can choose which class of Bootstrap table that you want to display in your application. In this tutorial, we will use table-striped.

Name
Description
Category
Friend
Item
Target Date
Progress

Save the file. Run your application in the browser and see what happens.
Nice! Now go back to your project folder then select views.
Inside the views folder, create a new file named view.go.
Click here to view our progress so far.
In the next part, we will talk about establishing a connection to the HTTP Handler, setting the URL path name, and executing an HTML file.


--- layout: single author_profile: true permanentlink: /_pages/about.md ---
Hi! I am a Ph.D. Fellow at the Cybersecurity Research Group at Aalborg University, Denmark. My topics of interest include Cyber Deception, Threat Intelligence, and Internet Security Measurements.
I work primarily with honeypots to gather the threat landscape and understand attacker behavior. Other than honeypots, I scan the Internet to find gaps in the deployment and configuration of systems. I believe that most security incidents are caused either due to improper testing or misconfigured deployments.
If my work interests you or you would like to collaborate, please feel free to contact me!
02-09-2022 Our paper "Interaction Matters: a comprehensive analysis and a dataset of hybrid IoT/OT honeypots" is accepted at ACSAC 2022


Multi-class classifier with synthesised data
This Markov Chain model takes in real place names, and generates new place names based on the letter patterns within those place names.
Fiddle with the input options to generate crazy or realistic place names.
Japan
UK
China
Germany
Total
--%
--%
--%
--%
--%
Data Settings
Real data:Use synthesised data?
Number Of Samples Input into Markov Model: Number of place names generated: Synthesised data (using Markov model):
Markov Chain Text Generation Settings
Conservativeness: Lookback:
Neural Network Settings
Epochs:
Inspired by this great project. All the code is my own. More information on Markov chains can be found at Wikipedia.


|
MoveToCode
|
Protected Member Functions | |
| override void | SetUpOnEnable () |
| override void | RunOnDisable () |
| Protected Member Functions inherited from MoveToCode.MazePiece | |
| virtual void | SetUpOnEnable () |
| virtual void | RunOnDisable () |
| void | SetUpLayerMask (LayerMask lm) |
Additional Inherited Members | |
| Public Types inherited from MoveToCode.MazePiece | |
| enum | CONNECTDIR |
| Public Member Functions inherited from MoveToCode.MazePiece | |
| MazeConnector | GetConnector (Vector3 direction) |
| void | DisableMyPiece () |
| override string | ToString () |
| Static Public Member Functions inherited from MoveToCode.MazePiece | |
| static CONNECTDIR | GetOppositeDir (CONNECTDIR dir) |
| Static Public Attributes inherited from MoveToCode.MazePiece | |
| static Dictionary< CONNECTDIR, Vector3 > | dirToVector |
| Properties inherited from MoveToCode.MazePiece | |
| Dictionary< CONNECTDIR, MazeConnector > | ConnectionDict [get] |
| MPType | MyMPType [get] |
| bool | HasBeenTracked [get] |
| bool | IsAnchored [get, set] |
| bool | IsBabyKuriPiece [get] |
| bool | IsGoalPiece [get] |
| Vector3 | Center [get] |
| Color | MyColor [get] |
|
protectedvirtual |
Reimplemented from MoveToCode.MazePiece.
|
protectedvirtual |
Reimplemented from MoveToCode.MazePiece.


