Program Version:EnergyPlus, Version 9.1.0-08d2e308bb, YMD=2019.04.09 23:11
Tabular Output Report in Format: HTML
Building: -MediumOffice-ASHRAE 169-2006-2A created: 2018-10-22 12:13:18 -0600
Environment: RUN PERIOD 1 ** Houston Bush Intercontinental TX USA TMY3 WMO#=722430
Simulation Timestamp: 2019-04-09 23:11:28
Report: Annual Building Utility Performance Summary
For: Entire Facility
Timestamp: 2019-04-09 23:11:28
Values gathered over 8760.00 hours| Total Energy [GJ] | Energy Per Total Building Area [MJ/m2] | Energy Per Conditioned Building Area [MJ/m2] | |
| Total Site Energy | 1864.34 | 374.20 | 374.20 |
| Net Site Energy | 1864.34 | 374.20 | 374.20 |
| Total Source Energy | 5684.16 | 1140.90 | 1140.90 |
| Net Source Energy | 5684.16 | 1140.90 | 1140.90 |
| Site=>Source Conversion Factor | |
| Electricity | 3.167 |
| Natural Gas | 1.084 |
| District Cooling | 1.056 |
| District Heating | 3.613 |
| Steam | 0.300 |
| Gasoline | 1.050 |
| Diesel | 1.050 |
| Coal | 1.050 |
| Fuel Oil #1 | 1.050 |
| Fuel Oil #2 | 1.050 |
| Propane | 1.050 |
| Other Fuel 1 | 1.000 |
| Other Fuel 2 | 1.000 |
| Area [m2] | |
| Total Building Area | 4982.19 |
| Net Conditioned Building Area | 4982.19 |
| Unconditioned Building Area | 0.00 |
| Electricity [GJ] | Natural Gas [GJ] | Additional Fuel [GJ] | District Cooling [GJ] | District Heating [GJ] | Water [m3] | |
| Heating | 0.00 | 26.59 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | 413.75 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 335.95 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 104.80 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 763.69 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 60.10 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 68.19 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 12.14 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 79.12 | 0.00 | 0.00 | 0.00 | 278.19 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total End Uses | 1758.63 | 105.71 | 0.00 | 0.00 | 0.00 | 278.19 |
| Subcategory | Electricity [GJ] | Natural Gas [GJ] | Additional Fuel [GJ] | District Cooling [GJ] | District Heating [GJ] | Water [m3] | |
| Heating | General | 0.00 | 26.59 | 0.00 | 0.00 | 0.00 | 0.00 |
| Boiler Parasitic | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Cooling | General | 413.75 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | General | 335.95 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | General | 104.80 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | General | 763.69 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | General | 60.10 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | General | 68.19 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | General | 12.14 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | General | 0.00 | 79.12 | 0.00 | 0.00 | 0.00 | 278.19 |
| Refrigeration | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Electricity Intensity [MJ/m2] | Natural Gas Intensity [MJ/m2] | Additional Fuel Intensity [MJ/m2] | District Cooling Intensity [MJ/m2] | District Heating Intensity [MJ/m2] | Water Intensity [m3/m2] | |
| Lighting | 88.46 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| HVAC | 108.80 | 21.22 | 0.00 | 0.00 | 0.00 | 0.06 |
| Other | 155.72 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total | 352.98 | 21.22 | 0.00 | 0.00 | 0.00 | 0.06 |
| Electricity Intensity [MJ/m2] | Natural Gas Intensity [MJ/m2] | Additional Fuel Intensity [MJ/m2] | District Cooling Intensity [MJ/m2] | District Heating Intensity [MJ/m2] | Water Intensity [m3/m2] | |
| Lighting | 88.46 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| HVAC | 108.80 | 21.22 | 0.00 | 0.00 | 0.00 | 0.06 |
| Other | 155.72 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total | 352.98 | 21.22 | 0.00 | 0.00 | 0.00 | 0.06 |
| Electricity [GJ] | Percent Electricity [%] | |
| Fuel-Fired Power Generation | 0.000 | 0.00 |
| High Temperature Geothermal* | 0.000 | 0.00 |
| Photovoltaic Power | 0.000 | 0.00 |
| Wind Power | 0.000 | 0.00 |
| Power Conversion | 0.000 | 0.00 |
| Net Decrease in On-Site Storage | 0.000 | 0.00 |
| Total On-Site Electric Sources | 0.000 | 0.00 |
| Electricity Coming From Utility | 1758.626 | 100.00 |
| Surplus Electricity Going To Utility | 0.000 | 0.00 |
| Net Electricity From Utility | 1758.626 | 100.00 |
| Total On-Site and Utility Electric Sources | 1758.626 | 100.00 |
| Total Electricity End Uses | 1758.626 | 100.00 |
| Heat [GJ] | Percent Heat [%] | |
| Water-Side Heat Recovery | 0.00 | 0.00 |
| Air to Air Heat Recovery for Cooling | 222.99 | 89.38 |
| Air to Air Heat Recovery for Heating | 26.50 | 10.62 |
| High-Temperature Geothermal* | 0.00 | 0.00 |
| Solar Water Thermal | 0.00 | 0.00 |
| Solar Air Thermal | 0.00 | 0.00 |
| Total On-Site Thermal Sources | 249.49 | 100.00 |
| Water [m3] | Percent Water [%] | |
| Rainwater Collection | 0.00 | 0.00 |
| Condensate Collection | 0.00 | 0.00 |
| Groundwater Well | 0.00 | 0.00 |
| Total On Site Water Sources | 0.00 | 0.00 |
| - | - | - |
| Initial Storage | 0.00 | 0.00 |
| Final Storage | 0.00 | 0.00 |
| Change in Storage | 0.00 | 0.00 |
| - | - | - |
| Water Supplied by Utility | 278.19 | 100.00 |
| - | - | - |
| Total On Site, Change in Storage, and Utility Water Sources | 278.19 | 100.00 |
| Total Water End Uses | 278.19 | 100.00 |
| Degrees [deltaC] | |
| Tolerance for Zone Heating Setpoint Not Met Time | 0.56 |
| Tolerance for Zone Cooling Setpoint Not Met Time | 0.56 |
| Facility [Hours] | |
| Time Setpoint Not Met During Occupied Heating | 131.00 |
| Time Setpoint Not Met During Occupied Cooling | 332.50 |
| Time Not Comfortable Based on Simple ASHRAE 55-2004 | 893.00 |
Table of Contents
TopBUILDING ENERGY PERFORMANCE - ELECTRICITY
| Meter |BUILDING ENERGY PERFORMANCE - NATURAL GAS
| Meter |BUILDING ENERGY PERFORMANCE - ELECTRICITY PEAK DEMAND
| Meter |BUILDING ENERGY PERFORMANCE - NATURAL GAS PEAK DEMAND
| Meter |Life-Cycle Cost Report
| Entire Facility |Report: Input Verification and Results Summary
For: Entire Facility
Timestamp: 2019-04-09 23:11:28
General| Value | |
| Program Version and Build | EnergyPlus, Version 9.1.0-08d2e308bb, YMD=2019.04.09 23:11 |
| RunPeriod | RUN PERIOD 1 |
| Weather File | Houston Bush Intercontinental TX USA TMY3 WMO#=722430 |
| Latitude [deg] | 30.00 |
| Longitude [deg] | -95.4 |
| Elevation [m] | 29.00 |
| Time Zone | -6.0 |
| North Axis Angle [deg] | 0.00 |
| Rotation for Appendix G [deg] | 0.00 |
| Hours Simulated [hrs] | 8760.00 |
| Total | North (315 to 45 deg) | East (45 to 135 deg) | South (135 to 225 deg) | West (225 to 315 deg) | |
| Gross Wall Area [m2] | 1977.67 | 593.30 | 395.53 | 593.30 | 395.53 |
| Above Ground Wall Area [m2] | 1977.67 | 593.30 | 395.53 | 593.30 | 395.53 |
| Window Opening Area [m2] | 652.83 | 195.85 | 130.57 | 195.85 | 130.57 |
| Gross Window-Wall Ratio [%] | 33.01 | 33.01 | 33.01 | 33.01 | 33.01 |
| Above Ground Window-Wall Ratio [%] | 33.01 | 33.01 | 33.01 | 33.01 | 33.01 |
| Total | North (315 to 45 deg) | East (45 to 135 deg) | South (135 to 225 deg) | West (225 to 315 deg) | |
| Gross Wall Area [m2] | 1369.16 | 410.75 | 273.83 | 410.75 | 273.83 |
| Above Ground Wall Area [m2] | 1369.16 | 410.75 | 273.83 | 410.75 | 273.83 |
| Window Opening Area [m2] | 652.83 | 195.85 | 130.57 | 195.85 | 130.57 |
| Gross Window-Wall Ratio [%] | 47.68 | 47.68 | 47.68 | 47.68 | 47.68 |
| Above Ground Window-Wall Ratio [%] | 47.68 | 47.68 | 47.68 | 47.68 | 47.68 |
| Total | |
| Gross Roof Area [m2] | 1660.73 |
| Skylight Area [m2] | 0.00 |
| Skylight-Roof Ratio [%] | 0.00 |
| Area [m2] | Conditioned (Y/N) | Part of Total Floor Area (Y/N) | Volume [m3] | Multipliers | Above Ground Gross Wall Area [m2] | Underground Gross Wall Area [m2] | Window Glass Area [m2] | Opening Area [m2] | Lighting [W/m2] | People [m2 per person] | Plug and Process [W/m2] | |
| CORE_BOTTOM ZN | 983.54 | Yes | Yes | 2698.04 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 8.8264 | 18.58 | 40.8492 |
| CORE_MID ZN | 983.54 | Yes | Yes | 2698.04 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 8.8264 | 18.58 | 8.0729 |
| CORE_TOP ZN | 983.54 | Yes | Yes | 2698.04 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 8.8264 | 18.58 | 8.0729 |
| FIRSTFLOOR_PLENUM ZN | 1660.73 | No | No | 2024.76 | 1.00 | 202.84 | 0.00 | 0.00 | 0.00 | 0.0000 | 0.0000 | |
| MIDFLOOR_PLENUM ZN | 1660.73 | No | No | 2024.76 | 1.00 | 202.84 | 0.00 | 0.00 | 0.00 | 0.0000 | 0.0000 | |
| PERIMETER_BOT_ZN_1 ZN | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 8.8264 | 18.58 | 8.0729 |
| PERIMETER_BOT_ZN_2 ZN | 131.26 | Yes | Yes | 360.08 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 8.8264 | 18.58 | 8.0729 |
| PERIMETER_BOT_ZN_3 ZN | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 8.8264 | 18.58 | 8.0729 |
| PERIMETER_BOT_ZN_4 ZN | 131.25 | Yes | Yes | 360.05 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 8.8264 | 18.58 | 8.0729 |
| PERIMETER_MID_ZN_1 ZN | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 8.8264 | 18.58 | 8.0729 |
| PERIMETER_MID_ZN_2 ZN | 131.26 | Yes | Yes | 360.08 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 8.8264 | 18.58 | 8.0729 |
| PERIMETER_MID_ZN_3 ZN | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 8.8264 | 18.58 | 8.0729 |
| PERIMETER_MID_ZN_4 ZN | 131.25 | Yes | Yes | 360.05 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 8.8264 | 18.58 | 8.0729 |
| PERIMETER_TOP_ZN_1 ZN | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 8.8264 | 18.58 | 8.0729 |
| PERIMETER_TOP_ZN_2 ZN | 131.26 | Yes | Yes | 360.08 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 8.8264 | 18.58 | 8.0729 |
| PERIMETER_TOP_ZN_3 ZN | 207.34 | Yes | Yes | 568.77 | 1.00 | 136.92 | 0.00 | 65.28 | 65.28 | 8.8264 | 18.58 | 8.0729 |
| PERIMETER_TOP_ZN_4 ZN | 131.25 | Yes | Yes | 360.05 | 1.00 | 91.28 | 0.00 | 43.52 | 43.52 | 8.8264 | 18.58 | 8.0729 |
| TOPFLOOR_PLENUM ZN | 1660.73 | No | No | 2024.76 | 1.00 | 202.84 | 0.00 | 0.00 | 0.00 | 0.0000 | 0.0000 | |
| Total | 4982.19 | 13667.13 | 1369.16 | 0.00 | 652.83 | 652.83 | 8.8264 | 18.58 | 14.5433 | |||
| Conditioned Total | 4982.19 | 13667.13 | 1369.16 | 0.00 | 652.83 | 652.83 | 8.8264 | 18.58 | 14.5433 | |||
| Unconditioned Total | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | ||||||
| Not Part of Total | 4982.19 | 6074.28 | 608.51 | 0.00 | 0.00 | 0.00 | 0.0000 | 0.0000 |
Report: Demand End Use Components Summary
For: Entire Facility
Timestamp: 2019-04-09 23:11:28
End Uses| Electricity [W] | Natural Gas [W] | Propane [W] | District Cooling [W] | Steam [W] | Water [m3/s] | |
| Time of Peak | 02-AUG-15:00 | 23-JAN-07:10 | - | - | - | 02-JAN-12:09 |
| Heating | 0.00 | 169484.86 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling | 75728.07 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 26850.19 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 49329.42 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 14697.68 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 4395.19 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 1593.56 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 1276.95 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total End Uses | 172594.12 | 170761.81 | 0.00 | 0.00 | 0.00 | 0.00 |
| Subcategory | Electricity [W] | Natural Gas [W] | Propane [W] | District Cooling [W] | Steam [W] | Water [m3/s] | |
| Heating | General | 0.00 | 169484.86 | 0.00 | 0.00 | 0.00 | 0.00 |
