Table of Contents
Program Version:EnergyPlus, Version 8.6.0-198c6a3cff, YMD=2016.12.10 12:34
Tabular Output Report in Format: HTML
Building: Building 1
Environment: RUN PERIOD 1 ** New York Laguardia Arpt NY USA TMY3 WMO#=725030
Simulation Timestamp: 2016-12-10
12:34:41
Table of Contents
Report: Annual Building Utility Performance Summary
For: Entire Facility
Timestamp: 2016-12-10
12:34:41
Values gathered over 8760.00 hours
Site and Source Energy
|
Total Energy [GJ] |
Energy Per Total Building Area [MJ/m2] |
Energy Per Conditioned Building Area [MJ/m2] |
| Total Site Energy |
3156.24 |
631.25 |
631.25 |
| Net Site Energy |
3156.24 |
631.25 |
631.25 |
| Total Source Energy |
6651.55 |
1330.31 |
1330.31 |
| Net Source Energy |
6651.55 |
1330.31 |
1330.31 |
Site to Source Energy Conversion Factors
|
Site=>Source Conversion Factor |
| Electricity |
3.167 |
| Natural Gas |
1.084 |
| District Cooling |
1.056 |
| District Heating |
3.613 |
| Steam |
0.300 |
| Gasoline |
1.050 |
| Diesel |
1.050 |
| Coal |
1.050 |
| Fuel Oil #1 |
1.050 |
| Fuel Oil #2 |
1.050 |
| Propane |
1.050 |
| Other Fuel 1 |
1.000 |
| Other Fuel 2 |
1.000 |
Building Area
|
Area [m2] |
| Total Building Area |
5000.00 |
| Net Conditioned Building Area |
5000.00 |
| Unconditioned Building Area |
0.00 |
End Uses
|
Electricity [GJ] |
Natural Gas [GJ] |
Additional Fuel [GJ] |
District Cooling [GJ] |
District Heating [GJ] |
Water [m3] |
| Heating |
84.45 |
1605.50 |
0.00 |
0.00 |
0.00 |
0.00 |
| Cooling |
544.01 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Interior Lighting |
459.78 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Exterior Lighting |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Interior Equipment |
0.92 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Exterior Equipment |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Fans |
461.57 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Pumps |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Heat Rejection |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Humidification |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Heat Recovery |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Water Systems |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Refrigeration |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Generators |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| |
|
|
|
|
|
|
| Total End Uses |
1550.74 |
1605.50 |
0.00 |
0.00 |
0.00 |
0.00 |
Note: Natural gas appears to be the principal heating source based on energy usage.
End Uses By Subcategory
|
Subcategory |
Electricity [GJ] |
Natural Gas [GJ] |
Additional Fuel [GJ] |
District Cooling [GJ] |
District Heating [GJ] |
Water [m3] |
| Heating |
General |
84.45 |
1605.50 |
0.00 |
0.00 |
0.00 |
0.00 |
| Cooling |
General |
544.01 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Interior Lighting |
General |
459.78 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Exterior Lighting |
General |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Interior Equipment |
ElectricEquipment |
0.92 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Exterior Equipment |
General |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Fans |
General |
461.57 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Pumps |
General |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Heat Rejection |
General |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Humidification |
General |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Heat Recovery |
General |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Water Systems |
General |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Refrigeration |
General |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Generators |
General |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
Normalized Metrics
Utility Use Per Conditioned Floor Area
|
Electricity Intensity [MJ/m2] |
Natural Gas Intensity [MJ/m2] |
Additional Fuel Intensity [MJ/m2] |
District Cooling Intensity [MJ/m2] |
District Heating Intensity [MJ/m2] |
Water Intensity [m3/m2] |
| Lighting |
91.96 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| HVAC |
218.01 |
321.10 |
0.00 |
0.00 |
0.00 |
0.00 |
| Other |
0.18 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Total |
310.15 |
321.10 |
0.00 |
0.00 |
0.00 |
0.00 |
Utility Use Per Total Floor Area
|
Electricity Intensity [MJ/m2] |
Natural Gas Intensity [MJ/m2] |
Additional Fuel Intensity [MJ/m2] |
District Cooling Intensity [MJ/m2] |
District Heating Intensity [MJ/m2] |
Water Intensity [m3/m2] |
| Lighting |
91.96 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| HVAC |
218.01 |
321.10 |
0.00 |
0.00 |
0.00 |
0.00 |
| Other |
0.18 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Total |
310.15 |
321.10 |
0.00 |
0.00 |
0.00 |
0.00 |
Electric Loads Satisfied
|
Electricity [GJ] |
Percent Electricity [%] |
| Fuel-Fired Power Generation |
0.000 |
0.00 |
| High Temperature Geothermal* |
0.000 |
0.00 |
| Photovoltaic Power |
0.000 |
0.00 |
| Wind Power |
0.000 |
0.00 |
| Power Conversion |
0.000 |
0.00 |
| Net Decrease in On-Site Storage |
0.000 |
0.00 |
| Total On-Site Electric Sources |
0.000 |
0.00 |
| |
|
|
| Electricity Coming From Utility |
1550.738 |
100.00 |
| Surplus Electricity Going To Utility |
0.000 |
0.00 |
| Net Electricity From Utility |
1550.738 |
100.00 |
| |
|
|
| Total On-Site and Utility Electric Sources |
1550.738 |
100.00 |
| Total Electricity End Uses |
1550.738 |
100.00 |
On-Site Thermal Sources
|
Heat [GJ] |
Percent Heat [%] |
| Water-Side Heat Recovery |
0.00 |
|
| Air to Air Heat Recovery for Cooling |
0.00 |
|
| Air to Air Heat Recovery for Heating |
0.00 |
|
| High-Temperature Geothermal* |
0.00 |
|
| Solar Water Thermal |
0.00 |
|
| Solar Air Thermal |
0.00 |
|
| Total On-Site Thermal Sources |
0.00 |
|
Water Source Summary
|
Water [m3] |
Percent Water [%] |
| Rainwater Collection |
0.00 |
- |
| Condensate Collection |
0.00 |
- |
| Groundwater Well |
0.00 |
- |
| Total On Site Water Sources |
0.00 |
- |
| - |
- |
- |
| Initial Storage |
0.00 |
- |
| Final Storage |
0.00 |
- |
| Change in Storage |
0.00 |
- |
| - |
- |
- |
| Water Supplied by Utility |
0.00 |
- |
| - |
- |
- |
| Total On Site, Change in Storage, and Utility Water Sources |
0.00 |
- |
| Total Water End Uses |
0.00 |
- |
Setpoint Not Met Criteria
|
Degrees [deltaC] |
| Tolerance for Zone Heating Setpoint Not Met Time |
0.20 |
| Tolerance for Zone Cooling Setpoint Not Met Time |
0.20 |
Comfort and Setpoint Not Met Summary
|
Facility [Hours] |
| Time Setpoint Not Met During Occupied Heating |
419.67 |
| Time Setpoint Not Met During Occupied Cooling |
192.00 |
| Time Not Comfortable Based on Simple ASHRAE 55-2004 |
2989.33 |
Note 1: An asterisk (*) indicates that the feature is not yet implemented.
Table of Contents
Top
Annual Building Utility Performance Summary
Input Verification and Results Summary
Demand End Use Components Summary
Source Energy End Use Components Summary
Component Sizing Summary
Surface Shadowing Summary
Adaptive Comfort Summary
Climatic Data Summary
Envelope Summary
Shading Summary
Lighting Summary
Equipment Summary
HVAC Sizing Summary
System Summary
Outdoor Air Summary
Object Count Summary
Energy Meters
Sensible Heat Gain Summary
Standard 62.1 Summary
LEED Summary
Life-Cycle Cost Report
|
Entire Facility |
Table of Contents
Report: Input Verification and Results Summary
For: Entire Facility
Timestamp: 2016-12-10
12:34:41
General
|
Value |
| Program Version and Build |
EnergyPlus, Version 8.6.0-198c6a3cff, YMD=2016.12.10 12:34 |
| RunPeriod |
RUN PERIOD 1 |
| Weather File |
New York Laguardia Arpt NY USA TMY3 WMO#=725030 |
| Latitude [deg] |
40.78 |
| Longitude [deg] |
-73.9 |
| Elevation [m] |
3.00 |
| Time Zone |
-5.0 |
| North Axis Angle [deg] |
0.00 |
| Rotation for Appendix G [deg] |
0.00 |
| Hours Simulated [hrs] |
8760.00 |
ENVELOPE
Window-Wall Ratio
|
Total |
North (315 to 45 deg) |
East (45 to 135 deg) |
South (135 to 225 deg) |
West (225 to 315 deg) |
| Gross Wall Area [m2] |
2262.74 |
565.69 |
565.69 |
565.69 |
565.69 |
| Above Ground Wall Area [m2] |
2262.74 |
565.69 |
565.69 |
565.69 |
565.69 |
| Window Opening Area [m2] |
678.82 |
169.71 |
339.41 |
0.00 |
169.71 |
| Gross Window-Wall Ratio [%] |
30.00 |
30.00 |
60.00 |
0.00 |
30.00 |
| Above Ground Window-Wall Ratio [%] |
30.00 |
30.00 |
60.00 |
0.00 |
30.00 |
Conditioned Window-Wall Ratio
|
Total |
North (315 to 45 deg) |
East (45 to 135 deg) |
South (135 to 225 deg) |
West (225 to 315 deg) |
| Gross Wall Area [m2] |
2262.74 |
565.69 |
565.69 |
565.69 |
565.69 |
| Above Ground Wall Area [m2] |
2262.74 |
565.69 |
565.69 |
565.69 |
565.69 |
| Window Opening Area [m2] |
678.82 |
169.71 |
339.41 |
0.00 |
169.71 |
| Gross Window-Wall Ratio [%] |
30.00 |
30.00 |
60.00 |
0.00 |
30.00 |
| Above Ground Window-Wall Ratio [%] |
30.00 |
30.00 |
60.00 |
0.00 |
30.00 |
Skylight-Roof Ratio
|
Total |
| Gross Roof Area [m2] |
1250.00 |
| Skylight Area [m2] |
0.00 |
| Skylight-Roof Ratio [%] |
0.00 |
PERFORMANCE
Zone Summary
|
Area [m2] |
Conditioned (Y/N) |
Part of Total Floor Area (Y/N) |
Volume [m3] |
Multipliers |
Above Ground Gross Wall Area [m2] |
Underground Gross Wall Area [m2] |
Window Glass Area [m2] |
Opening Area [m2] |
Lighting [W/m2] |
People [m2 per person] |
Plug and Process [W/m2] |
| OFFICE--OPENOFFICE1 |
151.78 |
Yes |
Yes |
607.11 |
1.00 |
141.42 |
0.00 |
42.43 |
42.43 |
10.7639 |
92.90 |
0.0108 |
| OFFICE--OPENOFFICE10 |
151.78 |
Yes |
Yes |
607.11 |
1.00 |
141.42 |
0.00 |
42.43 |
42.43 |
10.7639 |
92.90 |
0.0108 |
| OFFICE--OPENOFFICE11 |
151.78 |
Yes |
Yes |
607.11 |
1.00 |
141.42 |
0.00 |
42.43 |
42.43 |
10.7639 |
92.90 |
0.0108 |
| OFFICE--OPENOFFICE12 |
151.78 |
Yes |
Yes |
607.11 |
1.00 |
141.42 |
0.00 |
42.43 |
42.43 |
10.7639 |
92.90 |
0.0108 |
| OFFICE--OPENOFFICE13 |
642.89 |
Yes |
Yes |
2571.57 |
1.00 |
0.00 |
0.00 |
0.00 |
0.00 |
10.7639 |
929.03 |
0.0108 |
| OFFICE--OPENOFFICE14 |
151.78 |
Yes |
Yes |
607.11 |
1.00 |
141.42 |
0.00 |
42.43 |
42.43 |
10.7639 |
92.90 |
0.0108 |
| OFFICE--OPENOFFICE15 |
151.78 |
Yes |
Yes |
607.11 |
1.00 |
141.42 |
0.00 |
42.43 |
42.43 |
10.7639 |
92.90 |
0.0108 |
| OFFICE--OPENOFFICE16 |
151.78 |
Yes |
Yes |
607.11 |
1.00 |
141.42 |
0.00 |
42.43 |
42.43 |
10.7639 |
92.90 |
0.0108 |
| OFFICE--OPENOFFICE17 |
151.78 |
Yes |
Yes |
607.11 |
1.00 |
141.42 |
0.00 |
42.43 |
42.43 |
10.7639 |
92.90 |
0.0108 |
| OFFICE--OPENOFFICE18 |
642.89 |
Yes |
Yes |
2571.57 |
1.00 |
0.00 |
0.00 |
0.00 |
0.00 |
10.7639 |
929.03 |
0.0108 |
| OFFICE--OPENOFFICE19 |
151.78 |
Yes |
Yes |
607.11 |
1.00 |
141.42 |
0.00 |
42.43 |
42.43 |
10.7639 |
92.90 |
0.0108 |
| OFFICE--OPENOFFICE2 |
151.78 |
Yes |
Yes |
607.11 |
1.00 |
141.42 |
0.00 |
42.43 |
42.43 |
10.7639 |
92.90 |
0.0108 |
| OFFICE--OPENOFFICE20 |
151.78 |
Yes |
Yes |
607.11 |
1.00 |
141.42 |
0.00 |
42.43 |
42.43 |
10.7639 |
92.90 |
0.0108 |
| OFFICE--OPENOFFICE3 |
642.89 |
Yes |
Yes |
2571.57 |
1.00 |
0.00 |
0.00 |
0.00 |
0.00 |
10.7639 |
929.03 |
0.0108 |
| OFFICE--OPENOFFICE4 |
151.78 |
Yes |
Yes |
607.11 |
1.00 |
141.42 |
0.00 |
42.43 |
42.43 |
10.7639 |
92.90 |
0.0108 |
| OFFICE--OPENOFFICE5 |
151.78 |
Yes |
Yes |
607.11 |
1.00 |
141.42 |
0.00 |
42.43 |
42.43 |
10.7639 |
92.90 |
0.0108 |
| OFFICE--OPENOFFICE6 |
151.78 |
Yes |
Yes |
607.11 |
1.00 |
141.42 |
0.00 |
42.43 |
42.43 |
10.7639 |
92.90 |
0.0108 |
| OFFICE--OPENOFFICE7 |
151.78 |
Yes |
Yes |
607.11 |
1.00 |
141.42 |
0.00 |
42.43 |
42.43 |
10.7639 |
92.90 |
0.0108 |
| OFFICE--OPENOFFICE8 |
642.89 |
Yes |
Yes |
2571.57 |
1.00 |
0.00 |
0.00 |
0.00 |
0.00 |
10.7639 |
929.03 |
0.0108 |
| OFFICE--OPENOFFICE9 |
151.78 |
Yes |
Yes |
607.11 |
1.00 |
141.42 |
0.00 |
42.43 |
42.43 |
10.7639 |
92.90 |
0.0108 |
| Total |
5000.00 |
|
|
20000.00 |
|
2262.74 |
0.00 |
678.82 |
678.82 |
10.7639 |
172.97 |
0.0108 |
| Conditioned Total |
5000.00 |
|
|
20000.00 |
|
2262.74 |
0.00 |
678.82 |
678.82 |
10.7639 |
172.97 |
0.0108 |
| Unconditioned Total |
0.00 |
|
|
0.00 |
|
0.00 |
0.00 |
0.00 |
0.00 |
|
|
|
| Not Part of Total |
0.00 |
|
|
0.00 |
|
0.00 |
0.00 |
0.00 |
0.00 |
|
|
|
Table of Contents
Report: Demand End Use Components Summary
For: Entire Facility
Timestamp: 2016-12-10
12:34:41
End Uses
|
Electricity [W] |
Natural Gas [W] |
Propane [W] |
District Cooling [W] |
Steam [W] |
Water [m3/s] |
| Time of Peak |
06-JUL-13:00 |
06-FEB-04:10 |
- |
- |
- |
- |
| Heating |
0.00 |
232806.38 |
0.00 |
0.00 |
0.00 |
0.00 |
| Cooling |
100168.35 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Interior Lighting |
31969.79 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Exterior Lighting |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Interior Equipment |
48.44 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Exterior Equipment |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Fans |
14636.29 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Pumps |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Heat Rejection |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Humidification |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Heat Recovery |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Water Systems |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Refrigeration |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Generators |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| |
|
|
|
|
|
|
| Total End Uses |
146822.87 |
232806.38 |
0.00 |
0.00 |
0.00 |
0.00 |
End Uses By Subcategory
|
Subcategory |
Electricity [W] |
Natural Gas [W] |
Propane [W] |
District Cooling [W] |
Steam [W] |
Water [m3/s] |
| Heating |
General |
0.00 |
232806.38 |
0.00 |
0.00 |
0.00 |
0.00 |
| Cooling |
General |
100168.35 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Interior Lighting |
General |
31969.79 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Exterior Lighting |
General |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Interior Equipment |
ElectricEquipment |
48.44 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Exterior Equipment |
General |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Fans |
General |
14636.29 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Pumps |
General |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Heat Rejection |
General |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Humidification |
General |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Heat Recovery |
General |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Water Systems |
General |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Refrigeration |
General |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Generators |
General |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
Table of Contents
Report: Source Energy End Use Components Summary
For: Entire Facility
Timestamp: 2016-12-10
12:34:41
Values gathered over 8760.00 hours
Source Energy End Use Components Summary
|
Source Electricity [GJ] |
Source Natural Gas [GJ] |
Source Additional Fuel [GJ] |
Source District Cooling [GJ] |
Source District Heating [GJ] |
| Heating |
267.46 |
1740.36 |
0.00 |
0.00 |
0.00 |
| Cooling |
1722.89 |
0.00 |
0.00 |
0.00 |
0.00 |
| Interior Lighting |
1456.13 |
0.00 |
0.00 |
0.00 |
0.00 |
| Exterior Lighting |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Interior Equipment |
2.91 |
0.00 |
0.00 |
0.00 |
0.00 |
| Exterior Equipment |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Fans |
1461.79 |
0.00 |
0.00 |
0.00 |
0.00 |
| Pumps |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Heat Rejection |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Humidification |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Heat Recovery |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Water Systems |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Refrigeration |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Generators |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| |
|
|
|
|
|
| Total Source Energy End Use Components |
4911.19 |
1740.36 |
0.00 |
0.00 |
0.00 |
Normalized Metrics
Source Energy End Use Components Per Conditioned Floor Area
|
Source Electricity [MJ/m2] |
Source Natural Gas [MJ/m2] |
Source Additional Fuel [MJ/m2] |
Source District Cooling [MJ/m2] |
Source District Heating [MJ/m2] |
| Heating |
53.49 |
348.07 |
0.00 |
0.00 |
0.00 |
| Cooling |
344.58 |
0.00 |
0.00 |
0.00 |
0.00 |
| Interior Lighting |
291.23 |
0.00 |
0.00 |
0.00 |
0.00 |
| Exterior Lighting |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Interior Equipment |
0.58 |
0.00 |
0.00 |
0.00 |
0.00 |
| Exterior Equipment |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Fans |
292.36 |
0.00 |
0.00 |
0.00 |
0.00 |
| Pumps |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Heat Rejection |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Humidification |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Heat Recovery |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Water Systems |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Refrigeration |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Generators |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| |
|
|
|
|
|
| Total Source Energy End Use Components |
982.24 |
348.07 |
0.00 |
0.00 |
0.00 |
Source Energy End Use Components Per Total Floor Area
|
Source Electricity [MJ/m2] |
Source Natural Gas [MJ/m2] |
Source Additional Fuel [MJ/m2] |
Source District Cooling [MJ/m2] |
Source District Heating [MJ/m2] |
| Heating |
53.49 |
348.07 |
0.00 |
0.00 |
0.00 |
| Cooling |
344.58 |
0.00 |
0.00 |
0.00 |
0.00 |
| Interior Lighting |
291.23 |
0.00 |
0.00 |
0.00 |
0.00 |
| Exterior Lighting |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Interior Equipment |
0.58 |
0.00 |
0.00 |
0.00 |
0.00 |
| Exterior Equipment |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Fans |
292.36 |
0.00 |
0.00 |
0.00 |
0.00 |
| Pumps |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Heat Rejection |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Humidification |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Heat Recovery |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Water Systems |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Refrigeration |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Generators |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| |