ChainZilla provides the most efficient and flexible end-to-end blockchain solutions. These include project onboarding, tokenization, app development, ICO management, and blockchain migrations.
A crypto Battle Royale is coming… are you ready? Did Oyster $PRL just exit scam?!? Reasons why the bear market is actually good, Chinese $BTC documentary, Tr...
Janet Yellen ranted against Bitcoin today at a finance conference in Canada.
Retweet this photo to remind her that Bitcoin is more transparent than the Federal Reserve.
Retweets
1443
Likes
2309
[dscrd-cz] <PTYX> notice the buy bitcoin sign behind her. that's an old photo though.
Janet Yellen....BITCOIN....BLAH BLAH BLAH.....BITCOIN Thanks For Watch My Video, Really Appreciate It. DONT FORGET TO SUBSCRIBE http://bit.ly/2xcoUCe Instagr...
When services like Uber (2009), and later Lyft (2012), first introduced their concepts to the world, they revolutionized the way many of…
[dscrd-cz] <Instel7> I'd like your opinion on it, do you see it as a feasible project for the rideshare market for the next years?
[dscrd-cz] <Hungry_BullBear> Is this like Uber but for long distance travel ?
[dscrd-cz] <PTYX> Just like Uber but with a better business model
[dscrd-cz] <PTYX> And they have a partnership with Dash in order to provide the drivers an instant payment cryptocurrency
[dscrd-cz] <PTYX> Their app accepts the traditional Fiat payments and Dash. The drivers get 90% if their fair and will have ability to vote on certain aspects of the company and its operations
[dscrd-cz] <PTYX> Abee Foundation is focused on the whole sharing economy so expect also airbnb-style solutions from them in the future. We partnered with them to provide them consulting services and assist with the launch process in Latin American countries.
GatewayBOT31-Oct-18 03:18 PM
[dscrd-cz] <phideas> !tip thunder 0.0777
[dscrd-cz] <Instel7> @phideas try !zillatip thunder at #botchat
GatewayBOT31-Oct-18 05:17 PM
[dscrd-cz] <PTYX> These are the sort of messages I get daily
[dscrd-cz] <Emmanuel> There use to be beggars too.
[dscrd-cz] <Emmanuel> Once one guy wanted me to pay for his phone bill.
[dscrd-cz] <Emmanuel> - "No, I won't pay for your phone bill. Study, learn programming and get a job."
- "How can I study without internet in my phone? Please pay my bill, it's nothing for you."
- "No!"
[dscrd-cz] <Emmanuel> This went like this for hours.
[dscrd-cz] <Emmanuel> Very annoying.
GatewayBOT31-Oct-18 06:54 PM
[dscrd-cz] <pdtm> very antisocial behavior
GatewayBOT31-Oct-18 07:30 PM
[dscrd-cz] <ch6ris> @Instel7 opps, I missed the " , " Looked like $19.666 to me
[dscrd-cz] <ch6ris> @Emmanuel I've got a few bills that need paying. (edited)
GatewayBOT31-Oct-18 08:51 PM
[dscrd-cz] <JstMtlQc> Hi
[dscrd-cz] <JstMtlQc> Can I talk to the community manager?
[dscrd-cz] <PTYX> @JstMtlQc how can we help you?
GatewayBOT01-Nov-18 12:04 AM
[dscrd-cz] <PTYX> Let's help Verus coin get listed on txbit.io Remember, you can vote every 24 hours. Winning this round looks completely within reach, and there are a little over 5 days left! Can we make it happen?! vote here https://txbit.io/Coin
GatewayBOT01-Nov-18 12:32 AM
[dscrd-cz] <Instel7> @everyone Please, let's support Verus coin voting to get listed on txbit.io! (edited)
GatewayBOT01-Nov-18 03:15 AM
[dscrd-cz] <Regnar> voted
GatewayBOT01-Nov-18 06:36 AM
[dscrd-cz] <deathsgrip> Verus got this np, but I’ll still vote the next 5 days as well
GatewayBOT01-Nov-18 08:00 AM
[dscrd-cz] <Bo> done
GatewayBOT01-Nov-18 10:21 AM
[dscrd-cz] <figgy132> Keep getting a daily (at everyone) reminder out though, just in case some forget :)
[dscrd-cz] <Instel7> You can leave them a vote each 24 hours, so don't stop voting
[dscrd-cz] <Instel7> Hello @bigkid45 Welcome to Chainzilla
GatewayBOT01-Nov-18 01:39 PM
[dscrd-cz] <JoTD> In a landmark study, 20 top US corporate lawyers with decades of experience in corporate law and contract review were pitted against an AI. The study says that the lawyers took 92 minutes to find the problem, while the AI took 26 seconds, we will need more cups of coffee?
https://www.zerohedge.com/news/2018-10-29/ai-beats-20-lawyers-legal-showdown
[dscrd-cz] <wookie25> Are all kmd assetchains on there?
[dscrd-cz] <PTYX> Not by default no
GatewayBOT01-Nov-18 10:09 PM
[dscrd-cz] <PTYX> @everyone Trick question to see who was paying attention. The prize is 10 ZILLA:
Why is ABEE called ABEE?
(edited)
[dscrd-cz] <ch6ris> Ride Partner?
[dscrd-cz] <SadykovT> a meteorite ?
[dscrd-cz] <ch6ris> Located in Canada?
[dscrd-cz] <BlockTech> About Abee Pierre ? XD
[dscrd-cz] <crumb> a business for ethical enterpreneurship?
[dscrd-cz] <TLMTroublemaker> The ABEE Foundation is a non-US entity established in Saint Kitts & Nevis for a seamless international reach. ABEE Rideshare is the first among many companies that will be using the ABEE name and will be receiving equity-free funding from the A.F.
[dscrd-cz] < | Khlilo98> Because of the ABEE first company
[dscrd-cz] <wookie25> ABEE stands for "all of us". ABEE foundation is was set up to help children of Guyana. @PTYX
[dscrd-cz] <st3rling0x> OK remember. It's a rideshare company. That takes people places.