| Boiler Parasitic | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Cooling | General | 75728.07 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | General | 26850.19 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | General | 49329.42 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | General | 14697.68 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | General | 4395.19 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | General | 1593.56 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | General | 0.00 | 1276.95 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
Report: Source Energy End Use Components Summary
For: Entire Facility
Timestamp: 2019-04-09 23:11:28
Values gathered over 8760.00 hours| Source Electricity [GJ] | Source Natural Gas [GJ] | Source Additional Fuel [GJ] | Source District Cooling [GJ] | Source District Heating [GJ] | |
| Heating | 0.00 | 28.82 | 0.00 | 0.00 | 0.00 |
| Cooling | 1310.35 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 1063.95 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 331.89 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 2418.61 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 190.34 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 215.97 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 38.46 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 85.77 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total Source Energy End Use Components | 5569.57 | 114.59 | 0.00 | 0.00 | 0.00 |
| Source Electricity [MJ/m2] | Source Natural Gas [MJ/m2] | Source Additional Fuel [MJ/m2] | Source District Cooling [MJ/m2] | Source District Heating [MJ/m2] | |
| Heating | 0.00 | 5.78 | 0.00 | 0.00 | 0.00 |
| Cooling | 263.01 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 213.55 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 66.62 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 485.45 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 38.20 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 43.35 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 7.72 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 17.22 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total Source Energy End Use Components | 1117.90 | 23.00 | 0.00 | 0.00 | 0.00 |
| Source Electricity [MJ/m2] | Source Natural Gas [MJ/m2] | Source Additional Fuel [MJ/m2] | Source District Cooling [MJ/m2] | Source District Heating [MJ/m2] | |
| Heating | 0.00 | 5.78 | 0.00 | 0.00 | 0.00 |
| Cooling | 263.01 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting | 213.55 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting | 66.62 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment | 485.45 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans | 38.20 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps | 43.35 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery | 7.72 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems | 0.00 | 17.22 | 0.00 | 0.00 | 0.00 |
| Refrigeration | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total Source Energy End Use Components | 1117.90 | 23.00 | 0.00 | 0.00 | 0.00 |
Report: Component Sizing Summary
For: Entire Facility
Timestamp: 2019-04-09 23:11:28
AirTerminal:SingleDuct:VAV:Reheat| Design Size Maximum Air Flow Rate [m3/s] | Design Size Constant Minimum Air Flow Fraction | User-Specified Constant Minimum Air Flow Fraction | Design Size Minimum Air Flow Rate [m3/s] | Design Size Maximum Flow Fraction during Reheat [] | User-Specified Maximum Flow Fraction during Reheat [] | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | Design Size Maximum Reheat Water Flow Rate [m3/s] | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | |
| CORE_BOTTOM ZN VAV TERMINAL | 2.95 | 0.253833 | 0.100000 | 0.295256 | 0.676887 | 0.500000 | 0.001501 | 0.000199 | 0.295256 | 12.78 | 0.008000 |
| CORE_MID ZN VAV TERMINAL | 2.11 | 0.355008 | 0.100000 | 0.211109 | 0.946688 | 0.500000 | 0.001073 | 0.000346 | 0.469194 | 12.78 | 0.008000 |
| CORE_TOP ZN VAV TERMINAL | 2.21 | 0.339088 | 0.100000 | 0.221021 | 0.904234 | 0.500000 | 0.001124 | 0.000630 | 0.857950 | 12.78 | 0.008000 |
| PERIMETER_BOT_ZN_1 ZN VAV TERMINAL | 0.582980 | 0.271007 | 0.100000 | 0.058298 | 0.722685 | 0.500000 | 0.001406 | 0.000187 | 0.255723 | 12.78 | 0.008000 |
| PERIMETER_BOT_ZN_2 ZN VAV TERMINAL | 0.632280 | 0.158192 | 0.100000 | 0.063228 | 0.421846 | 0.500000 | 0.002408 | 0.000126 | 0.172460 | 12.78 | 0.008000 |
| PERIMETER_BOT_ZN_3 ZN VAV TERMINAL | 0.509724 | 0.309956 | 0.100000 | 0.050972 | 0.826548 | 0.500000 | 0.001229 | 0.000186 | 0.253885 | 12.78 | 0.008000 |
| PERIMETER_BOT_ZN_4 ZN VAV TERMINAL | 0.672199 | 0.148788 | 0.100000 | 0.067220 | 0.396768 | 0.500000 | 0.002561 | 0.000126 | 0.172458 | 12.78 | 0.008000 |
| PERIMETER_MID_ZN_1 ZN VAV TERMINAL | 0.671565 | 0.235259 | 0.100000 | 0.067156 | 0.627357 | 0.500000 | 0.001619 | 0.000232 | 0.317540 | 12.78 | 0.008000 |
| PERIMETER_MID_ZN_2 ZN VAV TERMINAL | 0.690276 | 0.144901 | 0.100000 | 0.069028 | 0.386403 | 0.500000 | 0.002629 | 0.000155 | 0.211953 | 12.78 | 0.008000 |
| PERIMETER_MID_ZN_3 ZN VAV TERMINAL | 0.600061 | 0.263293 | 0.100000 | 0.060006 | 0.702113 | 0.500000 | 0.001447 | 0.000232 | 0.317300 | 12.78 | 0.008000 |
| PERIMETER_MID_ZN_4 ZN VAV TERMINAL | 0.727631 | 0.137453 | 0.100000 | 0.072763 | 0.366542 | 0.500000 | 0.002772 | 0.000155 | 0.211948 | 12.78 | 0.008000 |
| PERIMETER_TOP_ZN_1 ZN VAV TERMINAL | 0.741692 | 0.213015 | 0.100000 | 0.074169 | 0.568041 | 0.500000 | 0.001789 | 0.000289 | 0.394250 | 12.78 | 0.008000 |
| PERIMETER_TOP_ZN_2 ZN VAV TERMINAL | 0.696872 | 0.143530 | 0.100000 | 0.069687 | 0.382746 | 0.500000 | 0.002655 | 0.000190 | 0.260288 | 12.78 | 0.008000 |
| PERIMETER_TOP_ZN_3 ZN VAV TERMINAL | 0.677752 | 0.233111 | 0.100000 | 0.067775 | 0.621630 | 0.500000 | 0.001634 | 0.000289 | 0.394530 | 12.78 | 0.008000 |
| PERIMETER_TOP_ZN_4 ZN VAV TERMINAL | 0.773613 | 0.129283 | 0.100000 | 0.077361 | 0.344755 | 0.500000 | 0.002947 | 0.000190 | 0.260281 | 12.78 | 0.008000 |
| Design Size Rated Capacity [W] | Design Size Maximum Water Flow Rate [m3/s] | Design Size U-Factor Times Area Value [W/K] | |
| CORE_BOTTOM ZN REHEAT COIL | 9090.10 | 0.000199 | 584.52 |
| CORE_MID ZN REHEAT COIL | 15814.03 | 0.000346 | 1144.22 |
| CORE_TOP ZN REHEAT COIL | 28786.86 | 0.000630 | 2068.78 |
| PERIMETER_BOT_ZN_1 ZN REHEAT COIL | 8564.32 | 0.000187 | 613.75 |
| PERIMETER_BOT_ZN_2 ZN REHEAT COIL | 5774.75 | 0.000126 | 413.73 |
| PERIMETER_BOT_ZN_3 ZN REHEAT COIL | 8502.95 | 0.000186 | 609.37 |
| PERIMETER_BOT_ZN_4 ZN REHEAT COIL | 5774.68 | 0.000126 | 413.72 |
| PERIMETER_MID_ZN_1 ZN REHEAT COIL | 10628.80 | 0.000232 | 761.07 |
| PERIMETER_MID_ZN_2 ZN REHEAT COIL | 7093.58 | 0.000155 | 507.83 |
| PERIMETER_MID_ZN_3 ZN REHEAT COIL | 10620.76 | 0.000232 | 760.50 |
| PERIMETER_MID_ZN_4 ZN REHEAT COIL | 7093.42 | 0.000155 | 507.82 |
| PERIMETER_TOP_ZN_1 ZN REHEAT COIL | 13190.00 | 0.000289 | 943.78 |
| PERIMETER_TOP_ZN_2 ZN REHEAT COIL | 8707.35 | 0.000190 | 622.94 |
| PERIMETER_TOP_ZN_3 ZN REHEAT COIL | 13199.32 | 0.000289 | 944.44 |
| PERIMETER_TOP_ZN_4 ZN REHEAT COIL | 8707.09 | 0.000190 | 622.92 |
| 15 ZONE VAV MAIN HTG COIL | 19132.02 | 0.000418 | 604.80 |
| Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | Sum of Air Terminal Maximum Flow Rates [m3/s] | Adjusted Heating Design Air Flow Rate [m3/s] | Adjusted Cooling Design Air Flow Rate [m3/s] | Adjusted Main Design Air Flow Rate [m3/s] | User Heating Air Flow Ratio [] | Calculated Heating Air Flow Ratio [] | Design Supply Air Flow Rate [m3/s] | |
| 15 ZONE VAV | 7.63 | 1.53 | 15.25 | 4.97 | 13.60 | 13.60 | 0.300000 | 0.365687 | 13.60 |
| Maximum Outdoor Air Flow Rate [m3/s] | |
| 15 ZONE VAV OA CONTROLLER | 13.60 |
| Design Size Nominal Supply Air Flow Rate [m3/s] | |
| 15 ZONE VAV ERV | 2.15 |
| Design Size Design Inlet Air Temperature [C] | Design Size Design Inlet Water Temperature [C] | Design Size Design Outlet Air Temperature [C] | Design Size Design Inlet Air Humidity Ratio | Design Size Design Outlet Air Humidity Ratio | Design Size Design Coil Load [W] | Design Size Design Water Flow Rate [m3/s] | Design Size Design Air Flow Rate [m3/s] | |
| 15 ZONE VAV CLG COIL | 25.89 | 6.67 | 11.52 | 0.009855 | 0.008500 | 295772.86 | 0.012558 | 13.60 |
| Design Size Maximum Flow Rate [m3/s] | |
| 15 ZONE VAV FAN | 13.60 |
| Maximum Actuated Flow [m3/s] | Controller Convergence Tolerance | |
| 15 ZONE VAV CLG COIL CONTROLLER | 0.012558 | 0.000038 |
| 15 ZONE VAV MAIN HTG COIL CONTROLLER | 0.000418 |
| Maximum Loop Flow Rate [m3/s] | Plant Loop Volume [m3] | |
| CHILLED WATER LOOP | 0.012558 | 1.51 |
| HOT WATER LOOP | 0.003952 | 0.474238 |
| MAIN SERVICE WATER LOOP | 0.000054 | 0.006435 |
| Design Flow Rate [m3/s] | Design Power Consumption [W] | |
| CHILLED WATER LOOP PUMP | 0.012558 | 4379.04 |
| HOT WATER LOOP PUMP | 0.003952 | 1190.16 |
| Design Size Reference Chilled Water Flow Rate [m3/s] | Design Size Reference Capacity [W] | Design Size Reference Condenser Fluid Flow Rate [m3/s] | |
| NREL ZNE READY 2017 CHILLER 0 84TONS 1.1KW/TON | 0.012558 | 295772.86 | 33.72 |
| Design Size Nominal Capacity [W] | Design Size Design Water Flow Rate [m3/s] | |
| BOILER 617KBTU/HR 0.94 COMBUSTION EFF | 180680.03 | 0.003952 |
| Design Flow Rate [m3/s] | Design Power Consumption [W] | |
| SERVICE WATER LOOP PUMP | 0.000054 | 16.15 |
| Use Side Design Flow Rate [m3/s] | |
| 100GAL NATURAL GAS WATER HEATER - 100KBTU/HR 0.802 THERM EFF 0.808 THERM EFF | 0.000054 |
Report: Surface Shadowing Summary
For: Entire Facility
Timestamp: 2019-04-09 23:11:28
Surfaces (Walls, Roofs, etc) that may be Shadowed by Other Surfaces| None |
| Possible Shadow Receivers | |
| PERIMETER_BOT_ZN_1_WALL_SOUTH | PERIMETER_BOT_ZN_1_WALL_SOUTH_WINDOW | |
| PERIMETER_BOT_ZN_2_WALL_EAST | PERIMETER_BOT_ZN_2_WALL_EAST_WINDOW | |
| PERIMETER_BOT_ZN_3_WALL_NORTH | PERIMETER_BOT_ZN_3_WALL_NORTH_WINDOW | |
| PERIMETER_BOT_ZN_4_WALL_WEST | PERIMETER_BOT_ZN_4_WALL_WEST_WINDOW | |
| PERIMETER_MID_ZN_1_WALL_SOUTH | PERIMETER_MID_ZN_1_WALL_SOUTH_WINDOW | |
| PERIMETER_MID_ZN_2_WALL_EAST | PERIMETER_MID_ZN_2_WALL_EAST_WINDOW | |
| PERIMETER_MID_ZN_3_WALL_NORTH | PERIMETER_MID_ZN_3_WALL_NORTH_WINDOW | |
| PERIMETER_MID_ZN_4_WALL_WEST | PERIMETER_MID_ZN_4_WALL_WEST_WINDOW | |
| PERIMETER_TOP_ZN_1_WALL_SOUTH | PERIMETER_TOP_ZN_1_WALL_SOUTH_WINDOW | |
| PERIMETER_TOP_ZN_2_WALL_EAST | PERIMETER_TOP_ZN_2_WALL_EAST_WINDOW | |
| PERIMETER_TOP_ZN_3_WALL_NORTH | PERIMETER_TOP_ZN_3_WALL_NORTH_WINDOW | |
| PERIMETER_TOP_ZN_4_WALL_WEST | PERIMETER_TOP_ZN_4_WALL_WEST_WINDOW | |
Report: Adaptive Comfort Summary
For: Entire Facility
Timestamp: 2019-04-09 23:11:28
Time Not Meeting the Adaptive Comfort Models during Occupied Hours| ASHRAE55 90% Acceptability Limits [Hours] | ASHRAE55 80% Acceptability Limits [Hours] | CEN15251 Category I Acceptability Limits [Hours] | CEN15251 Category II Acceptability Limits [Hours] | CEN15251 Category III Acceptability Limits [Hours] |
Report: Initialization Summary
For: Entire Facility
Timestamp: 2019-04-09 23:11:28
Version| Version ID | |
| 1 | 9.1 |
| #TimeSteps | Minutes per TimeStep {minutes} | |
| 1 | 6 | 10 |
| Minimum System TimeStep {minutes} | Max HVAC Iterations | Minimum Plant Iterations | Maximum Plant Iterations | |
| 1 | 2 | 25 | 2 | 8 |
| Do Zone Sizing | Do System Sizing | Do Plant Sizing | Do Design Days | Do Weather Simulation | Do HVAC Sizing Simulation | |
| 1 | Yes | Yes | Yes | No | Yes | No |