|
|
|
|
|
| Total Source Energy End Use Components |
982.24 |
348.07 |
0.00 |
0.00 |
0.00 |
Table of Contents
Report: Climatic Data Summary
For: Entire Facility
Timestamp: 2016-12-10
12:34:41
SizingPeriod:DesignDay
|
Maximum Dry Bulb [C] |
Daily Temperature Range [deltaC] |
Humidity Value |
Humidity Type |
Wind Speed [m/s] |
Wind Direction |
| NEW YORK LAGUARDIA ARPT ANN CLG .4% CONDNS DB=>MWB |
33.50 |
7.70 |
23.50 |
Wetbulb [C] |
5.60 |
270.00 |
| NEW YORK LAGUARDIA ARPT ANN HTG 99.6% CONDNS DB |
-10.80 |
0.00 |
-10.80 |
Wetbulb [C] |
7.50 |
320.00 |
Weather Statistics File
|
Value |
| Reference |
USA_NY_New.York-LaGuardia.AP.725030_TMY3 |
| Site:Location |
New York Laguardia Arpt NY USA |
| Latitude |
{N 40° 46'} |
| Longitude |
{W 73° 52'} |
| Time Zone |
{GMT -5.0 Hours} |
| Elevation (m) above sea level |
3 |
| Standard Pressure at Elevation |
101289Pa |
| Data Source |
TMY3 |
| WMO Station |
725030 |
| Weather File Design Conditions |
Climate Design Data 2009 ASHRAE Handbook |
| Heating Design Temperature 99.6% (C) |
-10.8° |
| Heating Design Temperature 99% (C) |
-8.2° |
| Cooling Design Temperature 0.4% (C) |
33.5° |
| Cooling Design Temperature 1% (C) |
31.8° |
| Cooling Design Temperature 2% (C) |
30.3° |
| Maximum Dry Bulb Temperature (C) |
36.7° |
| Maximum Dry Bulb Occurs on |
Jul 13 |
| Minimum Dry Bulb Temperature (C) |
-15.0° |
| Minimum Dry Bulb Occurs on |
Feb 6 |
| Maximum Dew Point Temperature (C) |
25.0° |
| Maximum Dew Point Occurs on |
Jul 20 |
| Minimum Dew Point Temperature (C) |
-23.3° |
| Minimum Dew Point Occurs on |
Feb 6 |
| ASHRAE Handbook 2009 Cooling Degree-Days (base 10°C) |
2118 |
| Weather File Cooling Degree-Days (base 10°C) |
2201 |
| ASHRAE Handbook 2009 Heating Degree-Days (base 18.3°C) |
2557 |
| Weather File Heating Degree-Days (base 18°C) |
2368 |
| Köppen Classification |
Cfa |
| Köppen Description |
Humid subtropical (mild with no dry season, hot summer, lat. 20-35°N) |
| Köppen Recommendation |
|
| ASHRAE Climate Zone |
4A |
| ASHRAE Description |
Mixed-Humid |
Table of Contents
Report: Envelope Summary
For: Entire Facility
Timestamp: 2016-12-10
12:34:41
Opaque Exterior
|
Construction |
Reflectance |
U-Factor with Film [W/m2-K] |
U-Factor no Film [W/m2-K] |
Gross Area [m2] |
Net Area [m2] |
Azimuth [deg] |
Tilt [deg] |
Cardinal Direction |
| OFFICE--OPENOFFICE1_SRF_4 |
WALL |
0.40 |
0.358 |
0.379 |
141.42 |
98.99 |
135.00 |
90.00 |
S |
| OFFICE--OPENOFFICE1_SRF_0 |
INTERIOR FLOOR |
0.70 |
1.174 |
1.449 |
151.78 |
151.78 |
135.00 |
180.00 |
|
| OFFICE--OPENOFFICE10_SRF_4 |
WALL |
0.40 |
0.358 |
0.379 |
141.42 |
98.99 |
225.00 |
90.00 |
W |
| OFFICE--OPENOFFICE11_SRF_4 |
WALL |
0.40 |
0.358 |
0.379 |
141.42 |
98.99 |
135.00 |
90.00 |
S |
| OFFICE--OPENOFFICE12_SRF_4 |
WALL |
0.40 |
0.358 |
0.379 |
141.42 |
98.99 |
45.00 |
90.00 |
E |
| OFFICE--OPENOFFICE14_SRF_4 |
WALL |
0.40 |
0.358 |
0.379 |
141.42 |
98.99 |
315.00 |
90.00 |
N |
| OFFICE--OPENOFFICE15_SRF_4 |
WALL |
0.40 |
0.358 |
0.379 |
141.42 |
98.99 |
225.00 |
90.00 |
W |
| OFFICE--OPENOFFICE16_SRF_4 |
WALL |
0.40 |
0.358 |
0.379 |
141.42 |
98.99 |
135.00 |
90.00 |
S |
| OFFICE--OPENOFFICE16_SRF_5 |
ROOF |
0.40 |
0.273 |
0.284 |
151.78 |
151.78 |
315.00 |
0.00 |
|
| OFFICE--OPENOFFICE17_SRF_4 |
WALL |
0.40 |
0.358 |
0.379 |
141.42 |
98.99 |
45.00 |
90.00 |
E |
| OFFICE--OPENOFFICE17_SRF_5 |
ROOF |
0.40 |
0.273 |
0.284 |
151.78 |
151.78 |
225.00 |
0.00 |
|
| OFFICE--OPENOFFICE18_SRF_5 |
ROOF |
0.40 |
0.273 |
0.284 |
642.89 |
642.89 |
225.00 |
0.00 |
|
| OFFICE--OPENOFFICE19_SRF_4 |
WALL |
0.40 |
0.358 |
0.379 |
141.42 |
98.99 |
315.00 |
90.00 |
N |
| OFFICE--OPENOFFICE19_SRF_5 |
ROOF |
0.40 |
0.273 |
0.284 |
151.78 |
151.78 |
135.00 |
0.00 |
|
| OFFICE--OPENOFFICE2_SRF_4 |
WALL |
0.40 |
0.358 |
0.379 |
141.42 |
98.99 |
45.00 |
90.00 |
E |
| OFFICE--OPENOFFICE2_SRF_0 |
INTERIOR FLOOR |
0.70 |
1.174 |
1.449 |
151.78 |
151.78 |
45.00 |
180.00 |
|
| OFFICE--OPENOFFICE20_SRF_4 |
WALL |
0.40 |
0.358 |
0.379 |
141.42 |
98.99 |
225.00 |
90.00 |
W |
| OFFICE--OPENOFFICE20_SRF_5 |
ROOF |
0.40 |
0.273 |
0.284 |
151.78 |
151.78 |
225.00 |
0.00 |
|
| OFFICE--OPENOFFICE3_SRF_0 |
INTERIOR FLOOR |
0.70 |
1.174 |
1.449 |
642.89 |
642.89 |
45.00 |
180.00 |
|
| OFFICE--OPENOFFICE4_SRF_4 |
WALL |
0.40 |
0.358 |
0.379 |
141.42 |
98.99 |
315.00 |
90.00 |
N |
| OFFICE--OPENOFFICE4_SRF_0 |
INTERIOR FLOOR |
0.70 |
1.174 |
1.449 |
151.78 |
151.78 |
315.00 |
180.00 |
|
| OFFICE--OPENOFFICE5_SRF_4 |
WALL |
0.40 |
0.358 |
0.379 |
141.42 |
98.99 |
225.00 |
90.00 |
W |
| OFFICE--OPENOFFICE5_SRF_0 |
INTERIOR FLOOR |
0.70 |
1.174 |
1.449 |
151.78 |
151.78 |
45.00 |
180.00 |
|
| OFFICE--OPENOFFICE6_SRF_4 |
WALL |
0.40 |
0.358 |
0.379 |
141.42 |
98.99 |
135.00 |
90.00 |
S |
| OFFICE--OPENOFFICE7_SRF_4 |
WALL |
0.40 |
0.358 |
0.379 |
141.42 |
98.99 |
45.00 |
90.00 |
E |
| OFFICE--OPENOFFICE9_SRF_4 |
WALL |
0.40 |
0.358 |
0.379 |
141.42 |
98.99 |
315.00 |
90.00 |
N |
Exterior Fenestration
|
Construction |
Glass Area [m2] |
Frame Area [m2] |
Divider Area [m2] |
Area of One Opening [m2] |
Area of Multiplied Openings [m2] |
Glass U-Factor [W/m2-K] |
Glass SHGC |
Glass Visible Transmittance |
Frame Conductance [W/m2-K] |
Divider Conductance [W/m2-K] |
Shade Control |
Parent Surface |
Azimuth [deg] |
Tilt [deg] |
Cardinal Direction |
| OFFICE--OPENOFFICE1_SRF_4_GLZ_0 |
EXTERIOR WINDOW |
42.43 |
0.00 |
0.00 |
42.43 |
42.43 |
2.720 |
0.761 |
0.807 |
|
|
No |
OFFICE--OPENOFFICE1_SRF_4 |
135.00 |
90.00 |
E |
| OFFICE--OPENOFFICE10_SRF_4_GLZ_0 |
EXTERIOR WINDOW |
42.43 |
0.00 |
0.00 |
42.43 |
42.43 |
2.720 |
0.761 |
0.807 |
|
|
No |
OFFICE--OPENOFFICE10_SRF_4 |
225.00 |
90.00 |
W |
| OFFICE--OPENOFFICE11_SRF_4_GLZ_0 |
EXTERIOR WINDOW |
42.43 |
0.00 |
0.00 |
42.43 |
42.43 |
2.720 |
0.761 |
0.807 |
|
|
No |
OFFICE--OPENOFFICE11_SRF_4 |
135.00 |
90.00 |
E |
| OFFICE--OPENOFFICE12_SRF_4_GLZ_0 |
EXTERIOR WINDOW |
42.43 |
0.00 |
0.00 |
42.43 |
42.43 |
2.720 |
0.761 |
0.807 |
|
|
No |
OFFICE--OPENOFFICE12_SRF_4 |
45.00 |
90.00 |
E |
| OFFICE--OPENOFFICE14_SRF_4_GLZ_0 |
EXTERIOR WINDOW |
42.43 |
0.00 |
0.00 |
42.43 |
42.43 |
2.720 |
0.761 |
0.807 |
|
|
No |
OFFICE--OPENOFFICE14_SRF_4 |
315.00 |
90.00 |
N |
| OFFICE--OPENOFFICE15_SRF_4_GLZ_0 |
EXTERIOR WINDOW |
42.43 |
0.00 |
0.00 |
42.43 |
42.43 |
2.720 |
0.761 |
0.807 |
|
|
No |
OFFICE--OPENOFFICE15_SRF_4 |
225.00 |
90.00 |
W |
| OFFICE--OPENOFFICE16_SRF_4_GLZ_0 |
EXTERIOR WINDOW |
42.43 |
0.00 |
0.00 |
42.43 |
42.43 |
2.720 |
0.761 |
0.807 |
|
|
No |
OFFICE--OPENOFFICE16_SRF_4 |
135.00 |
90.00 |
E |
| OFFICE--OPENOFFICE17_SRF_4_GLZ_0 |
EXTERIOR WINDOW |
42.43 |
0.00 |
0.00 |
42.43 |
42.43 |
2.720 |
0.761 |
0.807 |
|
|
No |
OFFICE--OPENOFFICE17_SRF_4 |
45.00 |
90.00 |
E |
| OFFICE--OPENOFFICE19_SRF_4_GLZ_0 |
EXTERIOR WINDOW |
42.43 |
0.00 |
0.00 |
42.43 |
42.43 |
2.720 |
0.761 |
0.807 |
|
|
No |
OFFICE--OPENOFFICE19_SRF_4 |
315.00 |
90.00 |
N |
| OFFICE--OPENOFFICE2_SRF_4_GLZ_0 |
EXTERIOR WINDOW |
42.43 |
0.00 |
0.00 |
42.43 |
42.43 |
2.720 |
0.761 |
0.807 |
|
|
No |
OFFICE--OPENOFFICE2_SRF_4 |
45.00 |
90.00 |
E |
| OFFICE--OPENOFFICE20_SRF_4_GLZ_0 |
EXTERIOR WINDOW |
42.43 |
0.00 |
0.00 |
42.43 |
42.43 |
2.720 |
0.761 |
0.807 |
|
|
No |
OFFICE--OPENOFFICE20_SRF_4 |
225.00 |
90.00 |
W |
| OFFICE--OPENOFFICE4_SRF_4_GLZ_0 |
EXTERIOR WINDOW |
42.43 |
0.00 |
0.00 |
42.43 |
42.43 |
2.720 |
0.761 |
0.807 |
|
|
No |
OFFICE--OPENOFFICE4_SRF_4 |
315.00 |
90.00 |
N |
| OFFICE--OPENOFFICE5_SRF_4_GLZ_0 |
EXTERIOR WINDOW |
42.43 |
0.00 |
0.00 |
42.43 |
42.43 |
2.720 |
0.761 |
0.807 |
|
|
No |
OFFICE--OPENOFFICE5_SRF_4 |
225.00 |
90.00 |
W |
| OFFICE--OPENOFFICE6_SRF_4_GLZ_0 |
EXTERIOR WINDOW |
42.43 |
0.00 |
0.00 |
42.43 |
42.43 |
2.720 |
0.761 |
0.807 |
|
|
No |
OFFICE--OPENOFFICE6_SRF_4 |
135.00 |
90.00 |
E |
| OFFICE--OPENOFFICE7_SRF_4_GLZ_0 |
EXTERIOR WINDOW |
42.43 |
0.00 |
0.00 |
42.43 |
42.43 |
2.720 |
0.761 |
0.807 |
|
|
No |
OFFICE--OPENOFFICE7_SRF_4 |
45.00 |
90.00 |
E |
| OFFICE--OPENOFFICE9_SRF_4_GLZ_0 |
EXTERIOR WINDOW |
42.43 |
0.00 |
0.00 |
42.43 |
42.43 |
2.720 |
0.761 |
0.807 |
|
|
No |
OFFICE--OPENOFFICE9_SRF_4 |
315.00 |
90.00 |
N |
| Total or Average |
|
|
|
|
|
678.82 |
2.720 |
0.761 |
0.807 |
|
|
|
|
|
|
|
| North Total or Average |
|
|
|
|
|
169.71 |
2.720 |
0.761 |
0.807 |
|
|
|
|
|
|
|
| Non-North Total or Average |
|
|
|
|
|
509.12 |
2.720 |
0.761 |
0.807 |
|
|
|
|
|
|
|
Interior Fenestration
|
Construction |
Area of One Opening [m2] |
Area of Openings [m2] |
Glass U-Factor [W/m2-K] |
Glass SHGC |
Glass Visible Transmittance |
Parent Surface |
| Total or Average |
|
|
0.00 |
- |
- |
- |
|
Exterior Door
|
Construction |
U-Factor with Film [W/m2-K] |
U-Factor no Film [W/m2-K] |
Gross Area [m2] |
Parent Surface |
| None |
|
|
|
|
|
Table of Contents
Report: Shading Summary
For: Entire Facility
Timestamp: 2016-12-10
12:34:41
Sunlit Fraction
|
March 21 9am |
March 21 noon |
March 21 3pm |
June 21 9am |
June 21 noon |
June 21 3pm |
December 21 9am |
December 21 noon |
December 21 3pm |
| OFFICE--OPENOFFICE1_SRF_4_GLZ_0 |
1.00 |
1.00 |
0.00 |
1.00 |
1.00 |
0.00 |
1.00 |
1.00 |
1.00 |
| OFFICE--OPENOFFICE10_SRF_4_GLZ_0 |
0.00 |
1.00 |
1.00 |
0.00 |
1.00 |
1.00 |
1.00 |
1.00 |
1.00 |
| OFFICE--OPENOFFICE11_SRF_4_GLZ_0 |
1.00 |
1.00 |
0.00 |
1.00 |
1.00 |
0.00 |
1.00 |
1.00 |
1.00 |
| OFFICE--OPENOFFICE12_SRF_4_GLZ_0 |
1.00 |
0.00 |
0.00 |
1.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| OFFICE--OPENOFFICE14_SRF_4_GLZ_0 |
0.00 |
0.00 |
1.00 |
0.00 |
0.00 |
1.00 |
0.00 |
0.00 |
0.00 |
| OFFICE--OPENOFFICE15_SRF_4_GLZ_0 |
0.00 |
1.00 |
1.00 |
0.00 |
1.00 |
1.00 |
1.00 |
1.00 |
1.00 |
| OFFICE--OPENOFFICE16_SRF_4_GLZ_0 |
1.00 |
1.00 |
0.00 |
1.00 |
1.00 |
0.00 |
1.00 |
1.00 |
1.00 |
| OFFICE--OPENOFFICE17_SRF_4_GLZ_0 |
1.00 |
0.00 |
0.00 |
1.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| OFFICE--OPENOFFICE19_SRF_4_GLZ_0 |
0.00 |
0.00 |
1.00 |
0.00 |
0.00 |
1.00 |
0.00 |
0.00 |
0.00 |
| OFFICE--OPENOFFICE2_SRF_4_GLZ_0 |
1.00 |
0.00 |
0.00 |
1.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| OFFICE--OPENOFFICE20_SRF_4_GLZ_0 |
0.00 |
1.00 |
1.00 |
0.00 |
1.00 |
1.00 |
1.00 |
1.00 |
1.00 |
| OFFICE--OPENOFFICE4_SRF_4_GLZ_0 |
0.00 |
0.00 |
1.00 |
0.00 |
0.00 |
1.00 |
0.00 |
0.00 |
0.00 |
| OFFICE--OPENOFFICE5_SRF_4_GLZ_0 |
0.00 |
1.00 |
1.00 |
0.00 |
1.00 |
1.00 |
1.00 |
1.00 |
1.00 |
| OFFICE--OPENOFFICE6_SRF_4_GLZ_0 |
1.00 |
1.00 |
0.00 |
1.00 |
1.00 |
0.00 |
1.00 |
1.00 |
1.00 |
| OFFICE--OPENOFFICE7_SRF_4_GLZ_0 |
1.00 |
0.00 |
0.00 |
1.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| OFFICE--OPENOFFICE9_SRF_4_GLZ_0 |
0.00 |
0.00 |
1.00 |
0.00 |
0.00 |
1.00 |
0.00 |
0.00 |
0.00 |
Window Control
|
Name |
Type |
Shaded Construction |
Control |
Glare Control |
| None |
|
|
|
|
|
Table of Contents
Report: Lighting Summary
For: Entire Facility
Timestamp: 2016-12-10
12:34:41
Interior Lighting
|
Zone |
Lighting Power Density [W/m2] |
Zone Area [m2] |
Total Power [W] |
End Use Subcategory |
Schedule Name |
Scheduled Hours/Week [hr] |
Hours/Week > 1% [hr] |
Full Load Hours/Week [hr] |
Return Air Fraction |
Conditioned (Y/N) |
Consumption [GJ] |
| OFFICE--OPENOFFICE1_LIGHTSOBJECT |
OFFICE--OPENOFFICE1 |
10.7639 |
151.78 |
1633.71 |
General |
OFFICE BLDG LIGHT |
62.05 |
168.00 |
28.05 |
0.0000 |
Y |
8.60 |
| OFFICE--OPENOFFICE10_LIGHTSOBJECT |
OFFICE--OPENOFFICE10 |
10.7639 |
151.78 |
1633.71 |
General |
OFFICE BLDG LIGHT |
62.05 |
168.00 |
27.90 |
0.0000 |
Y |
8.56 |
| OFFICE--OPENOFFICE11_LIGHTSOBJECT |
OFFICE--OPENOFFICE11 |
10.7639 |
151.78 |
1633.71 |
General |
OFFICE BLDG LIGHT |
62.05 |
168.00 |
28.05 |
0.0000 |
Y |
8.60 |
| OFFICE--OPENOFFICE12_LIGHTSOBJECT |
OFFICE--OPENOFFICE12 |
10.7639 |
151.78 |
1633.71 |
General |
OFFICE BLDG LIGHT |
62.05 |
168.00 |
28.08 |
0.0000 |
Y |
8.61 |
| OFFICE--OPENOFFICE13_LIGHTSOBJECT |
OFFICE--OPENOFFICE13 |
10.7639 |
642.89 |
6920.04 |
General |
OFFICE BLDG LIGHT |
62.05 |
168.00 |
62.05 |
0.0000 |
Y |
80.60 |
| OFFICE--OPENOFFICE14_LIGHTSOBJECT |
OFFICE--OPENOFFICE14 |
10.7639 |
151.78 |
1633.71 |
General |
OFFICE BLDG LIGHT |
62.05 |
168.00 |
27.94 |
0.0000 |
Y |
8.57 |
| OFFICE--OPENOFFICE15_LIGHTSOBJECT |
OFFICE--OPENOFFICE15 |
10.7639 |
151.78 |
1633.71 |
General |
OFFICE BLDG LIGHT |
62.05 |
168.00 |
27.90 |
0.0000 |
Y |
8.56 |
| OFFICE--OPENOFFICE16_LIGHTSOBJECT |
OFFICE--OPENOFFICE16 |
10.7639 |
151.78 |
1633.71 |
General |
OFFICE BLDG LIGHT |
62.05 |
168.00 |
28.08 |
0.0000 |
Y |
8.61 |
| OFFICE--OPENOFFICE17_LIGHTSOBJECT |
OFFICE--OPENOFFICE17 |
10.7639 |
151.78 |
1633.71 |
General |
OFFICE BLDG LIGHT |
62.05 |
168.00 |
28.12 |
0.0000 |
Y |
8.62 |
| OFFICE--OPENOFFICE18_LIGHTSOBJECT |
OFFICE--OPENOFFICE18 |
10.7639 |
642.89 |
6920.04 |
General |
OFFICE BLDG LIGHT |
62.05 |
168.00 |
62.05 |
0.0000 |
Y |
80.60 |
| OFFICE--OPENOFFICE19_LIGHTSOBJECT |
OFFICE--OPENOFFICE19 |
10.7639 |
151.78 |
1633.71 |
General |
OFFICE BLDG LIGHT |
62.05 |
168.00 |
27.97 |
0.0000 |
Y |
8.58 |
| OFFICE--OPENOFFICE2_LIGHTSOBJECT |
OFFICE--OPENOFFICE2 |
10.7639 |
151.78 |
1633.71 |
General |
OFFICE BLDG LIGHT |
62.05 |
168.00 |
28.09 |
0.0000 |
Y |
8.61 |
| OFFICE--OPENOFFICE20_LIGHTSOBJECT |
OFFICE--OPENOFFICE20 |
10.7639 |
151.78 |
1633.71 |
General |
OFFICE BLDG LIGHT |
62.05 |
168.00 |
27.92 |
0.0000 |
Y |
8.56 |
| OFFICE--OPENOFFICE3_LIGHTSOBJECT |
OFFICE--OPENOFFICE3 |
10.7639 |
642.89 |
6920.04 |
General |
OFFICE BLDG LIGHT |
62.05 |
168.00 |
62.05 |
0.0000 |
Y |
80.60 |
| OFFICE--OPENOFFICE4_LIGHTSOBJECT |
OFFICE--OPENOFFICE4 |
10.7639 |
151.78 |
1633.71 |
General |
OFFICE BLDG LIGHT |
62.05 |
168.00 |
27.95 |
0.0000 |
Y |
8.57 |
| OFFICE--OPENOFFICE5_LIGHTSOBJECT |
OFFICE--OPENOFFICE5 |
10.7639 |
151.78 |
1633.71 |
General |
OFFICE BLDG LIGHT |
62.05 |
168.00 |
27.90 |
0.0000 |
Y |
8.56 |
| OFFICE--OPENOFFICE6_LIGHTSOBJECT |
OFFICE--OPENOFFICE6 |
10.7639 |
151.78 |
1633.71 |
General |
OFFICE BLDG LIGHT |
62.05 |
168.00 |
28.05 |
0.0000 |
Y |
8.60 |
| OFFICE--OPENOFFICE7_LIGHTSOBJECT |
OFFICE--OPENOFFICE7 |
10.7639 |
151.78 |
1633.71 |
General |
OFFICE BLDG LIGHT |
62.05 |
168.00 |
28.08 |
0.0000 |
Y |
8.61 |
| OFFICE--OPENOFFICE8_LIGHTSOBJECT |
OFFICE--OPENOFFICE8 |
10.7639 |
642.89 |
6920.04 |
General |
OFFICE BLDG LIGHT |
62.05 |
168.00 |
62.05 |
0.0000 |
Y |
80.60 |
| OFFICE--OPENOFFICE9_LIGHTSOBJECT |
OFFICE--OPENOFFICE9 |
10.7639 |
151.78 |
1633.71 |
General |
OFFICE BLDG LIGHT |
62.05 |
168.00 |
27.94 |
0.0000 |
Y |
8.57 |
| Interior Lighting Total |
|
10.7639 |
5000.00 |
53819.55 |
|
|
|
|
|
|
|
459.78 |
Daylighting
|
Zone |
Daylighting Type |
Control Type |
Fraction Controlled |
Lighting Installed in Zone [W] |
Lighting Controlled [W] |
| DAYLIGHTING CONTROL 1 |
{3D7ED984-698C-4374-A386-10B4E46AD946} |
Detailed |
Continuous |
1.00 |
1633.71 |
1633.71 |
| DAYLIGHTING CONTROL 8 |
{5C2AAFBF-AC4A-4B4C-88D9-A76CE95E791C} |
Detailed |
Continuous |
1.00 |
1633.71 |
1633.71 |
| DAYLIGHTING CONTROL 9 |
{010F758B-5D54-4AF3-A372-914C3DFC5C36} |
Detailed |
Continuous |
1.00 |
1633.71 |
1633.71 |
| DAYLIGHTING CONTROL 10 |
{A6520DB2-58B5-41B7-BC64-986BCC496527} |
Detailed |
Continuous |
1.00 |
1633.71 |
1633.71 |
| DAYLIGHTING CONTROL 19 |
{B9FF180D-BFED-4189-BC6F-CDAE702C04A3} |
Detailed |
Continuous |
1.00 |
6920.04 |
6920.04 |
| DAYLIGHTING CONTROL 11 |
{29968293-4633-4F4E-B064-27DB125A8075} |
Detailed |
Continuous |
1.00 |
1633.71 |
1633.71 |
| DAYLIGHTING CONTROL 12 |
{D7A719AA-1463-4A65-9872-882196A332DC} |
Detailed |
Continuous |
1.00 |
1633.71 |
1633.71 |
| DAYLIGHTING CONTROL 13 |
{067780B4-52DF-4A7D-A5B1-A68C8732E8B9} |
Detailed |
Continuous |
1.00 |
1633.71 |
1633.71 |
| DAYLIGHTING CONTROL 14 |
{BBD8D012-37A3-4E25-9CFF-E0E18CEF57AC} |
Detailed |
Continuous |
1.00 |
1633.71 |
1633.71 |
| DAYLIGHTING CONTROL 20 |
{5AB8DF0B-24DA-46E1-BE2C-72C6A51C9578} |
Detailed |
Continuous |
1.00 |
6920.04 |
6920.04 |
| DAYLIGHTING CONTROL 15 |
{3B42AE72-08E5-4B2B-BBEF-45C5C17842E7} |
Detailed |
Continuous |
1.00 |
1633.71 |
1633.71 |
| DAYLIGHTING CONTROL 2 |
{CE71DB2B-3186-48C5-8FD1-BAB179E30E4F} |
Detailed |
Continuous |
1.00 |
1633.71 |
1633.71 |
| DAYLIGHTING CONTROL 16 |
{2C93648F-E3FE-4A6F-8EC3-EA15749DD651} |
Detailed |
Continuous |
1.00 |
1633.71 |
1633.71 |
| DAYLIGHTING CONTROL 17 |
{EDC60F07-BFF1-4D32-B06B-1FDA6C05A4E4} |
Detailed |
Continuous |
1.00 |
6920.04 |
6920.04 |
| DAYLIGHTING CONTROL 3 |
{A7D8F541-C73A-4BCC-AFB3-A449EDCA2C03} |
Detailed |
Continuous |
1.00 |
1633.71 |
1633.71 |
| DAYLIGHTING CONTROL 4 |
{54F231D2-14E8-4751-8310-C80C08AECBD2} |
Detailed |
Continuous |
1.00 |
1633.71 |
1633.71 |
| DAYLIGHTING CONTROL 5 |
{FC0B2789-E311-439B-9AB8-53946372917B} |
Detailed |
Continuous |
1.00 |
1633.71 |
1633.71 |
| DAYLIGHTING CONTROL 6 |
{39589154-3202-47DA-BB27-C3A3B908D7E9} |
Detailed |
Continuous |
1.00 |
1633.71 |
1633.71 |
| DAYLIGHTING CONTROL 18 |
{0BF4E6EE-D5D4-42B0-BA77-2ABF2E0775E7} |
Detailed |
Continuous |
1.00 |
6920.04 |
6920.04 |
| DAYLIGHTING CONTROL 7 |
{D45C227E-1526-48D5-8046-05C3C95A4C94} |
Detailed |
Continuous |
1.00 |
1633.71 |
1633.71 |
Exterior Lighting
|
Total Watts |
Astronomical Clock/Schedule |
Schedule Name |
Scheduled Hours/Week [hr] |
Hours/Week > 1% [hr] |
Full Load Hours/Week [hr] |
Consumption [GJ] |
| Exterior Lighting Total |
0.00 |
|
|
|
|
|
0.00 |
Table of Contents
Report: Equipment Summary
For: Entire Facility
Timestamp: 2016-12-10
12:34:41
Central Plant
|
Type |
Nominal Capacity [W] |
Nominal Efficiency [W/W] |
IPLV in SI Units [W/W] |
IPLV in IP Units [Btu/W-h] |
| None |
|
|
|
|
|
Cooling Coils
|
Type |
Design Coil Load [W] |
Nominal Total Capacity [W] |
Nominal Sensible Capacity [W] |
Nominal Latent Capacity [W] |
Nominal Sensible Heat Ratio |
Nominal Efficiency [W/W] |
Nominal Coil UA Value [W/C] |
Nominal Coil Surface Area [m2] |
| COIL COOLING DX SINGLE SPEED 1 |
Coil:Cooling:DX:SingleSpeed |
|
111323.23 |
75263.77 |
36059.46 |
0.68 |
4.00 |
|
|
Nominal values are gross at rated conditions, i.e., the supply air fan heat and electric power NOT accounted for.