{% extends "govuk_template.html" %}
{% block head %}
{% include "includes/head.html" %}
{% endblock %}
{% block cookie_message %}
GOV.UK uses cookies to make the site simpler. Find out more about cookies
{% endblock %}
{% block proposition_header %}
{% include "includes/propositional_navigation.html" %}
{% endblock %}
{% block header_class %}
with-proposition
{% endblock %}
{% block body_end %}
{% include "includes/scripts.html" %}
{% endblock %}


Currently a sophomore at IIITH, pursuing BTech in Computer Science and Engineering, with integrated MS by research in Computational Sciences.
Check out our blog at room333.
Also, my personal site which I built during freshman year at college: home. I don’t update my website very often. It merely serves as a linktree :P
“You can’t cross the sea merely by standing and staring at the water.”
– Tagore


Edit your personal information
First name
Last name
Email address
Password
Password confirm
Save changes
Change profile photo


Constructor
new Nf3(clientBaseUrl, optimistBaseUrl, optimistWsUrl, web3WsUrl, ethereumSigningKey, zkpKeys)
Parameters:
| Name | Type | Description |
|---|---|---|
clientBaseUrl |
string | The base url for nightfall-client |
optimistBaseUrl |
string | The base url for nightfall-optimist |
optimistWsUrl |
string | The webscocket url for nightfall-optimist |
web3WsUrl |
string | The websocket url for the web3js client |
ethereumSigningKey |
string | the Ethereum siging key to be used for transactions (hex string). |
zkpKeys |
object | An object containing the zkp keys to use. These will be auto-generated if left undefined. |
Methods
(async) addPeer(peerUrl)
Adds a new Proposer peer to a list of proposers that are available for accepting
offchain (direct) transfers and withdraws. The client will submit direct transfers
and withdraws to all of these peers.
Parameters:
| Name | Type | Description |
|---|---|---|
peerUrl |
string | the URL of the Proposer being added. This will be from the point of view of nightfall-client, not the SDK user (e.g. 'http://optimist1:80'). Nightfall-client will use this URL to contact the Proposer. |
(async) advanceInstantWithdrawal(withdrawTransactionHash)
Enables someone to service a request for an instant withdrawal
Parameters:
| Name | Type | Description |
|---|---|---|
withdrawTransactionHash |
string | the hash of the Layer 2 transaction in question |
(async) close()
Closes the Nf3 connection to the blockchain and any open websockets to NF_3
(async) deposit(fee, ercAddress, tokenType, value, tokenId, keys) → {Promise}
Deposits a Layer 1 token into Layer 2, so that it can be transacted
privately.
Parameters:
| Name | Type | Description |
|---|---|---|
fee |
number | The amount (Wei) to pay a proposer for the transaction |
ercAddress |
string | The address of the ERCx contract from which the token is being taken. Note that the Nightfall_3 State.sol contract must be approved by the token's owner to be able to withdraw the token. |
tokenType |
string | The type of token to deposit. Possible values are 'ERC20', 'ERC721', 'ERC1155'. |
value |
number | The value of the token, in the case of an ERC20 or ERC1155 token. For ERC721 this should be set to zero. |
tokenId |
string | The ID of an ERC721 or ERC1155 token. In the case of an 'ERC20' coin, this should be set to '0x00'. |
keys |
object | The ZKP private key set. |
Returns:
Resolves into the Ethereum transaction receipt.
- Type
- Promise
(async) getChallengeEmitter() → {Promise}
Returns an emitter, whose 'data' event fires whenever a challengeable block is
detected, passing out the transaction needed to raise the challenge. This
is a lower level method than `Nf3.startChallenger` because it does not sign and
send the transaction to the blockchain. If required, `Nf3.submitTransaction`
can be used to do that.
Returns:
A Promise that resolves into an event emitter.
- Type
- Promise
(async) getContractAddress(contractName) → {Promise}
Returns the address of a Nightfall_3 contract.
Parameters:
| Name | Type | Description |
|---|---|---|
contractName |
string | the name of the smart contract in question. Possible values are 'Shield', 'State', 'Proposers', 'Challengers'. |
Returns:
Resolves into the Ethereum address of the contract
- Type
- Promise
(async) getInstantWithdrawalRequestedEmitter()
Returns an event emitter that fires each time an InstantWithdrawalRequested
event is detected on the blockchain
(async) getLayer2Balances() → {Promise}
Returns the balance of tokens held in layer 2
Returns:
This promise rosolves into an object whose properties are the
addresses of the ERC contracts of the tokens held by this account in Layer 2. The
value of each propery is the number of tokens originating from that contract.
- Type
- Promise
(async) getNewBlockEmitter() → {Promise}
Returns an emitter, whose 'data' event fires whenever a block is
detected, passing out the transaction needed to propose the block. This
is a lower level method than `Nf3.startProposer` because it does not sign and
send the transaction to the blockchain. If required, `Nf3.submitTransaction`
can be used to do that.
Returns:
A Promise that resolves into an event emitter.
- Type
- Promise
(async) healthcheck(server) → {Promise}
Determines if a Nightfall_3 server is running and healthy.
Parameters:
| Name | Type | Description |
|---|---|---|
server |
string | The name of the server being checked ['client', 'optimist'] |
Returns:
This will resolve into a boolean - true if the healthcheck passed.
- Type
- Promise
(async) init() → {Promise}
Initialises the Nf_3 object so that it can communicate with Nightfall_3 and the
blockchain.
Returns:
- Type
- Promise
(async) registerChallenger() → {Promise}
Registers our address as a challenger address with the optimist container.
This is so that the optimist container can tell when a challenge that we have
committed to has appeared on chain.
Returns:
A promise that resolves to an axios response.
- Type
- Promise
(async) registerProposer() → {Promise}
Registers a new proposer and pays the Bond required to register.
It will use the address of the Ethereum Signing key that is holds to register
the proposer.
Returns:
A promise that resolves to the Ethereum transaction receipt.
- Type
- Promise
(async) requestInstantWithdrawal(withdrawTransactionHash, fee)
Enables someone with a valid withdraw transaction in flight to request instant
withdrawal of funds (only relevant for ERC20).
Parameters:
| Name | Type | Description |
|---|---|---|
withdrawTransactionHash |
string | the hash of the Layer 2 transaction in question |
fee |
number | the amount being paid for the instant withdrawal service |
setEthereumSigningKey(key)
Setter for the ethereum private key, in case it wasn't known at build time.
This will also update the corresponding Ethereum address that Nf_3 uses.
Parameters:
| Name | Type | Description |
|---|---|---|
key |
string | the ethereum private key as a hex string. |
setzkpKeys(keys)
Setter for the zkp keys, in case it wasn't known at build time and we don't
want to use autogenerated ones.
Parameters:
| Name | Type | Description |
|---|---|---|
keys |
object | The zkp keys object. |
(async) startChallenger()
Starts a Challenger that listens for challengable blocks and submits challenge
transactions to the blockchain to challenge the block.
(async) startProposer()
Starts a Proposer that listens for blocks and submits block proposal
transactions to the blockchain.
(async) submitTransaction(unsignedTransaction, shieldContractAddress, fee) → {Promise}
Method for signing and submitting an Ethereum transaction to the
blockchain.
Parameters:
| Name | Type | Description |
|---|---|---|
unsignedTransaction |
object | An unsigned web3js transaction object. |
shieldContractAddress |
string | The address of the Nightfall_3 shield address. |
fee |
number | the value of the transaction. This can be found using the getContractAddress convenience function. |
Returns:
This will resolve into a transaction receipt.
- Type
- Promise
(async) subscribeToIncomingViewingKeys(keys)
Provides nightfall-client with a set of viewing keys. Without these,
it won't listen for BlockProposed events and so won't update its transaction collection
with information about which are on-line.
Parameters:
| Name | Type | Description |
|---|---|---|
keys |
object | Object containing the ZKP key set (this may be generated with the makeKeys function). |
(async) transfer(fee, ercAddress, tokenType, value, tokenId, keys, pkd) → {Promise}
Transfers a token within Layer 2.
Parameters:
| Name | Type | Description |
|---|---|---|
fee |
number | The amount (Wei) to pay a proposer for the transaction |
ercAddress |
string | The address of the ERCx contract from which the token is being taken. Note that the Nightfall_3 State.sol contract must be approved by the token's owner to be able to withdraw the token. |
tokenType |
string | The type of token to deposit. Possible values are 'ERC20', 'ERC721', 'ERC1155'. |
value |
number | The value of the token, in the case of an ERC20 or ERC1155 token. For ERC721 this should be set to zero. |
tokenId |
string | The ID of an ERC721 or ERC1155 token. In the case of an 'ERC20' coin, this should be set to '0x00'. |
keys |
object | The ZKP private key set of the sender. |
pkd |
array | The transmission key of the recipient (this is a curve point represented as an array of two hex strings). |
Returns:
Resolves into the Ethereum transaction receipt.
- Type
- Promise
(async) withdraw(fee, ercAddress, tokenType, value, tokenId, keys, recipientAddress) → {Promise}
Withdraws a token from Layer 2 back to Layer 1. It can then be withdrawn from
the Shield contract's account by the owner in Layer 1.
Parameters:
| Name | Type | Description |
|---|---|---|
fee |
number | The amount (Wei) to pay a proposer for the transaction |
ercAddress |
string | The address of the ERCx contract from which the token is being taken. Note that the Nightfall_3 State.sol contract must be approved by the token's owner to be able to withdraw the token. |
tokenType |
string | The type of token to deposit. Possible values are 'ERC20', 'ERC721', 'ERC1155'. |
value |
number | The value of the token, in the case of an ERC20 or ERC1155 token. For ERC721 this should be set to zero. |
tokenId |
string | The ID of an ERC721 or ERC1155 token. In the case of an 'ERC20' coin, this should be set to '0x00'. |
keys |
object | The ZKP private key set of the sender. |
recipientAddress |
string | The Ethereum address to where the withdrawn tokens should be deposited. |
Returns:
Resolves into the Ethereum transaction receipt.
- Type
- Promise