| Tolerance for Time Heating Setpoint Not Met | Tolerance for Zone Cooling Setpoint Not Met Time | |
| 1 | 0.556 | 0.556 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | 20.73 | 20.68 | 20.76 | 20.84 | 20.94 | 23.13 | 23.50 | 23.58 | 23.60 | 21.36 | 21.01 | 20.81 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | 15.78 | 13.03 | 12.28 | 12.93 | 16.64 | 20.79 | 24.70 | 27.53 | 28.35 | 27.02 | 23.82 | 19.79 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 | 13.00 |
| Jan{C} | Feb{C} | Mar{C} | Apr{C} | May{C} | Jun{C} | Jul{C} | Aug{C} | Sep{C} | Oct{C} | Nov{C} | Dec{C} | |
| 1 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 | 16.00 |
| Jan{dimensionless} | Feb{dimensionless} | Mar{dimensionless} | Apr{dimensionless} | May{dimensionless} | Jun{dimensionless} | Jul{dimensionless} | Aug{dimensionless} | Sep{dimensionless} | Oct{dimensionless} | Nov{dimensionless} | Dec{dimensionless} | |
| 1 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 |
| Normal | Daylighting {dimensionless} | |
| 1 | 1.000 | 1.000 |
| Jan{dimensionless} | Feb{dimensionless} | Mar{dimensionless} | Apr{dimensionless} | May{dimensionless} | Jun{dimensionless} | Jul{dimensionless} | Aug{dimensionless} | Sep{dimensionless} | Oct{dimensionless} | Nov{dimensionless} | Dec{dimensionless} | |
| 1 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 |
| Jan{dimensionless} | Feb{dimensionless} | Mar{dimensionless} | Apr{dimensionless} | May{dimensionless} | Jun{dimensionless} | Jul{dimensionless} | Aug{dimensionless} | Sep{dimensionless} | Oct{dimensionless} | Nov{dimensionless} | Dec{dimensionless} | |
| 1 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 | 0.20 |
| Wind Sensor Height Above Ground {m} | Wind Speed Profile Exponent {} | Wind Speed Profile Boundary Layer Thickness {m} | Air Temperature Sensor Height Above Ground {m} | Wind Speed Modifier Coefficient-Internal | Temperature Modifier Coefficient-Internal | |
| 1 | 10.000 | 0.140 | 270.000 | 1.500 | 1.586 | 9.750E-003 |
| Location Name | Latitude {N+/S- Deg} | Longitude {E+/W- Deg} | Time Zone Number {GMT+/-} | Elevation {m} | Standard Pressure at Elevation {Pa} | Standard RhoAir at Elevation | |
| 1 | Houston Bush Intercontinental TX USA TMY3 WMO#=722430 | 30.00 | -95.37 | -6.00 | 29.00 | 100977 | 1.2002 |
| Calculation Method{} | Water Mains Temperature Schedule Name{} | Annual Average Outdoor Air Temperature{C} | Maximum Difference In Monthly Average Outdoor Air Temperatures{deltaC} | Fixed Default Water Mains Temperature{C} | |
| 1 | Correlation | NA | 20.32 | 17.80 | NA |
| Building Name | North Axis {deg} | Terrain | Loads Convergence Tolerance Value | Temperature Convergence Tolerance Value | Solar Distribution | Maximum Number of Warmup Days | Minimum Number of Warmup Days | |
| 1 | -MediumOffice-ASHRAE 169-2006-2A created: 2018-10-22 12:13:18 -0600 | 0.000 | City | 4.00000E-002 | 0.20000 | FullInteriorAndExterior | 25 | 6 |
| Algorithm {Simple TARP CeilingDiffuser AdaptiveConvectionAlgorithm} |
|
| 1 | TARP |
| Algorithm {SimpleCombined TARP MoWitt DOE-2 AdaptiveConvectionAlgorithm} |
|
| 1 | TARP |
| Value {Anisotropic} | |
| 1 | Anisotropic |
| Value {ThirdOrderBackwardDifference AnalyticalSolution EulerMethod} |
|
| 1 | ThirdOrderBackwardDifference |
| Simulation {Yes/No} | Carbon Dioxide Concentration | |
| 1 | No | N/A |
| Simulation {Yes/No} | Generic Contaminant Concentration | |
| 1 | No | N/A |
| Enforce Mass Balance |
Adjust Zone Mixing |
Adjust Zone Infiltration {AddInfiltration AdjustInfiltration None} |
Infiltration Zones {MixingSourceZonesOnly AllZones} |
|
| 1 | No | N/A | N/A | N/A |
| Value {RegulaFalsi Bisection BisectionThenRegulaFalsi RegulaFalsiThenBisection} |
|
| 1 | RegulaFalsi |
| Wind Speed Profile Exponent {} | Wind Speed Profile Boundary Layer Thickness {m} | Air Temperature Gradient Coefficient {K/m} | |
| 1 | 0.330 | 460.000 | 6.500000E-003 |
| Starting Corner | Vertex Input Direction | Coordinate System | Daylight Reference Point Coordinate System | Rectangular (Simple) Surface Coordinate System | |
| 1 | UpperLeftCorner | Counterclockwise | RelativeCoordinateSystem | RelativeCoordinateSystem | RelativeToZoneOrigin |
| Value {CTF - ConductionTransferFunction EMPD - MoisturePenetrationDepthConductionTransferFunction CondFD - ConductionFiniteDifference HAMT - CombinedHeatAndMoistureFiniteElement} - Description |
Inside Surface Max Temperature Limit{C} |
Surface Convection Coefficient Lower Limit {W/m2-K} |
Surface Convection Coefficient Upper Limit {W/m2-K} |
|
| 1 | CTF - ConductionTransferFunction | 200 | 0.10 | 1000.0 |
| Number of Fixed Detached Shades | Number of Building Detached Shades | Number of Attached Shades | |
| 1 | 0 | 0 | 0 |
| Number of Zones | Number of Zone Surfaces | Number of SubSurfaces | |
| 1 | 18 | 155 | 12 |
| Zone Name | North Axis {deg} | Origin X-Coordinate {m} | Origin Y-Coordinate {m} | Origin Z-Coordinate {m} | Centroid X-Coordinate {m} | Centroid Y-Coordinate {m} | Centroid Z-Coordinate {m} | Type | Zone Multiplier | Zone List Multiplier | Minimum X {m} | Maximum X {m} | Minimum Y {m} | Maximum Y {m} | Minimum Z {m} | Maximum Z {m} | Ceiling Height {m} | Volume {m3} | Zone Inside Convection Algorithm {Simple-Detailed-CeilingDiffuser-TrombeWall} | Zone Outside Convection Algorithm {Simple-Detailed-Tarp-MoWitt-DOE-2-BLAST} | Floor Area {m2} | Exterior Gross Wall Area {m2} | Exterior Net Wall Area {m2} | Exterior Window Area {m2} | Number of Surfaces | Number of SubSurfaces | Number of Shading SubSurfaces | Part of Total Building Area | |
| 1 | CORE_BOTTOM ZN | 0.0 | 0.00 | 0.00 | 0.00 | 24.96 | 16.64 | 1.37 | 1 | 1 | 1 | 4.57 | 45.34 | 4.57 | 28.70 | 0.00 | 2.74 | 2.74 | 2698.04 | TARP | TARP | 983.54 | 0.00 | 0.00 | 0.00 | 6 | 0 | 0 | Yes |
| 2 | CORE_MID ZN | 0.0 | 0.00 | 0.00 | 0.00 | 24.96 | 16.64 | 5.33 | 1 | 1 | 1 | 4.57 | 45.34 | 4.57 | 28.70 | 3.96 | 6.71 | 2.74 | 2698.04 | TARP | TARP | 983.54 | 0.00 | 0.00 | 0.00 | 6 | 0 | 0 | Yes |
| 3 | CORE_TOP ZN | 0.0 | 0.00 | 0.00 | 0.00 | 24.96 | 16.64 | 9.30 | 1 | 1 | 1 | 4.57 | 45.34 | 4.57 | 28.70 | 7.92 | 10.67 | 2.74 | 2698.04 | TARP | TARP | 983.54 | 0.00 | 0.00 | 0.00 | 6 | 0 | 0 | Yes |
| 4 | FIRSTFLOOR_PLENUM ZN | 0.0 | 0.00 | 0.00 | 0.00 | 24.96 | 16.64 | 3.35 | 1 | 1 | 1 | 0.00 | 49.91 | 0.00 | 33.27 | 2.74 | 3.96 | 1.22 | 2024.76 | TARP | TARP | 1660.73 | 202.84 | 202.84 | 0.00 | 14 | 0 | 0 | No |
| 5 | MIDFLOOR_PLENUM ZN | 0.0 | 0.00 | 0.00 | 0.00 | 24.96 | 16.64 | 7.32 | 1 | 1 | 1 | 0.00 | 49.91 | 0.00 | 33.27 | 6.71 | 7.92 | 1.22 | 2024.76 | TARP | TARP | 1660.73 | 202.84 | 202.84 | 0.00 | 14 | 0 | 0 | No |
| 6 | PERIMETER_BOT_ZN_1 ZN | 0.0 | 0.00 | 0.00 | 0.00 | 24.96 | 2.16 | 1.37 | 1 | 1 | 1 | 0.00 | 49.91 | 0.00 | 4.57 | 0.00 | 2.74 | 2.74 | 568.77 | TARP | TARP | 207.34 | 136.92 | 71.63 | 65.28 | 6 | 1 | 0 | Yes |
| 7 | PERIMETER_BOT_ZN_2 ZN | 0.0 | 0.00 | 0.00 | 0.00 | 47.82 | 16.64 | 1.37 | 1 | 1 | 1 | 45.34 | 49.91 | 0.00 | 33.27 | 0.00 | 2.74 | 2.74 | 360.08 | TARP | TARP | 131.26 | 91.28 | 47.75 | 43.52 | 6 | 1 | 0 | Yes |
| 8 | PERIMETER_BOT_ZN_3 ZN | 0.0 | 0.00 | 0.00 | 0.00 | 24.96 | 31.11 | 1.37 | 1 | 1 | 1 | 0.00 | 49.91 | 28.70 | 33.27 | 0.00 | 2.74 | 2.74 | 568.77 | TARP | TARP | 207.34 | 136.92 | 71.63 | 65.28 | 6 | 1 | 0 | Yes |
| 9 | PERIMETER_BOT_ZN_4 ZN | 0.0 | 0.00 | 0.00 | 0.00 | 2.09 | 16.64 | 1.37 | 1 | 1 | 1 | 0.00 | 4.57 | 0.00 | 33.27 | 0.00 | 2.74 | 2.74 | 360.05 | TARP | TARP | 131.25 | 91.28 | 47.75 | 43.52 | 6 | 1 | 0 | Yes |
| 10 | PERIMETER_MID_ZN_1 ZN | 0.0 | 0.00 | 0.00 | 0.00 | 24.96 | 2.16 | 5.33 | 1 | 1 | 1 | 0.00 | 49.91 | 0.00 | 4.57 | 3.96 | 6.71 | 2.74 | 568.77 | TARP | TARP | 207.34 | 136.92 | 71.63 | 65.28 | 6 | 1 | 0 | Yes |
| 11 | PERIMETER_MID_ZN_2 ZN | 0.0 | 0.00 | 0.00 | 0.00 | 47.82 | 16.64 | 5.33 | 1 | 1 | 1 | 45.34 | 49.91 | 0.00 | 33.27 | 3.96 | 6.71 | 2.74 | 360.08 | TARP | TARP | 131.26 | 91.28 | 47.75 | 43.52 | 6 | 1 | 0 | Yes |
| 12 | PERIMETER_MID_ZN_3 ZN | 0.0 | 0.00 | 0.00 | 0.00 | 24.96 | 31.11 | 5.33 | 1 | 1 | 1 | 0.00 | 49.91 | 28.70 | 33.27 | 3.96 | 6.71 | 2.74 | 568.77 | TARP | TARP | 207.34 | 136.92 | 71.63 | 65.28 | 6 | 1 | 0 | Yes |
| 13 | PERIMETER_MID_ZN_4 ZN | 0.0 | 0.00 | 0.00 | 0.00 | 2.09 | 16.64 | 5.33 | 1 | 1 | 1 | 0.00 | 4.57 | 0.00 | 33.27 | 3.96 | 6.71 | 2.74 | 360.05 | TARP | TARP | 131.25 | 91.28 | 47.75 | 43.52 | 6 | 1 | 0 | Yes |
| 14 | PERIMETER_TOP_ZN_1 ZN | 0.0 | 0.00 | 0.00 | 0.00 | 24.96 | 2.16 | 9.30 | 1 | 1 | 1 | 0.00 | 49.91 | 0.00 | 4.57 | 7.92 | 10.67 | 2.74 | 568.77 | TARP | TARP | 207.34 | 136.92 | 71.63 | 65.28 | 6 | 1 | 0 | Yes |
| 15 | PERIMETER_TOP_ZN_2 ZN | 0.0 | 0.00 | 0.00 | 0.00 | 47.82 | 16.64 | 9.30 | 1 | 1 | 1 | 45.34 | 49.91 | 0.00 | 33.27 | 7.92 | 10.67 | 2.74 | 360.08 | TARP | TARP | 131.26 | 91.28 | 47.75 | 43.52 | 6 | 1 | 0 | Yes |
| 16 | PERIMETER_TOP_ZN_3 ZN | 0.0 | 0.00 | 0.00 | 0.00 | 24.96 | 31.11 | 9.30 | 1 | 1 | 1 | 0.00 | 49.91 | 28.70 | 33.27 | 7.92 | 10.67 | 2.74 | 568.77 | TARP | TARP | 207.34 | 136.92 | 71.63 | 65.28 | 6 | 1 | 0 | Yes |
| 17 | PERIMETER_TOP_ZN_4 ZN | 0.0 | 0.00 | 0.00 | 0.00 | 2.09 | 16.64 | 9.30 | 1 | 1 | 1 | 0.00 | 4.57 | 0.00 | 33.27 | 7.92 | 10.67 | 2.74 | 360.05 | TARP | TARP | 131.25 | 91.28 | 47.75 | 43.52 | 6 | 1 | 0 | Yes |
| 18 | TOPFLOOR_PLENUM ZN | 0.0 | 0.00 | 0.00 | 0.00 | 24.96 | 16.64 | 11.28 | 1 | 1 | 1 | 0.00 | 49.91 | 0.00 | 33.27 | 10.67 | 11.89 | 1.22 | 2024.76 | TARP | TARP | 1660.73 | 202.84 | 202.84 | 0.00 | 10 | 0 | 0 | No |
| Zone Name | Floor Area {m2} | # Occupants | Area per Occupant {m2/person} | Occupant per Area {person/m2} | Interior Lighting {W/m2} | Electric Load {W/m2} | Gas Load {W/m2} | Other Load {W/m2} | Hot Water Eq {W/m2} | Steam Equipment {W/m2} | Sum Loads per Area {W/m2} | Outdoor Controlled Baseboard Heat | |
| 1 | CORE_BOTTOM ZN | 983.54 | 52.9 | 18.581 | 5.382E-002 | 8.826 | 40.849 | 0.000 | 0.000 | 0.000 | 0.000 | 49.676 | No |
| 2 | CORE_MID ZN | 983.54 | 52.9 | 18.581 | 5.382E-002 | 8.826 | 8.073 | 0.000 | 0.000 | 0.000 | 0.000 | 16.899 | No |
| 3 | CORE_TOP ZN | 983.54 | 52.9 | 18.581 | 5.382E-002 | 8.826 | 8.073 | 0.000 | 0.000 | 0.000 | 0.000 | 16.899 | No |
| 4 | FIRSTFLOOR_PLENUM ZN | 1660.73 | 0.0 | N/A | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | No |
| 5 | MIDFLOOR_PLENUM ZN | 1660.73 | 0.0 | N/A | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | No |
| 6 | PERIMETER_BOT_ZN_1 ZN | 207.34 | 11.2 | 18.581 | 5.382E-002 | 8.826 | 8.073 | 0.000 | 0.000 | 0.000 | 0.000 | 16.899 | No |
| 7 | PERIMETER_BOT_ZN_2 ZN | 131.26 | 7.1 | 18.581 | 5.382E-002 | 8.826 | 8.073 | 0.000 | 0.000 | 0.000 | 0.000 | 16.899 | No |
| 8 | PERIMETER_BOT_ZN_3 ZN | 207.34 | 11.2 | 18.581 | 5.382E-002 | 8.826 | 8.073 | 0.000 | 0.000 | 0.000 | 0.000 | 16.899 | No |
| 9 | PERIMETER_BOT_ZN_4 ZN | 131.25 | 7.1 | 18.581 | 5.382E-002 | 8.826 | 8.073 | 0.000 | 0.000 | 0.000 | 0.000 | 16.899 | No |
| 10 | PERIMETER_MID_ZN_1 ZN | 207.34 | 11.2 | 18.581 | 5.382E-002 | 8.826 | 8.073 | 0.000 | 0.000 | 0.000 | 0.000 | 16.899 | No |
| 11 | PERIMETER_MID_ZN_2 ZN | 131.26 | 7.1 | 18.581 | 5.382E-002 | 8.826 | 8.073 | 0.000 | 0.000 | 0.000 | 0.000 | 16.899 | No |
| 12 | PERIMETER_MID_ZN_3 ZN | 207.34 | 11.2 | 18.581 | 5.382E-002 | 8.826 | 8.073 | 0.000 | 0.000 | 0.000 | 0.000 | 16.899 | No |
| 13 | PERIMETER_MID_ZN_4 ZN | 131.25 | 7.1 | 18.581 | 5.382E-002 | 8.826 | 8.073 | 0.000 | 0.000 | 0.000 | 0.000 | 16.899 | No |
| 14 | PERIMETER_TOP_ZN_1 ZN | 207.34 | 11.2 | 18.581 | 5.382E-002 | 8.826 | 8.073 | 0.000 | 0.000 | 0.000 | 0.000 | 16.899 | No |
