Program Version:EnergyPlus, Version 9.1.0-fafb9d5652, YMD=2020.03.22 22:58
Tabular Output Report in Format: HTML
Building: 90.1-2004|SmallOffice
Environment: RUN PERIOD 1 ** Denver Centennial Golden Nr CO USA TMY3 WMO#=724666
Simulation Timestamp: 2020-03-22 22:58:43
Report: Annual Building Utility Performance Summary
For: Entire Facility
Timestamp: 2020-03-22 22:58:43
Values gathered over 24.00 hours| Total Energy [GJ] | Energy Per Total Building Area [MJ/m2] | Energy Per Conditioned Building Area [MJ/m2] | |
| Total Site Energy | 0.37 | 1.34 | 1.34 |
| Net Site Energy | 0.37 | 1.34 | 1.34 |
| Total Source Energy | 1.14 | 4.09 | 4.09 |
| Net Source Energy | 1.14 | 4.09 | 4.09 |
| Site=>Source Conversion Factor | |
| Electricity | 3.167 |
| Natural Gas | 1.084 |
| District Cooling | 1.056 |
| District Heating | 3.613 |
| Steam | 0.300 |
| Gasoline | 1.050 |
| Diesel | 1.050 |
| Coal | 1.050 |
| Fuel Oil #1 | 1.050 |
| Fuel Oil #2 | 1.050 |
| Propane | 1.050 |
| Other Fuel 1 | 1.000 |
| Other Fuel 2 | 1.000 |
| Area [m2] | |
| Total Building Area | 278.71 |
| Net Conditioned Building Area | 278.71 |
| Unconditioned Building Area | 0.00 |
| Electricity [GJ] | Natural Gas [GJ] | Additional Fuel [GJ] | District Cooling [GJ] | District Heating [GJ] | Water [m3] | |
| Heating | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | 0.02 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 0.13 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 0.04 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 0.10 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 0.06 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 0.02 | 0.00 | 0.00 | 0.00 | 0.05 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total End Uses | 0.35 | 0.02 | 0.00 | 0.00 | 0.00 | 0.05 |
| Subcategory | Electricity [GJ] | Natural Gas [GJ] | Additional Fuel [GJ] | District Cooling [GJ] | District Heating [GJ] | Water [m3] | |
| Heating | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Boiler Parasitic | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Cooling | General | 0.02 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | General | 0.13 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | Building Facades | 0.01 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Main Entries | 0.01 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Other Doors | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Parking Areas and Drives | 0.03 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Interior Equipment | General | 0.10 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | General | 0.06 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | General | 0.00 | 0.02 | 0.00 | 0.00 | 0.00 | 0.05 |
| Refrigeration | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Electricity Intensity [MJ/m2] | Natural Gas Intensity [MJ/m2] | Additional Fuel Intensity [MJ/m2] | District Cooling Intensity [MJ/m2] | District Heating Intensity [MJ/m2] | Water Intensity [m3/m2] | |
| Lighting | 0.63 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| HVAC | 0.28 | 0.07 | 0.00 | 0.00 | 0.00 | 0.00 |
| Other | 0.36 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total | 1.27 | 0.07 | 0.00 | 0.00 | 0.00 | 0.00 |
| Electricity Intensity [MJ/m2] | Natural Gas Intensity [MJ/m2] | Additional Fuel Intensity [MJ/m2] | District Cooling Intensity [MJ/m2] | District Heating Intensity [MJ/m2] | Water Intensity [m3/m2] | |
| Lighting | 0.63 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| HVAC | 0.28 | 0.07 | 0.00 | 0.00 | 0.00 | 0.00 |
| Other | 0.36 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total | 1.27 | 0.07 | 0.00 | 0.00 | 0.00 | 0.00 |
| Electricity [GJ] | Percent Electricity [%] | |
| Fuel-Fired Power Generation | 0.000 | 0.00 |
| High Temperature Geothermal* | 0.000 | 0.00 |
| Photovoltaic Power | 0.000 | 0.00 |
| Wind Power | 0.000 | 0.00 |
| Power Conversion | 0.000 | 0.00 |
| Net Decrease in On-Site Storage | 0.000 | 0.00 |
| Total On-Site Electric Sources | 0.000 | 0.00 |
| Electricity Coming From Utility | 0.354 | 100.00 |
| Surplus Electricity Going To Utility | 0.000 | 0.00 |
| Net Electricity From Utility | 0.354 | 100.00 |
| Total On-Site and Utility Electric Sources | 0.354 | 100.00 |
| Total Electricity End Uses | 0.354 | 100.00 |
| Heat [GJ] | Percent Heat [%] | |
| Water-Side Heat Recovery | 0.00 | |
| Air to Air Heat Recovery for Cooling | 0.00 | |
| Air to Air Heat Recovery for Heating | 0.00 | |
| High-Temperature Geothermal* | 0.00 | |
| Solar Water Thermal | 0.00 | |
| Solar Air Thermal | 0.00 | |
| Total On-Site Thermal Sources | 0.00 |
| Water [m3] | Percent Water [%] | |
| Rainwater Collection | 0.00 | 0.00 |
| Condensate Collection | 0.00 | 0.00 |
| Groundwater Well | 0.00 | 0.00 |
| Total On Site Water Sources | 0.00 | 0.00 |
| - | - | - |
| Initial Storage | 0.00 | 0.00 |
| Final Storage | 0.00 | 0.00 |
| Change in Storage | 0.00 | 0.00 |
| - | - | - |
| Water Supplied by Utility | 0.05 | 100.00 |
| - | - | - |
| Total On Site, Change in Storage, and Utility Water Sources | 0.05 | 100.00 |
| Total Water End Uses | 0.05 | 100.00 |
| Degrees [deltaC] | |
| Tolerance for Zone Heating Setpoint Not Met Time | 0.56 |
| Tolerance for Zone Cooling Setpoint Not Met Time | 0.56 |
| Facility [Hours] | |
| Time Setpoint Not Met During Occupied Heating | 0.00 |
| Time Setpoint Not Met During Occupied Cooling | 0.00 |
| Time Not Comfortable Based on Simple ASHRAE 55-2004 | 0.00 |
Table of Contents
TopBUILDING ENERGY PERFORMANCE - ELECTRICITY
| Meter |BUILDING ENERGY PERFORMANCE - NATURAL GAS
| Meter |BUILDING ENERGY PERFORMANCE - ELECTRICITY PEAK DEMAND
| Meter |BUILDING ENERGY PERFORMANCE - NATURAL GAS PEAK DEMAND
| Meter |Tariff Report
| ELECTRICITY TARIFF | GAS TARIFF | WATER TARIFF | DISTRICTHEATING TARIFF | DISTRICTCOOLING TARIFF |Economics Results Summary Report
| Entire Facility |Life-Cycle Cost Report
| Entire Facility |Report: Input Verification and Results Summary
For: Entire Facility
Timestamp: 2020-03-22 22:58:43
General| Value | |
| Program Version and Build | EnergyPlus, Version 9.1.0-fafb9d5652, YMD=2020.03.22 22:58 |
| RunPeriod | RUN PERIOD 1 |
| Weather File | Denver Centennial Golden Nr CO USA TMY3 WMO#=724666 |
| Latitude [deg] | 39.74 |
| Longitude [deg] | -105.2 |
| Elevation [m] | 1829.00 |
| Time Zone | -7.0 |
| North Axis Angle [deg] | 0.00 |
| Rotation for Appendix G [deg] | 0.00 |
| Hours Simulated [hrs] | 24.00 |
| Total | North (315 to 45 deg) | East (45 to 135 deg) | South (135 to 225 deg) | West (225 to 315 deg) | |
| Gross Wall Area [m2] | 207.74 | 62.32 | 41.55 | 62.32 | 41.55 |
| Above Ground Wall Area [m2] | 207.74 | 62.32 | 41.55 | 62.32 | 41.55 |
| Window Opening Area [m2] | 31.16 | 9.35 | 6.23 | 9.35 | 6.23 |
| Gross Window-Wall Ratio [%] | 15.00 | 15.00 | 15.00 | 15.00 | 15.00 |
| Above Ground Window-Wall Ratio [%] | 15.00 | 15.00 | 15.00 | 15.00 | 15.00 |
| Total | North (315 to 45 deg) | East (45 to 135 deg) | South (135 to 225 deg) | West (225 to 315 deg) | |
| Gross Wall Area [m2] | 207.74 | 62.32 | 41.55 | 62.32 | 41.55 |
| Above Ground Wall Area [m2] | 207.74 | 62.32 | 41.55 | 62.32 | 41.55 |
| Window Opening Area [m2] | 31.16 | 9.35 | 6.23 | 9.35 | 6.23 |
| Gross Window-Wall Ratio [%] | 15.00 | 15.00 | 15.00 | 15.00 | 15.00 |
| Above Ground Window-Wall Ratio [%] | 15.00 | 15.00 | 15.00 | 15.00 | 15.00 |
| Total | |
| Gross Roof Area [m2] | 278.71 |
| Skylight Area [m2] | 0.00 |
| Skylight-Roof Ratio [%] | 0.00 |
| Area [m2] | Conditioned (Y/N) | Part of Total Floor Area (Y/N) | Volume [m3] | Multipliers | Above Ground Gross Wall Area [m2] | Underground Gross Wall Area [m2] | Window Glass Area [m2] | Opening Area [m2] | Lighting [W/m2] | People [m2 per person] | Plug and Process [W/m2] | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND | 51.68 | Yes | Yes | 157.51 | 1.00 | 34.45 | 0.00 | 5.17 | 5.17 | 10.7639 | 16.59 | 6.7813 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND | 20.90 | Yes | Yes | 63.71 | 1.00 | 27.87 | 0.00 | 4.18 | 4.18 | 10.7639 | 16.59 | 6.7813 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND | 20.90 | Yes | Yes | 63.71 | 1.00 | 27.87 | 0.00 | 4.18 | 4.18 | 10.7639 | 16.59 | 6.7813 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND | 50.72 | Yes | Yes | 154.58 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 10.7639 | 16.59 | 6.7813 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND | 20.51 | Yes | Yes | 62.53 | 1.00 | 13.68 | 0.00 | 2.05 | 2.05 | 10.7639 | 16.59 | 6.7813 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND | 20.51 | Yes | Yes | 62.53 | 1.00 | 13.68 | 0.00 | 2.05 | 2.05 | 10.7639 | 16.59 | 6.7813 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND | 51.68 | Yes | Yes | 157.51 | 1.00 | 34.45 | 0.00 | 5.17 | 5.17 | 10.7639 | 16.59 | 6.7813 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND | 20.90 | Yes | Yes | 63.71 | 1.00 | 27.87 | 0.00 | 4.18 | 4.18 | 10.7639 | 16.59 | 6.7813 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND | 20.90 | Yes | Yes | 63.71 | 1.00 | 27.87 | 0.00 | 4.18 | 4.18 | 10.7639 | 16.59 | 6.7813 |
| Total | 278.71 | 849.51 | 207.74 | 0.00 | 31.16 | 31.16 | 10.7639 | 16.59 | 6.7813 | |||
| Conditioned Total | 278.71 | 849.51 | 207.74 | 0.00 | 31.16 | 31.16 | 10.7639 | 16.59 | 6.7813 | |||
| Unconditioned Total | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | ||||||
| Not Part of Total | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
Report: Demand End Use Components Summary
For: Entire Facility
Timestamp: 2020-03-22 22:58:43
End Uses| Electricity [W] | Natural Gas [W] | Propane [W] | District Cooling [W] | Steam [W] | Water [m3/s] | |
| Time of Peak | 01-JUN-13:00 | 01-JUN-16:00 | - | - | - | 01-JUN-11:00 |
| Heating | 0.00 | 180.58 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | 1622.18 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 2700.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 1890.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 1465.05 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 0.08 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 613.86 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total End Uses | 7677.31 | 794.45 | 0.00 | 0.00 | 0.00 | 0.00 |
| Subcategory | Electricity [W] | Natural Gas [W] | Propane [W] | District Cooling [W] | Steam [W] | Water [m3/s] | |
| Heating | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Boiler Parasitic | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Cooling | General | 1622.18 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | General | 2700.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | Building Facades | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Main Entries | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Other Doors | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Parking Areas and Drives | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Interior Equipment | General | 1890.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | General | 1465.05 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | General | 0.08 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | General | 0.00 | 613.86 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
Report: Source Energy End Use Components Summary
For: Entire Facility
Timestamp: 2020-03-22 22:58:43
Values gathered over 24.00 hours| Source Electricity [GJ] | Source Natural Gas [GJ] | Source Additional Fuel [GJ] | Source District Cooling [GJ] | Source District Heating [GJ] | |
| Heating | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | 0.06 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 0.42 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 0.14 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 0.32 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 0.18 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 0.02 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total Source Energy End Use Components | 1.12 | 0.02 | 0.00 | 0.00 | 0.00 |
| Source Electricity [MJ/m2] | Source Natural Gas [MJ/m2] | Source Additional Fuel [MJ/m2] | Source District Cooling [MJ/m2] | Source District Heating [MJ/m2] | |
| Heating | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | 0.23 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 1.51 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 0.49 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 1.13 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 0.66 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 0.07 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total Source Energy End Use Components | 4.02 | 0.07 | 0.00 | 0.00 | 0.00 |
| Source Electricity [MJ/m2] | Source Natural Gas [MJ/m2] | Source Additional Fuel [MJ/m2] | Source District Cooling [MJ/m2] | Source District Heating [MJ/m2] | |
| Heating | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | 0.23 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 1.51 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 0.49 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 1.13 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 0.66 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 0.07 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total Source Energy End Use Components | 4.02 | 0.07 | 0.00 | 0.00 | 0.00 |
Report: Component Sizing Summary
For: Entire Facility
Timestamp: 2020-03-22 22:58:43
AirTerminal:SingleDuct:ConstantVolume:NoReheat| Design Size Maximum Air Flow Rate [m3/s] | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC DIFFUSER | 0.221096 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC DIFFUSER | 0.138394 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC DIFFUSER | 0.120272 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC DIFFUSER | 0.145311 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC DIFFUSER | 0.116906 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC DIFFUSER | 0.099360 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC DIFFUSER | 0.180727 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC DIFFUSER | 0.130464 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC DIFFUSER | 0.109078 |
| Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | Sum of Air Terminal Maximum Flow Rates [m3/s] | Adjusted Heating Design Air Flow Rate [m3/s] | Adjusted Cooling Design Air Flow Rate [m3/s] | Adjusted Main Design Air Flow Rate [m3/s] | User Heating Air Flow Ratio [] | Calculated Heating Air Flow Ratio [] | Design Supply Air Flow Rate [m3/s] | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC | 0.000000 | 0.000000 | 0.221096 | 0.094748 | 0.221096 | 0.221096 | 1.00 | 0.428538 | 0.221096 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC | 0.000000 | 0.000000 | 0.138394 | 0.061631 | 0.138394 | 0.138394 | 1.00 | 0.445330 | 0.138394 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC | 0.000000 | 0.000000 | 0.120272 | 0.061729 | 0.120272 | 0.120272 | 1.00 | 0.513249 | 0.120272 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC | 0.000000 | 0.000000 | 0.145311 | 0.042271 | 0.145311 | 0.145311 | 1.00 | 0.290902 | 0.145311 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC | 0.000000 | 0.000000 | 0.116906 | 0.039480 | 0.116906 | 0.116906 | 1.00 | 0.337709 | 0.116906 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC | 0.000000 | 0.000000 | 0.099360 | 0.039578 | 0.099360 | 0.099360 | 1.00 | 0.398333 | 0.099360 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC | 0.000000 | 0.000000 | 0.180727 | 0.094220 | 0.180727 | 0.180727 | 1.00 | 0.521342 | 0.180727 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC | 0.000000 | 0.000000 | 0.130464 | 0.061595 | 0.130464 | 0.130464 | 1.00 | 0.472121 | 0.130464 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC | 0.000000 | 0.000000 | 0.109078 | 0.061694 | 0.109078 | 0.109078 | 1.00 | 0.565592 | 0.109078 |
| Maximum Outdoor Air Flow Rate [m3/s] | Minimum Outdoor Air Flow Rate [m3/s] | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC OA SYSTEM CONTROLLER | 0.221096 | 0.026251 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC OA SYSTEM CONTROLLER | 0.138394 | 0.010619 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC OA SYSTEM CONTROLLER | 0.120272 | 0.010619 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC OA SYSTEM CONTROLLER | 0.145311 | 0.025764 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC OA SYSTEM CONTROLLER | 0.116906 | 0.010422 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC OA SYSTEM CONTROLLER | 0.099360 | 0.010422 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC OA SYSTEM CONTROLLER | 0.180727 | 0.026251 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC OA SYSTEM CONTROLLER | 0.130464 | 0.010619 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC OA SYSTEM CONTROLLER | 0.109078 | 0.010619 |
| Design Size Rated Air Flow Rate [m3/s] | Design Size Gross Rated Total Cooling Capacity [W] | Design Size Gross Rated Sensible Heat Ratio | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 12KBTU/HR 9.7SEER | 0.221096 | 3659.92 | 0.800655 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 8KBTU/HR 9.7SEER | 0.138394 | 2290.90 | 0.800655 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 7KBTU/HR 9.7SEER | 0.120272 | 1990.92 | 0.800655 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 8KBTU/HR 9.7SEER | 0.145311 | 2405.42 | 0.800655 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 7KBTU/HR 9.7SEER | 0.116906 | 1935.22 | 0.800655 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 6KBTU/HR 9.7SEER | 0.099360 | 1644.76 | 0.800655 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 10KBTU/HR 9.7SEER | 0.180727 | 2991.67 | 0.800655 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 7KBTU/HR 9.7SEER | 0.130464 | 2159.64 | 0.800655 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 6KBTU/HR 9.7SEER | 0.109078 | 1805.63 | 0.800655 |
| Design Size Nominal Capacity [W] | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC GAS HTG COIL | 7211.04 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC GAS HTG COIL | 4289.02 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC GAS HTG COIL | 3781.20 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC GAS HTG COIL | 5068.28 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC GAS HTG COIL | 3679.01 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC GAS HTG COIL | 3187.36 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC GAS HTG COIL | 6079.90 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC GAS HTG COIL | 4066.81 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC GAS HTG COIL | 3467.53 |
| Design Size Nominal Capacity [W] | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | 7211.04 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | 4289.02 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | 3781.20 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | 5068.28 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | 3679.01 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | 3187.36 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | 6079.90 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | 4066.81 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | 3467.53 |
| Design Size Maximum Flow Rate [m3/s] | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC FAN | 0.221096 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC FAN | 0.138394 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC FAN | 0.120272 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC FAN | 0.145311 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC FAN | 0.116906 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC FAN | 0.099360 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC FAN | 0.180727 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC FAN | 0.130464 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC FAN | 0.109078 |
| Maximum Loop Flow Rate [m3/s] | Plant Loop Volume [m3] | |
| HOT WATER LOOP | 0.000000 | 0.000000 |
| OFFICE SHARED SERVICE WATER LOOP | 0.000002 | 0.000206 |
| Design Flow Rate [m3/s] | Design Power Consumption [W] | |
| HOT WATER LOOP PUMP | 0.000000 | 0.000000 |
| Design Size Nominal Capacity [W] | Design Size Design Water Flow Rate [m3/s] | |
| BOILER | 0.000000 | 0.000000 |
| Design Flow Rate [m3/s] | Design Power Consumption [W] | |
| OFFICE SHARED SERVICE WATER LOOP CIRCULATOR PUMP | 0.000002 | 0.079895 |
| Use Side Design Flow Rate [m3/s] | |
| 40GAL NATURALGAS WATER HEATER - 2KBTU/HR 0.82 THERM EFF | 0.000002 |
Report: Surface Shadowing Summary
For: Entire Facility
Timestamp: 2020-03-22 22:58:43
Surfaces (Walls, Roofs, etc) that may be Shadowed by Other Surfaces| None |
| Possible Shadow Receivers | |
| SURFACE 23 | SUB SURFACE 1 | |
| SURFACE 2 | SUB SURFACE 4 | |
| SURFACE 5 | SUB SURFACE 3 | |
| SURFACE 40 | SUB SURFACE 11 | |
| SURFACE 41 | SUB SURFACE 12 | |
| SURFACE 8 | SUB SURFACE 5 | |
| SURFACE 46 | SUB SURFACE 8 | |
| SURFACE 33 | SUB SURFACE 2 | |
| SURFACE 14 | SUB SURFACE 7 | |
| SURFACE 15 | SUB SURFACE 6 | |
| SURFACE 51 | SUB SURFACE 10 | |
| SURFACE 52 | SUB SURFACE 9 | |
Report: Adaptive Comfort Summary
For: Entire Facility
Timestamp: 2020-03-22 22:58:43
Time Not Meeting the Adaptive Comfort Models during Occupied Hours| ASHRAE55 90% Acceptability Limits [Hours] | ASHRAE55 80% Acceptability Limits [Hours] | CEN15251 Category I Acceptability Limits [Hours] | CEN15251 Category II Acceptability Limits [Hours] | CEN15251 Category III Acceptability Limits [Hours] |
Report: Initialization Summary
For: Entire Facility
Timestamp: 2020-03-22 22:58:43
Version| Version ID | |
| 1 | 9.1 |
| #TimeSteps | Minutes per TimeStep {minutes} | |
| 1 | 1 | 60 |
| Minimum System TimeStep {minutes} | Max HVAC Iterations | Minimum Plant Iterations | Maximum Plant Iterations | |
| 1 | 1 | 20 | 2 | 8 |
| Do Zone Sizing | Do System Sizing | Do Plant Sizing | Do Design Days | Do Weather Simulation | Do HVAC Sizing Simulation | |
| 1 | Yes | Yes | Yes | No | Yes | No |
| Tolerance for Time Heating Setpoint Not Met | Tolerance for Zone Cooling Setpoint Not Met Time | |
| 1 | 0.556 | 0.556 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | 19.53 | 19.50 | 19.54 | 19.60 | 20.00 | 21.64 | 22.23 | 22.38 | 21.45 | 20.12 | 19.80 | 19.63 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | -0.60 | 1.34 | 5.12 | 8.69 | 15.46 | 19.02 | 20.00 | 18.20 | 14.02 | 8.83 | 3.71 | 0.32 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 |
| Jan{dimensionless} | Feb{dimensionless} | Mar{dimensionless} | Apr{dimensionless} | May{dimensionless} | Jun{dimensionless} | Jul{dimensionless} | Aug{dimensionless} | Sep{dimensionless} | Oct{dimensionless} | Nov{dimensionless} | Dec{dimensionless} | |
| 1 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 |
| Normal | Daylighting {dimensionless} | |
| 1 | 1.000 | 1.000 |
| Jan{dimensionless} | Feb{dimensionless} | Mar{dimensionless} | Apr{dimensionless} | May{dimensionless} | Jun{dimensionless} | Jul{dimensionless} | Aug{dimensionless} | Sep{dimensionless} | Oct{dimensionless} | Nov{dimensionless} | Dec{dimensionless} | |
| 1 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 |
| Jan{dimensionless} | Feb{dimensionless} | Mar{dimensionless} | Apr{dimensionless} | May{dimensionless} | Jun{dimensionless} | Jul{dimensionless} | Aug{dimensionless} | Sep{dimensionless} | Oct{dimensionless} | Nov{dimensionless} | Dec{dimensionless} | |
| 1 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 |
| Wind Sensor Height Above Ground {m} | Wind Speed Profile Exponent {} | Wind Speed Profile Boundary Layer Thickness {m} | Air Temperature Sensor Height Above Ground {m} | Wind Speed Modifier Coefficient-Internal | Temperature Modifier Coefficient-Internal | |
| 1 | 10.000 | 0.140 | 270.000 | 1.500 | 1.586 | 9.750E-003 |
| Location Name | Latitude {N+/S- Deg} | Longitude {E+/W- Deg} | Time Zone Number {GMT+/-} | Elevation {m} | Standard Pressure at Elevation {Pa} | Standard RhoAir at Elevation | |
| 1 | Denver Centennial Golden Nr CO USA TMY3 WMO#=724666 | 39.74 | -105.18 | -7.00 | 1829.00 | 81198 | 0.9651 |
| Calculation Method{} | Water Mains Temperature Schedule Name{} | Annual Average Outdoor Air Temperature{C} | Maximum Difference In Monthly Average Outdoor Air Temperatures{deltaC} | Fixed Default Water Mains Temperature{C} | |
| 1 | Correlation | NA | 9.70 | 22.80 | NA |
| Building Name | North Axis {deg} | Terrain | Loads Convergence Tolerance Value | Temperature Convergence Tolerance Value | Solar Distribution | Maximum Number of Warmup Days | Minimum Number of Warmup Days | |
| 1 | 90.1-2004|SmallOffice | 0.000 | City | 4.00000E-002 | 0.40000 | FullExterior | 25 | 6 |
| Algorithm {Simple TARP CeilingDiffuser AdaptiveConvectionAlgorithm} |
|
| 1 | TARP |
| Algorithm {SimpleCombined TARP MoWitt DOE-2 AdaptiveConvectionAlgorithm} |
|
| 1 | DOE-2 |
| Value {Anisotropic} | |
| 1 | Anisotropic |
| Value {ThirdOrderBackwardDifference AnalyticalSolution EulerMethod} |
|
| 1 | ThirdOrderBackwardDifference |
| Simulation {Yes/No} | Carbon Dioxide Concentration | |
| 1 | No | N/A |
| Simulation {Yes/No} | Generic Contaminant Concentration | |
| 1 | No | N/A |
| Enforce Mass Balance |
Adjust Zone Mixing |
Adjust Zone Infiltration {AddInfiltration AdjustInfiltration None} |
Infiltration Zones {MixingSourceZonesOnly AllZones} |
|
| 1 | No | N/A | N/A | N/A |
| Value {RegulaFalsi Bisection BisectionThenRegulaFalsi RegulaFalsiThenBisection} |
|
| 1 | RegulaFalsi |
| Wind Speed Profile Exponent {} | Wind Speed Profile Boundary Layer Thickness {m} | Air Temperature Gradient Coefficient {K/m} | |
| 1 | 0.330 | 460.000 | 6.500000E-003 |
| Starting Corner | Vertex Input Direction | Coordinate System | Daylight Reference Point Coordinate System | Rectangular (Simple) Surface Coordinate System | |
| 1 | UpperLeftCorner | Counterclockwise | RelativeCoordinateSystem | RelativeCoordinateSystem | RelativeToZoneOrigin |
| Value {CTF - ConductionTransferFunction EMPD - MoisturePenetrationDepthConductionTransferFunction CondFD - ConductionFiniteDifference HAMT - CombinedHeatAndMoistureFiniteElement} - Description |
Inside Surface Max Temperature Limit{C} |
Surface Convection Coefficient Lower Limit {W/m2-K} |
Surface Convection Coefficient Upper Limit {W/m2-K} |
|
| 1 | CTF - ConductionTransferFunction | 200 | 0.10 | 1000.0 |
| Number of Fixed Detached Shades | Number of Building Detached Shades | Number of Attached Shades | |
| 1 | 0 | 0 | 0 |
| Number of Zones | Number of Zone Surfaces | Number of SubSurfaces | |
| 1 | 9 | 75 | 12 |
| Zone Name | North Axis {deg} | Origin X-Coordinate {m} | Origin Y-Coordinate {m} | Origin Z-Coordinate {m} | Centroid X-Coordinate {m} | Centroid Y-Coordinate {m} | Centroid Z-Coordinate {m} | Type | Zone Multiplier | Zone List Multiplier | Minimum X {m} | Maximum X {m} | Minimum Y {m} | Maximum Y {m} | Minimum Z {m} | Maximum Z {m} | Ceiling Height {m} | Volume {m3} | Zone Inside Convection Algorithm {Simple-Detailed-CeilingDiffuser-TrombeWall} | Zone Outside Convection Algorithm {Simple-Detailed-Tarp-MoWitt-DOE-2-BLAST} | Floor Area {m2} | Exterior Gross Wall Area {m2} | Exterior Net Wall Area {m2} | Exterior Window Area {m2} | Number of Surfaces | Number of SubSurfaces | Number of Shading SubSurfaces | Part of Total Building Area | |
| 1 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND | 0.0 | -5.65 | -6.82 | 0.00 | 9.85E-015 | -4.53 | 1.52 | 1 | 1 | 1 | -5.65 | 5.65 | -6.82 | -2.24 | 0.00 | 3.05 | 3.05 | 157.51 | TARP | DOE-2 | 51.68 | 34.45 | 29.28 | 5.17 | 6 | 1 | 0 | Yes |
| 2 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND | 0.0 | -10.22 | -6.82 | 0.00 | -7.94 | -4.53 | 1.52 | 1 | 1 | 1 | -10.22 | -5.65 | -6.82 | -2.24 | 0.00 | 3.05 | 3.05 | 63.71 | TARP | DOE-2 | 20.90 | 27.87 | 23.69 | 4.18 | 6 | 2 | 0 | Yes |
| 3 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND | 0.0 | 5.65 | -6.82 | 0.00 | 7.94 | -4.53 | 1.52 | 1 | 1 | 1 | 5.65 | 10.22 | -6.82 | -2.24 | 0.00 | 3.05 | 3.05 | 63.71 | TARP | DOE-2 | 20.90 | 27.87 | 23.69 | 4.18 | 6 | 2 | 0 | Yes |
| 4 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND | 0.0 | -5.65 | -2.24 | 0.00 | 9.81E-015 | -3.58E-016 | 1.52 | 1 | 1 | 1 | -5.65 | 5.65 | -2.24 | 2.24 | 0.00 | 3.05 | 3.05 | 154.58 | TARP | DOE-2 | 50.72 | 0.00 | 0.00 | 0.00 | 6 | 0 | 0 | Yes |