The world needs automation and I am here to help!
yay
| head1 | head two | three |
|---|---|---|
| ok | good swedish fish | nice |
| out of stock | good and plenty | nice |
| ok | good oreos |
hmm |
| ok | good zoute drop |
yumm |
Long, single-line code blocks should not wrap. They should horizontally scroll if they are too long. This line should be long enough to demonstrate this.
The final element.


'use strict';
// GRAPH_OT_interpolation_type
/**
* FCurve interpolation types, between two keyframes.
* @enum {number}
* @readonly
*/
var Interpolation = {
/** No interpolation, value gets held. */
CONSTANT: 0,
/** Straight-line interpolation. */
LINEAR: 1,
/** Smooth interpolation. */
BEZIER: 2,
/** Cubic easing with overshoot and settle. */
BACK: 3,
/** Exponentially decaying parabolic bounce. */
BOUNCE: 4,
/** Circular easing. */
CIRCULAR: 5,
/** Cubic easing. */
CUBIC: 6,
/** Exponentially decaying sine wave. */
ELASTIC: 7,
/** Exponential easing. */
EXPONENTIAL: 8,
/** Quadratic easing. */
QUADRATIC: 9,
/** Quartic easing. */
QUARTIC: 10,
/** Quintic easing. */
QUINTIC: 11,
/** Sinusoidal easing. */
SINUSOIDAL: 12,
};
module.exports = Interpolation;


{{ You appear to have no IPv6 at this time.. }}
{{ You appear to have no IPv6 address. }}
[% PROCESS "faq/dontfeelbad.inc" %] [% PROCESS "faq/whyipv6.inc" %] [% PROCESS "faq/unable_to_see_ipv6.inc" %] [% PROCESS "faq/brokers.inc" %][% PROCESS "inc/header.inc" %] [% $page := "No IPv6" %] [% PROCESS "inc/list-nav.inc" %]
{{ You appear to have no IPv6 address. }}
[% PROCESS "faq/dontfeelbad.inc" %] [% PROCESS "faq/whyipv6.inc" %] [% PROCESS "faq/unable_to_see_ipv6.inc" %] [% PROCESS "faq/brokers.inc" %]