| 15 | PERIMETER_TOP_ZN_2 ZN | 131.26 | 7.1 | 18.581 | 5.382E-002 | 8.826 | 8.073 | 0.000 | 0.000 | 0.000 | 0.000 | 16.899 | No |
| 16 | PERIMETER_TOP_ZN_3 ZN | 207.34 | 11.2 | 18.581 | 5.382E-002 | 8.826 | 8.073 | 0.000 | 0.000 | 0.000 | 0.000 | 16.899 | No |
| 17 | PERIMETER_TOP_ZN_4 ZN | 131.25 | 7.1 | 18.581 | 5.382E-002 | 8.826 | 8.073 | 0.000 | 0.000 | 0.000 | 0.000 | 16.899 | No |
| 18 | TOPFLOOR_PLENUM ZN | 1660.73 | 0.0 | N/A | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | No |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Number of People {} | People/Floor Area {person/m2} | Floor Area per person {m2/person} | Fraction Radiant | Fraction Convected | Sensible Fraction Calculation | Activity level | ASHRAE 55 Warnings | Carbon Dioxide Generation Rate | Nominal Minimum Number of People | Nominal Maximum Number of People | |
| 1 | CORE_BOTTOM ZN OFFICE WHOLEBUILDING - MD OFFICE PEOPLE | OFFICEMEDIUM BLDG_OCC_SCH | CORE_BOTTOM ZN | 983.54 | 52.9 | 52.9 | 5.382E-002 | 18.581 | 0.300 | 0.700 | AutoCalculate | OFFICEMEDIUM ACTIVITY_SCH | No | 3.8200E-008 | 0 | 53 |
| 2 | CORE_MID ZN OFFICE WHOLEBUILDING - MD OFFICE PEOPLE | OFFICEMEDIUM BLDG_OCC_SCH | CORE_MID ZN | 983.54 | 52.9 | 52.9 | 5.382E-002 | 18.581 | 0.300 | 0.700 | AutoCalculate | OFFICEMEDIUM ACTIVITY_SCH | No | 3.8200E-008 | 0 | 53 |
| 3 | CORE_TOP ZN OFFICE WHOLEBUILDING - MD OFFICE PEOPLE | OFFICEMEDIUM BLDG_OCC_SCH | CORE_TOP ZN | 983.54 | 52.9 | 52.9 | 5.382E-002 | 18.581 | 0.300 | 0.700 | AutoCalculate | OFFICEMEDIUM ACTIVITY_SCH | No | 3.8200E-008 | 0 | 53 |
| 4 | PERIMETER_BOT_ZN_1 ZN OFFICE WHOLEBUILDING - MD OFFICE PEOPLE | OFFICEMEDIUM BLDG_OCC_SCH | PERIMETER_BOT_ZN_1 ZN | 207.34 | 11.2 | 11.2 | 5.382E-002 | 18.581 | 0.300 | 0.700 | AutoCalculate | OFFICEMEDIUM ACTIVITY_SCH | No | 3.8200E-008 | 0 | 11 |
| 5 | PERIMETER_BOT_ZN_2 ZN OFFICE WHOLEBUILDING - MD OFFICE PEOPLE | OFFICEMEDIUM BLDG_OCC_SCH | PERIMETER_BOT_ZN_2 ZN | 131.26 | 7.1 | 7.1 | 5.382E-002 | 18.581 | 0.300 | 0.700 | AutoCalculate | OFFICEMEDIUM ACTIVITY_SCH | No | 3.8200E-008 | 0 | 7 |
| 6 | PERIMETER_BOT_ZN_3 ZN OFFICE WHOLEBUILDING - MD OFFICE PEOPLE | OFFICEMEDIUM BLDG_OCC_SCH | PERIMETER_BOT_ZN_3 ZN | 207.34 | 11.2 | 11.2 | 5.382E-002 | 18.581 | 0.300 | 0.700 | AutoCalculate | OFFICEMEDIUM ACTIVITY_SCH | No | 3.8200E-008 | 0 | 11 |
| 7 | PERIMETER_BOT_ZN_4 ZN OFFICE WHOLEBUILDING - MD OFFICE PEOPLE | OFFICEMEDIUM BLDG_OCC_SCH | PERIMETER_BOT_ZN_4 ZN | 131.25 | 7.1 | 7.1 | 5.382E-002 | 18.581 | 0.300 | 0.700 | AutoCalculate | OFFICEMEDIUM ACTIVITY_SCH | No | 3.8200E-008 | 0 | 7 |
| 8 | PERIMETER_MID_ZN_1 ZN OFFICE WHOLEBUILDING - MD OFFICE PEOPLE | OFFICEMEDIUM BLDG_OCC_SCH | PERIMETER_MID_ZN_1 ZN | 207.34 | 11.2 | 11.2 | 5.382E-002 | 18.581 | 0.300 | 0.700 | AutoCalculate | OFFICEMEDIUM ACTIVITY_SCH | No | 3.8200E-008 | 0 | 11 |
| 9 | PERIMETER_MID_ZN_2 ZN OFFICE WHOLEBUILDING - MD OFFICE PEOPLE | OFFICEMEDIUM BLDG_OCC_SCH | PERIMETER_MID_ZN_2 ZN | 131.26 | 7.1 | 7.1 | 5.382E-002 | 18.581 | 0.300 | 0.700 | AutoCalculate | OFFICEMEDIUM ACTIVITY_SCH | No | 3.8200E-008 | 0 | 7 |
| 10 | PERIMETER_MID_ZN_3 ZN OFFICE WHOLEBUILDING - MD OFFICE PEOPLE | OFFICEMEDIUM BLDG_OCC_SCH | PERIMETER_MID_ZN_3 ZN | 207.34 | 11.2 | 11.2 | 5.382E-002 | 18.581 | 0.300 | 0.700 | AutoCalculate | OFFICEMEDIUM ACTIVITY_SCH | No | 3.8200E-008 | 0 | 11 |
| 11 | PERIMETER_MID_ZN_4 ZN OFFICE WHOLEBUILDING - MD OFFICE PEOPLE | OFFICEMEDIUM BLDG_OCC_SCH | PERIMETER_MID_ZN_4 ZN | 131.25 | 7.1 | 7.1 | 5.382E-002 | 18.581 | 0.300 | 0.700 | AutoCalculate | OFFICEMEDIUM ACTIVITY_SCH | No | 3.8200E-008 | 0 | 7 |
| 12 | PERIMETER_TOP_ZN_1 ZN OFFICE WHOLEBUILDING - MD OFFICE PEOPLE | OFFICEMEDIUM BLDG_OCC_SCH | PERIMETER_TOP_ZN_1 ZN | 207.34 | 11.2 | 11.2 | 5.382E-002 | 18.581 | 0.300 | 0.700 | AutoCalculate | OFFICEMEDIUM ACTIVITY_SCH | No | 3.8200E-008 | 0 | 11 |
| 13 | PERIMETER_TOP_ZN_2 ZN OFFICE WHOLEBUILDING - MD OFFICE PEOPLE | OFFICEMEDIUM BLDG_OCC_SCH | PERIMETER_TOP_ZN_2 ZN | 131.26 | 7.1 | 7.1 | 5.382E-002 | 18.581 | 0.300 | 0.700 | AutoCalculate | OFFICEMEDIUM ACTIVITY_SCH | No | 3.8200E-008 | 0 | 7 |
| 14 | PERIMETER_TOP_ZN_3 ZN OFFICE WHOLEBUILDING - MD OFFICE PEOPLE | OFFICEMEDIUM BLDG_OCC_SCH | PERIMETER_TOP_ZN_3 ZN | 207.34 | 11.2 | 11.2 | 5.382E-002 | 18.581 | 0.300 | 0.700 | AutoCalculate | OFFICEMEDIUM ACTIVITY_SCH | No | 3.8200E-008 | 0 | 11 |
| 15 | PERIMETER_TOP_ZN_4 ZN OFFICE WHOLEBUILDING - MD OFFICE PEOPLE | OFFICEMEDIUM BLDG_OCC_SCH | PERIMETER_TOP_ZN_4 ZN | 131.25 | 7.1 | 7.1 | 5.382E-002 | 18.581 | 0.300 | 0.700 | AutoCalculate | OFFICEMEDIUM ACTIVITY_SCH | No | 3.8200E-008 | 0 | 7 |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Lighting Level {W} | Lights/Floor Area {W/m2} | Lights per person {W/person} | Fraction Return Air | Fraction Radiant | Fraction Short Wave | Fraction Convected | Fraction Replaceable | End-Use Category | Nominal Minimum Lighting Level {W} | Nominal Maximum Lighting Level {W} | |
| 1 | CORE_BOTTOM ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | CORE_BOTTOM ZN | 983.54 | 52.9 | 8681.094 | 8.826 | 164.000 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 8681.094 |
| 2 | CORE_MID ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | CORE_MID ZN | 983.54 | 52.9 | 8681.094 | 8.826 | 164.000 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 8681.094 |
| 3 | CORE_TOP ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | CORE_TOP ZN | 983.54 | 52.9 | 8681.094 | 8.826 | 164.000 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 8681.094 |
| 4 | PERIMETER_BOT_ZN_1 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | PERIMETER_BOT_ZN_1 ZN | 207.34 | 11.2 | 1830.051 | 8.826 | 164.000 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 1830.051 |
| 5 | PERIMETER_BOT_ZN_2 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | PERIMETER_BOT_ZN_2 ZN | 131.26 | 7.1 | 1158.573 | 8.826 | 164.000 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 1158.573 |
| 6 | PERIMETER_BOT_ZN_3 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | PERIMETER_BOT_ZN_3 ZN | 207.34 | 11.2 | 1830.051 | 8.826 | 164.000 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 1830.051 |
| 7 | PERIMETER_BOT_ZN_4 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | PERIMETER_BOT_ZN_4 ZN | 131.25 | 7.1 | 1158.497 | 8.826 | 164.000 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 1158.497 |
| 8 | PERIMETER_MID_ZN_1 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | PERIMETER_MID_ZN_1 ZN | 207.34 | 11.2 | 1830.051 | 8.826 | 164.000 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 1830.051 |
| 9 | PERIMETER_MID_ZN_2 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | PERIMETER_MID_ZN_2 ZN | 131.26 | 7.1 | 1158.573 | 8.826 | 164.000 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 1158.573 |
| 10 | PERIMETER_MID_ZN_3 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | PERIMETER_MID_ZN_3 ZN | 207.34 | 11.2 | 1830.051 | 8.826 | 164.000 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 1830.051 |
| 11 | PERIMETER_MID_ZN_4 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | PERIMETER_MID_ZN_4 ZN | 131.25 | 7.1 | 1158.497 | 8.826 | 164.000 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 1158.497 |
| 12 | PERIMETER_TOP_ZN_1 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | PERIMETER_TOP_ZN_1 ZN | 207.34 | 11.2 | 1830.051 | 8.826 | 164.000 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 1830.051 |
| 13 | PERIMETER_TOP_ZN_2 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | PERIMETER_TOP_ZN_2 ZN | 131.26 | 7.1 | 1158.573 | 8.826 | 164.000 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 1158.573 |
| 14 | PERIMETER_TOP_ZN_3 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | PERIMETER_TOP_ZN_3 ZN | 207.34 | 11.2 | 1830.051 | 8.826 | 164.000 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 1830.051 |
| 15 | PERIMETER_TOP_ZN_4 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | PERIMETER_TOP_ZN_4 ZN | 131.25 | 7.1 | 1158.497 | 8.826 | 164.000 | 0.000 | 0.700 | 0.200 | 0.100 | 1.000 | General | 0.000 | 1158.497 |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Equipment Level {W} | Equipment/Floor Area {W/m2} | Equipment per person {W/person} | Fraction Latent | Fraction Radiant | Fraction Lost | Fraction Convected | End-Use SubCategory | Nominal Minimum Equipment Level {W} | Nominal Maximum Equipment Level {W} | |
| 1 | 2 ELEVATOR FANS | OFFICEMEDIUM ELEV_LIGHT_FAN_SCH_ADD_DF | CORE_BOTTOM ZN | 983.54 | 52.9 | 61.915 | 6.295E-002 | 1.170 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 42.721 |
| 2 | 2 ELEVATOR LIFT MOTORS | OFFICEMEDIUM BLDG_ELEVATORS | CORE_BOTTOM ZN | 983.54 | 52.9 | 32110.000 | 32.647 | 606.610 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 22155.900 |
| 3 | 2 ELEVATOR LIGHTS | OFFICEMEDIUM ELEV_LIGHT_FAN_SCH_ADD_DF | CORE_BOTTOM ZN | 983.54 | 52.9 | 64.697 | 6.578E-002 | 1.222 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 44.641 |
| 4 | CORE_BOTTOM ZN OFFICE WHOLEBUILDING - MD OFFICE ELEC EQUIP | OFFICEMEDIUM BLDG_EQUIP_SCH_2013 | CORE_BOTTOM ZN | 983.54 | 52.9 | 7940.025 | 8.073 | 150.000 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 7940.025 |
| 5 | CORE_MID ZN OFFICE WHOLEBUILDING - MD OFFICE ELEC EQUIP | OFFICEMEDIUM BLDG_EQUIP_SCH_2013 | CORE_MID ZN | 983.54 | 52.9 | 7940.025 | 8.073 | 150.000 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 7940.025 |
| 6 | CORE_TOP ZN OFFICE WHOLEBUILDING - MD OFFICE ELEC EQUIP | OFFICEMEDIUM BLDG_EQUIP_SCH_2013 | CORE_TOP ZN | 983.54 | 52.9 | 7940.025 | 8.073 | 150.000 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 7940.025 |
| 7 | PERIMETER_BOT_ZN_1 ZN OFFICE WHOLEBUILDING - MD OFFICE ELEC EQUIP | OFFICEMEDIUM BLDG_EQUIP_SCH_2013 | PERIMETER_BOT_ZN_1 ZN | 207.34 | 11.2 | 1673.827 | 8.073 | 150.000 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 1673.827 |
| 8 | PERIMETER_BOT_ZN_2 ZN OFFICE WHOLEBUILDING - MD OFFICE ELEC EQUIP | OFFICEMEDIUM BLDG_EQUIP_SCH_2013 | PERIMETER_BOT_ZN_2 ZN | 131.26 | 7.1 | 1059.671 | 8.073 | 150.000 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 1059.671 |
| 9 | PERIMETER_BOT_ZN_3 ZN OFFICE WHOLEBUILDING - MD OFFICE ELEC EQUIP | OFFICEMEDIUM BLDG_EQUIP_SCH_2013 | PERIMETER_BOT_ZN_3 ZN | 207.34 | 11.2 | 1673.827 | 8.073 | 150.000 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 1673.827 |
| 10 | PERIMETER_BOT_ZN_4 ZN OFFICE WHOLEBUILDING - MD OFFICE ELEC EQUIP | OFFICEMEDIUM BLDG_EQUIP_SCH_2013 | PERIMETER_BOT_ZN_4 ZN | 131.25 | 7.1 | 1059.601 | 8.073 | 150.000 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 1059.601 |
| 11 | PERIMETER_MID_ZN_1 ZN OFFICE WHOLEBUILDING - MD OFFICE ELEC EQUIP | OFFICEMEDIUM BLDG_EQUIP_SCH_2013 | PERIMETER_MID_ZN_1 ZN | 207.34 | 11.2 | 1673.827 | 8.073 | 150.000 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 1673.827 |
| 12 | PERIMETER_MID_ZN_2 ZN OFFICE WHOLEBUILDING - MD OFFICE ELEC EQUIP | OFFICEMEDIUM BLDG_EQUIP_SCH_2013 | PERIMETER_MID_ZN_2 ZN | 131.26 | 7.1 | 1059.671 | 8.073 | 150.000 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 1059.671 |
| 13 | PERIMETER_MID_ZN_3 ZN OFFICE WHOLEBUILDING - MD OFFICE ELEC EQUIP | OFFICEMEDIUM BLDG_EQUIP_SCH_2013 | PERIMETER_MID_ZN_3 ZN | 207.34 | 11.2 | 1673.827 | 8.073 | 150.000 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 1673.827 |
| 14 | PERIMETER_MID_ZN_4 ZN OFFICE WHOLEBUILDING - MD OFFICE ELEC EQUIP | OFFICEMEDIUM BLDG_EQUIP_SCH_2013 | PERIMETER_MID_ZN_4 ZN | 131.25 | 7.1 | 1059.601 | 8.073 | 150.000 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 1059.601 |