DX Cooling Coils
|
DX Cooling Coil Type |
Standard Rated Net Cooling Capacity [W] |
Standard Rated Net COP [W/W] |
EER [Btu/W-h] |
SEER [Btu/W-h] |
IEER [Btu/W-h] |
| COIL COOLING DX SINGLE SPEED 1 |
|
107838.6 |
3.45 |
11.76 |
12.47 |
12.07 |
ANSI/AHRI ratings account for supply air fan heat and electric power.
DX Cooling Coil ASHRAE 127 Standard Ratings Report
|
DX Cooling Coil Type |
Rated Net Cooling Capacity Test A [W] |
Rated Electric Power Test A [W] |
Rated Net Cooling Capacity Test B [W] |
Rated Electric Power Test B [W] |
Rated Net Cooling Capacity Test C [W] |
Rated Electric Power Test C [W] |
Rated Net Cooling Capacity Test D [W] |
Rated Electric Power Test D [W] |
| COIL COOLING DX SINGLE SPEED 1 |
Coil:Cooling:DX:SingleSpeed |
|
|
|
|
|
|
|
|
DX Heating Coils
|
DX Heating Coil Type |
High Temperature Heating (net) Rating Capacity [W] |
Low Temperature Heating (net) Rating Capacity [W] |
HSPF [Btu/W-h] |
Region Number |
| None |
|
|
|
|
|
Heating Coils
|
Type |
Design Coil Load [W] |
Nominal Total Capacity [W] |
Nominal Efficiency [W/W] |
| COIL HEATING GAS 1 |
Coil:Heating:Fuel |
|
275498.63 |
0.80 |
Fans
|
Type |
Total Efficiency [W/W] |
Delta Pressure [pa] |
Max Air Flow Rate [m3/s] |
Rated Electric Power [W] |
Rated Power Per Max Air Flow Rate [W-s/m3] |
Motor Heat In Air Fraction |
End Use |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 1 FAN |
Fan:OnOff |
0.60 |
300.00 |
0.96 |
478.44 |
500.00 |
1.00 |
General |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 8 FAN |
Fan:OnOff |
0.60 |
300.00 |
1.17 |
584.72 |
500.00 |
1.00 |
General |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 9 FAN |
Fan:OnOff |
0.60 |
300.00 |
1.14 |
568.85 |
500.00 |
1.00 |
General |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 10 FAN |
Fan:OnOff |
0.60 |
300.00 |
0.90 |
451.61 |
500.00 |
1.00 |
General |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 19 FAN |
Fan:OnOff |
0.60 |
300.00 |
1.40 |
697.62 |
500.00 |
1.00 |
General |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 11 FAN |
Fan:OnOff |
0.60 |
300.00 |
1.01 |
506.21 |
500.00 |
1.00 |
General |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 12 FAN |
Fan:OnOff |
0.60 |
300.00 |
1.18 |
591.12 |
500.00 |
1.00 |
General |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 13 FAN |
Fan:OnOff |
0.60 |
300.00 |
1.25 |
624.18 |
500.00 |
1.00 |
General |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 14 FAN |
Fan:OnOff |
0.60 |
300.00 |
0.98 |
489.02 |
500.00 |
1.00 |
General |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 20 FAN |
Fan:OnOff |
0.60 |
300.00 |
1.43 |
715.01 |
500.00 |
1.00 |
General |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 15 FAN |
Fan:OnOff |
0.60 |
300.00 |
1.10 |
551.53 |
500.00 |
1.00 |
General |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 2 FAN |
Fan:OnOff |
0.60 |
300.00 |
0.73 |
366.22 |
500.00 |
1.00 |
General |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 16 FAN |
Fan:OnOff |
0.60 |
300.00 |
1.30 |
651.41 |
500.00 |
1.00 |
General |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 17 FAN |
Fan:OnOff |
0.60 |
300.00 |
1.06 |
529.04 |
500.00 |
1.00 |
General |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 3 FAN |
Fan:OnOff |
0.60 |
300.00 |
0.84 |
420.66 |
500.00 |
1.00 |
General |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 4 FAN |
Fan:OnOff |
0.60 |
300.00 |
1.00 |
501.26 |
500.00 |
1.00 |
General |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 5 FAN |
Fan:OnOff |
0.60 |
300.00 |
1.13 |
562.70 |
500.00 |
1.00 |
General |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 6 FAN |
Fan:OnOff |
0.60 |
300.00 |
0.89 |
444.93 |
500.00 |
1.00 |
General |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 18 FAN |
Fan:OnOff |
0.60 |
300.00 |
1.33 |
666.83 |
500.00 |
1.00 |
General |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 7 FAN |
Fan:OnOff |
0.60 |
300.00 |
1.00 |
499.11 |
500.00 |
1.00 |
General |
| FAN CONSTANT VOLUME 1 |
Fan:ConstantVolume |
0.60 |
500.00 |
4.48 |
3735.82 |
833.33 |
1.00 |
General |
Pumps
|
Type |
Control |
Head [pa] |
Water Flow [m3/s] |
Electric Power [W] |
Power Per Water Flow Rate [W-s/m3] |
Motor Efficiency [W/W] |
| None |
|
|
|
|
|
|
|
Service Water Heating
|
Type |
Storage Volume [m3] |
Input [W] |
Thermal Efficiency [W/W] |
Recovery Efficiency [W/W] |
Energy Factor |
| None |
|
|
|
|
|
|
Table of Contents
Report: HVAC Sizing Summary
For: Entire Facility
Timestamp: 2016-12-10
12:34:41
Zone Sensible Cooling
|
Calculated Design Load [W] |
User Design Load [W] |
User Design Load per Area [W/m2] |
Calculated Design Air Flow [m3/s] |
User Design Air Flow [m3/s] |
Design Day Name |
Date/Time Of Peak {TIMESTAMP} |
Thermostat Setpoint Temperature at Peak Load [C] |
Indoor Temperature at Peak Load [C] |
Indoor Humidity Ratio at Peak Load [kgWater/kgAir] |
Outdoor Temperature at Peak Load [C] |
Outdoor Humidity Ratio at Peak Load [kgWater/kgAir] |
Minimum Outdoor Air Flow Rate [m3/s] |
Heat Gain Rate from DOAS [W] |
| OFFICE--OPENOFFICE1 |
10110.09 |
11626.61 |
76.60 |
0.832 |
0.957 |
NEW YORK LAGUARDIA ARPT ANN CLG .4% CONDNS DB=>MWB |
7/21 10:30:00 |
23.89 |
23.89 |
0.00853 |
31.15 |
0.01412 |
0.231 |
0.00 |
| OFFICE--OPENOFFICE10 |
12355.96 |
14209.36 |
93.62 |
1.017 |
1.169 |
NEW YORK LAGUARDIA ARPT ANN CLG .4% CONDNS DB=>MWB |
7/21 16:20:00 |
23.89 |
23.89 |
0.00853 |
32.83 |
0.01412 |
0.231 |
0.00 |
| OFFICE--OPENOFFICE11 |
12020.64 |
13823.74 |
91.08 |
0.989 |
1.138 |
NEW YORK LAGUARDIA ARPT ANN CLG .4% CONDNS DB=>MWB |
7/21 10:40:00 |
23.89 |
23.89 |
0.00853 |
31.34 |
0.01412 |
0.231 |
0.00 |
| OFFICE--OPENOFFICE12 |
9543.11 |
10974.57 |
72.31 |
0.785 |
0.903 |
NEW YORK LAGUARDIA ARPT ANN CLG .4% CONDNS DB=>MWB |
7/21 08:30:00 |
23.89 |
23.89 |
0.00853 |
28.53 |
0.01412 |
0.231 |
0.00 |
| OFFICE--OPENOFFICE13 |
15710.31 |
18066.86 |
28.10 |
1.213 |
1.395 |
NEW YORK LAGUARDIA ARPT ANN CLG .4% CONDNS DB=>MWB |
7/21 07:00:00 |
23.89 |
23.89 |
0.00851 |
26.49 |
0.01412 |
0.196 |
0.00 |
| OFFICE--OPENOFFICE14 |
10697.01 |
12301.56 |
81.05 |
0.880 |
1.012 |
NEW YORK LAGUARDIA ARPT ANN CLG .4% CONDNS DB=>MWB |
7/21 17:50:00 |
23.89 |
23.89 |
0.00853 |
31.78 |
0.01412 |
0.231 |
0.00 |
| OFFICE--OPENOFFICE15 |
12491.14 |
14364.81 |
94.64 |
1.028 |
1.182 |
NEW YORK LAGUARDIA ARPT ANN CLG .4% CONDNS DB=>MWB |
7/21 16:20:00 |
23.89 |
23.89 |
0.00853 |
32.83 |
0.01412 |
0.231 |
0.00 |
| OFFICE--OPENOFFICE16 |
13189.81 |
15168.28 |
99.94 |
1.086 |
1.248 |
NEW YORK LAGUARDIA ARPT ANN CLG .4% CONDNS DB=>MWB |
7/21 10:40:00 |
23.89 |
23.89 |
0.00852 |
31.34 |
0.01412 |
0.231 |
0.00 |
| OFFICE--OPENOFFICE17 |
10333.69 |
11883.75 |
78.30 |
0.850 |
0.978 |
NEW YORK LAGUARDIA ARPT ANN CLG .4% CONDNS DB=>MWB |
7/21 08:40:00 |
23.89 |
23.89 |
0.00853 |
28.78 |
0.01412 |
0.231 |
0.00 |
| OFFICE--OPENOFFICE18 |
16077.47 |
18489.09 |
28.76 |
1.243 |
1.430 |
NEW YORK LAGUARDIA ARPT ANN CLG .4% CONDNS DB=>MWB |
7/21 07:00:00 |
23.89 |
23.89 |
0.00851 |
26.49 |
0.01412 |
0.196 |
0.00 |
| OFFICE--OPENOFFICE19 |
11654.54 |
13402.72 |
88.31 |
0.959 |
1.103 |
NEW YORK LAGUARDIA ARPT ANN CLG .4% CONDNS DB=>MWB |
7/21 17:40:00 |
23.89 |
23.89 |
0.00853 |
31.91 |
0.01412 |
0.231 |
0.00 |
| OFFICE--OPENOFFICE2 |
7738.73 |
8899.54 |
58.64 |
0.637 |
0.732 |
NEW YORK LAGUARDIA ARPT ANN CLG .4% CONDNS DB=>MWB |
7/21 08:30:00 |
23.89 |
23.89 |
0.00854 |
28.53 |
0.01412 |
0.231 |
0.00 |
| OFFICE--OPENOFFICE20 |
13765.26 |
15830.05 |
104.30 |
1.133 |
1.303 |
NEW YORK LAGUARDIA ARPT ANN CLG .4% CONDNS DB=>MWB |
7/21 16:00:00 |
23.89 |
23.89 |
0.00852 |
33.04 |
0.01412 |
0.231 |
0.00 |
| OFFICE--OPENOFFICE3 |
12148.05 |
13970.26 |
21.73 |
0.920 |
1.058 |
NEW YORK LAGUARDIA ARPT ANN CLG .4% CONDNS DB=>MWB |
7/21 07:00:00 |
23.89 |
23.89 |
0.00851 |
26.49 |
0.01412 |
0.196 |
0.00 |
| OFFICE--OPENOFFICE4 |
8889.14 |
10222.51 |
67.35 |
0.732 |
0.841 |
NEW YORK LAGUARDIA ARPT ANN CLG .4% CONDNS DB=>MWB |
7/21 17:50:00 |
23.89 |
23.89 |
0.00854 |
31.78 |
0.01412 |
0.231 |
0.00 |
| OFFICE--OPENOFFICE5 |
10592.35 |
12181.20 |
80.26 |
0.872 |
1.003 |
NEW YORK LAGUARDIA ARPT ANN CLG .4% CONDNS DB=>MWB |
7/21 16:10:00 |
23.89 |
23.89 |
0.00853 |
32.94 |
0.01412 |
0.231 |
0.00 |
| OFFICE--OPENOFFICE6 |
11890.74 |
13674.36 |
90.10 |
0.979 |
1.125 |
NEW YORK LAGUARDIA ARPT ANN CLG .4% CONDNS DB=>MWB |
7/21 10:40:00 |
23.89 |
23.89 |
0.00853 |
31.34 |
0.01412 |
0.231 |
0.00 |
| OFFICE--OPENOFFICE7 |
9402.04 |
10812.35 |
71.24 |
0.774 |
0.890 |
NEW YORK LAGUARDIA ARPT ANN CLG .4% CONDNS DB=>MWB |
7/21 08:30:00 |
23.89 |
23.89 |
0.00853 |
28.53 |
0.01412 |
0.231 |
0.00 |
| OFFICE--OPENOFFICE8 |
15061.06 |
17320.22 |
26.94 |
1.160 |
1.334 |
NEW YORK LAGUARDIA ARPT ANN CLG .4% CONDNS DB=>MWB |
7/21 07:00:00 |
23.89 |
23.89 |
0.00851 |
26.49 |
0.01412 |
0.196 |
0.00 |
| OFFICE--OPENOFFICE9 |
10546.92 |
12128.96 |
79.91 |
0.868 |
0.998 |
NEW YORK LAGUARDIA ARPT ANN CLG .4% CONDNS DB=>MWB |
7/21 17:50:00 |
23.89 |
23.89 |
0.00853 |
31.78 |
0.01412 |
0.231 |
0.00 |
The Design Load is the zone sensible load only. It does not include any system effects or ventilation loads.
Zone Sensible Heating
|
Calculated Design Load [W] |
User Design Load [W] |
User Design Load per Area [W/m2] |
Calculated Design Air Flow [m3/s] |
User Design Air Flow [m3/s] |
Design Day Name |
Date/Time Of Peak {TIMESTAMP} |
Thermostat Setpoint Temperature at Peak Load [C] |
Indoor Temperature at Peak Load [C] |
Indoor Humidity Ratio at Peak Load [kgWater/kgAir] |
Outdoor Temperature at Peak Load [C] |
Outdoor Humidity Ratio at Peak Load [kgWater/kgAir] |
Minimum Outdoor Air Flow Rate [m3/s] |
Heat Gain Rate from DOAS [W] |
| OFFICE--OPENOFFICE1 |
3946.24 |
4932.80 |
32.50 |
0.170 |
0.231 |
NEW YORK LAGUARDIA ARPT ANN HTG 99.6% CONDNS DB |
1/21 24:00:00 |
21.11 |
21.11 |
0.00800 |
-10.80 |
0.00149 |
0.231 |
0.00 |
| OFFICE--OPENOFFICE10 |
3954.90 |
4943.63 |
32.57 |
0.171 |
0.231 |
NEW YORK LAGUARDIA ARPT ANN HTG 99.6% CONDNS DB |
1/21 24:00:00 |
21.11 |
21.11 |
0.00800 |
-10.80 |
0.00149 |
0.231 |
0.00 |
| OFFICE--OPENOFFICE11 |
4016.36 |
5020.46 |
33.08 |
0.173 |
0.231 |
NEW YORK LAGUARDIA ARPT ANN HTG 99.6% CONDNS DB |
1/21 24:00:00 |
21.11 |
21.11 |
0.00800 |
-10.80 |
0.00149 |
0.231 |
0.00 |
| OFFICE--OPENOFFICE12 |
4072.37 |
5090.47 |
33.54 |
0.176 |
0.231 |
NEW YORK LAGUARDIA ARPT ANN HTG 99.6% CONDNS DB |
1/21 24:00:00 |
21.11 |
21.11 |
0.00800 |
-10.80 |
0.00149 |
0.231 |
0.00 |
| OFFICE--OPENOFFICE13 |
1940.72 |
2425.90 |
3.77 |
0.084 |
0.196 |
NEW YORK LAGUARDIA ARPT ANN HTG 99.6% CONDNS DB |
1/21 24:00:00 |
21.11 |
21.11 |
0.00800 |
-10.80 |
0.00149 |
0.196 |
0.00 |
| OFFICE--OPENOFFICE14 |
4073.22 |
5091.53 |
33.55 |
0.176 |
0.231 |
NEW YORK LAGUARDIA ARPT ANN HTG 99.6% CONDNS DB |
1/21 24:00:00 |
21.11 |
21.11 |
0.00800 |
-10.80 |
0.00149 |
0.231 |
0.00 |
| OFFICE--OPENOFFICE15 |
4072.37 |
5090.47 |
33.54 |
0.176 |
0.231 |
NEW YORK LAGUARDIA ARPT ANN HTG 99.6% CONDNS DB |
1/21 24:00:00 |
21.11 |
21.11 |
0.00800 |
-10.80 |
0.00149 |
0.231 |
0.00 |
| OFFICE--OPENOFFICE16 |
5123.82 |
6404.77 |
42.20 |
0.221 |
0.276 |
NEW YORK LAGUARDIA ARPT ANN HTG 99.6% CONDNS DB |
1/21 24:00:00 |
21.11 |
21.11 |
0.00800 |
-10.80 |
0.00149 |
0.231 |
0.00 |
| OFFICE--OPENOFFICE17 |
5184.93 |
6481.17 |
42.70 |
0.224 |
0.280 |
NEW YORK LAGUARDIA ARPT ANN HTG 99.6% CONDNS DB |
1/21 24:00:00 |
21.11 |
21.11 |
0.00800 |
-10.80 |
0.00149 |
0.231 |
0.00 |
| OFFICE--OPENOFFICE18 |
6030.08 |
7537.60 |
11.72 |
0.260 |
0.325 |
NEW YORK LAGUARDIA ARPT ANN HTG 99.6% CONDNS DB |
1/21 24:00:00 |
21.11 |
21.11 |
0.00800 |
-10.80 |
0.00149 |
0.196 |
0.00 |
| OFFICE--OPENOFFICE19 |
5185.81 |
6482.26 |
42.71 |
0.224 |
0.280 |
NEW YORK LAGUARDIA ARPT ANN HTG 99.6% CONDNS DB |
1/21 24:00:00 |
21.11 |
21.11 |
0.00800 |
-10.80 |
0.00149 |
0.231 |
0.00 |
| OFFICE--OPENOFFICE2 |
3967.60 |
4959.50 |
32.68 |
0.171 |
0.231 |
NEW YORK LAGUARDIA ARPT ANN HTG 99.6% CONDNS DB |
1/21 24:00:00 |
21.11 |
21.11 |
0.00800 |
-10.80 |
0.00149 |
0.231 |
0.00 |
| OFFICE--OPENOFFICE20 |
5184.93 |
6481.17 |
42.70 |
0.224 |
0.280 |
NEW YORK LAGUARDIA ARPT ANN HTG 99.6% CONDNS DB |
1/21 24:00:00 |
21.11 |
21.11 |
0.00800 |
-10.80 |
0.00149 |
0.231 |
0.00 |
| OFFICE--OPENOFFICE3 |
2487.60 |
3109.50 |
4.84 |
0.107 |
0.196 |
NEW YORK LAGUARDIA ARPT ANN HTG 99.6% CONDNS DB |
1/21 24:00:00 |
21.11 |
21.11 |
0.00800 |
-10.80 |
0.00149 |
0.196 |
0.00 |
| OFFICE--OPENOFFICE4 |
3967.93 |
4959.91 |
32.68 |
0.171 |
0.231 |
NEW YORK LAGUARDIA ARPT ANN HTG 99.6% CONDNS DB |
1/21 24:00:00 |
21.11 |
21.11 |
0.00800 |
-10.80 |
0.00149 |
0.231 |
0.00 |
| OFFICE--OPENOFFICE5 |
3967.60 |
4959.50 |
32.68 |
0.171 |
0.231 |
NEW YORK LAGUARDIA ARPT ANN HTG 99.6% CONDNS DB |
1/21 24:00:00 |
21.11 |
21.11 |
0.00800 |
-10.80 |
0.00149 |
0.231 |
0.00 |
| OFFICE--OPENOFFICE6 |
3910.15 |
4887.68 |
32.20 |
0.169 |
0.231 |
NEW YORK LAGUARDIA ARPT ANN HTG 99.6% CONDNS DB |
1/21 24:00:00 |
21.11 |
21.11 |
0.00800 |
-10.80 |
0.00149 |
0.231 |
0.00 |
| OFFICE--OPENOFFICE7 |
3954.90 |
4943.63 |
32.57 |
0.171 |
0.231 |
NEW YORK LAGUARDIA ARPT ANN HTG 99.6% CONDNS DB |
1/21 24:00:00 |
21.11 |
21.11 |
0.00800 |
-10.80 |
0.00149 |
0.231 |
0.00 |
| OFFICE--OPENOFFICE8 |
1567.31 |
1959.14 |
3.05 |
0.068 |
0.196 |
NEW YORK LAGUARDIA ARPT ANN HTG 99.6% CONDNS DB |
1/21 24:00:00 |
21.11 |
21.11 |
0.00800 |
-10.80 |
0.00149 |
0.196 |
0.00 |
| OFFICE--OPENOFFICE9 |
3955.58 |
4944.48 |
32.58 |
0.171 |
0.231 |
NEW YORK LAGUARDIA ARPT ANN HTG 99.6% CONDNS DB |
1/21 24:00:00 |
21.11 |
21.11 |
0.00800 |
-10.80 |
0.00149 |
0.231 |
0.00 |
The Design Load is the zone sensible load only. It does not include any system effects or ventilation loads.