| 5 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND | 0.0 | -10.22 | -2.24 | 0.00 | -7.94 | -2.91E-016 | 1.52 | 1 | 1 | 1 | -10.22 | -5.65 | -2.24 | 2.24 | 0.00 | 3.05 | 3.05 | 62.53 | TARP | DOE-2 | 20.51 | 13.68 | 11.63 | 2.05 | 6 | 1 | 0 | Yes |
| 6 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND | 0.0 | 5.65 | -2.24 | 0.00 | 7.94 | -2.79E-016 | 1.52 | 1 | 1 | 1 | 5.65 | 10.22 | -2.24 | 2.24 | 0.00 | 3.05 | 3.05 | 62.53 | TARP | DOE-2 | 20.51 | 13.68 | 11.63 | 2.05 | 6 | 1 | 0 | Yes |
| 7 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND | 0.0 | -5.65 | 2.24 | 0.00 | 9.91E-015 | 4.53 | 1.52 | 1 | 1 | 1 | -5.65 | 5.65 | 2.24 | 6.82 | 0.00 | 3.05 | 3.05 | 157.51 | TARP | DOE-2 | 51.68 | 34.45 | 29.28 | 5.17 | 6 | 1 | 0 | Yes |
| 8 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND | 0.0 | -10.22 | 2.24 | 0.00 | -7.94 | 4.53 | 1.52 | 1 | 1 | 1 | -10.22 | -5.65 | 2.24 | 6.82 | 0.00 | 3.05 | 3.05 | 63.71 | TARP | DOE-2 | 20.90 | 27.87 | 23.69 | 4.18 | 6 | 2 | 0 | Yes |
| 9 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND | 0.0 | 5.65 | 2.24 | 0.00 | 7.94 | 4.53 | 1.52 | 1 | 1 | 1 | 5.65 | 10.22 | 2.24 | 6.82 | 0.00 | 3.05 | 3.05 | 63.71 | TARP | DOE-2 | 20.90 | 27.87 | 23.69 | 4.18 | 6 | 2 | 0 | Yes |
| Zone Name | Floor Area {m2} | # Occupants | Area per Occupant {m2/person} | Occupant per Area {person/m2} | Interior Lighting {W/m2} | Electric Load {W/m2} | Gas Load {W/m2} | Other Load {W/m2} | Hot Water Eq {W/m2} | Steam Equipment {W/m2} | Sum Loads per Area {W/m2} | Outdoor Controlled Baseboard Heat | |
| 1 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND | 51.68 | 3.1 | 16.590 | 6.028E-002 | 10.764 | 6.781 | 0.000 | 0.000 | 0.000 | 0.000 | 17.545 | No |
| 2 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND | 20.90 | 1.3 | 16.590 | 6.028E-002 | 10.764 | 6.781 | 0.000 | 0.000 | 0.000 | 0.000 | 17.545 | No |
| 3 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND | 20.90 | 1.3 | 16.590 | 6.028E-002 | 10.764 | 6.781 | 0.000 | 0.000 | 0.000 | 0.000 | 17.545 | No |
| 4 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND | 50.72 | 3.1 | 16.590 | 6.028E-002 | 10.764 | 6.781 | 0.000 | 0.000 | 0.000 | 0.000 | 17.545 | No |
| 5 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND | 20.51 | 1.2 | 16.590 | 6.028E-002 | 10.764 | 6.781 | 0.000 | 0.000 | 0.000 | 0.000 | 17.545 | No |
| 6 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND | 20.51 | 1.2 | 16.590 | 6.028E-002 | 10.764 | 6.781 | 0.000 | 0.000 | 0.000 | 0.000 | 17.545 | No |
| 7 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND | 51.68 | 3.1 | 16.590 | 6.028E-002 | 10.764 | 6.781 | 0.000 | 0.000 | 0.000 | 0.000 | 17.545 | No |
| 8 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND | 20.90 | 1.3 | 16.590 | 6.028E-002 | 10.764 | 6.781 | 0.000 | 0.000 | 0.000 | 0.000 | 17.545 | No |
| 9 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND | 20.90 | 1.3 | 16.590 | 6.028E-002 | 10.764 | 6.781 | 0.000 | 0.000 | 0.000 | 0.000 | 17.545 | No |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Number of People {} | People/Floor Area {person/m2} | Floor Area per person {m2/person} | Fraction Radiant | Fraction Convected | Sensible Fraction Calculation | Activity level | ASHRAE 55 Warnings | Carbon Dioxide Generation Rate | Nominal Minimum Number of People | Nominal Maximum Number of People | MRT Calculation Type | Work Efficiency | Clothing Insulation Calculation Method | Clothing Insulation Calculation Method Schedule | Clothing | Air Velocity | Fanger Calculation | Pierce Calculation | KSU Calculation | |
| 1 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND OFFICE WHOLEBUILDING - SM OFFICE PEOPLE | OFFICESMALL BLDG_OCC_SCH | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND | 51.68 | 3.1 | 3.1 | 6.028E-002 | 16.590 | 0.300 | 0.700 | AutoCalculate | OFFICESMALL ACTIVITY_SCH | Yes | 3.8200E-008 | 0 | 3 | Zone Averaged | WORK EFFICIENCY SCHEDULE | Clothing Insulation Schedule | N/A | CLOTHING SCHEDULE | AIR VELOCITY SCHEDULE | Yes | No | No |
| 2 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND OFFICE WHOLEBUILDING - SM OFFICE PEOPLE | OFFICESMALL BLDG_OCC_SCH | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND | 20.90 | 1.3 | 1.3 | 6.028E-002 | 16.590 | 0.300 | 0.700 | AutoCalculate | OFFICESMALL ACTIVITY_SCH | Yes | 3.8200E-008 | 0 | 1 | Zone Averaged | WORK EFFICIENCY SCHEDULE | Clothing Insulation Schedule | N/A | CLOTHING SCHEDULE | AIR VELOCITY SCHEDULE | Yes | No | No |
| 3 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND OFFICE WHOLEBUILDING - SM OFFICE PEOPLE | OFFICESMALL BLDG_OCC_SCH | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND | 20.90 | 1.3 | 1.3 | 6.028E-002 | 16.590 | 0.300 | 0.700 | AutoCalculate | OFFICESMALL ACTIVITY_SCH | Yes | 3.8200E-008 | 0 | 1 | Zone Averaged | WORK EFFICIENCY SCHEDULE | Clothing Insulation Schedule | N/A | CLOTHING SCHEDULE | AIR VELOCITY SCHEDULE | Yes | No | No |
| 4 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND OFFICE WHOLEBUILDING - SM OFFICE PEOPLE | OFFICESMALL BLDG_OCC_SCH | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND | 50.72 | 3.1 | 3.1 | 6.028E-002 | 16.590 | 0.300 | 0.700 | AutoCalculate | OFFICESMALL ACTIVITY_SCH | Yes | 3.8200E-008 | 0 | 3 | Zone Averaged | WORK EFFICIENCY SCHEDULE | Clothing Insulation Schedule | N/A | CLOTHING SCHEDULE | AIR VELOCITY SCHEDULE | Yes | No | No |
| 5 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND OFFICE WHOLEBUILDING - SM OFFICE PEOPLE | OFFICESMALL BLDG_OCC_SCH | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND | 20.51 | 1.2 | 1.2 | 6.028E-002 | 16.590 | 0.300 | 0.700 | AutoCalculate | OFFICESMALL ACTIVITY_SCH | Yes | 3.8200E-008 | 0 | 1 | Zone Averaged | WORK EFFICIENCY SCHEDULE | Clothing Insulation Schedule | N/A | CLOTHING SCHEDULE | AIR VELOCITY SCHEDULE | Yes | No | No |
| 6 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND OFFICE WHOLEBUILDING - SM OFFICE PEOPLE | OFFICESMALL BLDG_OCC_SCH | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND | 20.51 | 1.2 | 1.2 | 6.028E-002 | 16.590 | 0.300 | 0.700 | AutoCalculate | OFFICESMALL ACTIVITY_SCH | Yes | 3.8200E-008 | 0 | 1 | Zone Averaged | WORK EFFICIENCY SCHEDULE | Clothing Insulation Schedule | N/A | CLOTHING SCHEDULE | AIR VELOCITY SCHEDULE | Yes | No | No |
| 7 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND OFFICE WHOLEBUILDING - SM OFFICE PEOPLE | OFFICESMALL BLDG_OCC_SCH | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND | 51.68 | 3.1 | 3.1 | 6.028E-002 | 16.590 | 0.300 | 0.700 | AutoCalculate | OFFICESMALL ACTIVITY_SCH | Yes | 3.8200E-008 | 0 | 3 | Zone Averaged | WORK EFFICIENCY SCHEDULE | Clothing Insulation Schedule | N/A | CLOTHING SCHEDULE | AIR VELOCITY SCHEDULE | Yes | No | No |
| 8 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND OFFICE WHOLEBUILDING - SM OFFICE PEOPLE | OFFICESMALL BLDG_OCC_SCH | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND | 20.90 | 1.3 | 1.3 | 6.028E-002 | 16.590 | 0.300 | 0.700 | AutoCalculate | OFFICESMALL ACTIVITY_SCH | Yes | 3.8200E-008 | 0 | 1 | Zone Averaged | WORK EFFICIENCY SCHEDULE | Clothing Insulation Schedule | N/A | CLOTHING SCHEDULE | AIR VELOCITY SCHEDULE | Yes | No | No |
| 9 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND OFFICE WHOLEBUILDING - SM OFFICE PEOPLE | OFFICESMALL BLDG_OCC_SCH | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND | 20.90 | 1.3 | 1.3 | 6.028E-002 | 16.590 | 0.300 | 0.700 | AutoCalculate | OFFICESMALL ACTIVITY_SCH | Yes | 3.8200E-008 | 0 | 1 | Zone Averaged | WORK EFFICIENCY SCHEDULE | Clothing Insulation Schedule | N/A | CLOTHING SCHEDULE | AIR VELOCITY SCHEDULE | Yes | No | No |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Lighting Level {W} | Lights/Floor Area {W/m2} | Lights per person {W/person} | Fraction Return Air | Fraction Radiant | Fraction Short Wave | Fraction Convected | Fraction Replaceable | End-Use Category | Nominal Minimum Lighting Level {W} | Nominal Maximum Lighting Level {W} | |
| 1 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND OFFICE WHOLEBUILDING - SM OFFICE LIGHTS | OFFICESMALL BLDG_LIGHT_SCH | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND | 51.68 | 3.1 | 556.231 | 10.764 | 178.571 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 556.231 |
| 2 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND OFFICE WHOLEBUILDING - SM OFFICE LIGHTS | OFFICESMALL BLDG_LIGHT_SCH | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND | 20.90 | 1.3 | 225.000 | 10.764 | 178.571 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 225.000 |
| 3 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND OFFICE WHOLEBUILDING - SM OFFICE LIGHTS | OFFICESMALL BLDG_LIGHT_SCH | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND | 20.90 | 1.3 | 225.000 | 10.764 | 178.571 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 225.000 |
| 4 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND OFFICE WHOLEBUILDING - SM OFFICE LIGHTS | OFFICESMALL BLDG_LIGHT_SCH | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND | 50.72 | 3.1 | 545.898 | 10.764 | 178.571 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 545.898 |
| 5 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND OFFICE WHOLEBUILDING - SM OFFICE LIGHTS | OFFICESMALL BLDG_LIGHT_SCH | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND | 20.51 | 1.2 | 220.820 | 10.764 | 178.571 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 220.820 |
| 6 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND OFFICE WHOLEBUILDING - SM OFFICE LIGHTS | OFFICESMALL BLDG_LIGHT_SCH | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND | 20.51 | 1.2 | 220.820 | 10.764 | 178.571 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 220.820 |
| 7 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND OFFICE WHOLEBUILDING - SM OFFICE LIGHTS | OFFICESMALL BLDG_LIGHT_SCH | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND | 51.68 | 3.1 | 556.231 | 10.764 | 178.571 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 556.231 |
| 8 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND OFFICE WHOLEBUILDING - SM OFFICE LIGHTS | OFFICESMALL BLDG_LIGHT_SCH | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND | 20.90 | 1.3 | 225.000 | 10.764 | 178.571 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 225.000 |
| 9 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND OFFICE WHOLEBUILDING - SM OFFICE LIGHTS | OFFICESMALL BLDG_LIGHT_SCH | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND | 20.90 | 1.3 | 225.000 | 10.764 | 178.571 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 225.000 |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Equipment Level {W} | Equipment/Floor Area {W/m2} | Equipment per person {W/person} | Fraction Latent | Fraction Radiant | Fraction Lost | Fraction Convected | End-Use SubCategory | Nominal Minimum Equipment Level {W} | Nominal Maximum Equipment Level {W} | |
| 1 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND OFFICE WHOLEBUILDING - SM OFFICE ELEC EQUIP | OFFICESMALL BLDG_EQUIP_SCH | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND | 51.68 | 3.1 | 350.425 | 6.781 | 112.500 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 350.425 |
| 2 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND OFFICE WHOLEBUILDING - SM OFFICE ELEC EQUIP | OFFICESMALL BLDG_EQUIP_SCH | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND | 20.90 | 1.3 | 141.750 | 6.781 | 112.500 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 141.750 |
| 3 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND OFFICE WHOLEBUILDING - SM OFFICE ELEC EQUIP | OFFICESMALL BLDG_EQUIP_SCH | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND | 20.90 | 1.3 | 141.750 | 6.781 | 112.500 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 141.750 |
| 4 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND OFFICE WHOLEBUILDING - SM OFFICE ELEC EQUIP | OFFICESMALL BLDG_EQUIP_SCH | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND | 50.72 | 3.1 | 343.916 | 6.781 | 112.500 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 343.916 |
| 5 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND OFFICE WHOLEBUILDING - SM OFFICE ELEC EQUIP | OFFICESMALL BLDG_EQUIP_SCH | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND | 20.51 | 1.2 | 139.117 | 6.781 | 112.500 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 139.117 |
| 6 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND OFFICE WHOLEBUILDING - SM OFFICE ELEC EQUIP | OFFICESMALL BLDG_EQUIP_SCH | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND | 20.51 | 1.2 | 139.117 | 6.781 | 112.500 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 139.117 |
| 7 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND OFFICE WHOLEBUILDING - SM OFFICE ELEC EQUIP | OFFICESMALL BLDG_EQUIP_SCH | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND | 51.68 | 3.1 | 350.425 | 6.781 | 112.500 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 350.425 |
| 8 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND OFFICE WHOLEBUILDING - SM OFFICE ELEC EQUIP | OFFICESMALL BLDG_EQUIP_SCH | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND | 20.90 | 1.3 | 141.750 | 6.781 | 112.500 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 141.750 |
| 9 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND OFFICE WHOLEBUILDING - SM OFFICE ELEC EQUIP | OFFICESMALL BLDG_EQUIP_SCH | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND | 20.90 | 1.3 | 141.750 | 6.781 | 112.500 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 141.750 |
| Calculation Method | Value {days} | Allowable Number Figures in Shadow Overlap {} | Polygon Clipping Algorithm | Sky Diffuse Modeling Algorithm | External Shading Calculation Method | Output External Shading Calculation Results | Disable Self-Shading Within Shading Zone Groups | Disable Self-Shading From Shading Zone Groups to Other Zones | |
| 1 | AverageOverDaysInFrequency | 20 | 15000 | SutherlandHodgman | SimpleSkyDiffuseModeling | InternalCalculation | No | No | No |
| Type | Name | Volume {m3} | Maximum Capacity {W} | Standard Rated Recovery Efficiency | Standard Rated Energy Factor | |