| 15 | PERIMETER_TOP_ZN_1 ZN OFFICE WHOLEBUILDING - MD OFFICE ELEC EQUIP | OFFICEMEDIUM BLDG_EQUIP_SCH_2013 | PERIMETER_TOP_ZN_1 ZN | 207.34 | 11.2 | 1673.827 | 8.073 | 150.000 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 1673.827 |
| 16 | PERIMETER_TOP_ZN_2 ZN OFFICE WHOLEBUILDING - MD OFFICE ELEC EQUIP | OFFICEMEDIUM BLDG_EQUIP_SCH_2013 | PERIMETER_TOP_ZN_2 ZN | 131.26 | 7.1 | 1059.671 | 8.073 | 150.000 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 1059.671 |
| 17 | PERIMETER_TOP_ZN_3 ZN OFFICE WHOLEBUILDING - MD OFFICE ELEC EQUIP | OFFICEMEDIUM BLDG_EQUIP_SCH_2013 | PERIMETER_TOP_ZN_3 ZN | 207.34 | 11.2 | 1673.827 | 8.073 | 150.000 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 1673.827 |
| 18 | PERIMETER_TOP_ZN_4 ZN OFFICE WHOLEBUILDING - MD OFFICE ELEC EQUIP | OFFICEMEDIUM BLDG_EQUIP_SCH_2013 | PERIMETER_TOP_ZN_4 ZN | 131.25 | 7.1 | 1059.601 | 8.073 | 150.000 | 0.000 | 0.500 | 0.000 | 0.500 | General | 0.000 | 1059.601 |
| Calculation Method | Value {days} | Allowable Number Figures in Shadow Overlap {} | Polygon Clipping Algorithm | Sky Diffuse Modeling Algorithm | External Shading Calculation Method | Output External Shading Calculation Results | Disable Self-Shading Within Shading Zone Groups | Disable Self-Shading From Shading Zone Groups to Other Zones | |
| 1 | AverageOverDaysInFrequency | 7 | 15000 | SutherlandHodgman | SimpleSkyDiffuseModeling | InternalCalculation | No | No | No |
| Zone Name | Number of Exterior Windows | Number of Exterior Windows in Adjacent Zones | |
| 1 | PERIMETER_BOT_ZN_1 ZN | 1 | 0 |
| 2 | PERIMETER_BOT_ZN_2 ZN | 1 | 0 |
| 3 | PERIMETER_BOT_ZN_3 ZN | 1 | 0 |
| 4 | PERIMETER_BOT_ZN_4 ZN | 1 | 0 |
| 5 | PERIMETER_MID_ZN_1 ZN | 1 | 0 |
| 6 | PERIMETER_MID_ZN_2 ZN | 1 | 0 |
| 7 | PERIMETER_MID_ZN_3 ZN | 1 | 0 |
| 8 | PERIMETER_MID_ZN_4 ZN | 1 | 0 |
| 9 | PERIMETER_TOP_ZN_1 ZN | 1 | 0 |
| 10 | PERIMETER_TOP_ZN_2 ZN | 1 | 0 |
| 11 | PERIMETER_TOP_ZN_3 ZN | 1 | 0 |
| 12 | PERIMETER_TOP_ZN_4 ZN | 1 | 0 |
| Zone Name | Number of Adjacent Zones with Windows | Adjacent Zone Names - 1st 100 (max) | |
| 1 | PERIMETER_BOT_ZN_1 ZN | 0 | |
| 2 | PERIMETER_BOT_ZN_2 ZN | 0 | |
| 3 | PERIMETER_BOT_ZN_3 ZN | 0 | |
| 4 | PERIMETER_BOT_ZN_4 ZN | 0 | |
| 5 | PERIMETER_MID_ZN_1 ZN | 0 | |
| 6 | PERIMETER_MID_ZN_2 ZN | 0 | |
| 7 | PERIMETER_MID_ZN_3 ZN | 0 | |
| 8 | PERIMETER_MID_ZN_4 ZN | 0 | |
| 9 | PERIMETER_TOP_ZN_1 ZN | 0 | |
| 10 | PERIMETER_TOP_ZN_2 ZN | 0 | |
| 11 | PERIMETER_TOP_ZN_3 ZN | 0 | |
| 12 | PERIMETER_TOP_ZN_4 ZN | 0 |
| Type | Name | Volume {m3} | Maximum Capacity {W} | Standard Rated Recovery Efficiency | Standard Rated Energy Factor | |
| 1 | WaterHeater:Mixed | 100GAL NATURAL GAS WATER HEATER - 100KBTU/HR 0.802 THERM EFF 0.808 THERM EFF | 0.3785 | 29307.1 | 1.016 | 0.2254 |
| Name | Schedule Name | Zone Name | Zone Floor Area {m2} | # Zone Occupants | Design Volume Flow Rate {m3/s} | Volume Flow Rate/Floor Area {m3/s-m2} | Volume Flow Rate/Exterior Surface Area {m3/s-m2} | ACH - Air Changes per Hour | Equation A - Constant Term Coefficient {} | Equation B - Temperature Term Coefficient {1/C} | Equation C - Velocity Term Coefficient {s/m} | Equation D - Velocity Squared Term Coefficient {s2/m2} | |
| 1 | FIRSTFLOOR_PLENUM INFILTRATION | OFFICEMEDIUM INFIL_SCH_PNNL | FIRSTFLOOR_PLENUM ZN | 1660.73 | 0.0 | 0.116 | 6.957E-005 | 5.696E-004 | 0.205 | 0.000 | 0.000 | 0.224 | 0.000 |
| 2 | MIDFLOOR_PLENUM INFILTRATION | OFFICEMEDIUM INFIL_SCH_PNNL | MIDFLOOR_PLENUM ZN | 1660.73 | 0.0 | 0.116 | 6.957E-005 | 5.696E-004 | 0.205 | 0.000 | 0.000 | 0.224 | 0.000 |
| 3 | ENTRY DOOR INFILTRATION | OFFICEMEDIUM INFIL_DOOR_OPENING_SCH | PERIMETER_BOT_ZN_1 ZN | 207.34 | 11.2 | 1.043 | 5.030E-003 | 7.618E-003 | 6.602 | 1.000 | 0.000 | 0.000 | 0.000 |
| 4 | PERIMETER_BOT_ZN_1 INFILTRATION | OFFICEMEDIUM INFIL_SCH_PNNL | PERIMETER_BOT_ZN_1 ZN | 207.34 | 11.2 | 7.798E-002 | 3.761E-004 | 5.696E-004 | 0.494 | 0.000 | 0.000 | 0.224 | 0.000 |
| 5 | PERIMETER_BOT_ZN_2 INFILTRATION | OFFICEMEDIUM INFIL_SCH_PNNL | PERIMETER_BOT_ZN_2 ZN | 131.26 | 7.1 | 5.199E-002 | 3.961E-004 | 5.696E-004 | 0.520 | 0.000 | 0.000 | 0.224 | 0.000 |
| 6 | PERIMETER_BOT_ZN_3 INFILTRATION | OFFICEMEDIUM INFIL_SCH_PNNL | PERIMETER_BOT_ZN_3 ZN | 207.34 | 11.2 | 7.798E-002 | 3.761E-004 | 5.696E-004 | 0.494 | 0.000 | 0.000 | 0.224 | 0.000 |
| 7 | PERIMETER_BOT_ZN_4 INFILTRATION | OFFICEMEDIUM INFIL_SCH_PNNL | PERIMETER_BOT_ZN_4 ZN | 131.25 | 7.1 | 5.199E-002 | 3.961E-004 | 5.696E-004 | 0.520 | 0.000 | 0.000 | 0.224 | 0.000 |
| 8 | PERIMETER_MID_ZN_1 INFILTRATION | OFFICEMEDIUM INFIL_SCH_PNNL | PERIMETER_MID_ZN_1 ZN | 207.34 | 11.2 | 7.798E-002 | 3.761E-004 | 5.696E-004 | 0.494 | 0.000 | 0.000 | 0.224 | 0.000 |
| 9 | PERIMETER_MID_ZN_2 INFILTRATION | OFFICEMEDIUM INFIL_SCH_PNNL | PERIMETER_MID_ZN_2 ZN | 131.26 | 7.1 | 5.199E-002 | 3.961E-004 | 5.696E-004 | 0.520 | 0.000 | 0.000 | 0.224 | 0.000 |
| 10 | PERIMETER_MID_ZN_3 INFILTRATION | OFFICEMEDIUM INFIL_SCH_PNNL | PERIMETER_MID_ZN_3 ZN | 207.34 | 11.2 | 7.798E-002 | 3.761E-004 | 5.696E-004 | 0.494 | 0.000 | 0.000 | 0.224 | 0.000 |
| 11 | PERIMETER_MID_ZN_4 INFILTRATION | OFFICEMEDIUM INFIL_SCH_PNNL | PERIMETER_MID_ZN_4 ZN | 131.25 | 7.1 | 5.199E-002 | 3.961E-004 | 5.696E-004 | 0.520 | 0.000 | 0.000 | 0.224 | 0.000 |
| 12 | PERIMETER_TOP_ZN_1 INFILTRATION | OFFICEMEDIUM INFIL_SCH_PNNL | PERIMETER_TOP_ZN_1 ZN | 207.34 | 11.2 | 7.798E-002 | 3.761E-004 | 5.696E-004 | 0.494 | 0.000 | 0.000 | 0.224 | 0.000 |
| 13 | PERIMETER_TOP_ZN_2 INFILTRATION | OFFICEMEDIUM INFIL_SCH_PNNL | PERIMETER_TOP_ZN_2 ZN | 131.26 | 7.1 | 5.199E-002 | 3.961E-004 | 5.696E-004 | 0.520 | 0.000 | 0.000 | 0.224 | 0.000 |
| 14 | PERIMETER_TOP_ZN_3 INFILTRATION | OFFICEMEDIUM INFIL_SCH_PNNL | PERIMETER_TOP_ZN_3 ZN | 207.34 | 11.2 | 7.798E-002 | 3.761E-004 | 5.696E-004 | 0.494 | 0.000 | 0.000 | 0.224 | 0.000 |
| 15 | PERIMETER_TOP_ZN_4 INFILTRATION | OFFICEMEDIUM INFIL_SCH_PNNL | PERIMETER_TOP_ZN_4 ZN | 131.25 | 7.1 | 5.199E-002 | 3.961E-004 | 5.696E-004 | 0.520 | 0.000 | 0.000 | 0.224 | 0.000 |
| 16 | TOPFLOOR_PLENUM INFILTRATION | OFFICEMEDIUM INFIL_SCH_PNNL | TOPFLOOR_PLENUM ZN | 1660.73 | 0.0 | 0.116 | 6.957E-005 | 6.199E-005 | 0.205 | 0.000 | 0.000 | 0.224 | 0.000 |
| Simple | |
| 1 | Simple |
| Zone Name | Mixing/Mundt/UCSDDV/UCSDCV/UCSDUFI/UCSDUFE/User Defined | |
| 1 | CORE_BOTTOM ZN | Mixing/Well-Stirred |
| 2 | CORE_MID ZN | Mixing/Well-Stirred |
| 3 | CORE_TOP ZN | Mixing/Well-Stirred |
| 4 | FIRSTFLOOR_PLENUM ZN | Mixing/Well-Stirred |
| 5 | MIDFLOOR_PLENUM ZN | Mixing/Well-Stirred |
| 6 | PERIMETER_BOT_ZN_1 ZN | Mixing/Well-Stirred |
| 7 | PERIMETER_BOT_ZN_2 ZN | Mixing/Well-Stirred |
| 8 | PERIMETER_BOT_ZN_3 ZN | Mixing/Well-Stirred |
| 9 | PERIMETER_BOT_ZN_4 ZN | Mixing/Well-Stirred |
| 10 | PERIMETER_MID_ZN_1 ZN | Mixing/Well-Stirred |
| 11 | PERIMETER_MID_ZN_2 ZN | Mixing/Well-Stirred |
| 12 | PERIMETER_MID_ZN_3 ZN | Mixing/Well-Stirred |
| 13 | PERIMETER_MID_ZN_4 ZN | Mixing/Well-Stirred |
| 14 | PERIMETER_TOP_ZN_1 ZN | Mixing/Well-Stirred |
| 15 | PERIMETER_TOP_ZN_2 ZN | Mixing/Well-Stirred |
| 16 | PERIMETER_TOP_ZN_3 ZN | Mixing/Well-Stirred |
| 17 | PERIMETER_TOP_ZN_4 ZN | Mixing/Well-Stirred |
| 18 | TOPFLOOR_PLENUM ZN | Mixing/Well-Stirred |
| No Multizone or Distribution/Multizone with Distribution/Multizone without Distribution/Multizone with Distribution only during Fan Operation | |
| 1 | NoMultizoneOrDistribution |
| Sensible Heat Capacity Multiplier | Moisture Capacity Multiplier | Carbon Dioxide Capacity Multiplier | Generic Contaminant Capacity Multiplier | |
| 1 | 1.000 | 1.000 | 1.000 | 1.000 |
| Value | |
| 1 | 6 |
| Sizing Factor ID | Value | |
| 1 | Global | 1.0000 |
| Sizing Factor ID | Value | |
| 1 | Global | 1.0000 |
| Zone Name | Load Type | Calc Des Load {W} | User Des Load {W} | Calc Des Air Flow Rate {m3/s} | User Des Air Flow Rate {m3/s} | Design Day Name | Date/Time of Peak | Temperature at Peak {C} | Humidity Ratio at Peak {kgWater/kgDryAir} | Floor Area {m2} | # Occupants | Calc Outdoor Air Flow Rate {m3/s} | Calc DOAS Heat Addition Rate {W} | |
| 1 | CORE_BOTTOM ZN | Cooling | 40923.94856 | 40923.94856 | 2.95256 | 2.95256 | HOUSTON BUSH INTERCONTINENTAL ANN CLG .4% CONDNS DB=>MWB | 7/21 08:00:00 | 28.52600 | 1.51947E-002 | 983.53657 | 52.93350 | 0.42469 | 0.00000 |
| 2 | CORE_BOTTOM ZN | Heating | 6119.05852 | 6119.05852 | 0.25685 | 0.42469 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | -1.60000 | 3.31476E-003 | 983.53657 | 52.93350 | 0.42469 | 0.00000 |
| 3 | CORE_MID ZN | Cooling | 29293.99443 | 29293.99443 | 2.11109 | 2.11109 | HOUSTON BUSH INTERCONTINENTAL ANN CLG .4% CONDNS DB=>MWB | 7/21 08:00:00 | 28.52600 | 1.51947E-002 | 983.53657 | 52.93350 | 0.42469 | 0.00000 |
| 4 | CORE_MID ZN | Heating | 11092.71400 | 11092.71400 | 0.46919 | 0.46919 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | -1.60000 | 3.31476E-003 | 983.53657 | 52.93350 | 0.42469 | 0.00000 |
| 5 | CORE_TOP ZN | Cooling | 30379.51476 | 30379.51476 | 2.21021 | 2.21021 | HOUSTON BUSH INTERCONTINENTAL ANN CLG .4% CONDNS DB=>MWB | 7/21 15:00:00 | 36.00000 | 1.51947E-002 | 983.53657 | 52.93350 | 0.42469 | 0.00000 |
| 6 | CORE_TOP ZN | Heating | 20153.65206 | 20153.65206 | 0.85795 | 0.85795 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | -1.60000 | 3.31476E-003 | 983.53657 | 52.93350 | 0.42469 | 0.00000 |
| 7 | PERIMETER_BOT_ZN_1 ZN | Cooling | 8013.08849 | 8013.08849 | 0.58298 | 0.58298 | HOUSTON BUSH INTERCONTINENTAL ANN CLG .4% CONDNS DB=>MWB | 7/21 13:40:00 | 35.83167 | 1.51947E-002 | 207.33814 | 11.15885 | 8.95286E-002 | 0.00000 |
| 8 | PERIMETER_BOT_ZN_1 ZN | Heating | 5993.00251 | 5993.00251 | 0.25572 | 0.25572 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | -1.60000 | 3.31476E-003 | 207.33814 | 11.15885 | 8.95286E-002 | 0.00000 |
| 9 | PERIMETER_BOT_ZN_2 ZN | Cooling | 8690.77975 | 8690.77975 | 0.63228 | 0.63228 | HOUSTON BUSH INTERCONTINENTAL ANN CLG .4% CONDNS DB=>MWB | 7/21 09:30:00 | 31.30350 | 1.51947E-002 | 131.26219 | 7.06447 | 5.66790E-002 | 0.00000 |
| 10 | PERIMETER_BOT_ZN_2 ZN | Heating | 4040.51956 | 4040.51956 | 0.17246 | 0.17246 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | -1.60000 | 3.31476E-003 | 131.26219 | 7.06447 | 5.66790E-002 | 0.00000 |
| 11 | PERIMETER_BOT_ZN_3 ZN | Cooling | 7006.16318 | 7006.16318 | 0.50972 | 0.50972 | HOUSTON BUSH INTERCONTINENTAL ANN CLG .4% CONDNS DB=>MWB | 7/21 14:50:00 | 36.00000 | 1.51947E-002 | 207.33814 | 11.15885 | 8.95286E-002 | 0.00000 |
| 12 | PERIMETER_BOT_ZN_3 ZN | Heating | 5950.14059 | 5950.14059 | 0.25389 | 0.25389 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | -1.60000 | 3.31476E-003 | 207.33814 | 11.15885 | 8.95286E-002 | 0.00000 |
| 13 | PERIMETER_BOT_ZN_4 ZN | Cooling | 9239.47201 | 9239.47201 | 0.67220 | 0.67220 | HOUSTON BUSH INTERCONTINENTAL ANN CLG .4% CONDNS DB=>MWB | 7/21 17:00:00 | 34.58600 | 1.51947E-002 | 131.25358 | 7.06401 | 5.66753E-002 | 0.00000 |
| 14 | PERIMETER_BOT_ZN_4 ZN | Heating | 4040.46755 | 4040.46755 | 0.17246 | 0.17246 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | -1.60000 | 3.31476E-003 | 131.25358 | 7.06401 | 5.66753E-002 | 0.00000 |
| 15 | PERIMETER_MID_ZN_1 ZN | Cooling | 9230.66061 | 9230.66061 | 0.67156 | 0.67156 | HOUSTON BUSH INTERCONTINENTAL ANN CLG .4% CONDNS DB=>MWB | 7/21 13:40:00 | 35.83167 | 1.51947E-002 | 207.33814 | 11.15885 | 8.95286E-002 | 0.00000 |
| 16 | PERIMETER_MID_ZN_1 ZN | Heating | 7435.33202 | 7435.33202 | 0.31754 | 0.31754 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | -1.60000 | 3.31476E-003 | 207.33814 | 11.15885 | 8.95286E-002 | 0.00000 |