System Design Air Flow Rates
|
Calculated cooling [m3/s] |
User cooling [m3/s] |
Calculated heating [m3/s] |
User heating [m3/s] |
| DOAS AIR LOOP HVAC1 |
21.80 |
4.48 |
4.80 |
4.48 |
Plant Loop Coincident Design Fluid Flow Rate Adjustments
|
Previous Design Volume Flow Rate [m3/s] |
Algorithm Volume Flow Rate [m3/s] |
Coincident Design Volume Flow Rate [m3/s] |
Coincident Size Adjusted |
Peak Sizing Period Name |
Peak Day into Period {TIMESTAMP}[day] |
Peak Hour Of Day {TIMESTAMP}[hr] |
Peak Step Start Minute {TIMESTAMP}[min] |
| None |
|
|
|
|
|
|
|
|
Table of Contents
Report: System Summary
For: Entire Facility
Timestamp: 2016-12-10
12:34:41
Economizer
|
High Limit Shutoff Control |
Minimum Outdoor Air [m3/s] |
Maximum Outdoor Air [m3/s] |
Return Air Temp Limit |
Return Air Enthalpy Limit |
Outdoor Air Temperature Limit [C] |
Outdoor Air Enthalpy Limit [C] |
| None |
|
|
|
|
|
|
|
Demand Controlled Ventilation using Controller:MechanicalVentilation
|
Controller:MechanicalVentilation Name |
Outdoor Air Per Person [m3/s-person] |
Outdoor Air Per Area [m3/s-m2] |
Outdoor Air Per Zone [m3/s] |
Outdoor Air ACH [ach] |
Outdoor Air Method |
Outdoor Air Schedule Name |
Air Distribution Effectiveness in Cooling Mode |
Air Distribution Effectiveness in Heating Mode |
Air Distribution Effectiveness Schedule Name |
| OFFICE--OPENOFFICE1 |
CONTROLLER MECHANICAL VENTILATION 1 |
0.000000 |
0.001523 |
0.000000 |
0.000000 |
Sum |
|
1.00 |
1.00 |
|
| OFFICE--OPENOFFICE10 |
CONTROLLER MECHANICAL VENTILATION 1 |
0.000000 |
0.001523 |
0.000000 |
0.000000 |
Sum |
|
1.00 |
1.00 |
|
| OFFICE--OPENOFFICE11 |
CONTROLLER MECHANICAL VENTILATION 1 |
0.000000 |
0.001523 |
0.000000 |
0.000000 |
Sum |
|
1.00 |
1.00 |
|
| OFFICE--OPENOFFICE12 |
CONTROLLER MECHANICAL VENTILATION 1 |
0.000000 |
0.001523 |
0.000000 |
0.000000 |
Sum |
|
1.00 |
1.00 |
|
| OFFICE--OPENOFFICE13 |
CONTROLLER MECHANICAL VENTILATION 1 |
0.000000 |
0.000305 |
0.000000 |
0.000000 |
Sum |
|
1.00 |
1.00 |
|
| OFFICE--OPENOFFICE14 |
CONTROLLER MECHANICAL VENTILATION 1 |
0.000000 |
0.001523 |
0.000000 |
0.000000 |
Sum |
|
1.00 |
1.00 |
|
| OFFICE--OPENOFFICE15 |
CONTROLLER MECHANICAL VENTILATION 1 |
0.000000 |
0.001523 |
0.000000 |
0.000000 |
Sum |
|
1.00 |
1.00 |
|
| OFFICE--OPENOFFICE16 |
CONTROLLER MECHANICAL VENTILATION 1 |
0.000000 |
0.001523 |
0.000000 |
0.000000 |
Sum |
|
1.00 |
1.00 |
|
| OFFICE--OPENOFFICE17 |
CONTROLLER MECHANICAL VENTILATION 1 |
0.000000 |
0.001523 |
0.000000 |
0.000000 |
Sum |
|
1.00 |
1.00 |
|
| OFFICE--OPENOFFICE18 |
CONTROLLER MECHANICAL VENTILATION 1 |
0.000000 |
0.000305 |
0.000000 |
0.000000 |
Sum |
|
1.00 |
1.00 |
|
| OFFICE--OPENOFFICE19 |
CONTROLLER MECHANICAL VENTILATION 1 |
0.000000 |
0.001523 |
0.000000 |
0.000000 |
Sum |
|
1.00 |
1.00 |
|
| OFFICE--OPENOFFICE2 |
CONTROLLER MECHANICAL VENTILATION 1 |
0.000000 |
0.001523 |
0.000000 |
0.000000 |
Sum |
|
1.00 |
1.00 |
|
| OFFICE--OPENOFFICE20 |
CONTROLLER MECHANICAL VENTILATION 1 |
0.000000 |
0.001523 |
0.000000 |
0.000000 |
Sum |
|
1.00 |
1.00 |
|
| OFFICE--OPENOFFICE3 |
CONTROLLER MECHANICAL VENTILATION 1 |
0.000000 |
0.000305 |
0.000000 |
0.000000 |
Sum |
|
1.00 |
1.00 |
|
| OFFICE--OPENOFFICE4 |
CONTROLLER MECHANICAL VENTILATION 1 |
0.000000 |
0.001523 |
0.000000 |
0.000000 |
Sum |
|
1.00 |
1.00 |
|
| OFFICE--OPENOFFICE5 |
CONTROLLER MECHANICAL VENTILATION 1 |
0.000000 |
0.001523 |
0.000000 |
0.000000 |
Sum |
|
1.00 |
1.00 |
|
| OFFICE--OPENOFFICE6 |
CONTROLLER MECHANICAL VENTILATION 1 |
0.000000 |
0.001523 |
0.000000 |
0.000000 |
Sum |
|
1.00 |
1.00 |
|
| OFFICE--OPENOFFICE7 |
CONTROLLER MECHANICAL VENTILATION 1 |
0.000000 |
0.001523 |
0.000000 |
0.000000 |
Sum |
|
1.00 |
1.00 |
|
| OFFICE--OPENOFFICE8 |
CONTROLLER MECHANICAL VENTILATION 1 |
0.000000 |
0.000305 |
0.000000 |
0.000000 |
Sum |
|
1.00 |
1.00 |
|
| OFFICE--OPENOFFICE9 |
CONTROLLER MECHANICAL VENTILATION 1 |
0.000000 |
0.001523 |
0.000000 |
0.000000 |
Sum |
|
1.00 |
1.00 |
|
Time Not Comfortable Based on Simple ASHRAE 55-2004
|
Winter Clothes [hr] |
Summer Clothes [hr] |
Summer or Winter Clothes [hr] |
| OFFICE--OPENOFFICE1 |
2754.50 |
3350.00 |
1383.00 |
| OFFICE--OPENOFFICE10 |
3043.33 |
3151.00 |
1415.67 |
| OFFICE--OPENOFFICE11 |
2969.83 |
2938.67 |
1217.50 |
| OFFICE--OPENOFFICE12 |
3265.67 |
3565.67 |
1986.33 |
| OFFICE--OPENOFFICE13 |
1127.50 |
3760.00 |
366.67 |
| OFFICE--OPENOFFICE14 |
3264.67 |
3631.50 |
2021.67 |
| OFFICE--OPENOFFICE15 |
3084.83 |
3129.00 |
1430.83 |
| OFFICE--OPENOFFICE16 |
3160.50 |
3175.33 |
1569.83 |
| OFFICE--OPENOFFICE17 |
3414.17 |
3598.83 |
2138.33 |
| OFFICE--OPENOFFICE18 |
1710.67 |
3668.67 |
655.17 |
| OFFICE--OPENOFFICE19 |
3446.83 |
3674.83 |
2206.50 |
| OFFICE--OPENOFFICE2 |
3084.83 |
4096.17 |
2282.33 |
| OFFICE--OPENOFFICE20 |
3304.67 |
3355.83 |
1799.67 |
| OFFICE--OPENOFFICE3 |
703.83 |
5270.00 |
703.83 |
| OFFICE--OPENOFFICE4 |
3080.83 |
4142.17 |
2304.83 |
| OFFICE--OPENOFFICE5 |
2912.67 |
3516.00 |
1603.50 |
| OFFICE--OPENOFFICE6 |
2928.83 |
2956.33 |
1199.50 |
| OFFICE--OPENOFFICE7 |
3213.17 |
3629.00 |
1990.17 |
| OFFICE--OPENOFFICE8 |
815.33 |
4046.83 |
397.67 |
| OFFICE--OPENOFFICE9 |
3213.83 |
3692.00 |
2016.00 |
| Facility |
4405.33 |
5270.00 |
2989.33 |
Aggregated over the RunPeriods for Weather
Time Setpoint Not Met
|
During Heating [hr] |
During Cooling [hr] |
During Occupied Heating [hr] |
During Occupied Cooling [hr] |
| OFFICE--OPENOFFICE1 |
11.33 |
76.50 |
10.17 |
50.50 |
| OFFICE--OPENOFFICE10 |
4.50 |
40.83 |
4.00 |
12.17 |
| OFFICE--OPENOFFICE11 |
5.17 |
89.33 |
4.50 |
58.17 |
| OFFICE--OPENOFFICE12 |
208.00 |
1.00 |
189.33 |
1.00 |
| OFFICE--OPENOFFICE13 |
0.00 |
112.00 |
0.00 |
112.00 |
| OFFICE--OPENOFFICE14 |
225.00 |
0.17 |
202.33 |
0.00 |
| OFFICE--OPENOFFICE15 |
5.33 |
40.17 |
4.67 |
11.17 |
| OFFICE--OPENOFFICE16 |
13.33 |
76.33 |
12.17 |
49.33 |
| OFFICE--OPENOFFICE17 |
342.00 |
0.67 |
315.50 |
0.67 |
| OFFICE--OPENOFFICE18 |
6.67 |
2.00 |
5.67 |
2.00 |
| OFFICE--OPENOFFICE19 |
334.33 |
0.00 |
304.67 |
0.00 |
| OFFICE--OPENOFFICE2 |
393.33 |
0.17 |
338.50 |
0.17 |
| OFFICE--OPENOFFICE20 |
23.33 |
25.83 |
22.00 |
6.67 |
| OFFICE--OPENOFFICE3 |
0.17 |
6.33 |
0.17 |
6.33 |
| OFFICE--OPENOFFICE4 |
381.67 |
0.00 |
324.83 |
0.00 |
| OFFICE--OPENOFFICE5 |
25.17 |
24.00 |
21.17 |
6.50 |
| OFFICE--OPENOFFICE6 |
4.50 |
94.33 |
4.00 |
62.00 |
| OFFICE--OPENOFFICE7 |
185.33 |
0.33 |
168.67 |
0.33 |
| OFFICE--OPENOFFICE8 |
0.00 |
146.00 |
0.00 |
146.00 |
| OFFICE--OPENOFFICE9 |
200.67 |
0.00 |
180.17 |
0.00 |
| Facility |
493.00 |
241.17 |
419.67 |
192.00 |
Aggregated over the RunPeriods for Weather
Table of Contents
Report: Outdoor Air Summary
For: Entire Facility
Timestamp: 2016-12-10
12:34:41
Average Outdoor Air During Occupied Hours
|
Average Number of Occupants |
Nominal Number of Occupants |
Zone Volume [m3] |
Mechanical Ventilation [ach] |
Infiltration [ach] |
AFN Infiltration [ach] |
Simple Ventilation [ach] |
| OFFICE--OPENOFFICE1 |
0.90 |
1.63 |
607.11 |
1.395 |
0.000 |
0.000 |
0.000 |
| OFFICE--OPENOFFICE10 |
0.90 |
1.63 |
607.11 |
1.396 |
0.000 |
0.000 |
0.000 |
| OFFICE--OPENOFFICE11 |
0.90 |
1.63 |
607.11 |
1.396 |
0.000 |
0.000 |
0.000 |
| OFFICE--OPENOFFICE12 |
0.90 |
1.63 |
607.11 |
1.393 |
0.000 |
0.000 |
0.000 |
| OFFICE--OPENOFFICE13 |
0.38 |
0.69 |
2571.57 |
0.280 |
0.000 |
0.000 |
0.000 |
| OFFICE--OPENOFFICE14 |
0.90 |
1.63 |
607.11 |
1.393 |
0.000 |
0.000 |
0.000 |
| OFFICE--OPENOFFICE15 |
0.90 |
1.63 |
607.11 |
1.396 |
0.000 |
0.000 |
0.000 |
| OFFICE--OPENOFFICE16 |
0.90 |
1.63 |
607.11 |
1.396 |
0.000 |
0.000 |
0.000 |
| OFFICE--OPENOFFICE17 |
0.90 |
1.63 |
607.11 |
1.393 |
0.000 |
0.000 |
0.000 |
| OFFICE--OPENOFFICE18 |
0.38 |
0.69 |
2571.57 |
0.279 |
0.000 |
0.000 |
0.000 |
| OFFICE--OPENOFFICE19 |
0.90 |
1.63 |
607.11 |
1.393 |
0.000 |
0.000 |
0.000 |
| OFFICE--OPENOFFICE2 |
0.90 |
1.63 |
607.11 |
1.392 |
0.000 |
0.000 |
0.000 |
| OFFICE--OPENOFFICE20 |
0.90 |
1.63 |
607.11 |
1.395 |
0.000 |
0.000 |
0.000 |
| OFFICE--OPENOFFICE3 |
0.38 |
0.69 |
2571.57 |
0.279 |
0.000 |
0.000 |
0.000 |
| OFFICE--OPENOFFICE4 |
0.90 |
1.63 |
607.11 |
1.392 |
0.000 |
0.000 |
0.000 |
| OFFICE--OPENOFFICE5 |
0.90 |
1.63 |
607.11 |
1.394 |
0.000 |
0.000 |
0.000 |
| OFFICE--OPENOFFICE6 |
0.90 |
1.63 |
607.11 |
1.396 |
0.000 |
0.000 |
0.000 |
| OFFICE--OPENOFFICE7 |
0.90 |
1.63 |
607.11 |
1.393 |
0.000 |
0.000 |
0.000 |
| OFFICE--OPENOFFICE8 |
0.38 |
0.69 |
2571.57 |
0.280 |
0.000 |
0.000 |
0.000 |
| OFFICE--OPENOFFICE9 |
0.90 |
1.63 |
607.11 |
1.393 |
0.000 |
0.000 |
0.000 |
Values shown for a single zone without multipliers
Minimum Outdoor Air During Occupied Hours
|
Average Number of Occupants |
Nominal Number of Occupants |
Zone Volume [m3] |
Mechanical Ventilation [ach] |
Infiltration [ach] |
AFN Infiltration [ach] |
Simple Ventilation [ach] |
| OFFICE--OPENOFFICE1 |
0.90 |
1.63 |
607.11 |
1.332 |
0.000 |
0.000 |
0.000 |
| OFFICE--OPENOFFICE10 |
0.90 |
1.63 |
607.11 |
1.336 |
0.000 |
0.000 |
0.000 |
| OFFICE--OPENOFFICE11 |
0.90 |
1.63 |
607.11 |
1.334 |
0.000 |
0.000 |
0.000 |
| OFFICE--OPENOFFICE12 |
0.90 |
1.63 |
607.11 |
1.331 |
0.000 |
0.000 |
0.000 |
| OFFICE--OPENOFFICE13 |
0.38 |
0.69 |
2571.57 |
0.269 |
0.000 |
0.000 |
0.000 |
| OFFICE--OPENOFFICE14 |
0.90 |
1.63 |
607.11 |
1.331 |
0.000 |
0.000 |
0.000 |
| OFFICE--OPENOFFICE15 |
0.90 |
1.63 |
607.11 |
1.336 |
0.000 |
0.000 |
0.000 |
| OFFICE--OPENOFFICE16 |
0.90 |
1.63 |
607.11 |
1.331 |
0.000 |
0.000 |
0.000 |
| OFFICE--OPENOFFICE17 |
0.90 |
1.63 |
607.11 |
1.331 |
0.000 |
0.000 |
0.000 |
| OFFICE--OPENOFFICE18 |
0.38 |
0.69 |
2571.57 |
0.267 |
0.000 |
0.000 |
0.000 |
| OFFICE--OPENOFFICE19 |
0.90 |
1.63 |
607.11 |
1.331 |
0.000 |
0.000 |
0.000 |
| OFFICE--OPENOFFICE2 |
0.90 |
1.63 |
607.11 |
1.330 |
0.000 |
0.000 |
0.000 |
| OFFICE--OPENOFFICE20 |
0.90 |
1.63 |
607.11 |
1.332 |
0.000 |
0.000 |
0.000 |
| OFFICE--OPENOFFICE3 |
0.38 |
0.69 |
2571.57 |
0.268 |
0.000 |
0.000 |
0.000 |
| OFFICE--OPENOFFICE4 |
0.90 |
1.63 |
607.11 |
1.330 |
0.000 |
0.000 |
0.000 |
| OFFICE--OPENOFFICE5 |
0.90 |
1.63 |
607.11 |
1.333 |
0.000 |
0.000 |
0.000 |
| OFFICE--OPENOFFICE6 |
0.90 |
1.63 |
607.11 |
1.335 |
0.000 |
0.000 |
0.000 |
| OFFICE--OPENOFFICE7 |
0.90 |
1.63 |
607.11 |
1.331 |
0.000 |
0.000 |
0.000 |
| OFFICE--OPENOFFICE8 |
0.38 |
0.69 |
2571.57 |
0.269 |
0.000 |
0.000 |
0.000 |
| OFFICE--OPENOFFICE9 |
0.90 |
1.63 |
607.11 |
1.331 |
0.000 |
0.000 |
0.000 |
Values shown for a single zone without multipliers
Table of Contents
Report: Object Count Summary
For: Entire Facility
Timestamp: 2016-12-10
12:34:41
Surfaces by Class
|
Total |
Outdoors |
| Wall |
80 |
16 |
| Floor |
20 |
5 |
| Roof |
20 |
5 |
| Internal Mass |
0 |
0 |
| Building Detached Shading |
0 |
0 |
| Fixed Detached Shading |
0 |
0 |
| Window |
16 |
16 |
| Door |
0 |
0 |
| Glass Door |
0 |
0 |
| Shading |
0 |
0 |
| Overhang |
0 |
0 |
| Fin |
0 |
0 |
| Tubular Daylighting Device Dome |
0 |
0 |
| Tubular Daylighting Device Diffuser |
0 |
0 |
HVAC
|
Count |
| HVAC Air Loops |
1 |
| Conditioned Zones |
20 |
| Unconditioned Zones |
0 |
| Supply Plenums |
0 |
| Return Plenums |
0 |
Input Fields
|
Count |
| IDF Objects |
1065 |
| Defaulted Fields |
823 |
| Fields with Defaults |
2184 |
| Autosized Fields |
236 |
| Autosizable Fields |
299 |
| Autocalculated Fields |
352 |
| Autocalculatable Fields |
352 |
Table of Contents
Report: Energy Meters
For: Entire Facility
Timestamp: 2016-12-10
12:34:41
Annual and Peak Values - Electricity
|
Electricity Annual Value [GJ] |
Electricity Minimum Value [W] |
Timestamp of Minimum {TIMESTAMP} |
Electricity Maximum Value [W] |
Timestamp of Maximum {TIMESTAMP} |
| Electricity:Facility |
1550.74 |
16828.54 |
01-APR-06:00 |
146822.87 |
06-JUL-14:00 |
| Electricity:Building |
460.70 |
1792.25 |
08-JAN-07:50 |
48486.03 |
01-JAN-16:40 |
| Electricity:Zone:OFFICE--OPENOFFICE1 |
8.63 |
25.00 |
08-JAN-07:40 |
1471.81 |
01-JAN-16:40 |
| InteriorLights:Electricity |
459.78 |
1776.10 |
08-JAN-07:50 |
48437.60 |
01-JAN-16:40 |
| InteriorLights:Electricity:Zone:OFFICE--OPENOFFICE1 |
8.60 |
24.51 |
08-JAN-07:40 |
1470.34 |
01-JAN-16:40 |
| General:InteriorLights:Electricity |
459.78 |
1776.10 |
08-JAN-07:50 |
48437.60 |
01-JAN-16:40 |
| Electricity:Zone:OFFICE--OPENOFFICE10 |
8.58 |
25.00 |
08-JAN-07:50 |
1471.81 |
01-JAN-16:40 |
| InteriorLights:Electricity:Zone:OFFICE--OPENOFFICE10 |
8.56 |
24.51 |
08-JAN-07:50 |
1470.34 |
01-JAN-16:40 |
| Electricity:Zone:OFFICE--OPENOFFICE11 |
8.63 |
25.00 |
08-JAN-07:40 |
1471.81 |
01-JAN-16:40 |
| InteriorLights:Electricity:Zone:OFFICE--OPENOFFICE11 |
8.60 |
24.51 |
08-JAN-07:40 |
1470.34 |
01-JAN-16:40 |
| Electricity:Zone:OFFICE--OPENOFFICE12 |
8.64 |
25.00 |
08-JAN-07:50 |
1471.81 |
01-JAN-16:40 |
| InteriorLights:Electricity:Zone:OFFICE--OPENOFFICE12 |
8.61 |
24.51 |
08-JAN-07:50 |
1470.34 |
01-JAN-16:40 |
| Electricity:Zone:OFFICE--OPENOFFICE13 |
80.72 |
348.08 |
07-JAN-00:10 |
6234.27 |
01-JAN-08:10 |
| InteriorLights:Electricity:Zone:OFFICE--OPENOFFICE13 |
80.60 |
346.00 |
01-JAN-00:10 |
6228.04 |
01-JAN-08:10 |
| Electricity:Zone:OFFICE--OPENOFFICE14 |
8.60 |
25.00 |
08-JAN-07:50 |
1471.81 |
01-JAN-16:40 |
| InteriorLights:Electricity:Zone:OFFICE--OPENOFFICE14 |
8.57 |
24.51 |
08-JAN-07:50 |
1470.34 |
01-JAN-16:40 |
| Electricity:Zone:OFFICE--OPENOFFICE15 |
8.58 |
25.00 |
08-JAN-07:50 |
1471.81 |
01-JAN-16:40 |
| InteriorLights:Electricity:Zone:OFFICE--OPENOFFICE15 |
8.56 |
24.51 |
08-JAN-07:50 |
1470.34 |
01-JAN-16:40 |
| Electricity:Zone:OFFICE--OPENOFFICE16 |
8.64 |
25.00 |
08-JAN-07:40 |
1471.81 |
01-JAN-16:40 |
| InteriorLights:Electricity:Zone:OFFICE--OPENOFFICE16 |
8.61 |
24.51 |
08-JAN-07:40 |
1470.34 |
01-JAN-16:40 |
| Electricity:Zone:OFFICE--OPENOFFICE17 |
8.65 |
25.00 |
08-JAN-07:50 |
1471.81 |
01-JAN-16:40 |
| InteriorLights:Electricity:Zone:OFFICE--OPENOFFICE17 |
8.62 |
24.51 |
08-JAN-07:50 |
1470.34 |
01-JAN-16:40 |
| Electricity:Zone:OFFICE--OPENOFFICE18 |
80.72 |
348.08 |
07-JAN-00:10 |
6234.27 |
01-JAN-08:10 |
| InteriorLights:Electricity:Zone:OFFICE--OPENOFFICE18 |
80.60 |
346.00 |
01-JAN-00:10 |
6228.04 |
01-JAN-08:10 |
| Electricity:Zone:OFFICE--OPENOFFICE19 |
8.60 |
25.00 |
08-JAN-07:50 |
1471.81 |
01-JAN-16:40 |
| InteriorLights:Electricity:Zone:OFFICE--OPENOFFICE19 |
8.58 |
24.51 |
08-JAN-07:50 |
1470.34 |
01-JAN-16:40 |
| Electricity:Zone:OFFICE--OPENOFFICE2 |
8.64 |
25.00 |
08-JAN-07:50 |
1471.81 |
01-JAN-16:40 |
| InteriorLights:Electricity:Zone:OFFICE--OPENOFFICE2 |
8.61 |
24.51 |
08-JAN-07:50 |
1470.34 |
01-JAN-16:40 |
| Electricity:Zone:OFFICE--OPENOFFICE20 |
8.59 |
25.00 |
08-JAN-07:50 |
1471.81 |
01-JAN-16:40 |
| InteriorLights:Electricity:Zone:OFFICE--OPENOFFICE20 |
8.56 |
24.51 |
08-JAN-07:50 |
1470.34 |
01-JAN-16:40 |
| Electricity:Zone:OFFICE--OPENOFFICE3 |