| 1 | WaterHeater:Mixed | 40GAL NATURALGAS WATER HEATER - 2KBTU/HR 0.82 THERM EFF | 0.1514 | 503.3 | 0.220 | 1.3213 |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Design Volume Flow Rate {m3/s} | Volume Flow Rate/Floor Area {m3/s-m2} | Volume Flow Rate/Exterior Surface Area {m3/s-m2} | ACH - Air Changes per Hour | Equation A - Constant Term Coefficient {} | Equation B - Temperature Term Coefficient {1/C} | Equation C - Velocity Term Coefficient {s/m} | Equation D - Velocity Squared Term Coefficient {s2/m2} | |
| 1 | OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND INFILTRATION | ALWAYS ON DISCRETE | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND | 51.68 | 3.1 | 3.532E-002 | 6.835E-004 | 4.101E-004 | 0.807 | 0.000 | 0.000 | 0.224 | 0.000 |
| 2 | OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND INFILTRATION | ALWAYS ON DISCRETE | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND | 20.90 | 1.3 | 2.857E-002 | 1.367E-003 | 5.858E-004 | 1.615 | 0.000 | 0.000 | 0.224 | 0.000 |
| 3 | OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND INFILTRATION | ALWAYS ON DISCRETE | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND | 20.90 | 1.3 | 2.857E-002 | 1.367E-003 | 5.858E-004 | 1.615 | 0.000 | 0.000 | 0.224 | 0.000 |
| 4 | OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND INFILTRATION | ALWAYS ON DISCRETE | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND | 20.51 | 1.2 | 1.402E-002 | 6.835E-004 | 4.101E-004 | 0.807 | 0.000 | 0.000 | 0.224 | 0.000 |
| 5 | OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND INFILTRATION | ALWAYS ON DISCRETE | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND | 20.51 | 1.2 | 1.402E-002 | 6.835E-004 | 4.101E-004 | 0.807 | 0.000 | 0.000 | 0.224 | 0.000 |
| 6 | OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND INFILTRATION | ALWAYS ON DISCRETE | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND | 51.68 | 3.1 | 3.532E-002 | 6.835E-004 | 4.101E-004 | 0.807 | 0.000 | 0.000 | 0.224 | 0.000 |
| 7 | OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND INFILTRATION | ALWAYS ON DISCRETE | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND | 20.90 | 1.3 | 2.857E-002 | 1.367E-003 | 5.858E-004 | 1.615 | 0.000 | 0.000 | 0.224 | 0.000 |
| 8 | OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND INFILTRATION | ALWAYS ON DISCRETE | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND | 20.90 | 1.3 | 2.857E-002 | 1.367E-003 | 5.858E-004 | 1.615 | 0.000 | 0.000 | 0.224 | 0.000 |
| Simple | |
| 1 | Simple |
| Zone Name | Mixing/Mundt/UCSDDV/UCSDCV/UCSDUFI/UCSDUFE/User Defined | |
| 1 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND | Mixing/Well-Stirred |
| 2 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND | Mixing/Well-Stirred |
| 3 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND | Mixing/Well-Stirred |
| 4 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND | Mixing/Well-Stirred |
| 5 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND | Mixing/Well-Stirred |
| 6 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND | Mixing/Well-Stirred |
| 7 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND | Mixing/Well-Stirred |
| 8 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND | Mixing/Well-Stirred |
| 9 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND | Mixing/Well-Stirred |
| No Multizone or Distribution/Multizone with Distribution/Multizone without Distribution/Multizone with Distribution only during Fan Operation | |
| 1 | NoMultizoneOrDistribution |
| Sensible Heat Capacity Multiplier | Moisture Capacity Multiplier | Carbon Dioxide Capacity Multiplier | Generic Contaminant Capacity Multiplier | |
| 1 | 1.000 | 1.000 | 1.000 | 1.000 |
| Value | |
| 1 | 1 |
| Sizing Factor ID | Value | |
| 1 | Global | 1.2500 |
| 2 | Zone ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND | 1.2500 |
| 3 | Zone ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND | 1.2500 |
| 4 | Zone ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND | 1.2500 |
| 5 | Zone ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND | 1.2500 |
| 6 | Zone ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND | 1.2500 |
| 7 | Zone ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND | 1.2500 |
| 8 | Zone ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND | 1.2500 |
| 9 | Zone ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND | 1.2500 |
| 10 | Zone ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND | 1.2500 |
| Sizing Factor ID | Value | |
| 1 | Global | 1.1500 |
| 2 | Zone ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND | 1.1500 |
| 3 | Zone ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND | 1.1500 |
| 4 | Zone ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND | 1.1500 |
| 5 | Zone ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND | 1.1500 |
| 6 | Zone ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND | 1.1500 |
| 7 | Zone ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND | 1.1500 |
| 8 | Zone ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND | 1.1500 |
| 9 | Zone ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND | 1.1500 |
| 10 | Zone ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND | 1.1500 |
| Zone Name | Load Type | Calc Des Load {W} | User Des Load {W} | Calc Des Air Flow Rate {m3/s} | User Des Air Flow Rate {m3/s} | Design Day Name | Date/Time of Peak | Temperature at Peak {C} | Humidity Ratio at Peak {kgWater/kgDryAir} | Floor Area {m2} | # Occupants | Calc Outdoor Air Flow Rate {m3/s} | Calc DOAS Heat Addition Rate {W} | |
| 1 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND | Cooling | 2104.03741 | 2419.64303 | 0.19226 | 0.22110 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 14:00:00 | 33.00000 | 6.86230E-003 | 51.67551 | 3.11489 | 2.62512E-002 | 0.00000 |
| 2 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND | Heating | 2155.26989 | 2694.08736 | 7.57983E-002 | 9.47479E-002 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | -18.80000 | 8.88305E-004 | 51.67551 | 3.11489 | 2.62512E-002 | 0.00000 |
| 3 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND | Cooling | 1317.09764 | 1514.66228 | 0.12034 | 0.13839 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 16:00:00 | 32.08800 | 6.86229E-003 | 20.90318 | 1.26000 | 1.06188E-002 | 0.00000 |
| 4 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND | Heating | 1402.04603 | 1752.55754 | 4.93046E-002 | 6.16308E-002 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | -18.80000 | 8.88305E-004 | 20.90318 | 1.26000 | 1.06188E-002 | 0.00000 |
| 5 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND | Cooling | 1144.62510 | 1316.31886 | 0.10458 | 0.12027 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 11:00:00 | 29.50400 | 6.86230E-003 | 20.90318 | 1.26000 | 1.06188E-002 | 0.00000 |
| 6 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND | Heating | 1404.28574 | 1755.35717 | 4.93834E-002 | 6.17292E-002 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | -18.80000 | 8.88305E-004 | 20.90318 | 1.26000 | 1.06188E-002 | 0.00000 |
| 7 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND | Cooling | 1382.73968 | 1590.15064 | 0.12636 | 0.14531 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 14:00:00 | 33.00000 | 6.86230E-003 | 50.71559 | 3.05703 | 2.57635E-002 | 0.00000 |
| 8 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND | Heating | 961.44569 | 1201.80711 | 3.38171E-002 | 4.22713E-002 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | -18.80000 | 8.88305E-004 | 50.71559 | 3.05703 | 2.57635E-002 | 0.00000 |
| 9 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND | Cooling | 1112.55041 | 1279.43297 | 0.10166 | 0.11691 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 17:00:00 | 30.87200 | 6.86230E-003 | 20.51489 | 1.23659 | 1.04216E-002 | 0.00000 |
| 10 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND | Heating | 898.06496 | 1122.58120 | 3.15843E-002 | 3.94803E-002 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | -18.80000 | 8.88305E-004 | 20.51489 | 1.23659 | 1.04216E-002 | 0.00000 |
| 11 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND | Cooling | 945.54109 | 1087.37226 | 8.64000E-002 | 9.93600E-002 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 10:00:00 | 27.22400 | 6.86230E-003 | 20.51489 | 1.23659 | 1.04216E-002 | 0.00000 |
| 12 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND | Heating | 900.29590 | 1125.36988 | 3.16627E-002 | 3.95784E-002 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | -18.80000 | 8.88305E-004 | 20.51489 | 1.23659 | 1.04216E-002 | 0.00000 |
| 13 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND | Cooling | 1719.86458 | 1977.84426 | 0.15715 | 0.18073 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 14:00:00 | 33.00000 | 6.86230E-003 | 51.67551 | 3.11489 | 2.62512E-002 | 0.00000 |
| 14 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND | Heating | 2143.27045 | 2679.08806 | 7.53763E-002 | 9.42204E-002 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | -18.80000 | 8.88305E-004 | 51.67551 | 3.11489 | 2.62512E-002 | 0.00000 |
| 15 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND | Cooling | 1241.63003 | 1427.87453 | 0.11345 | 0.13046 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 17:00:00 | 30.87200 | 6.86230E-003 | 20.90318 | 1.26000 | 1.06188E-002 | 0.00000 |
| 16 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND | Heating | 1401.22599 | 1751.53249 | 4.92758E-002 | 6.15947E-002 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | -18.80000 | 8.88305E-004 | 20.90318 | 1.26000 | 1.06188E-002 | 0.00000 |
| 17 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND | Cooling | 1038.08279 | 1193.79521 | 9.48503E-002 | 0.10908 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 10:00:00 | 27.22400 | 6.86230E-003 | 20.90318 | 1.26000 | 1.06188E-002 | 0.00000 |
| 18 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND | Heating | 1403.47442 | 1754.34302 | 4.93548E-002 | 6.16935E-002 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | -18.80000 | 8.88305E-004 | 20.90318 | 1.26000 | 1.06188E-002 | 0.00000 |
| System Name | Load Type | Peak Load Kind | User Design Capacity | Calc Des Air Flow Rate [m3/s] | User Des Air Flow Rate [m3/s] | Design Day Name | Date/Time of Peak | |
| 1 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC | Cooling | Sensible | 2614.19 | 0.22110 | 0.22110 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 05:00:00 |
| 2 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC | Heating | Sensible | 3670.77 | 9.47479E-002 | 9.47479E-002 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 |
| 3 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC | Cooling | Sensible | 1575.67 | 0.13839 | 0.13839 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 05:00:00 |
| 4 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC | Heating | Sensible | 2137.96 | 6.16308E-002 | 6.16308E-002 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 |
| 5 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC | Cooling | Sensible | 1365.22 | 0.12027 | 0.12027 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 05:00:00 |
| 6 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC | Heating | Sensible | 2140.72 | 6.17292E-002 | 6.17292E-002 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 |
| 7 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC | Cooling | Sensible | 1793.24 | 0.14531 | 0.14531 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 05:00:00 |
| 8 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC | Heating | Sensible | 2181.44 | 4.22713E-002 | 4.22713E-002 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 |
| 9 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC | Cooling | Sensible | 1330.23 | 0.11691 | 0.11691 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 05:00:00 |
| 10 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC | Heating | Sensible | 1509.55 | 3.94803E-002 | 3.94803E-002 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 |
| 11 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC | Cooling | Sensible | 1104.27 | 9.93600E-002 | 9.93600E-002 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 05:00:00 |
| 12 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC | Heating | Sensible | 1512.30 | 3.95784E-002 | 3.95784E-002 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 |
| 13 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC | Cooling | Sensible | 2179.22 | 0.18073 | 0.18073 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 05:00:00 |
| 14 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC | Heating | Sensible | 3655.99 | 9.42204E-002 | 9.42204E-002 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 |
| 15 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC | Cooling | Sensible | 1488.83 | 0.13046 | 0.13046 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 05:00:00 |
| 16 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC | Heating | Sensible | 2136.95 | 6.15947E-002 | 6.15947E-002 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 |
| 17 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC | Cooling | Sensible | 1225.63 | 0.10908 | 0.10908 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 05:00:00 |
| 18 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC | Heating | Sensible | 2139.72 | 6.16935E-002 | 6.16935E-002 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 |
| Component Type | Component Name | Input Field Description | Value | |
| 1 | AirTerminal:SingleDuct:ConstantVolume:NoReheat | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC DIFFUSER | Design Size Maximum Air Flow Rate [m3/s] | 0.22110 |
| 2 | AirTerminal:SingleDuct:ConstantVolume:NoReheat | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC DIFFUSER | Design Size Maximum Air Flow Rate [m3/s] | 0.13839 |
| 3 | AirTerminal:SingleDuct:ConstantVolume:NoReheat | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC DIFFUSER | Design Size Maximum Air Flow Rate [m3/s] | 0.12027 |
| 4 | AirTerminal:SingleDuct:ConstantVolume:NoReheat | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC DIFFUSER | Design Size Maximum Air Flow Rate [m3/s] | 0.14531 |