ARMY OF DARKNESS
Review by John Beachem
* * * * 1/2
Directed by: Sam Raimi Written by: Sam Raimi, Ivan Raimi
Our one-handed, chainsaw wielding, fairly brainless hero, Ash (Bruce Campbell) is back. After being sucked into a vortex at the end of "Evil Dead II", Ash finds himself back in the middle ages, in the kingdom of King Arthur (Marcus Gilbert). Ash is taken captive by Arthur's men, along with Duke Henry the Red (Richard Grove), Arthur's mortal enemy. It seems Arthur and Henry are being attacked by the deadites (the demons Ash has already battled in the future), but they're still finding time to fight each other. Ash is taken back to Arthur's castle as a prisoner, despite the protestations of Arthur's advisor (Ian Abercrombie), who believes Ash to be the chosen one who will defeat the deadites. Ash soon escapes, entrances a young girl named Sheila (Embeth Davidtz), and promises to retrieve the Necronomicon for the wise man so the deadites can be stopped. Of course, Ash botches this retrieval pretty badly, and unleashes a massive army of the dead who will soon attack Arthur's castle. Now Ash, Arthur, and a handful of men must stop hundreds of walking skeletons from taking the Necronomicon and with it, the world. Maybe, just maybe Ash and his men can win.... yeah, and maybe I'm a Chinese jet pilot.
A lot of people call "Army of Darkness" the weakest entry into the "Evil Dead" trilogy. As a horror movie, yes, this is certainly the weakest film. While "Evil Dead" was a horror movie with occasional comic elements, and "Evil Dead II" was an almost 50/50 blend of horror and comedy, "Army of Darkness" is a comedy with an occasional horrific moment. For that reason, your average horror fanatic isn't going to have a great time.   It's a movie packed with one-liners (nearly all of which were stolen by the video game, "Duke Nukem") that you'll be quoting for weeks (or in my case years), until your friends are ready to kill you for calling everything groovy whether it's groovy or not. What makes the movie so funny, so quotable, and just so memorable? Simple...
... it's Bruce Campbell. Campbell plays Ash a little differently this time around, but who can blame him? Battling a horde of demons is bound to change any man, and it has turned Ash into a man who thinks he's a lot smarter than he actually is. This makes for some great comic moments, such as when he must speak the sacred words (a little tribute to "The Day the Earth Stood Still") before removing the Necronomicon from the graveyard. Campbell's facial expressions during this and dozens of other comical scenes are second to none.  One day Campbell's going to get his due, I just know it. Supporting characters meant little in the first two "Evil Dead" films, and they mean even less in "Army of Darkness". This is Campbell's movie, and no one tries to upstage him. Still, the supporting cast members do just fine in roles that require them to do little more than scream a lot. The only exception is Marcus Gilbert, who is really quite entertaining as the hard-as-nails King Arthur (No, I don't THINK it's that Arthur). Watch for Sam Raimi's younger brother, Ted, in three different cameos (a whining soldier, a cheering villager, and an S-Mart employee). Bridget Fonda ("A Simple Plan") appears briefly as Ash's girlfriend in a flashback (she's the third actress to play the same girlfriend).
While Bruce Campbell carries the film, he's assisted greatly by the always unique direction of Sam Raimi. Raimi toned his chaotic direction down a bit in "Evil Dead II", but he cranks it into overdrive here in part three. All the fat has been trimmed off this movie, which means no character development, no exposition of plot, no long scenes of dialogue, nothing by constant action and laughs. Obviously the film didn't fare too well with critics for those reasons, but it's sure to delight anyone ages 14 to 28 or so. It's frantic and wild, and it has more fun moments than you can shake a chainsaw at. My two personal favorite comic moments are Ash's scene in the graveyard, where he battles a horde of skeleton hands poking out of the ground (massive "Three Stooges" homage here), and Ash fighting a legion of tiny Ashes in a windmill. The latter scene leads into another great scene where Ash dances about singing "Mr. Goody Two-shoes" (don't worry, it'll make sense when you get there). But what about action, what about horror?! You're no doubt shouting that at your screen right now, and let me tell you, there is some great medieval action in "Army of Darkness". The final battle, involving an army of skeletons storming the castle, is packed with some of the best fantasy action you're likely to find in a movie. Sword fights and catapults and flaming arrows and - oh, sorry, I got a little worked up there.
But horror, where's the horror?! Well my friends, there's not much to be found. I suppose the scene with Ash fighting gouls in the pit could qualify as horror, but other than that you're not likely to find much here. Sorry. A lingering curiosity about "Army of Darkness" has always been the special effects. They're a curiosity because while they are, at times, really quite wonderful (particularly during the final battle, where we get hundreds of highly detailed skeletons marching in formation), they're also dreadful on occasion. I refer specifically to the matte jobs in a few scenes, like those with the tiny Ashes. They're so bad, and so dated, I can't help but think they're intentional for reasons buried deep within the mind of Sam Raimi (a terrifying place, I'm sure). One last thing worth noting is the film's score, and particularly one piece called "March of the Dead". It's composed by long-time Tim Burton collaborator, Danny Elfman, and a more perfect score could not possibly have been inserted in this film. "Army of Darkness" runs a lean, mean, 85 minutes. It stops just before it starts to wear out its welcome. I'd recommend it to fans of Bruce Campbell, fans of Raimi's unique directorial style, and fans of slap-stick comedy. I give it a well earned four and a half out of five stars.
Comments? Send to<EMAIL_ADDRESS>Past reviews can be found at: http://us.imdb.com/ReviewsBy?John+Beachem
* * * * * - One of the best movies of the year. * * * * - Great flick, try and catch this one. * * * - Okay movie, hits and misses. * * - Pretty bad, see it at your own risk. * - See this one only if you enjoy pain.
The review above was posted to the
rec.arts.movies.reviews newsgroup (de.rec.film.kritiken for German reviews).
The Internet Movie Database accepts no responsibility for the contents of the
review and has no editorial control. Unless stated otherwise, the copyright
belongs to the author.
Please direct comments/criticisms of the review to relevant newsgroups.
Broken URLs inthe reviews are the responsibility of the author.
The formatting of the review is likely to differ from the original due
to ASCII to HTML conversion.
Related links: index of all rec.arts.movies.reviews reviews