80.72 |
348.08 |
07-JAN-00:10 |
6234.27 |
01-JAN-08:10 |
| InteriorLights:Electricity:Zone:OFFICE--OPENOFFICE3 |
80.60 |
346.00 |
01-JAN-00:10 |
6228.04 |
01-JAN-08:10 |
| Electricity:Zone:OFFICE--OPENOFFICE4 |
8.60 |
25.00 |
08-JAN-07:50 |
1471.81 |
01-JAN-16:40 |
| InteriorLights:Electricity:Zone:OFFICE--OPENOFFICE4 |
8.57 |
24.51 |
08-JAN-07:50 |
1470.34 |
01-JAN-16:40 |
| Electricity:Zone:OFFICE--OPENOFFICE5 |
8.58 |
25.00 |
08-JAN-07:50 |
1471.81 |
01-JAN-16:40 |
| InteriorLights:Electricity:Zone:OFFICE--OPENOFFICE5 |
8.56 |
24.51 |
08-JAN-07:50 |
1470.34 |
01-JAN-16:40 |
| Electricity:Zone:OFFICE--OPENOFFICE6 |
8.63 |
25.00 |
08-JAN-07:40 |
1471.81 |
01-JAN-16:40 |
| InteriorLights:Electricity:Zone:OFFICE--OPENOFFICE6 |
8.60 |
24.51 |
08-JAN-07:40 |
1470.34 |
01-JAN-16:40 |
| Electricity:Zone:OFFICE--OPENOFFICE7 |
8.64 |
25.00 |
08-JAN-07:50 |
1471.81 |
01-JAN-16:40 |
| InteriorLights:Electricity:Zone:OFFICE--OPENOFFICE7 |
8.61 |
24.51 |
08-JAN-07:50 |
1470.34 |
01-JAN-16:40 |
| Electricity:Zone:OFFICE--OPENOFFICE8 |
80.72 |
348.08 |
07-JAN-00:10 |
6234.27 |
01-JAN-08:10 |
| InteriorLights:Electricity:Zone:OFFICE--OPENOFFICE8 |
80.60 |
346.00 |
01-JAN-00:10 |
6228.04 |
01-JAN-08:10 |
| Electricity:Zone:OFFICE--OPENOFFICE9 |
8.60 |
25.00 |
08-JAN-07:50 |
1471.81 |
01-JAN-16:40 |
| InteriorLights:Electricity:Zone:OFFICE--OPENOFFICE9 |
8.57 |
24.51 |
08-JAN-07:50 |
1470.34 |
01-JAN-16:40 |
| InteriorEquipment:Electricity |
0.92 |
16.15 |
07-JAN-00:10 |
48.44 |
01-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:OFFICE--OPENOFFICE1 |
0.03 |
0.49 |
07-JAN-00:10 |
1.47 |
01-JAN-08:10 |
| ElectricEquipment:InteriorEquipment:Electricity |
0.92 |
16.15 |
07-JAN-00:10 |
48.44 |
01-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:OFFICE--OPENOFFICE10 |
0.03 |
0.49 |
07-JAN-00:10 |
1.47 |
01-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:OFFICE--OPENOFFICE11 |
0.03 |
0.49 |
07-JAN-00:10 |
1.47 |
01-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:OFFICE--OPENOFFICE12 |
0.03 |
0.49 |
07-JAN-00:10 |
1.47 |
01-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:OFFICE--OPENOFFICE13 |
0.12 |
2.08 |
07-JAN-00:10 |
6.23 |
01-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:OFFICE--OPENOFFICE14 |
0.03 |
0.49 |
07-JAN-00:10 |
1.47 |
01-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:OFFICE--OPENOFFICE15 |
0.03 |
0.49 |
07-JAN-00:10 |
1.47 |
01-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:OFFICE--OPENOFFICE16 |
0.03 |
0.49 |
07-JAN-00:10 |
1.47 |
01-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:OFFICE--OPENOFFICE17 |
0.03 |
0.49 |
07-JAN-00:10 |
1.47 |
01-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:OFFICE--OPENOFFICE18 |
0.12 |
2.08 |
07-JAN-00:10 |
6.23 |
01-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:OFFICE--OPENOFFICE19 |
0.03 |
0.49 |
07-JAN-00:10 |
1.47 |
01-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:OFFICE--OPENOFFICE2 |
0.03 |
0.49 |
07-JAN-00:10 |
1.47 |
01-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:OFFICE--OPENOFFICE20 |
0.03 |
0.49 |
07-JAN-00:10 |
1.47 |
01-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:OFFICE--OPENOFFICE3 |
0.12 |
2.08 |
07-JAN-00:10 |
6.23 |
01-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:OFFICE--OPENOFFICE4 |
0.03 |
0.49 |
07-JAN-00:10 |
1.47 |
01-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:OFFICE--OPENOFFICE5 |
0.03 |
0.49 |
07-JAN-00:10 |
1.47 |
01-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:OFFICE--OPENOFFICE6 |
0.03 |
0.49 |
07-JAN-00:10 |
1.47 |
01-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:OFFICE--OPENOFFICE7 |
0.03 |
0.49 |
07-JAN-00:10 |
1.47 |
01-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:OFFICE--OPENOFFICE8 |
0.12 |
2.08 |
07-JAN-00:10 |
6.23 |
01-JAN-08:10 |
| InteriorEquipment:Electricity:Zone:OFFICE--OPENOFFICE9 |
0.03 |
0.49 |
07-JAN-00:10 |
1.47 |
01-JAN-08:10 |
| ElectricityPurchased:Facility |
1550.74 |
16828.54 |
06-MAY-18:10 |
146822.87 |
06-JUL-14:00 |
| ElectricityPurchased:Plant |
1550.74 |
16828.54 |
06-MAY-18:10 |
146822.87 |
06-JUL-14:00 |
| Cogeneration:ElectricityPurchased |
1550.74 |
16828.54 |
06-MAY-18:10 |
146822.87 |
06-JUL-14:00 |
| ElectricitySurplusSold:Facility |
0.00 |
0.00 |
01-JAN-00:10 |
0.00 |
01-JAN-00:10 |
| ElectricitySurplusSold:Plant |
0.00 |
0.00 |
01-JAN-00:10 |
0.00 |
01-JAN-00:10 |
| Cogeneration:ElectricitySurplusSold |
0.00 |
0.00 |
01-JAN-00:10 |
0.00 |
01-JAN-00:10 |
| ElectricityNet:Facility |
1550.74 |
16828.54 |
06-MAY-18:10 |
146822.87 |
06-JUL-14:00 |
| ElectricityNet:Plant |
1550.74 |
16828.54 |
06-MAY-18:10 |
146822.87 |
06-JUL-14:00 |
| Cogeneration:ElectricityNet |
1550.74 |
16828.54 |
06-MAY-18:10 |
146822.87 |
06-JUL-14:00 |
| Electricity:HVAC |
1090.04 |
15036.29 |
18-MAR-18:10 |
114822.76 |
08-JUL-12:10 |
| Fans:Electricity |
461.57 |
14636.29 |
01-JAN-06:20 |
14636.29 |
17-JAN-06:10 |
| General:Fans:Electricity |
461.57 |
14636.29 |
01-JAN-06:20 |
14636.29 |
17-JAN-06:10 |
| Cooling:Electricity |
544.01 |
0.00 |
15-JAN-16:40 |
100186.47 |
08-JUL-12:10 |
| Heating:Electricity |
84.45 |
0.00 |
01-JAN-09:50 |
65340.62 |
06-FEB-06:10 |
| Electricity:Plant |
0.00 |
0.00 |
01-JAN-00:10 |
0.00 |
01-JAN-00:10 |
Annual and Peak Values - Gas
|
Gas Annual Value [GJ] |
Gas Minimum Value [W] |
Timestamp of Minimum {TIMESTAMP} |
Gas Maximum Value [W] |
Timestamp of Maximum {TIMESTAMP} |
| Gas:Facility |
1605.50 |
0.00 |
13-MAR-14:00 |
232806.38 |
06-FEB-04:10 |
| Gas:HVAC |
1605.50 |
0.00 |
13-MAR-14:00 |
232806.38 |
06-FEB-04:10 |
| Heating:Gas |
1605.50 |
0.00 |
13-MAR-14:00 |
232806.38 |
06-FEB-04:10 |
Annual and Peak Values - Cooling
|
Cooling Annual Value [GJ] |
Cooling Minimum Value [W] |
Timestamp of Minimum {TIMESTAMP} |
Cooling Maximum Value [W] |
Timestamp of Maximum {TIMESTAMP} |
| None |
|
|
|
|
|
Annual and Peak Values - Water
|
Annual Value [m3] |
Minimum Value [m3/s] |
Timestamp of Minimum {TIMESTAMP} |
Maximum Value [m3/s] |
Timestamp of Maximum {TIMESTAMP} |
| None |
|
|
|
|
|
Annual and Peak Values - Other by Weight/Mass
|
Annual Value [kg] |
Minimum Value [kg/s] |
Timestamp of Minimum {TIMESTAMP} |
Maximum Value [kg/s] |
Timestamp of Maximum {TIMESTAMP} |
| Carbon Equivalent:Facility |
0.00 |
0.000 |
01-JAN-00:10 |
0.000 |
01-JAN-00:10 |
| CarbonEquivalentEmissions:Carbon Equivalent |
0.00 |
0.000 |
01-JAN-00:10 |
0.000 |
01-JAN-00:10 |
Annual and Peak Values - Other Volumetric
|
Annual Value [m3] |
Minimum Value [m3/s] |
Timestamp of Minimum {TIMESTAMP} |
Maximum Value [m3/s] |
Timestamp of Maximum {TIMESTAMP} |
| None |
|
|
|
|
|
Annual and Peak Values - Other Liquid/Gas
|
Annual Value [L] |
Minimum Value [L] |
Timestamp of Minimum {TIMESTAMP} |
Maximum Value [L] |
Timestamp of Maximum {TIMESTAMP} |
| None |
|
|
|
|
|
Annual and Peak Values - Other
|
Annual Value [GJ] |
Minimum Value [W] |
Timestamp of Minimum {TIMESTAMP} |
Maximum Value [W] |
Timestamp of Maximum {TIMESTAMP} |
| EnergyTransfer:Facility |
3778.33 |
2777.32 |
21-SEP-05:50 |
485980.17 |
06-FEB-06:10 |
| EnergyTransfer:Building |
1091.19 |
1162.64 |
01-OCT-14:30 |
156897.13 |
13-JUL-16:30 |
| EnergyTransfer:Zone:OFFICE--OPENOFFICE1 |
49.90 |
0.01 |
03-JAN-20:10 |
12081.11 |
03-OCT-10:30 |
| Heating:EnergyTransfer |
170.58 |
0.00 |
02-JAN-16:40 |
151655.15 |
06-FEB-06:10 |
| Heating:EnergyTransfer:Zone:OFFICE--OPENOFFICE1 |
7.39 |
0.00 |
01-JAN-08:00 |
7268.91 |
06-FEB-06:10 |
| Cooling:EnergyTransfer |
920.61 |
0.00 |
01-JAN-00:50 |
156897.13 |
13-JUL-16:30 |
| Cooling:EnergyTransfer:Zone:OFFICE--OPENOFFICE1 |
42.51 |
0.00 |
01-JAN-00:10 |
12081.11 |
03-OCT-10:30 |
| EnergyTransfer:Zone:OFFICE--OPENOFFICE10 |
66.08 |
0.05 |
18-DEC-20:20 |
18071.41 |
25-JAN-15:00 |
| Heating:EnergyTransfer:Zone:OFFICE--OPENOFFICE10 |
5.53 |
0.00 |
01-JAN-10:20 |
7130.49 |
07-FEB-06:10 |
| Cooling:EnergyTransfer:Zone:OFFICE--OPENOFFICE10 |
60.55 |
0.00 |
01-JAN-00:10 |
18071.41 |
25-JAN-15:00 |
| EnergyTransfer:Zone:OFFICE--OPENOFFICE11 |
67.22 |
0.08 |
28-SEP-06:00 |
13876.78 |
03-OCT-10:30 |
| Heating:EnergyTransfer:Zone:OFFICE--OPENOFFICE11 |
5.27 |
0.00 |
01-JAN-08:00 |
7256.78 |
06-FEB-06:10 |
| Cooling:EnergyTransfer:Zone:OFFICE--OPENOFFICE11 |
61.95 |
0.00 |
01-JAN-00:10 |
13876.78 |
03-OCT-10:30 |
| EnergyTransfer:Zone:OFFICE--OPENOFFICE12 |
41.50 |
0.05 |
02-APR-01:10 |
9186.11 |
13-JUL-08:10 |
| Heating:EnergyTransfer:Zone:OFFICE--OPENOFFICE12 |
10.46 |
0.00 |
02-JAN-16:30 |
7716.03 |
06-FEB-06:10 |
| Cooling:EnergyTransfer:Zone:OFFICE--OPENOFFICE12 |
31.04 |
0.00 |
01-JAN-00:10 |
9186.11 |
13-JUL-08:10 |
| EnergyTransfer:Zone:OFFICE--OPENOFFICE13 |
73.31 |
0.00 |
20-JAN-05:20 |
15383.64 |
25-JAN-15:00 |
| Heating:EnergyTransfer:Zone:OFFICE--OPENOFFICE13 |
0.96 |
0.00 |
01-JAN-07:10 |
3312.45 |
06-FEB-06:10 |
| Cooling:EnergyTransfer:Zone:OFFICE--OPENOFFICE13 |
72.35 |
0.00 |
01-JAN-00:10 |
15383.64 |
25-JAN-15:00 |
| EnergyTransfer:Zone:OFFICE--OPENOFFICE14 |
42.36 |
0.02 |
29-APR-05:30 |
11848.83 |
20-JUL-17:40 |
| Heating:EnergyTransfer:Zone:OFFICE--OPENOFFICE14 |
10.86 |
0.00 |
02-JAN-16:30 |
8005.00 |
06-FEB-06:10 |
| Cooling:EnergyTransfer:Zone:OFFICE--OPENOFFICE14 |
31.50 |
0.00 |
01-JAN-00:10 |
11848.83 |
20-JUL-17:40 |
| EnergyTransfer:Zone:OFFICE--OPENOFFICE15 |
68.04 |
0.01 |
21-NOV-14:40 |
18165.98 |
25-JAN-15:00 |
| Heating:EnergyTransfer:Zone:OFFICE--OPENOFFICE15 |
5.79 |
0.00 |
01-JAN-10:30 |
7360.49 |
07-FEB-06:10 |
| Cooling:EnergyTransfer:Zone:OFFICE--OPENOFFICE15 |
62.25 |
0.00 |
01-JAN-00:10 |
18165.98 |
25-JAN-15:00 |
| EnergyTransfer:Zone:OFFICE--OPENOFFICE16 |
72.82 |
0.01 |
12-OCT-05:30 |
15071.41 |
03-OCT-10:30 |
| Heating:EnergyTransfer:Zone:OFFICE--OPENOFFICE16 |
10.30 |
0.00 |
01-JAN-08:20 |
9274.85 |
06-FEB-06:10 |
| Cooling:EnergyTransfer:Zone:OFFICE--OPENOFFICE16 |
62.52 |
0.00 |
01-JAN-00:10 |
15071.41 |
03-OCT-10:30 |
| EnergyTransfer:Zone:OFFICE--OPENOFFICE17 |
49.97 |
0.04 |
15-APR-01:10 |
10068.74 |
13-JUL-08:20 |
| Heating:EnergyTransfer:Zone:OFFICE--OPENOFFICE17 |
16.68 |
0.00 |
02-JAN-16:40 |
9427.32 |
06-FEB-06:10 |
| Cooling:EnergyTransfer:Zone:OFFICE--OPENOFFICE17 |
33.28 |
0.00 |
01-JAN-00:10 |
10068.74 |
13-JUL-08:20 |
| EnergyTransfer:Zone:OFFICE--OPENOFFICE18 |
78.99 |
0.02 |
29-APR-03:30 |
16662.66 |
23-JAN-06:10 |
| Heating:EnergyTransfer:Zone:OFFICE--OPENOFFICE18 |
6.89 |
0.00 |
01-JAN-09:10 |
16662.66 |
23-JAN-06:10 |
| Cooling:EnergyTransfer:Zone:OFFICE--OPENOFFICE18 |
72.10 |
0.00 |
01-JAN-00:10 |
12710.92 |
13-JUL-12:20 |
| EnergyTransfer:Zone:OFFICE--OPENOFFICE19 |
51.07 |
0.01 |
20-JAN-15:50 |
12830.37 |
20-JUL-17:40 |
| Heating:EnergyTransfer:Zone:OFFICE--OPENOFFICE19 |
17.17 |
0.00 |
02-JAN-16:40 |
9608.94 |
06-FEB-06:10 |
| Cooling:EnergyTransfer:Zone:OFFICE--OPENOFFICE19 |
33.90 |
0.00 |
01-JAN-00:10 |
12830.37 |
20-JUL-17:40 |
| EnergyTransfer:Zone:OFFICE--OPENOFFICE2 |
30.16 |
0.01 |
06-JUN-06:50 |
7232.10 |
11-JUL-08:10 |
| Heating:EnergyTransfer:Zone:OFFICE--OPENOFFICE2 |
12.47 |
0.00 |
02-JAN-16:30 |
7135.54 |
06-FEB-06:10 |
| Cooling:EnergyTransfer:Zone:OFFICE--OPENOFFICE2 |
17.70 |
0.00 |
01-JAN-00:10 |
7232.10 |
11-JUL-08:10 |
| EnergyTransfer:Zone:OFFICE--OPENOFFICE20 |
74.49 |
0.04 |
18-OCT-23:40 |
18317.04 |
25-JAN-15:00 |
| Heating:EnergyTransfer:Zone:OFFICE--OPENOFFICE20 |
11.14 |
0.00 |
01-JAN-10:40 |
9316.34 |
06-FEB-06:10 |
| Cooling:EnergyTransfer:Zone:OFFICE--OPENOFFICE20 |
63.35 |
0.00 |
01-JAN-00:10 |
18317.04 |
25-JAN-15:00 |
| EnergyTransfer:Zone:OFFICE--OPENOFFICE3 |
31.86 |
0.00 |
17-SEP-02:20 |
8566.44 |
25-JAN-15:00 |
| Heating:EnergyTransfer:Zone:OFFICE--OPENOFFICE3 |
2.46 |
0.00 |
01-JAN-08:10 |
6312.92 |
09-JAN-06:10 |
| Cooling:EnergyTransfer:Zone:OFFICE--OPENOFFICE3 |
29.40 |
0.00 |
01-JAN-00:10 |
8566.44 |
25-JAN-15:00 |
| EnergyTransfer:Zone:OFFICE--OPENOFFICE4 |
31.36 |
0.00 |
05-NOV-09:20 |
9976.01 |
20-JUL-17:40 |
| Heating:EnergyTransfer:Zone:OFFICE--OPENOFFICE4 |
12.90 |
0.00 |
02-JAN-16:30 |
7624.58 |
06-FEB-06:10 |
| Cooling:EnergyTransfer:Zone:OFFICE--OPENOFFICE4 |
18.46 |
0.00 |
01-JAN-00:10 |
9976.01 |
20-JUL-17:40 |
| EnergyTransfer:Zone:OFFICE--OPENOFFICE5 |
51.82 |
0.00 |
14-SEP-07:30 |
15929.07 |
25-JAN-15:00 |
| Heating:EnergyTransfer:Zone:OFFICE--OPENOFFICE5 |
8.02 |
0.00 |
01-JAN-10:30 |
7265.20 |
06-FEB-06:10 |
| Cooling:EnergyTransfer:Zone:OFFICE--OPENOFFICE5 |
43.80 |
0.00 |
01-JAN-00:10 |
15929.07 |
25-JAN-15:00 |
| EnergyTransfer:Zone:OFFICE--OPENOFFICE6 |
65.34 |
0.00 |
03-FEB-21:40 |
13771.40 |
03-OCT-10:30 |
| Heating:EnergyTransfer:Zone:OFFICE--OPENOFFICE6 |
5.08 |
0.00 |
01-JAN-08:00 |
7062.32 |
06-FEB-06:10 |
| Cooling:EnergyTransfer:Zone:OFFICE--OPENOFFICE6 |
60.26 |
0.00 |
01-JAN-00:10 |
13771.40 |
03-OCT-10:30 |
| EnergyTransfer:Zone:OFFICE--OPENOFFICE7 |
39.27 |
0.02 |
31-OCT-21:40 |
8938.08 |
13-JUL-08:10 |
| Heating:EnergyTransfer:Zone:OFFICE--OPENOFFICE7 |
10.06 |
0.00 |
02-JAN-16:30 |
7557.01 |
06-FEB-06:10 |
| Cooling:EnergyTransfer:Zone:OFFICE--OPENOFFICE7 |
29.21 |
0.00 |
01-JAN-00:10 |
8938.08 |
13-JUL-08:10 |
| EnergyTransfer:Zone:OFFICE--OPENOFFICE8 |
65.55 |
0.02 |
18-MAR-04:00 |
16457.65 |
25-JAN-15:00 |
| Heating:EnergyTransfer:Zone:OFFICE--OPENOFFICE8 |
0.71 |
0.00 |
01-JAN-00:10 |
2181.80 |
09-JAN-06:10 |
| Cooling:EnergyTransfer:Zone:OFFICE--OPENOFFICE8 |
64.84 |
0.00 |
01-JAN-00:50 |
16457.65 |
25-JAN-15:00 |
| EnergyTransfer:Zone:OFFICE--OPENOFFICE9 |
40.08 |
0.00 |
21-NOV-10:20 |
11650.80 |
20-JUL-17:40 |
| Heating:EnergyTransfer:Zone:OFFICE--OPENOFFICE9 |
10.44 |
0.00 |
02-JAN-16:30 |
7828.58 |
06-FEB-06:10 |
| Cooling:EnergyTransfer:Zone:OFFICE--OPENOFFICE9 |
29.63 |
0.00 |
01-JAN-00:10 |
11650.80 |
20-JUL-17:40 |
| EnergyTransfer:HVAC |
2687.14 |
0.00 |
15-APR-19:00 |
334325.03 |
06-FEB-06:10 |
| CoolingCoils:EnergyTransfer |
1298.52 |
0.00 |
01-JAN-00:10 |
294932.82 |
20-JUL-16:20 |
| HeatingCoils:EnergyTransfer |
1388.62 |
0.00 |
13-MAR-14:00 |
334325.03 |
06-FEB-06:10 |
Table of Contents
Report: Sensible Heat Gain Summary
For: Entire Facility
Timestamp: 2016-12-10
12:34:41
Annual Building Sensible Heat Gain Components
|
HVAC Zone Eq & Other Sensible Air Heating [GJ] |
HVAC Zone Eq & Other Sensible Air Cooling [GJ] |
HVAC Terminal Unit Sensible Air Heating [GJ] |
HVAC Terminal Unit Sensible Air Cooling [GJ] |
HVAC Input Heated Surface Heating [GJ] |
HVAC Input Cooled Surface Cooling [GJ] |
People Sensible Heat Addition [GJ] |
Lights Sensible Heat Addition [GJ] |
Equipment Sensible Heat Addition [GJ] |
Window Heat Addition [GJ] |
Interzone Air Transfer Heat Addition [GJ] |
Infiltration Heat Addition [GJ] |
Opaque Surface Conduction and Other Heat Addition [GJ] |
Equipment Sensible Heat Removal [GJ] |
Window Heat Removal [GJ] |
Interzone Air Transfer Heat Removal [GJ] |