| 5 | AirTerminal:SingleDuct:ConstantVolume:NoReheat | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC DIFFUSER | Design Size Maximum Air Flow Rate [m3/s] | 0.11691 |
| 6 | AirTerminal:SingleDuct:ConstantVolume:NoReheat | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC DIFFUSER | Design Size Maximum Air Flow Rate [m3/s] | 9.93600E-002 |
| 7 | AirTerminal:SingleDuct:ConstantVolume:NoReheat | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC DIFFUSER | Design Size Maximum Air Flow Rate [m3/s] | 0.18073 |
| 8 | AirTerminal:SingleDuct:ConstantVolume:NoReheat | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC DIFFUSER | Design Size Maximum Air Flow Rate [m3/s] | 0.13046 |
| 9 | AirTerminal:SingleDuct:ConstantVolume:NoReheat | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC DIFFUSER | Design Size Maximum Air Flow Rate [m3/s] | 0.10908 |
| 10 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC | Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | 0.00000 |
| 11 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | 0.00000 |
| 12 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC | Sum of Air Terminal Maximum Flow Rates [m3/s] | 0.22110 |
| 13 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC | Adjusted Heating Design Air Flow Rate [m3/s] | 9.47479E-002 |
| 14 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC | Adjusted Cooling Design Air Flow Rate [m3/s] | 0.22110 |
| 15 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC | Adjusted Main Design Air Flow Rate [m3/s] | 0.22110 |
| 16 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC | User Heating Air Flow Ratio [] | 1.00000 |
| 17 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC | Calculated Heating Air Flow Ratio [] | 0.42854 |
| 18 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC | Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | 0.00000 |
| 19 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | 0.00000 |
| 20 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC | Sum of Air Terminal Maximum Flow Rates [m3/s] | 0.13839 |
| 21 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC | Adjusted Heating Design Air Flow Rate [m3/s] | 6.16308E-002 |
| 22 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC | Adjusted Cooling Design Air Flow Rate [m3/s] | 0.13839 |
| 23 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC | Adjusted Main Design Air Flow Rate [m3/s] | 0.13839 |
| 24 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC | User Heating Air Flow Ratio [] | 1.00000 |
| 25 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC | Calculated Heating Air Flow Ratio [] | 0.44533 |
| 26 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC | Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | 0.00000 |
| 27 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | 0.00000 |
| 28 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC | Sum of Air Terminal Maximum Flow Rates [m3/s] | 0.12027 |
| 29 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC | Adjusted Heating Design Air Flow Rate [m3/s] | 6.17292E-002 |
| 30 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC | Adjusted Cooling Design Air Flow Rate [m3/s] | 0.12027 |
| 31 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC | Adjusted Main Design Air Flow Rate [m3/s] | 0.12027 |
| 32 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC | User Heating Air Flow Ratio [] | 1.00000 |
| 33 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC | Calculated Heating Air Flow Ratio [] | 0.51325 |
| 34 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC | Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | 0.00000 |
| 35 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | 0.00000 |
| 36 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC | Sum of Air Terminal Maximum Flow Rates [m3/s] | 0.14531 |
| 37 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC | Adjusted Heating Design Air Flow Rate [m3/s] | 4.22713E-002 |
| 38 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC | Adjusted Cooling Design Air Flow Rate [m3/s] | 0.14531 |
| 39 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC | Adjusted Main Design Air Flow Rate [m3/s] | 0.14531 |
| 40 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC | User Heating Air Flow Ratio [] | 1.00000 |
| 41 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC | Calculated Heating Air Flow Ratio [] | 0.29090 |
| 42 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC | Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | 0.00000 |
| 43 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | 0.00000 |
| 44 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC | Sum of Air Terminal Maximum Flow Rates [m3/s] | 0.11691 |
| 45 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC | Adjusted Heating Design Air Flow Rate [m3/s] | 3.94803E-002 |
| 46 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC | Adjusted Cooling Design Air Flow Rate [m3/s] | 0.11691 |
| 47 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC | Adjusted Main Design Air Flow Rate [m3/s] | 0.11691 |
| 48 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC | User Heating Air Flow Ratio [] | 1.00000 |
| 49 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC | Calculated Heating Air Flow Ratio [] | 0.33771 |
| 50 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC | Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | 0.00000 |
| 51 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | 0.00000 |
| 52 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC | Sum of Air Terminal Maximum Flow Rates [m3/s] | 9.93600E-002 |
| 53 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC | Adjusted Heating Design Air Flow Rate [m3/s] | 3.95784E-002 |
| 54 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC | Adjusted Cooling Design Air Flow Rate [m3/s] | 9.93600E-002 |
| 55 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC | Adjusted Main Design Air Flow Rate [m3/s] | 9.93600E-002 |
| 56 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC | User Heating Air Flow Ratio [] | 1.00000 |
| 57 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC | Calculated Heating Air Flow Ratio [] | 0.39833 |
| 58 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC | Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | 0.00000 |
| 59 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | 0.00000 |
| 60 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC | Sum of Air Terminal Maximum Flow Rates [m3/s] | 0.18073 |
| 61 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC | Adjusted Heating Design Air Flow Rate [m3/s] | 9.42204E-002 |
| 62 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC | Adjusted Cooling Design Air Flow Rate [m3/s] | 0.18073 |
| 63 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC | Adjusted Main Design Air Flow Rate [m3/s] | 0.18073 |
| 64 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC | User Heating Air Flow Ratio [] | 1.00000 |
| 65 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC | Calculated Heating Air Flow Ratio [] | 0.52134 |
| 66 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC | Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | 0.00000 |
| 67 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | 0.00000 |
| 68 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC | Sum of Air Terminal Maximum Flow Rates [m3/s] | 0.13046 |
| 69 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC | Adjusted Heating Design Air Flow Rate [m3/s] | 6.15947E-002 |
| 70 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC | Adjusted Cooling Design Air Flow Rate [m3/s] | 0.13046 |
| 71 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC | Adjusted Main Design Air Flow Rate [m3/s] | 0.13046 |
| 72 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC | User Heating Air Flow Ratio [] | 1.00000 |
| 73 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC | Calculated Heating Air Flow Ratio [] | 0.47212 |
| 74 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC | Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | 0.00000 |
| 75 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | 0.00000 |
| 76 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC | Sum of Air Terminal Maximum Flow Rates [m3/s] | 0.10908 |
| 77 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC | Adjusted Heating Design Air Flow Rate [m3/s] | 6.16935E-002 |
| 78 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC | Adjusted Cooling Design Air Flow Rate [m3/s] | 0.10908 |
| 79 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC | Adjusted Main Design Air Flow Rate [m3/s] | 0.10908 |
| 80 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC | User Heating Air Flow Ratio [] | 1.00000 |
| 81 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC | Calculated Heating Air Flow Ratio [] | 0.56559 |
| 82 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC | Design Supply Air Flow Rate [m3/s] | 0.22110 |
| 83 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC | Design Supply Air Flow Rate [m3/s] | 0.13839 |
| 84 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC | Design Supply Air Flow Rate [m3/s] | 0.12027 |
| 85 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC | Design Supply Air Flow Rate [m3/s] | 0.14531 |
| 86 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC | Design Supply Air Flow Rate [m3/s] | 0.11691 |
| 87 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC | Design Supply Air Flow Rate [m3/s] | 9.93600E-002 |
| 88 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC | Design Supply Air Flow Rate [m3/s] | 0.18073 |
| 89 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC | Design Supply Air Flow Rate [m3/s] | 0.13046 |
| 90 | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC | Design Supply Air Flow Rate [m3/s] | 0.10908 |
| 91 | Controller:OutdoorAir | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC OA SYSTEM CONTROLLER | Maximum Outdoor Air Flow Rate [m3/s] | 0.22110 |
| 92 | Controller:OutdoorAir | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC OA SYSTEM CONTROLLER | Minimum Outdoor Air Flow Rate [m3/s] | 2.62512E-002 |
| 93 | Coil:Cooling:DX:SingleSpeed | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 12KBTU/HR 9.7SEER | Design Size Rated Air Flow Rate [m3/s] | 0.22110 |
| 94 | Coil:Cooling:DX:SingleSpeed | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 12KBTU/HR 9.7SEER | Design Size Gross Rated Total Cooling Capacity [W] | 3659.91847 |
| 95 | Coil:Cooling:DX:SingleSpeed | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 12KBTU/HR 9.7SEER | Design Size Gross Rated Sensible Heat Ratio | 0.80066 |
| 96 | Coil:Heating:Fuel | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC GAS HTG COIL | Design Size Nominal Capacity [W] | 7211.04344 |
| 97 | Coil:Heating:Electric | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | Design Size Nominal Capacity [W] | 7211.04344 |
| 98 | Fan:ConstantVolume | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC FAN | Design Size Maximum Flow Rate [m3/s] | 0.22110 |
| 99 | Controller:OutdoorAir | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC OA SYSTEM CONTROLLER | Maximum Outdoor Air Flow Rate [m3/s] | 0.13839 |
| 100 | Controller:OutdoorAir | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC OA SYSTEM CONTROLLER | Minimum Outdoor Air Flow Rate [m3/s] | 1.06188E-002 |
| 101 | Coil:Cooling:DX:SingleSpeed | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 8KBTU/HR 9.7SEER | Design Size Rated Air Flow Rate [m3/s] | 0.13839 |
| 102 | Coil:Cooling:DX:SingleSpeed | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 8KBTU/HR 9.7SEER | Design Size Gross Rated Total Cooling Capacity [W] | 2290.90471 |
| 103 | Coil:Cooling:DX:SingleSpeed | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 8KBTU/HR 9.7SEER | Design Size Gross Rated Sensible Heat Ratio | 0.80066 |
| 104 | Coil:Heating:Fuel | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC GAS HTG COIL | Design Size Nominal Capacity [W] | 4289.01999 |
| 105 | Coil:Heating:Electric | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | Design Size Nominal Capacity [W] | 4289.01999 |
| 106 | Fan:ConstantVolume | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC FAN | Design Size Maximum Flow Rate [m3/s] | 0.13839 |
| 107 | Controller:OutdoorAir | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC OA SYSTEM CONTROLLER | Maximum Outdoor Air Flow Rate [m3/s] | 0.12027 |
| 108 | Controller:OutdoorAir | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC OA SYSTEM CONTROLLER | Minimum Outdoor Air Flow Rate [m3/s] | 1.06188E-002 |
| 109 | Coil:Cooling:DX:SingleSpeed | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 7KBTU/HR 9.7SEER | Design Size Rated Air Flow Rate [m3/s] | 0.12027 |
| 110 | Coil:Cooling:DX:SingleSpeed | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 7KBTU/HR 9.7SEER | Design Size Gross Rated Total Cooling Capacity [W] | 1990.92085 |
| 111 | Coil:Cooling:DX:SingleSpeed | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 7KBTU/HR 9.7SEER | Design Size Gross Rated Sensible Heat Ratio | 0.80066 |
| 112 | Coil:Heating:Fuel | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC GAS HTG COIL | Design Size Nominal Capacity [W] | 3781.20074 |
| 113 | Coil:Heating:Electric | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | Design Size Nominal Capacity [W] | 3781.20074 |
| 114 | Fan:ConstantVolume | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC FAN | Design Size Maximum Flow Rate [m3/s] | 0.12027 |
| 115 | Controller:OutdoorAir | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC OA SYSTEM CONTROLLER | Maximum Outdoor Air Flow Rate [m3/s] | 0.14531 |
| 116 | Controller:OutdoorAir | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC OA SYSTEM CONTROLLER | Minimum Outdoor Air Flow Rate [m3/s] | 2.57635E-002 |
| 117 | Coil:Cooling:DX:SingleSpeed | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 8KBTU/HR 9.7SEER | Design Size Rated Air Flow Rate [m3/s] | 0.14531 |