| 17 | PERIMETER_MID_ZN_2 ZN | Cooling | 9487.89420 | 9487.89420 | 0.69028 | 0.69028 | HOUSTON BUSH INTERCONTINENTAL ANN CLG .4% CONDNS DB=>MWB | 7/21 09:30:00 | 31.30350 | 1.51947E-002 | 131.26219 | 7.06447 | 5.66790E-002 | 0.00000 |
| 18 | PERIMETER_MID_ZN_2 ZN | Heating | 4961.84015 | 4961.84015 | 0.21195 | 0.21195 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | -1.60000 | 3.31476E-003 | 131.26219 | 7.06447 | 5.66790E-002 | 0.00000 |
| 19 | PERIMETER_MID_ZN_3 ZN | Cooling | 8247.83453 | 8247.83453 | 0.60006 | 0.60006 | HOUSTON BUSH INTERCONTINENTAL ANN CLG .4% CONDNS DB=>MWB | 7/21 14:50:00 | 36.00000 | 1.51947E-002 | 207.33814 | 11.15885 | 8.95286E-002 | 0.00000 |
| 20 | PERIMETER_MID_ZN_3 ZN | Heating | 7429.71326 | 7429.71326 | 0.31730 | 0.31730 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | -1.60000 | 3.31476E-003 | 207.33814 | 11.15885 | 8.95286E-002 | 0.00000 |
| 21 | PERIMETER_MID_ZN_4 ZN | Cooling | 10001.35046 | 10001.35046 | 0.72763 | 0.72763 | HOUSTON BUSH INTERCONTINENTAL ANN CLG .4% CONDNS DB=>MWB | 7/21 17:00:00 | 34.58600 | 1.51947E-002 | 131.25358 | 7.06401 | 5.66753E-002 | 0.00000 |
| 22 | PERIMETER_MID_ZN_4 ZN | Heating | 4961.72734 | 4961.72734 | 0.21195 | 0.21195 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | -1.60000 | 3.31476E-003 | 131.25358 | 7.06401 | 5.66753E-002 | 0.00000 |
| 23 | PERIMETER_TOP_ZN_1 ZN | Cooling | 10194.53238 | 10194.53238 | 0.74169 | 0.74169 | HOUSTON BUSH INTERCONTINENTAL ANN CLG .4% CONDNS DB=>MWB | 7/21 13:50:00 | 35.91583 | 1.51947E-002 | 207.33814 | 11.15885 | 8.95286E-002 | 0.00000 |
| 24 | PERIMETER_TOP_ZN_1 ZN | Heating | 9223.99202 | 9223.99202 | 0.39425 | 0.39425 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | -1.60000 | 3.31476E-003 | 207.33814 | 11.15885 | 8.95286E-002 | 0.00000 |
| 25 | PERIMETER_TOP_ZN_2 ZN | Cooling | 9578.53055 | 9578.53055 | 0.69687 | 0.69687 | HOUSTON BUSH INTERCONTINENTAL ANN CLG .4% CONDNS DB=>MWB | 7/21 09:40:00 | 31.58967 | 1.51947E-002 | 131.26219 | 7.06447 | 5.66790E-002 | 0.00000 |
| 26 | PERIMETER_TOP_ZN_2 ZN | Heating | 6088.90917 | 6088.90917 | 0.26029 | 0.26029 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | -1.60000 | 3.31476E-003 | 131.26219 | 7.06447 | 5.66790E-002 | 0.00000 |
| 27 | PERIMETER_TOP_ZN_3 ZN | Cooling | 9315.67629 | 9315.67629 | 0.67775 | 0.67775 | HOUSTON BUSH INTERCONTINENTAL ANN CLG .4% CONDNS DB=>MWB | 7/21 15:00:00 | 36.00000 | 1.51947E-002 | 207.33814 | 11.15885 | 8.95286E-002 | 0.00000 |
| 28 | PERIMETER_TOP_ZN_3 ZN | Heating | 9230.49719 | 9230.49719 | 0.39453 | 0.39453 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | -1.60000 | 3.31476E-003 | 207.33814 | 11.15885 | 8.95286E-002 | 0.00000 |
| 29 | PERIMETER_TOP_ZN_4 ZN | Cooling | 10633.36035 | 10633.36035 | 0.77361 | 0.77361 | HOUSTON BUSH INTERCONTINENTAL ANN CLG .4% CONDNS DB=>MWB | 7/21 17:00:00 | 34.58600 | 1.51947E-002 | 131.25358 | 7.06401 | 5.66753E-002 | 0.00000 |
| 30 | PERIMETER_TOP_ZN_4 ZN | Heating | 6088.72498 | 6088.72498 | 0.26028 | 0.26028 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 08:00:00 | -1.60000 | 3.31476E-003 | 131.25358 | 7.06401 | 5.66753E-002 | 0.00000 |
| System Name | Load Type | Peak Load Kind | User Design Capacity | Calc Des Air Flow Rate [m3/s] | User Des Air Flow Rate [m3/s] | Design Day Name | Date/Time of Peak | |
| 1 | 15 ZONE VAV | Cooling | Sensible | 214476.97 | 13.60302 | 13.60302 | HOUSTON BUSH INTERCONTINENTAL ANN CLG .4% CONDNS DB=>MWB | 7/21 00:00:00 |
| 2 | 15 ZONE VAV | Heating | Sensible | 37302.97 | 4.97445 | 4.97445 | HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | 1/21 00:10:00 |
| Component Type | Component Name | Input Field Description | Value | |
| 1 | AirTerminal:SingleDuct:VAV:Reheat | CORE_BOTTOM ZN VAV TERMINAL | Design Size Maximum Air Flow Rate [m3/s] | 2.95256 |
| 2 | AirTerminal:SingleDuct:VAV:Reheat | CORE_BOTTOM ZN VAV TERMINAL | Design Size Constant Minimum Air Flow Fraction | 0.25383 |
| 3 | AirTerminal:SingleDuct:VAV:Reheat | CORE_BOTTOM ZN VAV TERMINAL | User-Specified Constant Minimum Air Flow Fraction | 0.10000 |
| 4 | AirTerminal:SingleDuct:VAV:Reheat | CORE_BOTTOM ZN VAV TERMINAL | Design Size Minimum Air Flow Rate [m3/s] | 0.29526 |
| 5 | AirTerminal:SingleDuct:VAV:Reheat | CORE_BOTTOM ZN VAV TERMINAL | Design Size Maximum Flow Fraction during Reheat [] | 0.67689 |
| 6 | AirTerminal:SingleDuct:VAV:Reheat | CORE_BOTTOM ZN VAV TERMINAL | User-Specified Maximum Flow Fraction during Reheat [] | 0.50000 |
| 7 | AirTerminal:SingleDuct:VAV:Reheat | CORE_BOTTOM ZN VAV TERMINAL | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 1.50099E-003 |
| 8 | AirTerminal:SingleDuct:VAV:Reheat | CORE_BOTTOM ZN VAV TERMINAL | Design Size Maximum Reheat Water Flow Rate [m3/s] | 1.98826E-004 |
| 9 | AirTerminal:SingleDuct:VAV:Reheat | CORE_BOTTOM ZN VAV TERMINAL | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | 0.29526 |
| 10 | AirTerminal:SingleDuct:VAV:Reheat | CORE_BOTTOM ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | 12.77778 |
| 11 | AirTerminal:SingleDuct:VAV:Reheat | CORE_BOTTOM ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | 8.00000E-003 |
| 12 | Coil:Heating:Water | CORE_BOTTOM ZN REHEAT COIL | Design Size Rated Capacity [W] | 9090.10058 |
| 13 | Coil:Heating:Water | CORE_BOTTOM ZN REHEAT COIL | Design Size Maximum Water Flow Rate [m3/s] | 1.98826E-004 |
| 14 | Coil:Heating:Water | CORE_BOTTOM ZN REHEAT COIL | Design Size U-Factor Times Area Value [W/K] | 584.51872 |
| 15 | AirTerminal:SingleDuct:VAV:Reheat | CORE_MID ZN VAV TERMINAL | Design Size Maximum Air Flow Rate [m3/s] | 2.11109 |
| 16 | AirTerminal:SingleDuct:VAV:Reheat | CORE_MID ZN VAV TERMINAL | Design Size Constant Minimum Air Flow Fraction | 0.35501 |
| 17 | AirTerminal:SingleDuct:VAV:Reheat | CORE_MID ZN VAV TERMINAL | User-Specified Constant Minimum Air Flow Fraction | 0.10000 |
| 18 | AirTerminal:SingleDuct:VAV:Reheat | CORE_MID ZN VAV TERMINAL | Design Size Minimum Air Flow Rate [m3/s] | 0.21111 |
| 19 | AirTerminal:SingleDuct:VAV:Reheat | CORE_MID ZN VAV TERMINAL | Design Size Maximum Flow Fraction during Reheat [] | 0.94669 |
| 20 | AirTerminal:SingleDuct:VAV:Reheat | CORE_MID ZN VAV TERMINAL | User-Specified Maximum Flow Fraction during Reheat [] | 0.50000 |
| 21 | AirTerminal:SingleDuct:VAV:Reheat | CORE_MID ZN VAV TERMINAL | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 1.07322E-003 |
| 22 | AirTerminal:SingleDuct:VAV:Reheat | CORE_MID ZN VAV TERMINAL | Design Size Maximum Reheat Water Flow Rate [m3/s] | 3.45898E-004 |
| 23 | AirTerminal:SingleDuct:VAV:Reheat | CORE_MID ZN VAV TERMINAL | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | 0.46919 |
| 24 | AirTerminal:SingleDuct:VAV:Reheat | CORE_MID ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | 12.77778 |
| 25 | AirTerminal:SingleDuct:VAV:Reheat | CORE_MID ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | 8.00000E-003 |
| 26 | Coil:Heating:Water | CORE_MID ZN REHEAT COIL | Design Size Rated Capacity [W] | 15814.02637 |
| 27 | Coil:Heating:Water | CORE_MID ZN REHEAT COIL | Design Size Maximum Water Flow Rate [m3/s] | 3.45898E-004 |
| 28 | Coil:Heating:Water | CORE_MID ZN REHEAT COIL | Design Size U-Factor Times Area Value [W/K] | 1144.21732 |
| 29 | AirTerminal:SingleDuct:VAV:Reheat | CORE_TOP ZN VAV TERMINAL | Design Size Maximum Air Flow Rate [m3/s] | 2.21021 |
| 30 | AirTerminal:SingleDuct:VAV:Reheat | CORE_TOP ZN VAV TERMINAL | Design Size Constant Minimum Air Flow Fraction | 0.33909 |
| 31 | AirTerminal:SingleDuct:VAV:Reheat | CORE_TOP ZN VAV TERMINAL | User-Specified Constant Minimum Air Flow Fraction | 0.10000 |
| 32 | AirTerminal:SingleDuct:VAV:Reheat | CORE_TOP ZN VAV TERMINAL | Design Size Minimum Air Flow Rate [m3/s] | 0.22102 |
| 33 | AirTerminal:SingleDuct:VAV:Reheat | CORE_TOP ZN VAV TERMINAL | Design Size Maximum Flow Fraction during Reheat [] | 0.90423 |
| 34 | AirTerminal:SingleDuct:VAV:Reheat | CORE_TOP ZN VAV TERMINAL | User-Specified Maximum Flow Fraction during Reheat [] | 0.50000 |
| 35 | AirTerminal:SingleDuct:VAV:Reheat | CORE_TOP ZN VAV TERMINAL | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 1.12360E-003 |
| 36 | AirTerminal:SingleDuct:VAV:Reheat | CORE_TOP ZN VAV TERMINAL | Design Size Maximum Reheat Water Flow Rate [m3/s] | 6.29650E-004 |
| 37 | AirTerminal:SingleDuct:VAV:Reheat | CORE_TOP ZN VAV TERMINAL | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | 0.85795 |
| 38 | AirTerminal:SingleDuct:VAV:Reheat | CORE_TOP ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | 12.77778 |
| 39 | AirTerminal:SingleDuct:VAV:Reheat | CORE_TOP ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | 8.00000E-003 |
| 40 | Coil:Heating:Water | CORE_TOP ZN REHEAT COIL | Design Size Rated Capacity [W] | 28786.86449 |
| 41 | Coil:Heating:Water | CORE_TOP ZN REHEAT COIL | Design Size Maximum Water Flow Rate [m3/s] | 6.29650E-004 |
| 42 | Coil:Heating:Water | CORE_TOP ZN REHEAT COIL | Design Size U-Factor Times Area Value [W/K] | 2068.78216 |
| 43 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_1 ZN VAV TERMINAL | Design Size Maximum Air Flow Rate [m3/s] | 0.58298 |
| 44 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_1 ZN VAV TERMINAL | Design Size Constant Minimum Air Flow Fraction | 0.27101 |
| 45 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_1 ZN VAV TERMINAL | User-Specified Constant Minimum Air Flow Fraction | 0.10000 |
| 46 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_1 ZN VAV TERMINAL | Design Size Minimum Air Flow Rate [m3/s] | 5.82980E-002 |
| 47 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_1 ZN VAV TERMINAL | Design Size Maximum Flow Fraction during Reheat [] | 0.72269 |
| 48 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_1 ZN VAV TERMINAL | User-Specified Maximum Flow Fraction during Reheat [] | 0.50000 |
| 49 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_1 ZN VAV TERMINAL | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 1.40587E-003 |
| 50 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_1 ZN VAV TERMINAL | Design Size Maximum Reheat Water Flow Rate [m3/s] | 1.87326E-004 |
| 51 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_1 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | 0.25572 |
| 52 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_1 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | 12.77778 |
| 53 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_1 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | 8.00000E-003 |
| 54 | Coil:Heating:Water | PERIMETER_BOT_ZN_1 ZN REHEAT COIL | Design Size Rated Capacity [W] | 8564.31597 |
| 55 | Coil:Heating:Water | PERIMETER_BOT_ZN_1 ZN REHEAT COIL | Design Size Maximum Water Flow Rate [m3/s] | 1.87326E-004 |
| 56 | Coil:Heating:Water | PERIMETER_BOT_ZN_1 ZN REHEAT COIL | Design Size U-Factor Times Area Value [W/K] | 613.74954 |
| 57 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_2 ZN VAV TERMINAL | Design Size Maximum Air Flow Rate [m3/s] | 0.63228 |
| 58 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_2 ZN VAV TERMINAL | Design Size Constant Minimum Air Flow Fraction | 0.15819 |
| 59 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_2 ZN VAV TERMINAL | User-Specified Constant Minimum Air Flow Fraction | 0.10000 |
| 60 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_2 ZN VAV TERMINAL | Design Size Minimum Air Flow Rate [m3/s] | 6.32280E-002 |