Infiltration Heat Removal [GJ] |
Opaque Surface Conduction and Other Heat Removal [GJ] |
| OFFICE--OPENOFFICE1 |
6.934 |
-19.849 |
0.451 |
-22.664 |
0.000 |
0.000 |
1.212 |
8.603 |
0.028 |
92.266 |
0.000 |
0.000 |
0.001 |
0.000 |
-20.263 |
0.000 |
-0.000 |
-46.718 |
| OFFICE--OPENOFFICE10 |
5.371 |
-33.461 |
0.158 |
-27.093 |
0.000 |
0.000 |
1.217 |
8.555 |
0.028 |
91.539 |
0.000 |
0.000 |
0.000 |
0.000 |
-23.448 |
0.000 |
-0.000 |
-22.866 |
| OFFICE--OPENOFFICE11 |
5.062 |
-34.813 |
0.208 |
-27.141 |
0.000 |
0.000 |
1.199 |
8.601 |
0.028 |
90.065 |
0.000 |
0.000 |
0.001 |
0.000 |
-22.867 |
0.000 |
-0.000 |
-20.342 |
| OFFICE--OPENOFFICE12 |
9.804 |
-9.182 |
0.652 |
-21.857 |
0.000 |
0.000 |
1.252 |
8.612 |
0.028 |
39.629 |
0.000 |
0.000 |
0.000 |
0.000 |
-21.411 |
0.000 |
-0.000 |
-7.527 |
| OFFICE--OPENOFFICE13 |
0.958 |
-44.865 |
0.000 |
-27.483 |
0.000 |
0.000 |
0.497 |
80.598 |
0.118 |
0.000 |
0.000 |
0.000 |
0.000 |
0.000 |
0.000 |
0.000 |
-0.000 |
-9.824 |
| OFFICE--OPENOFFICE14 |
10.267 |
-9.076 |
0.593 |
-22.420 |
0.000 |
0.000 |
1.254 |
8.569 |
0.028 |
41.174 |
0.000 |
0.000 |
0.000 |
0.000 |
-22.095 |
0.000 |
-0.000 |
-8.295 |
| OFFICE--OPENOFFICE15 |
5.614 |
-34.873 |
0.174 |
-27.377 |
0.000 |
0.000 |
1.216 |
8.555 |
0.028 |
91.074 |
0.000 |
0.000 |
0.001 |
0.000 |
-23.784 |
0.000 |
-0.000 |
-20.629 |
| OFFICE--OPENOFFICE16 |
9.654 |
-37.302 |
0.647 |
-25.215 |
0.000 |
0.000 |
1.205 |
8.610 |
0.028 |
90.504 |
0.000 |
0.000 |
0.003 |
0.000 |
-21.523 |
0.000 |
-0.000 |
-26.609 |
| OFFICE--OPENOFFICE17 |
15.572 |
-12.544 |
1.112 |
-20.740 |
0.000 |
0.000 |
1.256 |
8.622 |
0.028 |
39.813 |
0.000 |
0.000 |
0.000 |
0.000 |
-20.446 |
0.000 |
-0.000 |
-12.673 |
| OFFICE--OPENOFFICE18 |
6.856 |
-48.080 |
0.037 |
-24.016 |
0.000 |
0.000 |
0.503 |
80.598 |
0.118 |
0.000 |
0.000 |
0.000 |
0.000 |
0.000 |
0.000 |
0.000 |
-0.000 |
-16.017 |
| OFFICE--OPENOFFICE19 |
16.134 |
-12.665 |
1.036 |
-21.235 |
0.000 |
0.000 |
1.258 |
8.576 |
0.028 |
41.323 |
0.000 |
0.000 |
0.001 |
0.000 |
-21.079 |
0.000 |
-0.000 |
-13.376 |
| OFFICE--OPENOFFICE2 |
11.523 |
-0.012 |
0.943 |
-17.684 |
0.000 |
0.000 |
1.270 |
8.613 |
0.028 |
41.411 |
0.000 |
0.000 |
0.000 |
0.000 |
-19.162 |
0.000 |
-0.000 |
-26.931 |
| OFFICE--OPENOFFICE20 |
10.585 |
-38.016 |
0.558 |
-25.335 |
0.000 |
0.000 |
1.222 |
8.561 |
0.028 |
91.438 |
0.000 |
0.000 |
0.000 |
0.000 |
-22.370 |
0.000 |
-0.000 |
-26.672 |
| OFFICE--OPENOFFICE3 |
2.460 |
-8.325 |
0.000 |
-21.076 |
0.000 |
0.000 |
0.504 |
80.598 |
0.118 |
0.000 |
0.000 |
0.000 |
0.000 |
0.000 |
0.000 |
0.000 |
-0.000 |
-54.279 |
| OFFICE--OPENOFFICE4 |
12.049 |
-0.425 |
0.854 |
-18.035 |
0.000 |
0.000 |
1.275 |
8.570 |
0.028 |
43.020 |
0.000 |
0.000 |
0.000 |
0.000 |
-19.749 |
0.000 |
-0.000 |
-27.588 |
| OFFICE--OPENOFFICE5 |
7.648 |
-21.211 |
0.370 |
-22.587 |
0.000 |
0.000 |
1.233 |
8.556 |
0.028 |
93.462 |
0.000 |
0.000 |
0.000 |
0.000 |
-21.077 |
0.000 |
-0.000 |
-46.423 |
| OFFICE--OPENOFFICE6 |
4.892 |
-33.415 |
0.189 |
-26.846 |
0.000 |
0.000 |
1.199 |
8.601 |
0.028 |
90.477 |
0.000 |
0.000 |
0.001 |
0.000 |
-22.547 |
0.000 |
-0.000 |
-22.577 |
| OFFICE--OPENOFFICE7 |
9.434 |
-7.743 |
0.625 |
-21.469 |
0.000 |
0.000 |
1.252 |
8.612 |
0.028 |
39.928 |
0.000 |
0.000 |
0.000 |
0.000 |
-21.063 |
0.000 |
-0.000 |
-9.604 |
| OFFICE--OPENOFFICE8 |
0.711 |
-37.749 |
0.000 |
-27.087 |
0.000 |
0.000 |
0.497 |
80.598 |
0.118 |
0.000 |
0.000 |
0.000 |
0.000 |
0.000 |
0.000 |
0.000 |
-0.000 |
-17.088 |
| OFFICE--OPENOFFICE9 |
9.880 |
-7.592 |
0.563 |
-22.042 |
0.000 |
0.000 |
1.255 |
8.569 |
0.028 |
41.488 |
0.000 |
0.000 |
0.001 |
0.000 |
-21.731 |
0.000 |
-0.000 |
-10.418 |
| Total Facility |
161.410 |
-451.196 |
9.173 |
-469.402 |
0.000 |
0.000 |
21.775 |
459.782 |
0.919 |
1058.610 |
0.000 |
0.000 |
0.010 |
0.000 |
-344.613 |
0.000 |
-0.001 |
-446.458 |
Peak Cooling Sensible Heat Gain Components
|
Time of Peak {TIMESTAMP} |
HVAC Zone Eq & Other Sensible Air Heating [W] |
HVAC Zone Eq & Other Sensible Air Cooling [W] |
HVAC Terminal Unit Sensible Air Heating [W] |
HVAC Terminal Unit Sensible Air Cooling [W] |
HVAC Input Heated Surface Heating [W] |
HVAC Input Cooled Surface Cooling [W] |
People Sensible Heat Addition [W] |
Lights Sensible Heat Addition [W] |
Equipment Sensible Heat Addition [W] |
Window Heat Addition [W] |
Interzone Air Transfer Heat Addition [W] |
Infiltration Heat Addition [W] |
Opaque Surface Conduction and Other Heat Addition [W] |
Equipment Sensible Heat Removal [W] |
Window Heat Removal [W] |
Interzone Air Transfer Heat Removal [W] |
Infiltration Heat Removal [W] |
Opaque Surface Conduction and Other Heat Removal [W] |
| OFFICE--OPENOFFICE1 |
09-FEB-10:31 |
0.00 |
-13299.23 |
0.00 |
-2298.37 |
0.00 |
0.00 |
68.75 |
441.10 |
1.47 |
21285.57 |
0.00 |
0.00 |
0.00 |
0.00 |
-0.00 |
0.00 |
-0.00 |
-6199.29 |
| OFFICE--OPENOFFICE10 |
25-JAN-14:51 |
0.00 |
-16098.20 |
0.00 |
-3182.43 |
0.00 |
0.00 |
37.57 |
441.10 |
1.47 |
21242.61 |
0.00 |
0.00 |
0.00 |
0.00 |
-0.00 |
0.00 |
-0.00 |
-2442.12 |
| OFFICE--OPENOFFICE11 |
09-FEB-10:31 |
0.00 |
-15671.11 |
0.00 |
-2344.77 |
0.00 |
0.00 |
66.29 |
441.10 |
1.47 |
20986.62 |
0.00 |
0.00 |
0.00 |
0.00 |
-0.00 |
0.00 |
-0.00 |
-3479.59 |
| OFFICE--OPENOFFICE12 |
11-JUL-06:01 |
0.00 |
-12894.00 |
0.00 |
-1666.86 |
0.00 |
0.00 |
9.21 |
49.01 |
0.65 |
14983.56 |
0.00 |
0.00 |
0.00 |
0.00 |
-0.00 |
0.00 |
-0.00 |
-481.58 |
| OFFICE--OPENOFFICE13 |
25-JAN-14:51 |
0.00 |
-20018.49 |
0.00 |
-1359.95 |
0.00 |
0.00 |
39.41 |
6228.04 |
6.23 |
0.00 |
0.00 |
0.00 |
15104.76 |
0.00 |
-0.00 |
0.00 |
-0.00 |
0.00 |
| OFFICE--OPENOFFICE14 |
06-AUG-00:02 |
0.00 |
-12901.68 |
0.00 |
-1217.19 |
0.00 |
0.00 |
0.00 |
81.69 |
0.49 |
0.00 |
0.00 |
0.00 |
14529.38 |
0.00 |
-492.69 |
0.00 |
0.00 |
0.00 |
| OFFICE--OPENOFFICE15 |
25-JAN-14:51 |
0.00 |
-16264.67 |
0.00 |
-3123.29 |
0.00 |
0.00 |
39.60 |
441.10 |
1.47 |
21152.56 |
0.00 |
0.00 |
0.00 |
0.00 |
-0.00 |
0.00 |
-0.00 |
-2246.77 |
| OFFICE--OPENOFFICE16 |
09-FEB-10:31 |
0.00 |
-17102.15 |
0.00 |
-2282.12 |
0.00 |
0.00 |
67.66 |
441.10 |
1.47 |
21057.56 |
0.00 |
0.00 |
0.00 |
0.00 |
-0.00 |
0.00 |
-0.00 |
-2183.51 |
| OFFICE--OPENOFFICE17 |
11-JUL-06:01 |
0.00 |
-13809.39 |
0.00 |
-1616.43 |
0.00 |
0.00 |
9.25 |
49.01 |
0.65 |
15045.38 |
0.00 |
0.00 |
321.53 |
0.00 |
-0.00 |
0.00 |
-0.00 |
0.00 |
| OFFICE--OPENOFFICE18 |
25-JAN-14:51 |
0.00 |
-20509.09 |
0.00 |
-1073.08 |
0.00 |
0.00 |
43.36 |
6228.04 |
6.23 |
0.00 |
0.00 |
0.00 |
15304.54 |
0.00 |
-0.00 |
0.00 |
-0.00 |
0.00 |
| OFFICE--OPENOFFICE19 |
06-AUG-00:02 |
0.00 |
-12549.47 |
0.00 |
-1149.04 |
0.00 |
0.00 |
0.00 |
81.69 |
0.49 |
0.00 |
0.00 |
0.00 |
14065.57 |
0.00 |
-449.24 |
0.00 |
0.00 |
0.00 |
| OFFICE--OPENOFFICE2 |
11-JUL-06:01 |
0.00 |
-9907.72 |
0.00 |
-1343.26 |
0.00 |
0.00 |
10.23 |
49.01 |
0.65 |
15311.21 |
0.00 |
0.00 |
0.00 |
0.00 |
-0.00 |
0.00 |
-0.00 |
-4120.13 |
| OFFICE--OPENOFFICE20 |
25-JAN-14:51 |
0.00 |
-17815.04 |
0.00 |
-3125.29 |
0.00 |
0.00 |
38.82 |
441.10 |
1.47 |
21182.02 |
0.00 |
0.00 |
0.00 |
0.00 |
-0.00 |
0.00 |
-0.00 |
-723.08 |
| OFFICE--OPENOFFICE3 |
25-JAN-14:51 |
0.00 |
-15246.22 |
0.00 |
-1133.71 |
0.00 |
0.00 |
42.72 |
6228.04 |
6.23 |
0.00 |
0.00 |
0.00 |
10102.94 |
0.00 |
-0.00 |
0.00 |
-0.00 |
0.00 |
| OFFICE--OPENOFFICE4 |
12-JUL-17:50 |
0.00 |
-8867.98 |
0.00 |
-1106.82 |
0.00 |
0.00 |
80.11 |
343.08 |
1.31 |
16549.56 |
0.00 |
0.00 |
0.00 |
0.00 |
-0.00 |
0.00 |
0.00 |
-6999.26 |
| OFFICE--OPENOFFICE5 |
25-JAN-14:51 |
0.00 |
-13912.20 |
0.00 |
-3079.13 |
0.00 |
0.00 |
42.21 |
441.10 |
1.47 |
21529.12 |
0.00 |
0.00 |
0.00 |
0.00 |
-0.00 |
0.00 |
-0.00 |
-5022.57 |
| OFFICE--OPENOFFICE6 |
09-FEB-10:31 |
0.00 |
-15511.14 |
0.00 |
-2399.94 |
0.00 |
0.00 |
64.57 |
441.10 |
1.47 |
21045.11 |
0.00 |
0.00 |
0.00 |
0.00 |
-0.00 |
0.00 |
-0.00 |
-3641.18 |
| OFFICE--OPENOFFICE7 |
11-JUL-06:01 |
0.00 |
-12630.04 |
0.00 |
-1634.38 |
0.00 |
0.00 |
9.25 |
49.01 |
0.65 |
15055.46 |
0.00 |
0.00 |
0.00 |
0.00 |
-0.00 |
0.00 |
-0.00 |
-849.94 |
| OFFICE--OPENOFFICE8 |
25-JAN-14:51 |
0.00 |
-19149.64 |
0.00 |
-1406.65 |
0.00 |
0.00 |
38.78 |
6228.04 |
6.23 |
0.00 |
0.00 |
0.00 |
14283.24 |
0.00 |
-0.00 |
0.00 |
-0.00 |
0.00 |
| OFFICE--OPENOFFICE9 |
06-AUG-00:02 |
0.00 |
-12593.60 |
0.00 |
-1161.74 |
0.00 |
0.00 |
0.00 |
81.69 |
0.49 |
0.00 |
0.00 |
0.00 |
14140.00 |
0.00 |
-466.84 |
0.00 |
0.00 |
0.00 |
| Total Facility |
13-JUL-06:01 |
0.00 |
-215297.13 |
0.00 |
-23894.57 |
0.00 |
0.00 |
187.22 |
3552.20 |
21.53 |
97278.41 |
0.00 |
0.00 |
138152.33 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
Peak Heating Sensible Heat Gain Components
|
Time of Peak {TIMESTAMP} |
HVAC Zone Eq & Other Sensible Air Heating [W] |
HVAC Zone Eq & Other Sensible Air Cooling [W] |
HVAC Terminal Unit Sensible Air Heating [W] |
HVAC Terminal Unit Sensible Air Cooling [W] |
HVAC Input Heated Surface Heating [W] |
HVAC Input Cooled Surface Cooling [W] |
People Sensible Heat Addition [W] |
Lights Sensible Heat Addition [W] |
Equipment Sensible Heat Addition [W] |
Window Heat Addition [W] |
Interzone Air Transfer Heat Addition [W] |
Infiltration Heat Addition [W] |
Opaque Surface Conduction and Other Heat Addition [W] |
Equipment Sensible Heat Removal [W] |
Window Heat Removal [W] |
Interzone Air Transfer Heat Removal [W] |
Infiltration Heat Removal [W] |
Opaque Surface Conduction and Other Heat Removal [W] |
| OFFICE--OPENOFFICE1 |
28-NOV-06:02 |
15123.73 |
60.64 |
0.00 |
-60.64 |
0.00 |
0.00 |
14.64 |
163.37 |
0.65 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
-1264.33 |
0.00 |
-0.00 |
-14038.06 |
| OFFICE--OPENOFFICE10 |
28-NOV-06:02 |
18036.80 |
223.42 |
0.00 |
-223.42 |
0.00 |
0.00 |
14.42 |
163.37 |
0.65 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
-1320.22 |
0.00 |
-0.00 |
-16895.02 |
| OFFICE--OPENOFFICE11 |
28-NOV-06:02 |
17568.96 |
236.29 |
0.00 |
-236.29 |
0.00 |
0.00 |
14.37 |
163.37 |
0.65 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
-1340.39 |
0.00 |
-0.00 |
-16406.97 |
| OFFICE--OPENOFFICE12 |
28-NOV-06:02 |
14358.64 |
30.97 |
0.00 |
-30.97 |
0.00 |
0.00 |
14.67 |
163.37 |
0.65 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
-1267.67 |
0.00 |
-0.00 |
-13269.67 |
| OFFICE--OPENOFFICE13 |
09-JAN-06:01 |
15859.73 |
235.07 |
0.00 |
-235.07 |
0.00 |
0.00 |
5.79 |
692.00 |
2.77 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
-0.00 |
0.00 |
-0.00 |
-16560.28 |
| OFFICE--OPENOFFICE14 |
28-NOV-06:02 |
15917.92 |
79.52 |
0.00 |
-79.52 |
0.00 |
0.00 |
14.63 |
163.37 |
0.65 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
-1272.62 |
0.00 |
-0.00 |
-14823.96 |
| OFFICE--OPENOFFICE15 |
28-NOV-06:02 |
18232.47 |
211.00 |
0.00 |
-211.00 |
0.00 |
0.00 |
14.45 |
163.37 |
0.65 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
-1314.84 |
0.00 |
-0.00 |
-17096.10 |
| OFFICE--OPENOFFICE16 |
28-NOV-06:02 |
19323.33 |
66.36 |
0.00 |
-66.36 |
0.00 |
0.00 |
14.79 |
163.37 |
0.65 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
-1223.57 |
0.00 |
-0.00 |
-18278.58 |
| OFFICE--OPENOFFICE17 |
28-NOV-06:02 |
15501.00 |
0.00 |
124.47 |
0.00 |
0.00 |
0.00 |
15.03 |
163.37 |
0.65 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
-1166.54 |
0.00 |
-0.00 |
-14637.98 |
| OFFICE--OPENOFFICE18 |
28-NOV-06:02 |
23535.53 |
251.20 |
0.00 |
-251.20 |
0.00 |
0.00 |
5.82 |
692.00 |
2.77 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
-0.00 |
0.00 |
-0.00 |
-24236.12 |
| OFFICE--OPENOFFICE19 |
28-NOV-06:02 |
17320.10 |
0.00 |
68.75 |
0.00 |
0.00 |
0.00 |
14.99 |
163.37 |
0.65 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
-1173.03 |
0.00 |
-0.00 |
-16394.84 |
| OFFICE--OPENOFFICE2 |
28-NOV-06:02 |
11824.26 |
0.00 |
104.01 |
0.00 |
0.00 |
0.00 |
14.85 |
163.37 |
0.65 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
-1216.46 |
0.00 |
-0.00 |
-10890.69 |
| OFFICE--OPENOFFICE20 |
28-NOV-06:02 |
20098.40 |
58.26 |
0.00 |
-58.26 |
0.00 |
0.00 |
14.84 |
163.37 |
0.65 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
-1206.96 |
0.00 |
-0.00 |
-19070.30 |
| OFFICE--OPENOFFICE3 |
11-DEC-06:03 |
17292.50 |
253.01 |
0.00 |
-253.01 |
0.00 |
0.00 |
5.83 |
692.00 |
2.77 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
-0.00 |
0.00 |
-0.00 |
-17993.10 |
| OFFICE--OPENOFFICE4 |
28-NOV-06:02 |
13469.47 |
0.00 |
55.34 |
0.00 |
0.00 |
0.00 |
14.82 |
163.37 |
0.65 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
-1221.16 |
0.00 |
-0.00 |
-12482.49 |
| OFFICE--OPENOFFICE5 |
28-NOV-06:02 |
15803.45 |
51.58 |
0.00 |
-51.58 |
0.00 |
0.00 |
14.69 |
163.37 |
0.65 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
-1249.11 |
0.00 |
-0.00 |
-14733.05 |
| OFFICE--OPENOFFICE6 |
28-NOV-06:02 |
17378.37 |
249.74 |
0.00 |
-249.74 |
0.00 |
0.00 |
14.34 |
163.37 |
0.65 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
-1346.04 |
0.00 |
-0.00 |
-16210.68 |
| OFFICE--OPENOFFICE7 |
28-NOV-06:02 |
14147.89 |
42.69 |
0.00 |
-42.69 |
0.00 |
0.00 |
14.64 |
163.37 |
0.65 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
-1273.24 |
0.00 |
-0.00 |
-13053.31 |
| OFFICE--OPENOFFICE8 |
09-JAN-06:01 |
13094.56 |
263.45 |
0.00 |
-263.45 |
0.00 |
0.00 |
5.74 |
692.00 |
2.77 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
-0.00 |
0.00 |
-0.00 |
-13795.07 |
| OFFICE--OPENOFFICE9 |
28-NOV-06:02 |
15698.50 |
90.53 |
0.00 |
-90.53 |
0.00 |
0.00 |
14.60 |
163.37 |
0.65 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
-1277.88 |
0.00 |
-0.00 |
-14599.24 |
| Total Facility |
28-NOV-06:02 |
294227.44 |
2868.56 |
352.57 |
-2868.56 |
0.00 |
0.00 |
257.20 |
5381.96 |
21.53 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
-20134.08 |
0.00 |
-0.01 |
-280106.61 |
Table of Contents
Report: Standard 62.1 Summary
For: Entire Facility
Timestamp: 2016-12-10
12:34:41
System Ventilation Requirements for Cooling
|
Sum of Zone Primary Air Flow - Vpz-sum [m3/s] |
System Population - Ps |
Sum of Zone Population - Pz-sum |
Occupant Diversity - D |
Uncorrected Outdoor Air Intake Airflow - Vou [m3/s] |
System Primary Airflow - Vps [m3/s] |
Average Outdoor Air Fraction - Xs |
System Ventilation Efficiency - Ev |
Outdoor Air Intake Flow - Vot [m3/s] |
Percent Outdoor Air - %OA |
| DOAS AIR LOOP HVAC1 |
21.801 |
28.91 |
28.91 |
1.00 |
4.4830 |
4.483 |
1.000 |
1.000 |
4.4830 |
1.00 |
System Ventilation Requirements for Heating
|
Sum of Zone Primary Air Flow - Vpz-sum [m3/s] |
System Population - Ps |
Sum of Zone Population - Pz-sum |
Occupant Diversity - D |
Uncorrected Outdoor Air Intake Airflow - Vou [m3/s] |
System Primary Airflow - Vps [m3/s] |
Average Outdoor Air Fraction - Xs |
System Ventilation Efficiency - Ev |
Outdoor Air Intake Flow Vot [m3/s] |
Percent Outdoor Air - %OA |
| DOAS AIR LOOP HVAC1 |
4.802 |
28.91 |
28.91 |
1.00 |
4.4830 |
4.483 |