Shelter
Good Food
Good Drink
Good Company
We're a Cafe by Day & Atelier by Night.
But to keep it simple,
all you need to know is
we care about the good things in life:
Our kitchen is open 7 days a week for
Breakfast & Lunch at the cafe.
L'Atelier is open for Dinner
Wednesdays through Saturdays.


I am good at developing applications with Ruby on Rails and Django Frameworks along with this i am good at Mysql, Postgres and Nosql like MongoDB
I am goot at tools like Git, Jenkins, Ansible, Chef, Docker, Vagrant, Elk stack and automationg these tools with scripts.
Scripting for automating the IT infrastructure with strong Linux knowladge is like a gem on a crown of my automation


public class OBSectionBuilder extends java.lang.Object implements CSectionBuilder
The section-builder has an associated OModel
over which
the sanctioning will operate, and optionally a IReasoner
object to be be attached to the generated CFrame
objects
to provide updating of their IFrame
instantiations.
The configuration for the sanctioning mechanism can be provided
via the general MEKON configuration system, as can the configuration
for the OModel
over which the sanctioning will operate,
and for a ORClassifier
object (which is the default
OWL-classification-based implementation of IReasoner
) to
be attached to all generated frames.
| Constructor and Description |
|---|
OBSectionBuilder(uk.ac.manchester.cs.mekon_util.config.KConfigNode parentConfigNode)
Constructs section-builder with configuration defined via the
appropriately-tagged child of the specified
parent-configuration-node.
|
OBSectionBuilder(OModel model)
Constructs section-builder with default configuration, and with
no
IReasoner specified. |
OBSectionBuilder(OModel model,
uk.ac.manchester.cs.mekon_util.config.KConfigNode parentConfigNode)
Constructs section-builder with specified model over which the
sanctioning is to operate, and with configuration defined via
the appropriately-tagged child of the specified
parent-configuration-node.
|
| Modifier and Type | Method and Description |
|---|---|
void |
build(CBuilder builder)
Builds the model-section from the set of OWL ontologies via
the standard sanctioning mechanism.
|
OBAnnotations |
getAnnotations()
Provides the object responsible for copying annotations from
OWL entities to generated frames-based entities.
|
OBConcepts |
getConcepts()
Provides the object that specifies the OWL classes that will
be used in generating frames in the FM.
|
OBEntityLabels |
getEntityLabels()
Provides the object responsible for providing the labels for
the frames-based entities that will be generated from named
OWL entities.
|
OModel |
getModel()
Provides the model over which the sanctioning is operating.
|
OBProperties |
getProperties()
Provides the object that specifies the OWL properties that
will be used in generating slots in the FM.
|
void |
setAxiomPurgePolicy(OBAxiomPurgePolicy axiomPurgePolicy)
Sets the axiom-purge policy, which determines which axioms, if
any, will be removed from the OWL model after the section has
been built and the reasoner loaded.
|
void |
setDefaultFrameSlotsPolicy(OBFrameSlotsPolicy value)
Sets the attribute that defines the default value for the
policy to be used when creating frame-valued slots.
|
void |
setDefaultSlotSources(OBSlotSources value)
Sets the attribute that defines the default value for the
types of constructs to be used in creating slots.
|
void |
setIMatcher(IMatcher iMatcher)
Enables the specification of an
IMatcher to be added
to the generated model. |
void |
setIReasoner(IReasoner iReasoner)
Enables the specification of an
IReasoner to be attached
to all generated frames. |