| 61 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_2 ZN VAV TERMINAL | Design Size Maximum Flow Fraction during Reheat [] | 0.42185 |
| 62 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_2 ZN VAV TERMINAL | User-Specified Maximum Flow Fraction during Reheat [] | 0.50000 |
| 63 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_2 ZN VAV TERMINAL | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 2.40846E-003 |
| 64 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_2 ZN VAV TERMINAL | Design Size Maximum Reheat Water Flow Rate [m3/s] | 1.26310E-004 |
| 65 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_2 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | 0.17246 |
| 66 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_2 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | 12.77778 |
| 67 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_2 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | 8.00000E-003 |
| 68 | Coil:Heating:Water | PERIMETER_BOT_ZN_2 ZN REHEAT COIL | Design Size Rated Capacity [W] | 5774.74945 |
| 69 | Coil:Heating:Water | PERIMETER_BOT_ZN_2 ZN REHEAT COIL | Design Size Maximum Water Flow Rate [m3/s] | 1.26310E-004 |
| 70 | Coil:Heating:Water | PERIMETER_BOT_ZN_2 ZN REHEAT COIL | Design Size U-Factor Times Area Value [W/K] | 413.72829 |
| 71 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_3 ZN VAV TERMINAL | Design Size Maximum Air Flow Rate [m3/s] | 0.50972 |
| 72 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_3 ZN VAV TERMINAL | Design Size Constant Minimum Air Flow Fraction | 0.30996 |
| 73 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_3 ZN VAV TERMINAL | User-Specified Constant Minimum Air Flow Fraction | 0.10000 |
| 74 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_3 ZN VAV TERMINAL | Design Size Minimum Air Flow Rate [m3/s] | 5.09724E-002 |
| 75 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_3 ZN VAV TERMINAL | Design Size Maximum Flow Fraction during Reheat [] | 0.82655 |
| 76 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_3 ZN VAV TERMINAL | User-Specified Maximum Flow Fraction during Reheat [] | 0.50000 |
| 77 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_3 ZN VAV TERMINAL | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 1.22921E-003 |
| 78 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_3 ZN VAV TERMINAL | Design Size Maximum Reheat Water Flow Rate [m3/s] | 1.85984E-004 |
| 79 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_3 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | 0.25389 |
| 80 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_3 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | 12.77778 |
| 81 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_3 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | 8.00000E-003 |
| 82 | Coil:Heating:Water | PERIMETER_BOT_ZN_3 ZN REHEAT COIL | Design Size Rated Capacity [W] | 8502.95287 |
| 83 | Coil:Heating:Water | PERIMETER_BOT_ZN_3 ZN REHEAT COIL | Design Size Maximum Water Flow Rate [m3/s] | 1.85984E-004 |
| 84 | Coil:Heating:Water | PERIMETER_BOT_ZN_3 ZN REHEAT COIL | Design Size U-Factor Times Area Value [W/K] | 609.37195 |
| 85 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_4 ZN VAV TERMINAL | Design Size Maximum Air Flow Rate [m3/s] | 0.67220 |
| 86 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_4 ZN VAV TERMINAL | Design Size Constant Minimum Air Flow Fraction | 0.14879 |
| 87 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_4 ZN VAV TERMINAL | User-Specified Constant Minimum Air Flow Fraction | 0.10000 |
| 88 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_4 ZN VAV TERMINAL | Design Size Minimum Air Flow Rate [m3/s] | 6.72199E-002 |
| 89 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_4 ZN VAV TERMINAL | Design Size Maximum Flow Fraction during Reheat [] | 0.39677 |
| 90 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_4 ZN VAV TERMINAL | User-Specified Maximum Flow Fraction during Reheat [] | 0.50000 |
| 91 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_4 ZN VAV TERMINAL | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 2.56069E-003 |
| 92 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_4 ZN VAV TERMINAL | Design Size Maximum Reheat Water Flow Rate [m3/s] | 1.26309E-004 |
| 93 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_4 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | 0.17246 |
| 94 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_4 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | 12.77778 |
| 95 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_BOT_ZN_4 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | 8.00000E-003 |
| 96 | Coil:Heating:Water | PERIMETER_BOT_ZN_4 ZN REHEAT COIL | Design Size Rated Capacity [W] | 5774.67560 |
| 97 | Coil:Heating:Water | PERIMETER_BOT_ZN_4 ZN REHEAT COIL | Design Size Maximum Water Flow Rate [m3/s] | 1.26309E-004 |
| 98 | Coil:Heating:Water | PERIMETER_BOT_ZN_4 ZN REHEAT COIL | Design Size U-Factor Times Area Value [W/K] | 413.72291 |
| 99 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_1 ZN VAV TERMINAL | Design Size Maximum Air Flow Rate [m3/s] | 0.67156 |
| 100 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_1 ZN VAV TERMINAL | Design Size Constant Minimum Air Flow Fraction | 0.23526 |
| 101 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_1 ZN VAV TERMINAL | User-Specified Constant Minimum Air Flow Fraction | 0.10000 |
| 102 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_1 ZN VAV TERMINAL | Design Size Minimum Air Flow Rate [m3/s] | 6.71565E-002 |
| 103 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_1 ZN VAV TERMINAL | Design Size Maximum Flow Fraction during Reheat [] | 0.62736 |
| 104 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_1 ZN VAV TERMINAL | User-Specified Maximum Flow Fraction during Reheat [] | 0.50000 |
| 105 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_1 ZN VAV TERMINAL | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 1.61949E-003 |
| 106 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_1 ZN VAV TERMINAL | Design Size Maximum Reheat Water Flow Rate [m3/s] | 2.32482E-004 |
| 107 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_1 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | 0.31754 |
| 108 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_1 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | 12.77778 |
| 109 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_1 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | 8.00000E-003 |
| 110 | Coil:Heating:Water | PERIMETER_MID_ZN_1 ZN REHEAT COIL | Design Size Rated Capacity [W] | 10628.80287 |
| 111 | Coil:Heating:Water | PERIMETER_MID_ZN_1 ZN REHEAT COIL | Design Size Maximum Water Flow Rate [m3/s] | 2.32482E-004 |
| 112 | Coil:Heating:Water | PERIMETER_MID_ZN_1 ZN REHEAT COIL | Design Size U-Factor Times Area Value [W/K] | 761.07409 |
| 113 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_2 ZN VAV TERMINAL | Design Size Maximum Air Flow Rate [m3/s] | 0.69028 |
| 114 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_2 ZN VAV TERMINAL | Design Size Constant Minimum Air Flow Fraction | 0.14490 |
| 115 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_2 ZN VAV TERMINAL | User-Specified Constant Minimum Air Flow Fraction | 0.10000 |
| 116 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_2 ZN VAV TERMINAL | Design Size Minimum Air Flow Rate [m3/s] | 6.90276E-002 |
| 117 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_2 ZN VAV TERMINAL | Design Size Maximum Flow Fraction during Reheat [] | 0.38640 |
| 118 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_2 ZN VAV TERMINAL | User-Specified Maximum Flow Fraction during Reheat [] | 0.50000 |
| 119 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_2 ZN VAV TERMINAL | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 2.62938E-003 |
| 120 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_2 ZN VAV TERMINAL | Design Size Maximum Reheat Water Flow Rate [m3/s] | 1.55157E-004 |
| 121 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_2 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | 0.21195 |
| 122 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_2 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | 12.77778 |
| 123 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_2 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | 8.00000E-003 |
| 124 | Coil:Heating:Water | PERIMETER_MID_ZN_2 ZN REHEAT COIL | Design Size Rated Capacity [W] | 7093.58066 |
| 125 | Coil:Heating:Water | PERIMETER_MID_ZN_2 ZN REHEAT COIL | Design Size Maximum Water Flow Rate [m3/s] | 1.55157E-004 |
| 126 | Coil:Heating:Water | PERIMETER_MID_ZN_2 ZN REHEAT COIL | Design Size U-Factor Times Area Value [W/K] | 507.83233 |
| 127 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_3 ZN VAV TERMINAL | Design Size Maximum Air Flow Rate [m3/s] | 0.60006 |
| 128 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_3 ZN VAV TERMINAL | Design Size Constant Minimum Air Flow Fraction | 0.26329 |
| 129 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_3 ZN VAV TERMINAL | User-Specified Constant Minimum Air Flow Fraction | 0.10000 |
| 130 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_3 ZN VAV TERMINAL | Design Size Minimum Air Flow Rate [m3/s] | 6.00061E-002 |
| 131 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_3 ZN VAV TERMINAL | Design Size Maximum Flow Fraction during Reheat [] | 0.70211 |
| 132 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_3 ZN VAV TERMINAL | User-Specified Maximum Flow Fraction during Reheat [] | 0.50000 |
| 133 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_3 ZN VAV TERMINAL | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 1.44706E-003 |
| 134 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_3 ZN VAV TERMINAL | Design Size Maximum Reheat Water Flow Rate [m3/s] | 2.32306E-004 |
| 135 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_3 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | 0.31730 |
| 136 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_3 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | 12.77778 |
| 137 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_3 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | 8.00000E-003 |
| 138 | Coil:Heating:Water | PERIMETER_MID_ZN_3 ZN REHEAT COIL | Design Size Rated Capacity [W] | 10620.76268 |
| 139 | Coil:Heating:Water | PERIMETER_MID_ZN_3 ZN REHEAT COIL | Design Size Maximum Water Flow Rate [m3/s] | 2.32306E-004 |
| 140 | Coil:Heating:Water | PERIMETER_MID_ZN_3 ZN REHEAT COIL | Design Size U-Factor Times Area Value [W/K] | 760.49986 |
| 141 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_4 ZN VAV TERMINAL | Design Size Maximum Air Flow Rate [m3/s] | 0.72763 |
| 142 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_4 ZN VAV TERMINAL | Design Size Constant Minimum Air Flow Fraction | 0.13745 |
| 143 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_4 ZN VAV TERMINAL | User-Specified Constant Minimum Air Flow Fraction | 0.10000 |
| 144 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_4 ZN VAV TERMINAL | Design Size Minimum Air Flow Rate [m3/s] | 7.27631E-002 |
| 145 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_4 ZN VAV TERMINAL | Design Size Maximum Flow Fraction during Reheat [] | 0.36654 |
| 146 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_4 ZN VAV TERMINAL | User-Specified Maximum Flow Fraction during Reheat [] | 0.50000 |