0.934 |
1.000 |
4.4830 |
1.00 |
Zone Ventilation Parameters
|
AirLoop Name |
People Outdoor Air Rate - Rp [m3/s-person] |
Zone Population - Pz |
Area Outdoor Air Rate - Ra [m3/s-m2] |
Zone Floor Area - Az [m2] |
Breathing Zone Outdoor Airflow - Vbz [m3/s] |
Cooling Zone Air Distribution Effectiveness - Ez-clg |
Cooling Zone Outdoor Airflow - Voz-clg [m3/s] |
Heating Zone Air Distribution Effectiveness - Ez-htg |
Heating Zone Outdoor Airflow - Voz-htg [m3/s] |
| OFFICE--OPENOFFICE1 |
DOAS AIR LOOP HVAC1 |
0.000000 |
1.63 |
0.001523 |
151.78 |
0.2312 |
1.000 |
0.2312 |
1.000 |
0.2312 |
| OFFICE--OPENOFFICE10 |
DOAS AIR LOOP HVAC1 |
0.000000 |
1.63 |
0.001523 |
151.78 |
0.2312 |
1.000 |
0.2312 |
1.000 |
0.2312 |
| OFFICE--OPENOFFICE11 |
DOAS AIR LOOP HVAC1 |
0.000000 |
1.63 |
0.001523 |
151.78 |
0.2312 |
1.000 |
0.2312 |
1.000 |
0.2312 |
| OFFICE--OPENOFFICE12 |
DOAS AIR LOOP HVAC1 |
0.000000 |
1.63 |
0.001523 |
151.78 |
0.2312 |
1.000 |
0.2312 |
1.000 |
0.2312 |
| OFFICE--OPENOFFICE13 |
DOAS AIR LOOP HVAC1 |
0.000000 |
0.69 |
0.000305 |
642.89 |
0.1959 |
1.000 |
0.1959 |
1.000 |
0.1959 |
| OFFICE--OPENOFFICE14 |
DOAS AIR LOOP HVAC1 |
0.000000 |
1.63 |
0.001523 |
151.78 |
0.2312 |
1.000 |
0.2312 |
1.000 |
0.2312 |
| OFFICE--OPENOFFICE15 |
DOAS AIR LOOP HVAC1 |
0.000000 |
1.63 |
0.001523 |
151.78 |
0.2312 |
1.000 |
0.2312 |
1.000 |
0.2312 |
| OFFICE--OPENOFFICE16 |
DOAS AIR LOOP HVAC1 |
0.000000 |
1.63 |
0.001523 |
151.78 |
0.2312 |
1.000 |
0.2312 |
1.000 |
0.2312 |
| OFFICE--OPENOFFICE17 |
DOAS AIR LOOP HVAC1 |
0.000000 |
1.63 |
0.001523 |
151.78 |
0.2312 |
1.000 |
0.2312 |
1.000 |
0.2312 |
| OFFICE--OPENOFFICE18 |
DOAS AIR LOOP HVAC1 |
0.000000 |
0.69 |
0.000305 |
642.89 |
0.1959 |
1.000 |
0.1959 |
1.000 |
0.1959 |
| OFFICE--OPENOFFICE19 |
DOAS AIR LOOP HVAC1 |
0.000000 |
1.63 |
0.001523 |
151.78 |
0.2312 |
1.000 |
0.2312 |
1.000 |
0.2312 |
| OFFICE--OPENOFFICE2 |
DOAS AIR LOOP HVAC1 |
0.000000 |
1.63 |
0.001523 |
151.78 |
0.2312 |
1.000 |
0.2312 |
1.000 |
0.2312 |
| OFFICE--OPENOFFICE20 |
DOAS AIR LOOP HVAC1 |
0.000000 |
1.63 |
0.001523 |
151.78 |
0.2312 |
1.000 |
0.2312 |
1.000 |
0.2312 |
| OFFICE--OPENOFFICE3 |
DOAS AIR LOOP HVAC1 |
0.000000 |
0.69 |
0.000305 |
642.89 |
0.1959 |
1.000 |
0.1959 |
1.000 |
0.1959 |
| OFFICE--OPENOFFICE4 |
DOAS AIR LOOP HVAC1 |
0.000000 |
1.63 |
0.001523 |
151.78 |
0.2312 |
1.000 |
0.2312 |
1.000 |
0.2312 |
| OFFICE--OPENOFFICE5 |
DOAS AIR LOOP HVAC1 |
0.000000 |
1.63 |
0.001523 |
151.78 |
0.2312 |
1.000 |
0.2312 |
1.000 |
0.2312 |
| OFFICE--OPENOFFICE6 |
DOAS AIR LOOP HVAC1 |
0.000000 |
1.63 |
0.001523 |
151.78 |
0.2312 |
1.000 |
0.2312 |
1.000 |
0.2312 |
| OFFICE--OPENOFFICE7 |
DOAS AIR LOOP HVAC1 |
0.000000 |
1.63 |
0.001523 |
151.78 |
0.2312 |
1.000 |
0.2312 |
1.000 |
0.2312 |
| OFFICE--OPENOFFICE8 |
DOAS AIR LOOP HVAC1 |
0.000000 |
0.69 |
0.000305 |
642.89 |
0.1959 |
1.000 |
0.1959 |
1.000 |
0.1959 |
| OFFICE--OPENOFFICE9 |
DOAS AIR LOOP HVAC1 |
0.000000 |
1.63 |
0.001523 |
151.78 |
0.2312 |
1.000 |
0.2312 |
1.000 |
0.2312 |
System Ventilation Parameters
|
People Outdoor Air Rate - Rp [m3/s-person] |
Sum of Zone Population - Pz-sum |
Area Outdoor Air Rate - Ra [m3/s-m2] |
Sum of Zone Floor Area - Az-sum [m2] |
Breathing Zone Outdoor Airflow - Vbz [m3/s] |
Cooling Zone Outdoor Airflow - Voz-clg [m3/s] |
Heating Zone Outdoor Airflow - Voz-htg [m3/s] |
| DOAS AIR LOOP HVAC1 |
0.000000 |
28.91 |
0.000897 |
5000.00 |
4.4830 |
4.4830 |
4.4830 |
Zone Ventilation Calculations for Cooling Design
|
AirLoop Name |
Box Type |
Zone Primary Airflow - Vpz [m3/s] |
Zone Discharge Airflow - Vdz [m3/s] |
Minimum Zone Primary Airflow - Vpz-min [m3/s] |
Zone Outdoor Airflow Cooling - Voz-clg [m3/s] |
Primary Outdoor Air Fraction - Zpz |
Primary Air Fraction - Ep |
Secondary Recirculation Fraction- Er |
Supply Air Fraction- Fa |
Mixed Air Fraction - Fb |
Outdoor Air Fraction - Fc |
Zone Ventilation Efficiency - Evz |
| OFFICE--OPENOFFICE1 |
DOAS AIR LOOP HVAC1 |
|
0.957 |
0.9569 |
0.1157 |
0.2312 |
0.000 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
| OFFICE--OPENOFFICE10 |
DOAS AIR LOOP HVAC1 |
|
1.169 |
1.1694 |
0.1157 |
0.2312 |
0.000 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
| OFFICE--OPENOFFICE11 |
DOAS AIR LOOP HVAC1 |
|
1.138 |
1.1377 |
0.1157 |
0.2312 |
0.000 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
| OFFICE--OPENOFFICE12 |
DOAS AIR LOOP HVAC1 |
|
0.903 |
0.9032 |
0.1157 |
0.2312 |
0.000 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
| OFFICE--OPENOFFICE13 |
DOAS AIR LOOP HVAC1 |
|
1.395 |
1.3952 |
0.4899 |
0.1959 |
0.000 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
| OFFICE--OPENOFFICE14 |
DOAS AIR LOOP HVAC1 |
|
1.012 |
1.0124 |
0.1157 |
0.2312 |
0.000 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
| OFFICE--OPENOFFICE15 |
DOAS AIR LOOP HVAC1 |
|
1.182 |
1.1822 |
0.1157 |
0.2312 |
0.000 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
| OFFICE--OPENOFFICE16 |
DOAS AIR LOOP HVAC1 |
|
1.248 |
1.2484 |
0.1157 |
0.2312 |
0.000 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
| OFFICE--OPENOFFICE17 |
DOAS AIR LOOP HVAC1 |
|
0.978 |
0.9780 |
0.1157 |
0.2312 |
0.000 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
| OFFICE--OPENOFFICE18 |
DOAS AIR LOOP HVAC1 |
|
1.430 |
1.4300 |
0.4899 |
0.1959 |
0.000 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
| OFFICE--OPENOFFICE19 |
DOAS AIR LOOP HVAC1 |
|
1.103 |
1.1031 |
0.1157 |
0.2312 |
0.000 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
| OFFICE--OPENOFFICE2 |
DOAS AIR LOOP HVAC1 |
|
0.732 |
0.7324 |
0.1157 |
0.2312 |
0.000 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
| OFFICE--OPENOFFICE20 |
DOAS AIR LOOP HVAC1 |
|
1.303 |
1.3028 |
0.1157 |
0.2312 |
0.000 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
| OFFICE--OPENOFFICE3 |
DOAS AIR LOOP HVAC1 |
|
1.058 |
1.0581 |
0.4899 |
0.1959 |
0.000 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
| OFFICE--OPENOFFICE4 |
DOAS AIR LOOP HVAC1 |
|
0.841 |
0.8413 |
0.1157 |
0.2312 |
0.000 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
| OFFICE--OPENOFFICE5 |
DOAS AIR LOOP HVAC1 |
|
1.003 |
1.0025 |
0.1157 |
0.2312 |
0.000 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
| OFFICE--OPENOFFICE6 |
DOAS AIR LOOP HVAC1 |
|
1.125 |
1.1254 |
0.1157 |
0.2312 |
0.000 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
| OFFICE--OPENOFFICE7 |
DOAS AIR LOOP HVAC1 |
|
0.890 |
0.8899 |
0.1157 |
0.2312 |
0.000 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
| OFFICE--OPENOFFICE8 |
DOAS AIR LOOP HVAC1 |
|
1.334 |
1.3337 |
0.4899 |
0.1959 |
0.000 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
| OFFICE--OPENOFFICE9 |
DOAS AIR LOOP HVAC1 |
|
0.998 |
0.9982 |
0.1157 |
0.2312 |
0.000 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
System Ventilation Calculations for Cooling Design
|
Sum of Zone Primary Airflow - Vpz-sum [m3/s] |
System Primary Airflow - Vps [m3/s] |
Sum of Zone Discharge Airflow - Vdz-sum [m3/s] |
Sum of Min Zone Primary Airflow - Vpz-min [m3/s] |
Zone Outdoor Airflow Cooling - Voz-clg [m3/s] |
Zone Ventilation Efficiency - Evz-min |
| DOAS AIR LOOP HVAC1 |
21.80 |
4.483 |
21.80 |
3.8100 |
4.4830 |
1.000 |
Zone Ventilation Calculations for Heating Design
|
AirLoop Name |
Box Type |
Zone Primary Airflow - Vpz [m3/s] |
Zone Discharge Airflow - Vdz [m3/s] |
Minimum Zone Primary Airflow - Vpz-min [m3/s] |
Zone Outdoor Airflow Heating - Voz-htg [m3/s] |
Primary Outdoor Air Fraction - Zpz |
Primary Air Fraction - Ep |
Secondary Recirculation Fraction- Er |
Supply Air Fraction- Fa |
Mixed Air Fraction - Fb |
Outdoor Air Fraction - Fc |
Zone Ventilation Efficiency - Evz |
| OFFICE--OPENOFFICE1 |
DOAS AIR LOOP HVAC1 |
|
0.231 |
0.231 |
0.231 |
0.2312 |
1.000 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
| OFFICE--OPENOFFICE10 |
DOAS AIR LOOP HVAC1 |
|
0.231 |
0.231 |
0.231 |
0.2312 |
1.000 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
| OFFICE--OPENOFFICE11 |
DOAS AIR LOOP HVAC1 |
|
0.231 |
0.231 |
0.231 |
0.2312 |
1.000 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
| OFFICE--OPENOFFICE12 |
DOAS AIR LOOP HVAC1 |
|
0.231 |
0.231 |
0.231 |
0.2312 |
1.000 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
| OFFICE--OPENOFFICE13 |
DOAS AIR LOOP HVAC1 |
|
0.196 |
0.196 |
0.196 |
0.1959 |
1.000 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
| OFFICE--OPENOFFICE14 |
DOAS AIR LOOP HVAC1 |
|
0.231 |
0.231 |
0.231 |
0.2312 |
1.000 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
| OFFICE--OPENOFFICE15 |
DOAS AIR LOOP HVAC1 |
|
0.231 |
0.231 |
0.231 |
0.2312 |
1.000 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
| OFFICE--OPENOFFICE16 |
DOAS AIR LOOP HVAC1 |
|
0.276 |
0.276 |
0.276 |
0.2312 |
0.837 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
| OFFICE--OPENOFFICE17 |
DOAS AIR LOOP HVAC1 |
|
0.280 |
0.280 |
0.280 |
0.2312 |
0.827 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
| OFFICE--OPENOFFICE18 |
DOAS AIR LOOP HVAC1 |
|
0.325 |
0.325 |
0.325 |
0.1959 |
0.603 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
| OFFICE--OPENOFFICE19 |
DOAS AIR LOOP HVAC1 |
|
0.280 |
0.280 |
0.280 |
0.2312 |
0.827 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
| OFFICE--OPENOFFICE2 |
DOAS AIR LOOP HVAC1 |
|
0.231 |
0.231 |
0.231 |
0.2312 |
1.000 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
| OFFICE--OPENOFFICE20 |
DOAS AIR LOOP HVAC1 |
|
0.280 |
0.280 |
0.280 |
0.2312 |
0.827 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
| OFFICE--OPENOFFICE3 |
DOAS AIR LOOP HVAC1 |
|
0.196 |
0.196 |
0.196 |
0.1959 |
1.000 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
| OFFICE--OPENOFFICE4 |
DOAS AIR LOOP HVAC1 |
|
0.231 |
0.231 |
0.231 |
0.2312 |
1.000 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
| OFFICE--OPENOFFICE5 |
DOAS AIR LOOP HVAC1 |
|
0.231 |
0.231 |
0.231 |
0.2312 |
1.000 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
| OFFICE--OPENOFFICE6 |
DOAS AIR LOOP HVAC1 |
|
0.231 |
0.231 |
0.231 |
0.2312 |
1.000 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
| OFFICE--OPENOFFICE7 |
DOAS AIR LOOP HVAC1 |
|
0.231 |
0.231 |
0.231 |
0.2312 |
1.000 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
| OFFICE--OPENOFFICE8 |
DOAS AIR LOOP HVAC1 |
|
0.196 |
0.196 |
0.196 |
0.1959 |
1.000 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
| OFFICE--OPENOFFICE9 |
DOAS AIR LOOP HVAC1 |
|
0.231 |
0.231 |
0.231 |
0.2312 |
1.000 |
1.000 |
0.000 |
0.000 |
0.000 |
0.000 |
1.000 |
System Ventilation Calculations for Heating Design
|
Sum of Zone Primary Airflow - Vpz-sum [m3/s] |
System Primary Airflow - Vps [m3/s] |
Sum of Zone Discharge Airflow - Vdz-sum [m3/s] |
Sum of Min Zone Primary Airflow - Vpz-min [m3/s] |
Zone Outdoor Airflow Heating - Voz-htg [m3/s] |
Zone Ventilation Efficiency - Evz-min |
| DOAS AIR LOOP HVAC1 |
4.80 |
4.483 |
4.80 |
4.80 |
4.4830 |
1.000 |
Table of Contents
Report: LEED Summary
For: Entire Facility
Timestamp: 2016-12-10
12:34:41
Sec1.1A-General Information
|
Data |
| Cooling Degree Days |
2201 |
| Heating Degree Days |
2368 |
| HDD and CDD data source |
Weather File Stat |
| Climate Zone |
4A |
| Weather File |
RUN PERIOD 1 ** New York Laguardia Arpt NY USA TMY3 WMO#=725030 |
| Total gross floor area [m2] |
5000.00 |
| Principal Heating Source |
Natural Gas |
EAp2-1. Space Usage Type
|
Space Area [m2] |
Regularly Occupied Area [m2] |
Unconditioned Area [m2] |
Typical Hours/Week in Operation [hr/wk] |
| OFFICE--OPENOFFICE1 |
151.78 |
151.78 |
0.00 |
101.07 |
| OFFICE--OPENOFFICE10 |
151.78 |
151.78 |
0.00 |
101.07 |
| OFFICE--OPENOFFICE11 |
151.78 |
151.78 |
0.00 |
101.07 |
| OFFICE--OPENOFFICE12 |
151.78 |
151.78 |
0.00 |
101.07 |
| OFFICE--OPENOFFICE13 |
642.89 |
642.89 |
0.00 |
101.07 |
| OFFICE--OPENOFFICE14 |
151.78 |
151.78 |
0.00 |
101.07 |
| OFFICE--OPENOFFICE15 |
151.78 |
151.78 |
0.00 |
101.07 |
| OFFICE--OPENOFFICE16 |
151.78 |
151.78 |
0.00 |
101.07 |
| OFFICE--OPENOFFICE17 |
151.78 |
151.78 |
0.00 |
101.07 |
| OFFICE--OPENOFFICE18 |
642.89 |
642.89 |
0.00 |
101.07 |
| OFFICE--OPENOFFICE19 |
151.78 |
151.78 |
0.00 |
101.07 |
| OFFICE--OPENOFFICE2 |
151.78 |
151.78 |
0.00 |
101.07 |
| OFFICE--OPENOFFICE20 |
151.78 |
151.78 |
0.00 |
101.07 |
| OFFICE--OPENOFFICE3 |
642.89 |
642.89 |
0.00 |
101.07 |
| OFFICE--OPENOFFICE4 |
151.78 |
151.78 |
0.00 |
101.07 |
| OFFICE--OPENOFFICE5 |
151.78 |
151.78 |
0.00 |
101.07 |
| OFFICE--OPENOFFICE6 |
151.78 |
151.78 |
0.00 |
101.07 |
| OFFICE--OPENOFFICE7 |
151.78 |
151.78 |
0.00 |
101.07 |
| OFFICE--OPENOFFICE8 |
642.89 |
642.89 |
0.00 |
101.07 |
| OFFICE--OPENOFFICE9 |
151.78 |
151.78 |
0.00 |
101.07 |
| Totals |
5000.00 |
5000.00 |
0.00 |
|
EAp2-2. Advisory Messages
|
Data |
| Number of hours heating loads not met |
419.67 |
| Number of hours cooling loads not met |
192.00 |
| Number of hours not met |
606.33 |
EAp2-3. Energy Type Summary
|
Utility Rate |
Virtual Rate [$/unit energy] |
Units of Energy |
Units of Demand |
| None |
|
|
|
|
EAp2-4/5. Performance Rating Method Compliance
|
Electric Energy Use [GJ] |
Electric Demand [W] |
Natural Gas Energy Use [GJ] |
Natural Gas Demand [W] |
Additional Energy Use [GJ] |
Additional Demand [W] |
| Interior Lighting |
459.78 |
31969.79 |
0.00 |
0.00 |
0.00 |
0.00 |
| Exterior Lighting |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Space Heating |
84.45 |
0.00 |
1605.50 |
232806.38 |
0.00 |
0.00 |
| Space Cooling |
544.01 |
100168.35 |
0.00 |
0.00 |
0.00 |
0.00 |
| Pumps |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Heat Rejection |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Fans-Interior |
461.57 |
14636.29 |
0.00 |
0.00 |
0.00 |
0.00 |
| Fans-Parking Garage |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Service Water Heating |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Receptacle Equipment |
0.92 |
48.44 |
0.00 |
0.00 |
0.00 |
0.00 |
| Interior Lighting-Process |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Refrigeration Equipment |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Cooking |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Industrial Process |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Elevators and Escalators |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| Total Line |
1550.74 |
|
1605.50 |
|
0.00 |
|
EAp2-6. Energy Use Summary
|
Process Subtotal [GJ] |
Total Energy Use [GJ] |
| Electricity |
0.92 |
1550.74 |
| Natural Gas |
0.00 |
1605.50 |
| Additional |
0.00 |
0.00 |
| Total |
0.92 |
3156.24 |
EAp2-7. Energy Cost Summary
|
Process Subtotal [$] |
Total Energy Cost [$] |
| Electricity |
0.00 |
|
| Natural Gas |
0.00 |
|
| Additional |
0.00 |
|
| Total |
0.00 |
|
Process energy cost based on ratio of process to total energy.