| 118 | Coil:Cooling:DX:SingleSpeed | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 8KBTU/HR 9.7SEER | Design Size Gross Rated Total Cooling Capacity [W] | 2405.41683 |
| 119 | Coil:Cooling:DX:SingleSpeed | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 8KBTU/HR 9.7SEER | Design Size Gross Rated Sensible Heat Ratio | 0.80066 |
| 120 | Coil:Heating:Fuel | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC GAS HTG COIL | Design Size Nominal Capacity [W] | 5068.27590 |
| 121 | Coil:Heating:Electric | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | Design Size Nominal Capacity [W] | 5068.27590 |
| 122 | Fan:ConstantVolume | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC FAN | Design Size Maximum Flow Rate [m3/s] | 0.14531 |
| 123 | Controller:OutdoorAir | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC OA SYSTEM CONTROLLER | Maximum Outdoor Air Flow Rate [m3/s] | 0.11691 |
| 124 | Controller:OutdoorAir | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC OA SYSTEM CONTROLLER | Minimum Outdoor Air Flow Rate [m3/s] | 1.04216E-002 |
| 125 | Coil:Cooling:DX:SingleSpeed | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 7KBTU/HR 9.7SEER | Design Size Rated Air Flow Rate [m3/s] | 0.11691 |
| 126 | Coil:Cooling:DX:SingleSpeed | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 7KBTU/HR 9.7SEER | Design Size Gross Rated Total Cooling Capacity [W] | 1935.21712 |
| 127 | Coil:Cooling:DX:SingleSpeed | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 7KBTU/HR 9.7SEER | Design Size Gross Rated Sensible Heat Ratio | 0.80066 |
| 128 | Coil:Heating:Fuel | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC GAS HTG COIL | Design Size Nominal Capacity [W] | 3679.01132 |
| 129 | Coil:Heating:Electric | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | Design Size Nominal Capacity [W] | 3679.01132 |
| 130 | Fan:ConstantVolume | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC FAN | Design Size Maximum Flow Rate [m3/s] | 0.11691 |
| 131 | Controller:OutdoorAir | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC OA SYSTEM CONTROLLER | Maximum Outdoor Air Flow Rate [m3/s] | 9.93600E-002 |
| 132 | Controller:OutdoorAir | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC OA SYSTEM CONTROLLER | Minimum Outdoor Air Flow Rate [m3/s] | 1.04216E-002 |
| 133 | Coil:Cooling:DX:SingleSpeed | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 6KBTU/HR 9.7SEER | Design Size Rated Air Flow Rate [m3/s] | 9.93600E-002 |
| 134 | Coil:Cooling:DX:SingleSpeed | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 6KBTU/HR 9.7SEER | Design Size Gross Rated Total Cooling Capacity [W] | 1644.76083 |
| 135 | Coil:Cooling:DX:SingleSpeed | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 6KBTU/HR 9.7SEER | Design Size Gross Rated Sensible Heat Ratio | 0.80066 |
| 136 | Coil:Heating:Fuel | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC GAS HTG COIL | Design Size Nominal Capacity [W] | 3187.36336 |
| 137 | Coil:Heating:Electric | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | Design Size Nominal Capacity [W] | 3187.36336 |
| 138 | Fan:ConstantVolume | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC FAN | Design Size Maximum Flow Rate [m3/s] | 9.93600E-002 |
| 139 | Controller:OutdoorAir | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC OA SYSTEM CONTROLLER | Maximum Outdoor Air Flow Rate [m3/s] | 0.18073 |
| 140 | Controller:OutdoorAir | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC OA SYSTEM CONTROLLER | Minimum Outdoor Air Flow Rate [m3/s] | 2.62512E-002 |
| 141 | Coil:Cooling:DX:SingleSpeed | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 10KBTU/HR 9.7SEER | Design Size Rated Air Flow Rate [m3/s] | 0.18073 |
| 142 | Coil:Cooling:DX:SingleSpeed | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 10KBTU/HR 9.7SEER | Design Size Gross Rated Total Cooling Capacity [W] | 2991.66702 |
| 143 | Coil:Cooling:DX:SingleSpeed | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 10KBTU/HR 9.7SEER | Design Size Gross Rated Sensible Heat Ratio | 0.80066 |
| 144 | Coil:Heating:Fuel | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC GAS HTG COIL | Design Size Nominal Capacity [W] | 6079.89972 |
| 145 | Coil:Heating:Electric | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | Design Size Nominal Capacity [W] | 6079.89972 |
| 146 | Fan:ConstantVolume | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC FAN | Design Size Maximum Flow Rate [m3/s] | 0.18073 |
| 147 | Controller:OutdoorAir | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC OA SYSTEM CONTROLLER | Maximum Outdoor Air Flow Rate [m3/s] | 0.13046 |
| 148 | Controller:OutdoorAir | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC OA SYSTEM CONTROLLER | Minimum Outdoor Air Flow Rate [m3/s] | 1.06188E-002 |
| 149 | Coil:Cooling:DX:SingleSpeed | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 7KBTU/HR 9.7SEER | Design Size Rated Air Flow Rate [m3/s] | 0.13046 |
| 150 | Coil:Cooling:DX:SingleSpeed | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 7KBTU/HR 9.7SEER | Design Size Gross Rated Total Cooling Capacity [W] | 2159.63950 |
| 151 | Coil:Cooling:DX:SingleSpeed | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 7KBTU/HR 9.7SEER | Design Size Gross Rated Sensible Heat Ratio | 0.80066 |
| 152 | Coil:Heating:Fuel | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC GAS HTG COIL | Design Size Nominal Capacity [W] | 4066.81213 |
| 153 | Coil:Heating:Electric | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | Design Size Nominal Capacity [W] | 4066.81213 |
| 154 | Fan:ConstantVolume | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC FAN | Design Size Maximum Flow Rate [m3/s] | 0.13046 |
| 155 | Controller:OutdoorAir | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC OA SYSTEM CONTROLLER | Maximum Outdoor Air Flow Rate [m3/s] | 0.10908 |
| 156 | Controller:OutdoorAir | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC OA SYSTEM CONTROLLER | Minimum Outdoor Air Flow Rate [m3/s] | 1.06188E-002 |
| 157 | Coil:Cooling:DX:SingleSpeed | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 6KBTU/HR 9.7SEER | Design Size Rated Air Flow Rate [m3/s] | 0.10908 |
| 158 | Coil:Cooling:DX:SingleSpeed | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 6KBTU/HR 9.7SEER | Design Size Gross Rated Total Cooling Capacity [W] | 1805.62636 |
| 159 | Coil:Cooling:DX:SingleSpeed | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 6KBTU/HR 9.7SEER | Design Size Gross Rated Sensible Heat Ratio | 0.80066 |
| 160 | Coil:Heating:Fuel | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC GAS HTG COIL | Design Size Nominal Capacity [W] | 3467.53083 |
| 161 | Coil:Heating:Electric | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | Design Size Nominal Capacity [W] | 3467.53083 |
| 162 | Fan:ConstantVolume | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC FAN | Design Size Maximum Flow Rate [m3/s] | 0.10908 |
| 163 | PlantLoop | HOT WATER LOOP | Maximum Loop Flow Rate [m3/s] | 0.00000 |
| 164 | PlantLoop | HOT WATER LOOP | Plant Loop Volume [m3] | 0.00000 |
| 165 | Pump:VariableSpeed | HOT WATER LOOP PUMP | Design Flow Rate [m3/s] | 0.00000 |
| 166 | Pump:VariableSpeed | HOT WATER LOOP PUMP | Design Power Consumption [W] | 0.00000 |
| 167 | Boiler:HotWater | BOILER | Design Size Nominal Capacity [W] | 0.00000 |
| 168 | Boiler:HotWater | BOILER | Design Size Design Water Flow Rate [m3/s] | 0.00000 |
| 169 | PlantLoop | OFFICE SHARED SERVICE WATER LOOP | Maximum Loop Flow Rate [m3/s] | 1.72002E-006 |
| 170 | PlantLoop | OFFICE SHARED SERVICE WATER LOOP | Plant Loop Volume [m3] | 2.06402E-004 |
| 171 | Pump:ConstantSpeed | OFFICE SHARED SERVICE WATER LOOP CIRCULATOR PUMP | Design Flow Rate [m3/s] | 1.72002E-006 |
| 172 | Pump:ConstantSpeed | OFFICE SHARED SERVICE WATER LOOP CIRCULATOR PUMP | Design Power Consumption [W] | 7.98950E-002 |
| 173 | WaterHeater:Mixed | 40GAL NATURALGAS WATER HEATER - 2KBTU/HR 0.82 THERM EFF | Use Side Design Flow Rate [m3/s] | 1.72002E-006 |
| Component Type | Component Name | Standard Rating (Net) Cooling Capacity {W} | Standard Rated Net COP {W/W} | EER {Btu/W-h} | SEER {Btu/W-h} | IEER {Btu/W-h} | |
| 1 | Coil:Cooling:DX:SingleSpeed | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 12KBTU/HR 9.7SEER | 3483.1 | 2.61 | 8.92 | 9.40 | 8.96 |
| 2 | Coil:Cooling:DX:SingleSpeed | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 8KBTU/HR 9.7SEER | 2180.2 | 2.61 | 8.92 | 9.40 | 8.96 |
| 3 | Coil:Cooling:DX:SingleSpeed | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 7KBTU/HR 9.7SEER | 1894.7 | 2.61 | 8.92 | 9.40 | 8.96 |
| 4 | Coil:Cooling:DX:SingleSpeed | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 8KBTU/HR 9.7SEER | 2289.2 | 2.61 | 8.92 | 9.40 | 8.96 |
| 5 | Coil:Cooling:DX:SingleSpeed | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 7KBTU/HR 9.7SEER | 1841.7 | 2.61 | 8.92 | 9.40 | 8.96 |
| 6 | Coil:Cooling:DX:SingleSpeed | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 6KBTU/HR 9.7SEER | 1565.3 | 2.61 | 8.92 | 9.40 | 8.96 |
| 7 | Coil:Cooling:DX:SingleSpeed | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 10KBTU/HR 9.7SEER | 2847.1 | 2.61 | 8.92 | 9.40 | 8.96 |
| 8 | Coil:Cooling:DX:SingleSpeed | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 7KBTU/HR 9.7SEER | 2055.3 | 2.61 | 8.92 | 9.40 | 8.96 |
| 9 | Coil:Cooling:DX:SingleSpeed | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 6KBTU/HR 9.7SEER | 1718.4 | 2.61 | 8.92 | 9.40 | 8.96 |
| Environment Name | Environment Type | Start Date | End Date | Start DayOfWeek | Duration {#days} | Source:Start DayOfWeek | Use Daylight Saving | Use Holidays | Apply Weekend Holiday Rule | Use Rain Values | Use Snow Values | |
| 1 | RUN PERIOD 1 | WeatherFileRunPeriod | 06/01/2012 | 06/01/2012 | Friday | 1 | Use RunPeriod Specified Day | No | No | No | Yes | Yes |
| Daylight Saving Indicator | Source | Start Date | End Date | |
| 1 | Yes | InputFile | 03/11 | 11/04 |
| NumberofWarmupDays | |
| 1 | 6 |
| Style | Unit Conversion | |
| 1 | HTML | None |
| Zone Name | Environment Type/Name | Average Warmup Temperature Difference {deltaC} | Std Dev Warmup Temperature Difference {deltaC} | Max Temperature Pass/Fail Convergence | Min Temperature Pass/Fail Convergence | Average Warmup Load Difference {W} | Std Dev Warmup Load Difference {W} | Heating Load Pass/Fail Convergence | Cooling Load Pass/Fail Convergence | |
| 1 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND | RunPeriod: RUN PERIOD 1 | 0.2068470112 | 0.1833260267 | Pass | Pass | 0.3415409452 | 1.0503170685 | Pass | Pass |
| 2 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND | RunPeriod: RUN PERIOD 1 | 0.2676165842 | 0.1780287759 | Pass | Pass | 0.9716973374 | 1.7486912501 | Pass | Pass |
| 3 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND | RunPeriod: RUN PERIOD 1 | 0.2889765105 | 0.1916456214 | Pass | Pass | 4.8661008161 | 15.5805016119 | Pass | Pass |
| 4 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND | RunPeriod: RUN PERIOD 1 | 0.1297810564 | 0.2052979002 | Pass | Pass | 0.1038581220 | 0.1490917748 | Pass | Pass |
| 5 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND | RunPeriod: RUN PERIOD 1 | 0.2005727866 | 0.1939186554 | Pass | Pass | 0.3554981514 | 0.6772136134 | Pass | Pass |
| 6 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND | RunPeriod: RUN PERIOD 1 | 0.2174973804 | 0.1733560465 | Pass | Pass | 0.4110665801 | 1.2959978762 | Pass | Pass |
| 7 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND | RunPeriod: RUN PERIOD 1 | 0.2105208956 | 0.2020994047 | Pass | Pass | 0.2304046735 | 0.5864787712 | Pass | Pass |
| 8 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND | RunPeriod: RUN PERIOD 1 | 0.2723180943 | 0.1819824510 | Pass | Pass | 1.0071369285 | 2.0679616374 | Pass | Pass |
| 9 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND | RunPeriod: RUN PERIOD 1 | 0.2940116693 | 0.2072579478 | Pass | Pass | 0.8534580089 | 1.5534443671 | Pass | Pass |
Report: Annual Heat Emissions Summary
For: Entire Facility
Timestamp: 2020-03-22 22:58:43
Heat Emission by Components| Envelope Convection | Zone Exfiltration | Zone Exhaust Air | HVAC Relief Air | HVAC Reject Heat | Total | |
| Heat Emissions [GJ] | 1.48 | 0.05 | 0.00 | 0.14 | 0.09 | 1.78 |
Report: Climatic Data Summary
For: Entire Facility
Timestamp: 2020-03-22 22:58:43
SizingPeriod:DesignDay| Maximum Dry Bulb [C] | Daily Temperature Range [deltaC] | Humidity Value | Humidity Type | Wind Speed [m/s] | Wind Direction | |
| DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 33.00 | 15.20 | 15.70 | Wetbulb [C] | 4.90 | 0.00 |
| DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS WB=>MDB 1 | 27.30 | 15.20 | 18.40 | Wetbulb [C] | 4.90 | 0.00 |
| DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | -18.80 | 0.00 | -18.80 | Wetbulb [C] | 3.00 | 340.00 |
| Value | |
| None |
Report: Envelope Summary
For: Entire Facility
Timestamp: 2020-03-22 22:58:43
Opaque Exterior| Construction | Reflectance | U-Factor with Film [W/m2-K] | U-Factor no Film [W/m2-K] | Gross Area [m2] | Net Area [m2] | Azimuth [deg] | Tilt [deg] | Cardinal Direction | |
| SURFACE 23 | TYPICAL INSULATED EXTERIOR MASS WALL R-8.13 | 0.30 | 0.698 | 0.780 | 34.45 | 29.28 | 180.00 | 90.00 | S |
| SURFACE 19 | TYPICAL INSULATED CARPETED 6IN SLAB FLOOR | 0.30 | 2.250 | 3.540 | 51.68 | 51.68 | 180.00 | 180.00 | |
| SURFACE 24 | TYPICAL IEAD ROOF R-15.87 | 0.30 | 0.358 | 0.376 | 51.68 | 51.68 | 0.00 | 0.00 | |
| SURFACE 2 | TYPICAL INSULATED EXTERIOR MASS WALL R-8.13 | 0.30 | 0.698 | 0.780 | 13.94 | 11.85 | 270.00 | 90.00 | W |
| SURFACE 5 | TYPICAL INSULATED EXTERIOR MASS WALL R-8.13 | 0.30 | 0.698 | 0.780 | 13.94 | 11.85 | 180.00 | 90.00 | S |
| SURFACE 1 | TYPICAL INSULATED CARPETED 6IN SLAB FLOOR | 0.30 | 2.250 | 3.540 | 20.90 | 20.90 | 180.00 | 180.00 | |
| SURFACE 6 | TYPICAL IEAD ROOF R-15.87 | 0.30 | 0.358 | 0.376 | 20.90 | 20.90 | 0.00 | 0.00 | |
| SURFACE 40 | TYPICAL INSULATED EXTERIOR MASS WALL R-8.13 | 0.30 | 0.698 | 0.780 | 13.94 | 11.85 | 90.00 | 90.00 | E |
| SURFACE 41 | TYPICAL INSULATED EXTERIOR MASS WALL R-8.13 | 0.30 | 0.698 | 0.780 | 13.94 | 11.85 | 180.00 | 90.00 | S |
| SURFACE 37 | TYPICAL INSULATED CARPETED 6IN SLAB FLOOR | 0.30 | 2.250 | 3.540 | 20.90 | 20.90 | 180.00 | 180.00 | |