boolean |
supportsIncrementalBuild()
Specifies that incremental build is not supported.
|
public OBSectionBuilder(uk.ac.manchester.cs.mekon_util.config.KConfigNode parentConfigNode)
OModel
object over which
the sanctioning is to operate
ORClassifier
object to be attached
to all generated frames
parentConfigNode
- Parent of configuration node defining
appropriate configuration informationuk.ac.manchester.cs.mekon_util.KConfigException
- if required child-node does not exist
or does not contain correctly specified configuration
informationpublic OBSectionBuilder(OModel model, uk.ac.manchester.cs.mekon_util.config.KConfigNode parentConfigNode)
ORClassifier
object to be attached
to all generated frames
model
- Model over which sanctioning is to operateparentConfigNode
- Parent of configuration node defining
appropriate configuration informationuk.ac.manchester.cs.mekon_util.KConfigException
- if required child-node does not exist
or does not contain correctly specified configuration
informationpublic void setIReasoner(IReasoner iReasoner)
IReasoner
to be attached
to all generated frames.iReasoner
- Reasoner for generated framespublic void setIMatcher(IMatcher iMatcher)
IMatcher
to be added
to the generated model.iMatcher
- Matcher for generated framespublic void setDefaultSlotSources(OBSlotSources value)
OBSlotSources.ALL
if method is never invoked.value
- Required value of attributepublic void setDefaultFrameSlotsPolicy(OBFrameSlotsPolicy value)
OBFrameSlotsPolicy.IFRAME_VALUED_ONLY
if method is
never invoked.value
- Required value of attributepublic void setAxiomPurgePolicy(OBAxiomPurgePolicy axiomPurgePolicy)
OBAxiomPurgePolicy.RETAIN_ALL
if method is
never invoked.axiomPurgePolicy
- Required axiom-purge policypublic OModel getModel()
public OBConcepts getConcepts()
public OBProperties getProperties()
public OBEntityLabels getEntityLabels()
public OBAnnotations getAnnotations()
public boolean supportsIncrementalBuild()
supportsIncrementalBuild
in interface CSectionBuilder
public void build(CBuilder builder)
build
in interface CSectionBuilder
builder
- Builder for use in building model-section


--- layout: post title: "Linode Rocks!" date: 2011-05-18 03:13:28 +0000 permalink: /2011/05/18/linode-rocks/ category: Linux tags: - Linux - Linode - VPS - Debian - Ubuntu redirect_from: - /blog/linode-rocks/ ---
As you may know, my site is hosted by Linode, one of the older Linux VPS providers. I was excited when Linode announced native IPv6 support in some of their data centers, but then disappointed when I saw "No ETA" for the Atlanta datacenter where my site was hosted. I had been running my node with Hurricane Electric's IPv6 tunnel service, but I prefer a native solution when I can get it.
As a result, I decided to move my Linode to the New Jersey data center. At first, I contemplated just opening a ticket to get it moved, but I'd been wanting to do some "housekeeping" and had considered switching to pure Debian, so I decided to rebuild and migrate services. As of this morning, I had migrated most services (including web/database) to the new Linode in New Jersey. If it's at all possible, it seems even faster than my Atlanta Linode was. (Technically, it is: 2.5 GHz CPUs vs 2.0 GHz CPUs)
It required opening a ticket to get an IPv6 address assigned -- but the ticket was handled in less than one minute. At 11:00 PM Eastern time. I've known that Linode has great customer service, but this blew me away. Way to go, Linode!
(NB: If this entry helps inspire to join Linode, I'd appreciate you supporting my site and using my referral code of 680a893e24df3597d32f58cd41930e969027dc06).