L-1. Renewable Energy Source Summary
|
Rated Capacity [kW] |
Annual Energy Generated [GJ] |
| Photovoltaic |
0.00 |
0.00 |
| Wind |
0.00 |
0.00 |
EAp2-17a. Energy Use Intensity - Electricity
|
Electricty [MJ/m2] |
| Interior Lighting |
91.96 |
| Space Heating |
16.89 |
| Space Cooling |
108.80 |
| Fans-Interior |
92.31 |
| Service Water Heating |
0.00 |
| Receptacle Equipment |
0.18 |
| Miscellaneous |
0.00 |
| Subtotal |
310.15 |
EAp2-17b. Energy Use Intensity - Natural Gas
|
Natural Gas [MJ/m2] |
| Space Heating |
321.10 |
| Service Water Heating |
0.00 |
| Miscellaneous |
0.00 |
| Subtotal |
321.10 |
EAp2-17c. Energy Use Intensity - Additional
|
Additional [MJ/m2] |
| Miscellaneous |
0.00 |
| Subtotal |
0.00 |
EAp2-18. End Use Percentage
|
Percent [%] |
| Interior Lighting |
14.57 |
| Space Heating |
53.54 |
| Space Cooling |
17.24 |
| Fans-Interior |
14.62 |
| Service Water Heating |
0.00 |
| Receptacle Equipment |
0.03 |
| Miscellaneous |
0.00 |
Table of Contents
Report: Component Sizing Summary
For: Entire Facility
Timestamp: 2016-12-10
12:34:41
AirTerminal:SingleDuct:Uncontrolled
|
Design Size Maximum Air Flow Rate [m3/s] |
| AIR TERMINAL SINGLE DUCT UNCONTROLLED 1 |
0.231217 |
| AIR TERMINAL SINGLE DUCT UNCONTROLLED 8 |
0.231217 |
| AIR TERMINAL SINGLE DUCT UNCONTROLLED 9 |
0.231217 |
| AIR TERMINAL SINGLE DUCT UNCONTROLLED 10 |
0.231217 |
| AIR TERMINAL SINGLE DUCT UNCONTROLLED 19 |
0.195877 |
| AIR TERMINAL SINGLE DUCT UNCONTROLLED 11 |
0.231217 |
| AIR TERMINAL SINGLE DUCT UNCONTROLLED 12 |
0.231217 |
| AIR TERMINAL SINGLE DUCT UNCONTROLLED 13 |
0.231217 |
| AIR TERMINAL SINGLE DUCT UNCONTROLLED 14 |
0.231217 |
| AIR TERMINAL SINGLE DUCT UNCONTROLLED 20 |
0.195877 |
| AIR TERMINAL SINGLE DUCT UNCONTROLLED 15 |
0.231217 |
| AIR TERMINAL SINGLE DUCT UNCONTROLLED 2 |
0.231217 |
| AIR TERMINAL SINGLE DUCT UNCONTROLLED 16 |
0.231217 |
| AIR TERMINAL SINGLE DUCT UNCONTROLLED 17 |
0.195877 |
| AIR TERMINAL SINGLE DUCT UNCONTROLLED 3 |
0.231217 |
| AIR TERMINAL SINGLE DUCT UNCONTROLLED 4 |
0.231217 |
| AIR TERMINAL SINGLE DUCT UNCONTROLLED 5 |
0.231217 |
| AIR TERMINAL SINGLE DUCT UNCONTROLLED 6 |
0.231217 |
| AIR TERMINAL SINGLE DUCT UNCONTROLLED 18 |
0.195877 |
| AIR TERMINAL SINGLE DUCT UNCONTROLLED 7 |
0.231217 |
User-Specified values were used. Design Size values were used if no User-Specified values were provided.
ZoneHVAC:TerminalUnit:VariableRefrigerantFlow
|
Design Size Cooling Supply Air Flow Rate [m3/s] |
Design Size Heating Supply Air Flow Rate [m3/s] |
Design Size No Cooling Supply Air Flow Rate [m3/s] |
Design Size No Heating Supply Air Flow Rate [m3/s] |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 1 |
0.956878 |
0.956878 |
0.956878 |
0.956878 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 8 |
1.17 |
1.17 |
1.17 |
1.17 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 9 |
1.14 |
1.14 |
1.14 |
1.14 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 10 |
0.903215 |
0.903215 |
0.903215 |
0.903215 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 19 |
1.40 |
1.40 |
1.40 |
1.40 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 11 |
1.01 |
1.01 |
1.01 |
1.01 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 12 |
1.18 |
1.18 |
1.18 |
1.18 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 13 |
1.25 |
1.25 |
1.25 |
1.25 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 14 |
0.978041 |
0.978041 |
0.978041 |
0.978041 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 20 |
1.43 |
1.43 |
1.43 |
1.43 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 15 |
1.10 |
1.10 |
1.10 |
1.10 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 2 |
0.732439 |
0.732439 |
0.732439 |
0.732439 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 16 |
1.30 |
1.30 |
1.30 |
1.30 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 17 |
1.06 |
1.06 |
1.06 |
1.06 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 3 |
0.841320 |
0.841320 |
0.841320 |
0.841320 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 4 |
1.00 |
1.00 |
1.00 |
1.00 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 5 |
1.13 |
1.13 |
1.13 |
1.13 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 6 |
0.889864 |
0.889864 |
0.889864 |
0.889864 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 18 |
1.33 |
1.33 |
1.33 |
1.33 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 7 |
0.998221 |
0.998221 |
0.998221 |
0.998221 |
User-Specified values were used. Design Size values were used if no User-Specified values were provided.
Coil:Cooling:DX:VariableRefrigerantFlow
|
Design Size Rated Air Flow Rate [m3/s] |
Design Size Gross Rated Total Cooling Capacity [W] |
Design Size Gross Rated Sensible Heat Ratio |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 1 COOLING COIL |
0.956878 |
15839.73 |
0.798655 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 8 COOLING COIL |
1.17 |
19358.37 |
0.798655 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 9 COOLING COIL |
1.14 |
18833.02 |
0.798655 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 10 COOLING COIL |
0.903215 |
14951.41 |
0.798655 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 19 COOLING COIL |
1.40 |
23096.10 |
0.798655 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 11 COOLING COIL |
1.01 |
16759.26 |
0.798655 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 12 COOLING COIL |
1.18 |
19570.16 |
0.798655 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 13 COOLING COIL |
1.25 |
20664.77 |
0.798655 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 14 COOLING COIL |
0.978041 |
16190.05 |
0.798655 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 20 COOLING COIL |
1.43 |
23671.85 |
0.798655 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 15 COOLING COIL |
1.10 |
18259.44 |
0.798655 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 2 COOLING COIL |
0.732439 |
12124.47 |
0.798655 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 16 COOLING COIL |
1.30 |
21566.35 |
0.798655 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 17 COOLING COIL |
1.06 |
17514.89 |
0.798655 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 3 COOLING COIL |
0.841320 |
13926.84 |
0.798655 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 4 COOLING COIL |
1.00 |
16595.29 |
0.798655 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 5 COOLING COIL |
1.13 |
18629.51 |
0.798655 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 6 COOLING COIL |
0.889864 |
14730.41 |
0.798655 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 18 COOLING COIL |
1.33 |
22076.90 |
0.798655 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 7 COOLING COIL |
0.998221 |
16524.11 |
0.798655 |
User-Specified values were used. Design Size values were used if no User-Specified values were provided.
Coil:Heating:DX:VariableRefrigerantFlow
|
Design Size Rated Air Flow Rate [m3/s] |
Design Size Gross Rated Heating Capacity [W] |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 1 HEATING COIL |
0.956878 |
15839.73 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 8 HEATING COIL |
1.17 |
19358.37 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 9 HEATING COIL |
1.14 |
18833.02 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 10 HEATING COIL |
0.903215 |
14951.41 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 19 HEATING COIL |
1.40 |
23096.10 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 11 HEATING COIL |
1.01 |
16759.26 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 12 HEATING COIL |
1.18 |
19570.16 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 13 HEATING COIL |
1.25 |
20664.77 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 14 HEATING COIL |
0.978041 |
16190.05 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 20 HEATING COIL |
1.43 |
23671.85 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 15 HEATING COIL |
1.10 |
18259.44 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 2 HEATING COIL |
0.732439 |
12124.47 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 16 HEATING COIL |
1.30 |
21566.35 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 17 HEATING COIL |
1.06 |
17514.89 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 3 HEATING COIL |
0.841320 |
13926.84 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 4 HEATING COIL |
1.00 |
16595.29 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 5 HEATING COIL |
1.13 |
18629.51 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 6 HEATING COIL |
0.889864 |
14730.41 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 18 HEATING COIL |
1.33 |
22076.90 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 7 HEATING COIL |
0.998221 |
16524.11 |
User-Specified values were used. Design Size values were used if no User-Specified values were provided.
Fan:OnOff
|
Design Size Maximum Flow Rate [m3/s] |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 1 FAN |
0.956878 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 8 FAN |
1.17 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 9 FAN |
1.14 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 10 FAN |
0.903215 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 19 FAN |
1.40 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 11 FAN |
1.01 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 12 FAN |
1.18 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 13 FAN |
1.25 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 14 FAN |
0.978041 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 20 FAN |
1.43 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 15 FAN |
1.10 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 2 FAN |
0.732439 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 16 FAN |
1.30 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 17 FAN |
1.06 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 3 FAN |
0.841320 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 4 FAN |
1.00 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 5 FAN |
1.13 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 6 FAN |
0.889864 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 18 FAN |
1.33 |
| ZONE HVAC TERMINAL UNIT VARIABLE REFRIGERANT FLOW 7 FAN |
0.998221 |
User-Specified values were used. Design Size values were used if no User-Specified values were provided.
AirConditioner:VariableRefrigerantFlow
|
Design Size Rated Total Cooling Capacity (gross) [W] |
Design Size Rated Total Heating Capacity [W] |
Design Size Resistive Defrost Heater Capacity |
User-Specified Resistive Defrost Heater Capacity |
Design Size Evaporative Condenser Air Flow Rate [m3/s] |
Design Size Evaporative Condenser Pump Rated Power Consumption [W] |
| VRF HEAT PUMP - 1 |
360882.93 |
360882.93 |
360882.93 |
0.000000 |
41.14 |
1539.53 |
User-Specified values were used. Design Size values were used if no User-Specified values were provided.
AirLoopHVAC
|
Design Supply Air Flow Rate [m3/s] |
| DOAS AIR LOOP HVAC1 |
4.48 |
User-Specified values were used. Design Size values were used if no User-Specified values were provided.
Controller:OutdoorAir
|
Maximum Outdoor Air Flow Rate [m3/s] |
Minimum Outdoor Air Flow Rate [m3/s] |
| CONTROLLER OUTDOOR AIR 1 |
4.48 |
4.48 |
User-Specified values were used. Design Size values were used if no User-Specified values were provided.
Coil:Cooling:DX:SingleSpeed
|
Design Size Rated Air Flow Rate [m3/s] |
Design Size Gross Rated Total Cooling Capacity [W] |
Design Size Gross Rated Sensible Heat Ratio |
| COIL COOLING DX SINGLE SPEED 1 |
4.48 |
111323.23 |
0.676083 |
User-Specified values were used. Design Size values were used if no User-Specified values were provided.
Coil:Heating:Fuel
|
Design Size Nominal Capacity [W] |
| COIL HEATING GAS 1 |
275498.63 |
User-Specified values were used. Design Size values were used if no User-Specified values were provided.
Fan:ConstantVolume
|
Design Size Maximum Flow Rate [m3/s] |
| FAN CONSTANT VOLUME 1 |
4.48 |
User-Specified values were used. Design Size values were used if no User-Specified values were provided.
Table of Contents
Report: Surface Shadowing Summary
For: Entire Facility
Timestamp: 2016-12-10
12:34:41
Surfaces (Walls, Roofs, etc) that may be Shadowed by Other Surfaces
Subsurfaces (Windows and Doors) that may be Shadowed by Surfaces
|
Possible Shadow Receivers |
| OFFICE--OPENOFFICE1_SRF_4 |
OFFICE--OPENOFFICE1_SRF_4_GLZ_0 | |
| OFFICE--OPENOFFICE10_SRF_4 |
OFFICE--OPENOFFICE10_SRF_4_GLZ_0 | |
| OFFICE--OPENOFFICE11_SRF_4 |
OFFICE--OPENOFFICE11_SRF_4_GLZ_0 | |
| OFFICE--OPENOFFICE12_SRF_4 |
OFFICE--OPENOFFICE12_SRF_4_GLZ_0 | |
| OFFICE--OPENOFFICE14_SRF_4 |
OFFICE--OPENOFFICE14_SRF_4_GLZ_0 | |
| OFFICE--OPENOFFICE15_SRF_4 |
OFFICE--OPENOFFICE15_SRF_4_GLZ_0 | |
| OFFICE--OPENOFFICE16_SRF_4 |
OFFICE--OPENOFFICE16_SRF_4_GLZ_0 | |
| OFFICE--OPENOFFICE17_SRF_4 |
OFFICE--OPENOFFICE17_SRF_4_GLZ_0 | |
| OFFICE--OPENOFFICE19_SRF_4 |
OFFICE--OPENOFFICE19_SRF_4_GLZ_0 | |
| OFFICE--OPENOFFICE2_SRF_4 |
OFFICE--OPENOFFICE2_SRF_4_GLZ_0 | |
| OFFICE--OPENOFFICE20_SRF_4 |
OFFICE--OPENOFFICE20_SRF_4_GLZ_0 | |
| OFFICE--OPENOFFICE4_SRF_4 |
OFFICE--OPENOFFICE4_SRF_4_GLZ_0 | |
| OFFICE--OPENOFFICE5_SRF_4 |
OFFICE--OPENOFFICE5_SRF_4_GLZ_0 | |
| OFFICE--OPENOFFICE6_SRF_4 |
OFFICE--OPENOFFICE6_SRF_4_GLZ_0 | |
| OFFICE--OPENOFFICE7_SRF_4 |
OFFICE--OPENOFFICE7_SRF_4_GLZ_0 | |
| OFFICE--OPENOFFICE9_SRF_4 |
OFFICE--OPENOFFICE9_SRF_4_GLZ_0 | |
Table of Contents
Report: Adaptive Comfort Summary
For: Entire Facility
Timestamp: 2016-12-10
12:34:41
Time Not Meeting the Adaptive Comfort Models during Occupied Hours
|
ASHRAE55 90% Acceptability Limits [Hours] |
ASHRAE55 80% Acceptability Limits [Hours] |
CEN15251 Category I Acceptability Limits [Hours] |
CEN15251 Category II Acceptability Limits [Hours] |
CEN15251 Category III Acceptability Limits [Hours] |
Table of Contents
Report: Life-Cycle Cost Report
For: Entire Facility
Timestamp: 2016-12-10
12:34:41
Life-Cycle Cost Parameters
|
Value |
| Name |
{66631626-8ED1-46E4-A28C-2AAD5A3D186A} |
| Discounting Convention |
EndOfYear |
| Inflation Approach |
ConstantDollar |
| Real Discount Rate |
0.0300 |
| Nominal Discount Rate |
-- N/A -- |
| Inflation |
-- N/A -- |
| Base Date |
January 2011 |
| Service Date |
January 2011 |
| Length of Study Period in Years |
25 |
| Tax rate |
0.0000 |
| Depreciation Method |
None |
Use Price Escalation
|
U.S. AVG COMMERCIAL-ELECTRICITY |
U.S. AVG COMMERCIAL-DISTILLATE OIL |
U.S. AVG COMMERCIAL-RESIDUAL OIL |
U.S. AVG COMMERCIAL-NATURAL GAS |
U.S. AVG COMMERCIAL-COAL |
| Resource |
Electricity |
FuelOil#1 |
FuelOil#2 |
Gas |
Coal |
| Start Date |
January 2011 |
January 2011 |
January 2011 |
January 2011 |
January 2011 |
| 1 |
0.983800 |
0.971400 |
0.846900 |
0.982300 |
0.997000 |
| 2 |
0.973000 |
0.973000 |
0.825700 |
0.955700 |
1.008900 |
| 3 |
0.963200 |
0.994200 |
0.868100 |
0.927900 |
1.008900 |
| 4 |
0.961100 |
1.016400 |
0.898800 |
0.925700 |
0.994100 |
| 5 |
0.957100 |
1.054100 |
0.928900 |
0.934600 |
0.994100 |
| 6 |
0.955300 |
1.092800 |
0.960400 |
0.941200 |
1.000000 |
| 7 |
0.953900 |
1.126700 |
0.989700 |
0.951200 |
1.003000 |
| 8 |
0.952100 |
1.158000 |
1.007500 |
0.964500 |
1.005900 |
| 9 |
0.954600 |
1.179200 |
1.031400 |
0.985600 |
1.008900 |
| 10 |
0.955000 |
1.196700 |
1.055400 |
1.006700 |
1.011900 |
| 11 |
0.955300 |
1.220000 |
1.086100 |
1.022200 |
1.014800 |
| 12 |
0.956400 |
1.233300 |
1.127800 |
1.041000 |
1.017800 |
| 13 |
0.957500 |
1.256600 |
1.149700 |
1.061000 |
1.020800 |
| 14 |
0.959600 |
1.270900 |
1.162000 |
1.078700 |
1.026700 |
| 15 |
0.961800 |
1.282600 |
1.174300 |
1.094200 |
1.029700 |
| 16 |
0.961400 |
1.298500 |
1.185200 |
1.109800 |
1.035600 |
| 17 |
0.961800 |
1.310200 |
1.194800 |
1.122000 |
1.041500 |
| 18 |
0.961800 |
1.325000 |
1.203700 |
1.130800 |
1.053400 |
| 19 |
0.959300 |
1.326100 |
1.207100 |
1.138600 |
1.056400 |
| 20 |
0.958900 |
1.328200 |
1.211900 |
1.148600 |
1.059300 |
| 21 |
0.960700 |
1.332400 |
1.213900 |
1.161900 |
1.065300 |
| 22 |
0.962500 |
1.335600 |
1.219400 |
1.176300 |
1.071200 |
| 23 |
0.965000 |
1.343100 |
1.227600 |
1.191800 |
1.074200 |
| 24 |
0.970800 |
1.351000 |
1.236500 |
1.211800 |
1.080100 |
| 25 |
0.975100 |
1.356800 |
1.242000 |
1.228400 |
1.083100 |
Cash Flow for Recurring and Nonrecurring Costs (Without Escalation)
|
DEFAULT COST |
| |
Nonrecurring |
| January 2011 |
0.00 |
| January 2012 |
0.00 |
| January 2013 |
0.00 |
| January 2014 |
0.00 |
| January 2015 |
0.00 |
| January 2016 |
0.00 |
| January 2017 |
0.00 |
| January 2018 |
0.00 |
| January 2019 |
0.00 |
| January 2020 |
0.00 |
| January 2021 |
0.00 |
| January 2022 |
0.00 |
| January 2023 |
0.00 |
| January 2024 |
0.00 |
| January 2025 |
0.00 |
| January 2026 |
0.00 |
| January 2027 |
0.00 |
| January 2028 |
0.00 |
| January 2029 |
0.00 |
| January 2030 |
0.00 |
| January 2031 |
0.00 |
| January 2032 |
0.00 |
| January 2033 |
0.00 |
| January 2034 |
0.00 |
| January 2035 |
0.00 |
Energy and Water Cost Cash Flows (Without Escalation)
|
|
| January 2011 |
|
| January 2012 |
|
| January 2013 |
|
| January 2014 |
|
| January 2015 |
|
| January 2016 |
|
| January 2017 |
|
| January 2018 |
|
| January 2019 |
|
| January 2020 |
|
| January 2021 |
|
| January 2022 |
|
| January 2023 |
|
| January 2024 |
|
| January 2025 |
|
| January 2026 |
|
| January 2027 |
|
| January 2028 |
|
| January 2029 |
|
| January 2030 |
|
| January 2031 |
|
| January 2032 |
|
| January 2033 |
|
| January 2034 |
|
| January 2035 |
|
Capital Cash Flow by Category (Without Escalation)
|
Construction |
Salvage |
OtherCapital |
Total |
| January 2011 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2012 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2013 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2014 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2015 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2016 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2017 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2018 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2019 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2020 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2021 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2022 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2023 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2024 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2025 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2026 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2027 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2028 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2029 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2030 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2031 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2032 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2033 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2034 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2035 |
0.00 |
0.00 |
0.00 |
0.00 |
Operating Cash Flow by Category (Without Escalation)
|
Energy |
Water |
Maintenance |
Repair |
Operation |
Replacement |
MinorOverhaul |
MajorOverhaul |
OtherOperational |
Total |
| January 2011 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2012 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2013 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2014 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2015 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2016 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2017 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2018 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2019 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2020 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2021 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2022 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2023 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2024 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2025 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2026 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2027 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2028 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2029 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2030 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2031 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2032 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2033 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2034 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
| January 2035 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |
0.00 |