| SURFACE 42 | TYPICAL IEAD ROOF R-15.87 | 0.30 | 0.358 | 0.376 | 20.90 | 20.90 | 0.00 | 0.00 | |
| SURFACE 25 | TYPICAL INSULATED CARPETED 6IN SLAB FLOOR | 0.30 | 2.250 | 3.540 | 50.72 | 50.72 | 180.00 | 180.00 | |
| SURFACE 30 | TYPICAL IEAD ROOF R-15.87 | 0.30 | 0.358 | 0.376 | 50.72 | 50.72 | 0.00 | 0.00 | |
| SURFACE 8 | TYPICAL INSULATED EXTERIOR MASS WALL R-8.13 | 0.30 | 0.698 | 0.780 | 13.68 | 11.63 | 270.00 | 90.00 | W |
| SURFACE 7 | TYPICAL INSULATED CARPETED 6IN SLAB FLOOR | 0.30 | 2.250 | 3.540 | 20.51 | 20.51 | 180.00 | 180.00 | |
| SURFACE 12 | TYPICAL IEAD ROOF R-15.87 | 0.30 | 0.358 | 0.376 | 20.51 | 20.51 | 0.00 | 0.00 | |
| SURFACE 46 | TYPICAL INSULATED EXTERIOR MASS WALL R-8.13 | 0.30 | 0.698 | 0.780 | 13.68 | 11.63 | 90.00 | 90.00 | E |
| SURFACE 43 | TYPICAL INSULATED CARPETED 6IN SLAB FLOOR | 0.30 | 2.250 | 3.540 | 20.51 | 20.51 | 180.00 | 180.00 | |
| SURFACE 48 | TYPICAL IEAD ROOF R-15.87 | 0.30 | 0.358 | 0.376 | 20.51 | 20.51 | 0.00 | 0.00 | |
| SURFACE 33 | TYPICAL INSULATED EXTERIOR MASS WALL R-8.13 | 0.30 | 0.698 | 0.780 | 34.45 | 29.28 | 0.00 | 90.00 | N |
| SURFACE 31 | TYPICAL INSULATED CARPETED 6IN SLAB FLOOR | 0.30 | 2.250 | 3.540 | 51.68 | 51.68 | 180.00 | 180.00 | |
| SURFACE 36 | TYPICAL IEAD ROOF R-15.87 | 0.30 | 0.358 | 0.376 | 51.68 | 51.68 | 0.00 | 0.00 | |
| SURFACE 14 | TYPICAL INSULATED EXTERIOR MASS WALL R-8.13 | 0.30 | 0.698 | 0.780 | 13.94 | 11.85 | 270.00 | 90.00 | W |
| SURFACE 15 | TYPICAL INSULATED EXTERIOR MASS WALL R-8.13 | 0.30 | 0.698 | 0.780 | 13.94 | 11.85 | 0.00 | 90.00 | N |
| SURFACE 13 | TYPICAL INSULATED CARPETED 6IN SLAB FLOOR | 0.30 | 2.250 | 3.540 | 20.90 | 20.90 | 180.00 | 180.00 | |
| SURFACE 18 | TYPICAL IEAD ROOF R-15.87 | 0.30 | 0.358 | 0.376 | 20.90 | 20.90 | 0.00 | 0.00 | |
| SURFACE 51 | TYPICAL INSULATED EXTERIOR MASS WALL R-8.13 | 0.30 | 0.698 | 0.780 | 13.94 | 11.85 | 0.00 | 90.00 | N |
| SURFACE 52 | TYPICAL INSULATED EXTERIOR MASS WALL R-8.13 | 0.30 | 0.698 | 0.780 | 13.94 | 11.85 | 90.00 | 90.00 | E |
| SURFACE 49 | TYPICAL INSULATED CARPETED 6IN SLAB FLOOR | 0.30 | 2.250 | 3.540 | 20.90 | 20.90 | 180.00 | 180.00 | |
| SURFACE 54 | TYPICAL IEAD ROOF R-15.87 | 0.30 | 0.358 | 0.376 | 20.90 | 20.90 | 0.00 | 0.00 |
| Construction | Glass Area [m2] | Frame Area [m2] | Divider Area [m2] | Area of One Opening [m2] | Area of Multiplied Openings [m2] | Glass U-Factor [W/m2-K] | Glass SHGC | Glass Visible Transmittance | Frame Conductance [W/m2-K] | Divider Conductance [W/m2-K] | Shade Control | Parent Surface | Azimuth [deg] | Tilt [deg] | Cardinal Direction | |
| SUB SURFACE 1 | U 0.57 SHGC 0.49 DBL BLUE 6MM/6MM AIR | 5.17 | 0.00 | 0.00 | 5.17 | 5.17 | 3.058 | 0.502 | 0.505 | No | SURFACE 23 | 180.00 | 90.00 | S | ||
| SUB SURFACE 4 | U 0.57 SHGC 0.49 DBL BLUE 6MM/6MM AIR | 2.09 | 0.00 | 0.00 | 2.09 | 2.09 | 3.058 | 0.502 | 0.505 | No | SURFACE 2 | 270.00 | 90.00 | W | ||
| SUB SURFACE 3 | U 0.57 SHGC 0.49 DBL BLUE 6MM/6MM AIR | 2.09 | 0.00 | 0.00 | 2.09 | 2.09 | 3.058 | 0.502 | 0.505 | No | SURFACE 5 | 180.00 | 90.00 | S | ||
| SUB SURFACE 11 | U 0.57 SHGC 0.49 DBL BLUE 6MM/6MM AIR | 2.09 | 0.00 | 0.00 | 2.09 | 2.09 | 3.058 | 0.502 | 0.505 | No | SURFACE 40 | 90.00 | 90.00 | E | ||
| SUB SURFACE 12 | U 0.57 SHGC 0.49 DBL BLUE 6MM/6MM AIR | 2.09 | 0.00 | 0.00 | 2.09 | 2.09 | 3.058 | 0.502 | 0.505 | No | SURFACE 41 | 180.00 | 90.00 | S | ||
| SUB SURFACE 5 | U 0.57 SHGC 0.49 DBL BLUE 6MM/6MM AIR | 2.05 | 0.00 | 0.00 | 2.05 | 2.05 | 3.058 | 0.502 | 0.505 | No | SURFACE 8 | 270.00 | 90.00 | W | ||
| SUB SURFACE 8 | U 0.57 SHGC 0.49 DBL BLUE 6MM/6MM AIR | 2.05 | 0.00 | 0.00 | 2.05 | 2.05 | 3.058 | 0.502 | 0.505 | No | SURFACE 46 | 90.00 | 90.00 | E | ||
| SUB SURFACE 2 | U 0.57 SHGC 0.49 DBL BLUE 6MM/6MM AIR | 5.17 | 0.00 | 0.00 | 5.17 | 5.17 | 3.058 | 0.502 | 0.505 | No | SURFACE 33 | 0.00 | 90.00 | N | ||
| SUB SURFACE 7 | U 0.57 SHGC 0.49 DBL BLUE 6MM/6MM AIR | 2.09 | 0.00 | 0.00 | 2.09 | 2.09 | 3.058 | 0.502 | 0.505 | No | SURFACE 14 | 270.00 | 90.00 | W | ||
| SUB SURFACE 6 | U 0.57 SHGC 0.49 DBL BLUE 6MM/6MM AIR | 2.09 | 0.00 | 0.00 | 2.09 | 2.09 | 3.058 | 0.502 | 0.505 | No | SURFACE 15 | 0.00 | 90.00 | N | ||
| SUB SURFACE 10 | U 0.57 SHGC 0.49 DBL BLUE 6MM/6MM AIR | 2.09 | 0.00 | 0.00 | 2.09 | 2.09 | 3.058 | 0.502 | 0.505 | No | SURFACE 51 | 0.00 | 90.00 | N | ||
| SUB SURFACE 9 | U 0.57 SHGC 0.49 DBL BLUE 6MM/6MM AIR | 2.09 | 0.00 | 0.00 | 2.09 | 2.09 | 3.058 | 0.502 | 0.505 | No | SURFACE 52 | 90.00 | 90.00 | E | ||
| Total or Average | 31.16 | 3.058 | 0.502 | 0.505 | ||||||||||||
| North Total or Average | 9.35 | 3.058 | 0.502 | 0.505 | ||||||||||||
| Non-North Total or Average | 21.81 | 3.058 | 0.502 | 0.505 |
| Construction | Area of One Opening [m2] | Area of Openings [m2] | Glass U-Factor [W/m2-K] | Glass SHGC | Glass Visible Transmittance | Parent Surface | |
| Total or Average | 0.00 | - | - | - |
| Construction | U-Factor with Film [W/m2-K] | U-Factor no Film [W/m2-K] | Gross Area [m2] | Parent Surface | |
| None |
Report: Shading Summary
For: Entire Facility
Timestamp: 2020-03-22 22:58:43
Sunlit Fraction| March 21 9am | March 21 noon | March 21 3pm | June 21 9am | June 21 noon | June 21 3pm | December 21 9am | December 21 noon | December 21 3pm | |
| None |
| Name | Type | Shaded Construction | Control | Glare Control | |
| None |
Report: Lighting Summary
For: Entire Facility
Timestamp: 2020-03-22 22:58:43
Interior Lighting| Zone | Lighting Power Density [W/m2] | Zone Area [m2] | Total Power [W] | End Use Subcategory | Schedule Name | Scheduled Hours/Week [hr] | Hours/Week > 1% [hr] | Full Load Hours/Week [hr] | Return Air Fraction | Conditioned (Y/N) | Consumption [GJ] | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND OFFICE WHOLEBUILDING - SM OFFICE LIGHTS | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND | 10.7639 | 51.68 | 556.23 | General | OFFICESMALL BLDG_LIGHT_SCH | 70.08 | 161.00 | 84.70 | 0.0000 | Y | 0.02 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND OFFICE WHOLEBUILDING - SM OFFICE LIGHTS | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND | 10.7639 | 20.90 | 225.00 | General | OFFICESMALL BLDG_LIGHT_SCH | 70.08 | 161.00 | 84.70 | 0.0000 | Y | 0.01 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND OFFICE WHOLEBUILDING - SM OFFICE LIGHTS | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND | 10.7639 | 20.90 | 225.00 | General | OFFICESMALL BLDG_LIGHT_SCH | 70.08 | 161.00 | 84.70 | 0.0000 | Y | 0.01 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND OFFICE WHOLEBUILDING - SM OFFICE LIGHTS | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND | 10.7639 | 50.72 | 545.90 | General | OFFICESMALL BLDG_LIGHT_SCH | 70.08 | 161.00 | 84.70 | 0.0000 | Y | 0.02 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND OFFICE WHOLEBUILDING - SM OFFICE LIGHTS | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND | 10.7639 | 20.51 | 220.82 | General | OFFICESMALL BLDG_LIGHT_SCH | 70.08 | 161.00 | 84.70 | 0.0000 | Y | 0.01 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND OFFICE WHOLEBUILDING - SM OFFICE LIGHTS | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND | 10.7639 | 20.51 | 220.82 | General | OFFICESMALL BLDG_LIGHT_SCH | 70.08 | 161.00 | 84.70 | 0.0000 | Y | 0.01 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND OFFICE WHOLEBUILDING - SM OFFICE LIGHTS | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND | 10.7639 | 51.68 | 556.23 | General | OFFICESMALL BLDG_LIGHT_SCH | 70.08 | 161.00 | 84.70 | 0.0000 | Y | 0.02 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND OFFICE WHOLEBUILDING - SM OFFICE LIGHTS | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND | 10.7639 | 20.90 | 225.00 | General | OFFICESMALL BLDG_LIGHT_SCH | 70.08 | 161.00 | 84.70 | 0.0000 | Y | 0.01 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND OFFICE WHOLEBUILDING - SM OFFICE LIGHTS | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND | 10.7639 | 20.90 | 225.00 | General | OFFICESMALL BLDG_LIGHT_SCH | 70.08 | 161.00 | 84.70 | 0.0000 | Y | 0.01 |
| Interior Lighting Total | 10.7639 | 278.71 | 3000.00 | 0.13 |
| Zone | Control Name | Daylighting Method | Control Type | Fraction Controlled | Lighting Installed in Zone [W] | Lighting Controlled [W] | |
| None |
| Total Watts | Astronomical Clock/Schedule | Schedule Name | Scheduled Hours/Week [hr] | Hours/Week > 1% [hr] | Full Load Hours/Week [hr] | Consumption [GJ] | |
| BUILDING FACADES | 447.21 | AstronomicalClock | - | 28.00 | 28.00 | 0.01 | |
| MAIN ENTRIES | 240.00 | AstronomicalClock | - | 70.00 | 70.00 | 0.01 | |
| OTHER DOORS | 48.00 | AstronomicalClock | - | 70.00 | 70.00 | 0.00 | |
| PARKING AREAS AND DRIVES | 729.00 | AstronomicalClock | - | 70.00 | 70.00 | 0.03 | |
| Exterior Lighting Total | 1464.21 | 0.04 |
Report: Equipment Summary
For: Entire Facility
Timestamp: 2020-03-22 22:58:43
Central Plant| Type | Nominal Capacity [W] | Nominal Efficiency [W/W] | IPLV in SI Units [W/W] | IPLV in IP Units [Btu/W-h] | |
| BOILER | Boiler:HotWater | 0.00 | 0.78 |
| Type | Design Coil Load [W] | Nominal Total Capacity [W] | Nominal Sensible Capacity [W] | Nominal Latent Capacity [W] | Nominal Sensible Heat Ratio | Nominal Efficiency [W/W] | Nominal Coil UA Value [W/C] | Nominal Coil Surface Area [m2] | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 12KBTU/HR 9.7SEER | Coil:Cooling:DX:SingleSpeed | 3659.92 | 2930.33 | 729.59 | 0.80 | 3.15 | |||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 8KBTU/HR 9.7SEER | Coil:Cooling:DX:SingleSpeed | 2290.90 | 1834.22 | 456.68 | 0.80 | 3.15 | |||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 7KBTU/HR 9.7SEER | Coil:Cooling:DX:SingleSpeed | 1990.92 | 1594.04 | 396.88 | 0.80 | 3.15 | |||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 8KBTU/HR 9.7SEER | Coil:Cooling:DX:SingleSpeed | 2405.42 | 1925.91 | 479.51 | 0.80 | 3.15 | |||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 7KBTU/HR 9.7SEER | Coil:Cooling:DX:SingleSpeed | 1935.22 | 1549.44 | 385.78 | 0.80 | 3.15 | |||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 6KBTU/HR 9.7SEER | Coil:Cooling:DX:SingleSpeed | 1644.76 | 1316.89 | 327.87 | 0.80 | 3.15 | |||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 10KBTU/HR 9.7SEER | Coil:Cooling:DX:SingleSpeed | 2991.67 | 2395.29 | 596.37 | 0.80 | 3.15 | |||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 7KBTU/HR 9.7SEER | Coil:Cooling:DX:SingleSpeed | 2159.64 | 1729.13 | 430.51 | 0.80 | 3.15 | |||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 6KBTU/HR 9.7SEER | Coil:Cooling:DX:SingleSpeed | 1805.63 | 1445.68 | 359.94 | 0.80 | 3.15 |
| DX Cooling Coil Type | Standard Rated Net Cooling Capacity [W] | Standard Rated Net COP [W/W] | EER [Btu/W-h] | SEER [Btu/W-h] | IEER [Btu/W-h] | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 12KBTU/HR 9.7SEER | 3483.1 | 2.61 | 8.92 | 9.40 | 8.96 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 8KBTU/HR 9.7SEER | 2180.2 | 2.61 | 8.92 | 9.40 | 8.96 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 7KBTU/HR 9.7SEER | 1894.7 | 2.61 | 8.92 | 9.40 | 8.96 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 8KBTU/HR 9.7SEER | 2289.2 | 2.61 | 8.92 | 9.40 | 8.96 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 7KBTU/HR 9.7SEER | 1841.7 | 2.61 | 8.92 | 9.40 | 8.96 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 6KBTU/HR 9.7SEER | 1565.3 | 2.61 | 8.92 | 9.40 | 8.96 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 10KBTU/HR 9.7SEER | 2847.1 | 2.61 | 8.92 | 9.40 | 8.96 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 7KBTU/HR 9.7SEER | 2055.3 | 2.61 | 8.92 | 9.40 | 8.96 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 6KBTU/HR 9.7SEER | 1718.4 | 2.61 | 8.92 | 9.40 | 8.96 |
| DX Cooling Coil Type | Rated Net Cooling Capacity Test A [W] | Rated Electric Power Test A [W] | Rated Net Cooling Capacity Test B [W] | Rated Electric Power Test B [W] | Rated Net Cooling Capacity Test C [W] | Rated Electric Power Test C [W] | Rated Net Cooling Capacity Test D [W] | Rated Electric Power Test D [W] | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 12KBTU/HR 9.7SEER | Coil:Cooling:DX:SingleSpeed | ||||||||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 8KBTU/HR 9.7SEER | Coil:Cooling:DX:SingleSpeed | ||||||||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 7KBTU/HR 9.7SEER | Coil:Cooling:DX:SingleSpeed | ||||||||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 8KBTU/HR 9.7SEER | Coil:Cooling:DX:SingleSpeed | ||||||||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 7KBTU/HR 9.7SEER | Coil:Cooling:DX:SingleSpeed | ||||||||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 6KBTU/HR 9.7SEER | Coil:Cooling:DX:SingleSpeed | ||||||||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 10KBTU/HR 9.7SEER | Coil:Cooling:DX:SingleSpeed | ||||||||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 7KBTU/HR 9.7SEER | Coil:Cooling:DX:SingleSpeed | ||||||||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 6KBTU/HR 9.7SEER | Coil:Cooling:DX:SingleSpeed |
| DX Heating Coil Type | High Temperature Heating (net) Rating Capacity [W] | Low Temperature Heating (net) Rating Capacity [W] | HSPF [Btu/W-h] | Region Number | |
| None |
| Type | Design Coil Load [W] | Nominal Total Capacity [W] | Nominal Efficiency [W/W] | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC GAS HTG COIL | Coil:Heating:Fuel | 7211.04 | 0.80 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | Coil:Heating:Electric | 7211.04 | 1.00 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC GAS HTG COIL | Coil:Heating:Fuel | 4289.02 | 0.80 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | Coil:Heating:Electric | 4289.02 | 1.00 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC GAS HTG COIL | Coil:Heating:Fuel | 3781.20 | 0.80 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | Coil:Heating:Electric | 3781.20 | 1.00 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC GAS HTG COIL | Coil:Heating:Fuel | 5068.28 | 0.80 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | Coil:Heating:Electric | 5068.28 | 1.00 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC GAS HTG COIL | Coil:Heating:Fuel | 3679.01 | 0.80 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | Coil:Heating:Electric | 3679.01 | 1.00 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC GAS HTG COIL | Coil:Heating:Fuel | 3187.36 | 0.80 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | Coil:Heating:Electric | 3187.36 | 1.00 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC GAS HTG COIL | Coil:Heating:Fuel | 6079.90 | 0.80 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | Coil:Heating:Electric | 6079.90 | 1.00 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC GAS HTG COIL | Coil:Heating:Fuel | 4066.81 | 0.80 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | Coil:Heating:Electric | 4066.81 | 1.00 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC GAS HTG COIL | Coil:Heating:Fuel | 3467.53 | 0.80 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | Coil:Heating:Electric | 3467.53 | 1.00 |
| Type | Total Efficiency [W/W] | Delta Pressure [pa] | Max Air Flow Rate [m3/s] | Rated Electric Power [W] | Rated Power Per Max Air Flow Rate [W-s/m3] | Motor Heat In Air Fraction | Fan Energy Index | End Use Subcategory | Design Day Name for Fan Sizing Peak | Date/Time for Fan Sizing Peak | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC FAN | Fan:ConstantVolume | 0.54 | 622.72 | 0.22 | 256.75 | 1161.25 | 1.00 | 2.07 | General | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 14:00:00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC FAN | Fan:ConstantVolume | 0.54 | 622.72 | 0.14 | 160.71 | 1161.25 | 1.00 | 2.61 | General | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 16:00:00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC FAN | Fan:ConstantVolume | 0.54 | 622.72 | 0.12 | 139.67 | 1161.25 | 1.00 | 2.82 | General | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 11:00:00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC FAN | Fan:ConstantVolume | 0.54 | 622.72 | 0.15 | 168.74 | 1161.25 | 1.00 | 2.54 | General | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 14:00:00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC FAN | Fan:ConstantVolume | 0.54 | 622.72 | 0.12 | 135.76 | 1161.25 | 1.00 | 2.87 | General | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 17:00:00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC FAN | Fan:ConstantVolume | 0.54 | 622.72 | 0.10 | 115.38 | 1161.25 | 1.00 | 3.17 | General | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 10:00:00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC FAN | Fan:ConstantVolume | 0.54 | 622.72 | 0.18 | 209.87 | 1161.25 | 1.00 | 2.27 | General | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 14:00:00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC FAN | Fan:ConstantVolume | 0.54 | 622.72 | 0.13 | 151.50 | 1161.25 | 1.00 | 2.70 | General | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 17:00:00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC FAN | Fan:ConstantVolume | 0.54 | 622.72 | 0.11 | 126.67 | 1161.25 | 1.00 | 2.99 | General | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 10:00:00 |
| Type | Control | Head [pa] | Water Flow [m3/s] | Electric Power [W] | Power Per Water Flow Rate [W-s/m3] | Motor Efficiency [W/W] | End Use Subcategory | |
| HOT WATER LOOP PUMP | Pump:VariableSpeed | Intermittent | 179344.02 | 0.000000 | 0.00 | - | 1.00 | General |
| OFFICE SHARED SERVICE WATER LOOP CIRCULATOR PUMP | Pump:ConstantSpeed | Intermittent | 29890.67 | 0.000002 | 0.08 | 46450.15 | 0.82 | General |
| Type | Storage Volume [m3] | Input [W] | Thermal Efficiency [W/W] | Recovery Efficiency [W/W] | Energy Factor | |
| 40GAL NATURALGAS WATER HEATER - 2KBTU/HR 0.82 THERM EFF | WaterHeater:Mixed | 0.15 | 503.37 | 0.82 | 0.22 | 1.32 |
Report: HVAC Sizing Summary
For: Entire Facility
Timestamp: 2020-03-22 22:58:43
Zone Sensible Cooling| Calculated Design Load [W] | User Design Load [W] | User Design Load per Area [W/m2] | Calculated Design Air Flow [m3/s] | User Design Air Flow [m3/s] | Design Day Name | Date/Time Of Peak {TIMESTAMP} | Thermostat Setpoint Temperature at Peak Load [C] | Indoor Temperature at Peak Load [C] | Indoor Humidity Ratio at Peak Load [kgWater/kgAir] | Outdoor Temperature at Peak Load [C] | Outdoor Humidity Ratio at Peak Load [kgWater/kgAir] | Minimum Outdoor Air Flow Rate [m3/s] | Heat Gain Rate from DOAS [W] | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND | 2104.04 | 2419.64 | 46.82 | 0.192 | 0.221 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 14:00:00 | 23.89 | 23.89 | 0.00875 | 33.00 | 0.00686 | 0.026 | 0.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND | 1317.10 | 1514.66 | 72.46 | 0.120 | 0.138 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 16:00:00 | 23.89 | 23.89 | 0.00861 | 32.09 | 0.00686 | 0.011 | 0.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND | 1144.63 | 1316.32 | 62.97 | 0.105 | 0.120 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 11:00:00 | 23.89 | 23.89 | 0.00863 | 29.50 | 0.00686 | 0.011 | 0.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND | 1382.74 | 1590.15 | 31.35 | 0.126 | 0.145 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 14:00:00 | 23.89 | 23.89 | 0.00901 | 33.00 | 0.00686 | 0.026 | 0.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND | 1112.55 | 1279.43 | 62.37 | 0.102 | 0.117 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 17:00:00 | 23.89 | 23.89 | 0.00869 | 30.87 | 0.00686 | 0.010 | 0.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND | 945.54 | 1087.37 | 53.00 | 0.086 | 0.099 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 10:00:00 | 23.89 | 23.89 | 0.00872 | 27.22 | 0.00686 | 0.010 | 0.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND | 1719.86 | 1977.84 | 38.27 | 0.157 | 0.181 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 14:00:00 | 23.89 | 23.89 | 0.00881 | 33.00 | 0.00686 | 0.026 | 0.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND | 1241.63 | 1427.87 | 68.31 | 0.113 | 0.130 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 17:00:00 | 23.89 | 23.89 | 0.00862 | 30.87 | 0.00686 | 0.011 | 0.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND | 1038.08 | 1193.80 | 57.11 | 0.095 | 0.109 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 10:00:00 | 23.89 | 23.89 | 0.00864 | 27.22 | 0.00686 | 0.011 | 0.00 |
| Calculated Design Load [W] | User Design Load [W] | User Design Load per Area [W/m2] | Calculated Design Air Flow [m3/s] | User Design Air Flow [m3/s] | Design Day Name | Date/Time Of Peak {TIMESTAMP} | Thermostat Setpoint Temperature at Peak Load [C] | Indoor Temperature at Peak Load [C] | Indoor Humidity Ratio at Peak Load [kgWater/kgAir] | Outdoor Temperature at Peak Load [C] | Outdoor Humidity Ratio at Peak Load [kgWater/kgAir] | Minimum Outdoor Air Flow Rate [m3/s] | Heat Gain Rate from DOAS [W] | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND | 2155.27 | 2694.09 | 52.13 | 0.076 | 0.095 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 21.11 | 21.11 | 0.00743 | -18.80 | 0.00089 | 0.026 | 0.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND | 1402.05 | 1752.56 | 83.84 | 0.049 | 0.062 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 21.11 | 21.10 | 0.00731 | -18.80 | 0.00089 | 0.011 | 0.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND | 1404.29 | 1755.36 | 83.98 | 0.049 | 0.062 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 21.11 | 21.10 | 0.00731 | -18.80 | 0.00089 | 0.011 | 0.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND | 961.45 | 1201.81 | 23.70 | 0.034 | 0.042 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 21.11 | 21.11 | 0.00800 | -18.80 | 0.00089 | 0.026 | 0.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND | 898.06 | 1122.58 | 54.72 | 0.032 | 0.039 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 21.11 | 21.11 | 0.00746 | -18.80 | 0.00089 | 0.010 | 0.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND | 900.30 | 1125.37 | 54.86 | 0.032 | 0.040 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 21.11 | 21.11 | 0.00746 | -18.80 | 0.00089 | 0.010 | 0.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND | 2143.27 | 2679.09 | 51.84 | 0.075 | 0.094 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 21.11 | 21.11 | 0.00743 | -18.80 | 0.00089 | 0.026 | 0.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND | 1401.23 | 1751.53 | 83.79 | 0.049 | 0.062 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 21.11 | 21.10 | 0.00731 | -18.80 | 0.00089 | 0.011 | 0.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND | 1403.47 | 1754.34 | 83.93 | 0.049 | 0.062 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 21.11 | 21.10 | 0.00731 | -18.80 | 0.00089 | 0.011 | 0.00 |
| Calculated cooling [m3/s] | User cooling [m3/s] | Calculated heating [m3/s] | User heating [m3/s] | Adjusted cooling [m3/s] | Adjusted heating [m3/s] | Adjusted main [m3/s] | Calculated Heating Air Flow Ratio [] | User Heating Air Flow Ratio [] | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC | 0.22 | 0.22 | 0.09 | 0.09 | 0.2211 | 0.0947 | 0.2211 | 0.4285 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC | 0.14 | 0.14 | 0.06 | 0.06 | 0.1384 | 0.0616 | 0.1384 | 0.4453 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC | 0.12 | 0.12 | 0.06 | 0.06 | 0.1203 | 0.0617 | 0.1203 | 0.5132 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC | 0.15 | 0.15 | 0.04 | 0.04 | 0.1453 | 0.0423 | 0.1453 | 0.2909 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC | 0.12 | 0.12 | 0.04 | 0.04 | 0.1169 | 0.0395 | 0.1169 | 0.3377 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC | 0.10 | 0.10 | 0.04 | 0.04 | 0.0994 | 0.0396 | 0.0994 | 0.3983 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC | 0.18 | 0.18 | 0.09 | 0.09 | 0.1807 | 0.0942 | 0.1807 | 0.5213 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC | 0.13 | 0.13 | 0.06 | 0.06 | 0.1305 | 0.0616 | 0.1305 | 0.4721 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC | 0.11 | 0.11 | 0.06 | 0.06 | 0.1091 | 0.0617 | 0.1091 | 0.5656 | 1.0000 |
| Previous Design Volume Flow Rate [m3/s] | Algorithm Volume Flow Rate [m3/s] | Coincident Design Volume Flow Rate [m3/s] | Coincident Size Adjusted | Peak Sizing Period Name | Peak Day into Period {TIMESTAMP}[day] | Peak Hour Of Day {TIMESTAMP}[hr] | Peak Step Start Minute {TIMESTAMP}[min] | |
| None |
| Coil Type | HVAC Type | HVAC Name | Coil Final Gross Total Capacity [W] | Coil Final Gross Sensible Capacity [W] | Coil Final Reference Air Volume Flow Rate [m3/s] | Coil Final Reference Plant Fluid Volume Flow Rate [m3/s] | Coil U-value Times Area Value [W/K] | Design Day Name at Sensible Ideal Loads Peak | Date/Time at Sensible Ideal Loads Peak | Design Day Name at Air Flow Ideal Loads Peak | Date/Time at Air Flow Ideal Loads Peak | Coil Total Capacity at Ideal Loads Peak [W] | Coil Sensible Capacity at Ideal Loads Peak [W] | Coil Air Volume Flow Rate at Ideal Loads Peak [m3/s] | Coil Entering Air Drybulb at Ideal Loads Peak [C] | Coil Entering Air Wetbulb at Ideal Loads Peak [C] | Coil Entering Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Coil Leaving Air Drybulb at Ideal Loads Peak [C] | Coil Leaving Air Wetbulb at Ideal Loads Peak [C] | Coil Leaving Air Humidity Ratio at Ideal Loads Peak [C] | Outdoor Air Drybulb at Ideal Loads Peak [C] | Outdoor Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Outdoor Air Wetbulb at Ideal Loads Peak [C] | Outdoor Air Flow Percentage at Ideal Loads Peak [%] | Zone Air Drybulb at Ideal Loads Peak [C] | Zone Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Zone Air Relative Humidity at Ideal Loads Peak [%] | Zone Sensible Heat Gain at Ideal Loads Peak [W] | Zone Latent Heat Gain at Ideal Loads Peak [W] | Coil Total Capacity at Rating Conditions [W] | Coil Sensible Capacity at Rating Conditions [W] | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 12KBTU/HR 9.7SEER | Coil:Cooling:DX:SingleSpeed | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC | 3659.918 | 2930.333 | 0.221096 | -999.0 | -999.000 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 14:00:00 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 14:00:00 | 4144.81 | 4130.33 | 0.221096 | 24.97 | 14.44 | 0.00852343 | 11.60 | 9.62 | 0.00850000 | 33.00 | 0.00686230 | 15.70 | 11.8732 | 23.89 | 0.00874723 | 37.9773 | 1832.01 | 0.00 | 3654.08 | 2637.27 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC GAS HTG COIL | Coil:Heating:Fuel | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC | 7211.043 | 7211.043 | -999.0 | -999.0 | -999.000 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 7211.04 | 7211.04 | 0.221096 | 10.05 | 6.02 | 0.00561871 | 50.00 | 21.21 | 0.00800000 | -18.80 | 0.00088830 | -18.80 | 11.8732 | 21.11 | 0.00743162 | 38.2876 | 2155.27 | 0.00 | -999.00 | -999.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | Coil:Heating:Electric | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC | 7211.043 | 7211.043 | -999.0 | -999.0 | -999.000 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 7211.04 | 7211.04 | 0.221096 | 10.05 | 6.02 | 0.00561871 | 50.00 | 21.21 | 0.00800000 | -18.80 | 0.00088830 | -18.80 | 11.8732 | 21.11 | 0.00743162 | 38.2876 | 2155.27 | 0.00 | -999.00 | -999.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 8KBTU/HR 9.7SEER | Coil:Cooling:DX:SingleSpeed | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC | 2290.905 | 1834.225 | 0.138394 | -999.0 | -999.000 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 16:00:00 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 16:00:00 | 2585.40 | 2585.40 | 0.138394 | 24.52 | 14.25 | 0.00847836 | 11.60 | 9.60 | 0.00847836 | 32.09 | 0.00686229 | 15.41 | 7.6729 | 23.89 | 0.00861266 | 37.3994 | 1317.10 | 0.00 | 2287.25 | 1650.78 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC GAS HTG COIL | Coil:Heating:Fuel | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC | 4289.020 | 4289.020 | -999.0 | -999.0 | -999.000 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 4289.02 | 4289.02 | 0.138394 | 14.23 | 8.42 | 0.00620074 | 50.00 | 21.21 | 0.00800000 | -18.80 | 0.00088830 | -18.80 | 7.6729 | 21.10 | 0.00730659 | 37.6560 | 1402.05 | 0.00 | -999.00 | -999.00 |