| 147 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_4 ZN VAV TERMINAL | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 2.77185E-003 |
| 148 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_4 ZN VAV TERMINAL | Design Size Maximum Reheat Water Flow Rate [m3/s] | 1.55153E-004 |
| 149 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_4 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | 0.21195 |
| 150 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_4 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | 12.77778 |
| 151 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_MID_ZN_4 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | 8.00000E-003 |
| 152 | Coil:Heating:Water | PERIMETER_MID_ZN_4 ZN REHEAT COIL | Design Size Rated Capacity [W] | 7093.41986 |
| 153 | Coil:Heating:Water | PERIMETER_MID_ZN_4 ZN REHEAT COIL | Design Size Maximum Water Flow Rate [m3/s] | 1.55153E-004 |
| 154 | Coil:Heating:Water | PERIMETER_MID_ZN_4 ZN REHEAT COIL | Design Size U-Factor Times Area Value [W/K] | 507.82073 |
| 155 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_1 ZN VAV TERMINAL | Design Size Maximum Air Flow Rate [m3/s] | 0.74169 |
| 156 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_1 ZN VAV TERMINAL | Design Size Constant Minimum Air Flow Fraction | 0.21302 |
| 157 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_1 ZN VAV TERMINAL | User-Specified Constant Minimum Air Flow Fraction | 0.10000 |
| 158 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_1 ZN VAV TERMINAL | Design Size Minimum Air Flow Rate [m3/s] | 7.41692E-002 |
| 159 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_1 ZN VAV TERMINAL | Design Size Maximum Flow Fraction during Reheat [] | 0.56804 |
| 160 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_1 ZN VAV TERMINAL | User-Specified Maximum Flow Fraction during Reheat [] | 0.50000 |
| 161 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_1 ZN VAV TERMINAL | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 1.78860E-003 |
| 162 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_1 ZN VAV TERMINAL | Design Size Maximum Reheat Water Flow Rate [m3/s] | 2.88503E-004 |
| 163 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_1 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | 0.39425 |
| 164 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_1 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | 12.77778 |
| 165 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_1 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | 8.00000E-003 |
| 166 | Coil:Heating:Water | PERIMETER_TOP_ZN_1 ZN REHEAT COIL | Design Size Rated Capacity [W] | 13189.99572 |
| 167 | Coil:Heating:Water | PERIMETER_TOP_ZN_1 ZN REHEAT COIL | Design Size Maximum Water Flow Rate [m3/s] | 2.88503E-004 |
| 168 | Coil:Heating:Water | PERIMETER_TOP_ZN_1 ZN REHEAT COIL | Design Size U-Factor Times Area Value [W/K] | 943.77504 |
| 169 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_2 ZN VAV TERMINAL | Design Size Maximum Air Flow Rate [m3/s] | 0.69687 |
| 170 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_2 ZN VAV TERMINAL | Design Size Constant Minimum Air Flow Fraction | 0.14353 |
| 171 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_2 ZN VAV TERMINAL | User-Specified Constant Minimum Air Flow Fraction | 0.10000 |
| 172 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_2 ZN VAV TERMINAL | Design Size Minimum Air Flow Rate [m3/s] | 6.96872E-002 |
| 173 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_2 ZN VAV TERMINAL | Design Size Maximum Flow Fraction during Reheat [] | 0.38275 |
| 174 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_2 ZN VAV TERMINAL | User-Specified Maximum Flow Fraction during Reheat [] | 0.50000 |
| 175 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_2 ZN VAV TERMINAL | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 2.65450E-003 |
| 176 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_2 ZN VAV TERMINAL | Design Size Maximum Reheat Water Flow Rate [m3/s] | 1.90455E-004 |
| 177 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_2 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | 0.26029 |
| 178 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_2 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | 12.77778 |
| 179 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_2 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | 8.00000E-003 |
| 180 | Coil:Heating:Water | PERIMETER_TOP_ZN_2 ZN REHEAT COIL | Design Size Rated Capacity [W] | 8707.35482 |
| 181 | Coil:Heating:Water | PERIMETER_TOP_ZN_2 ZN REHEAT COIL | Design Size Maximum Water Flow Rate [m3/s] | 1.90455E-004 |
| 182 | Coil:Heating:Water | PERIMETER_TOP_ZN_2 ZN REHEAT COIL | Design Size U-Factor Times Area Value [W/K] | 622.94286 |
| 183 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_3 ZN VAV TERMINAL | Design Size Maximum Air Flow Rate [m3/s] | 0.67775 |
| 184 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_3 ZN VAV TERMINAL | Design Size Constant Minimum Air Flow Fraction | 0.23311 |
| 185 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_3 ZN VAV TERMINAL | User-Specified Constant Minimum Air Flow Fraction | 0.10000 |
| 186 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_3 ZN VAV TERMINAL | Design Size Minimum Air Flow Rate [m3/s] | 6.77752E-002 |
| 187 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_3 ZN VAV TERMINAL | Design Size Maximum Flow Fraction during Reheat [] | 0.62163 |
| 188 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_3 ZN VAV TERMINAL | User-Specified Maximum Flow Fraction during Reheat [] | 0.50000 |
| 189 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_3 ZN VAV TERMINAL | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 1.63441E-003 |
| 190 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_3 ZN VAV TERMINAL | Design Size Maximum Reheat Water Flow Rate [m3/s] | 2.88707E-004 |
| 191 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_3 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | 0.39453 |
| 192 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_3 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | 12.77778 |
| 193 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_3 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | 8.00000E-003 |
| 194 | Coil:Heating:Water | PERIMETER_TOP_ZN_3 ZN REHEAT COIL | Design Size Rated Capacity [W] | 13199.31622 |
| 195 | Coil:Heating:Water | PERIMETER_TOP_ZN_3 ZN REHEAT COIL | Design Size Maximum Water Flow Rate [m3/s] | 2.88707E-004 |
| 196 | Coil:Heating:Water | PERIMETER_TOP_ZN_3 ZN REHEAT COIL | Design Size U-Factor Times Area Value [W/K] | 944.43840 |
| 197 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_4 ZN VAV TERMINAL | Design Size Maximum Air Flow Rate [m3/s] | 0.77361 |
| 198 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_4 ZN VAV TERMINAL | Design Size Constant Minimum Air Flow Fraction | 0.12928 |
| 199 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_4 ZN VAV TERMINAL | User-Specified Constant Minimum Air Flow Fraction | 0.10000 |
| 200 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_4 ZN VAV TERMINAL | Design Size Minimum Air Flow Rate [m3/s] | 7.73613E-002 |
| 201 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_4 ZN VAV TERMINAL | Design Size Maximum Flow Fraction during Reheat [] | 0.34476 |
| 202 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_4 ZN VAV TERMINAL | User-Specified Maximum Flow Fraction during Reheat [] | 0.50000 |
| 203 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_4 ZN VAV TERMINAL | Design Size Maximum Flow per Zone Floor Area during Reheat [m3/s-m2] | 2.94702E-003 |
| 204 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_4 ZN VAV TERMINAL | Design Size Maximum Reheat Water Flow Rate [m3/s] | 1.90449E-004 |
| 205 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_4 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Air Volume Flow Rate [m3/s] | 0.26028 |
| 206 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_4 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Temperature [C] | 12.77778 |
| 207 | AirTerminal:SingleDuct:VAV:Reheat | PERIMETER_TOP_ZN_4 ZN VAV TERMINAL | Design Size Reheat Coil Sizing Inlet Air Humidity Ratio [kgWater/kgDryAir] | 8.00000E-003 |
| 208 | Coil:Heating:Water | PERIMETER_TOP_ZN_4 ZN REHEAT COIL | Design Size Rated Capacity [W] | 8707.09176 |
| 209 | Coil:Heating:Water | PERIMETER_TOP_ZN_4 ZN REHEAT COIL | Design Size Maximum Water Flow Rate [m3/s] | 1.90449E-004 |
| 210 | Coil:Heating:Water | PERIMETER_TOP_ZN_4 ZN REHEAT COIL | Design Size U-Factor Times Area Value [W/K] | 622.92397 |
| 211 | AirLoopHVAC | 15 ZONE VAV | Sum of Air Terminal Maximum Heating Flow Rates [m3/s] | 7.62525 |
| 212 | AirLoopHVAC | 15 ZONE VAV | Sum of Air Terminal Minimum Heating Flow Rates [m3/s] | 1.52505 |
| 213 | AirLoopHVAC | 15 ZONE VAV | Sum of Air Terminal Maximum Flow Rates [m3/s] | 15.25050 |
| 214 | AirLoopHVAC | 15 ZONE VAV | Adjusted Heating Design Air Flow Rate [m3/s] | 4.97445 |
| 215 | AirLoopHVAC | 15 ZONE VAV | Adjusted Cooling Design Air Flow Rate [m3/s] | 13.60302 |
| 216 | AirLoopHVAC | 15 ZONE VAV | Adjusted Main Design Air Flow Rate [m3/s] | 13.60302 |
| 217 | AirLoopHVAC | 15 ZONE VAV | User Heating Air Flow Ratio [] | 0.30000 |
| 218 | AirLoopHVAC | 15 ZONE VAV | Calculated Heating Air Flow Ratio [] | 0.36569 |
| 219 | AirLoopHVAC | 15 ZONE VAV | Design Supply Air Flow Rate [m3/s] | 13.60302 |
| 220 | Controller:OutdoorAir | 15 ZONE VAV OA CONTROLLER | Maximum Outdoor Air Flow Rate [m3/s] | 13.60302 |
| 221 | HeatExchanger:AirToAir:SensibleAndLatent | 15 ZONE VAV ERV | Design Size Nominal Supply Air Flow Rate [m3/s] | 2.15131 |
| 222 | Coil:Cooling:Water | 15 ZONE VAV CLG COIL | Design Size Design Inlet Air Temperature [C] | 25.88565 |
| 223 | Coil:Cooling:Water | 15 ZONE VAV CLG COIL | Design Size Design Inlet Water Temperature [C] | 6.66667 |
| 224 | Coil:Cooling:Water | 15 ZONE VAV CLG COIL | Design Size Design Outlet Air Temperature [C] | 11.51943 |
| 225 | Coil:Cooling:Water | 15 ZONE VAV CLG COIL | Design Size Design Inlet Air Humidity Ratio | 9.85498E-003 |
| 226 | Coil:Cooling:Water | 15 ZONE VAV CLG COIL | Design Size Design Outlet Air Humidity Ratio | 8.50000E-003 |
| 227 | Coil:Cooling:Water | 15 ZONE VAV CLG COIL | Design Size Design Coil Load [W] |<PHONE_NUMBER>0 |
| 228 | Coil:Cooling:Water | 15 ZONE VAV CLG COIL | Design Size Design Water Flow Rate [m3/s] | 1.25579E-002 |
| 229 | Coil:Cooling:Water | 15 ZONE VAV CLG COIL | Design Size Design Air Flow Rate [m3/s] | 13.60302 |
| 230 | Coil:Heating:Water | 15 ZONE VAV MAIN HTG COIL | Design Size Rated Capacity [W] | 19132.02474 |
| 231 | Coil:Heating:Water | 15 ZONE VAV MAIN HTG COIL | Design Size Maximum Water Flow Rate [m3/s] | 4.18472E-004 |
| 232 | Coil:Heating:Water | 15 ZONE VAV MAIN HTG COIL | Design Size U-Factor Times Area Value [W/K] | 604.80146 |
| 233 | Fan:VariableVolume | 15 ZONE VAV FAN | Design Size Maximum Flow Rate [m3/s] | 13.60302 |
| 234 | Controller:WaterCoil | 15 ZONE VAV CLG COIL CONTROLLER | Maximum Actuated Flow [m3/s] | 1.25579E-002 |
| 235 | Controller:WaterCoil | 15 ZONE VAV CLG COIL CONTROLLER | Controller Convergence Tolerance | 3.79195E-005 |
| 236 | Controller:WaterCoil | 15 ZONE VAV MAIN HTG COIL CONTROLLER | Maximum Actuated Flow [m3/s] | 4.18472E-004 |
| 237 | PlantLoop | CHILLED WATER LOOP | Maximum Loop Flow Rate [m3/s] | 1.25579E-002 |
| 238 | PlantLoop | CHILLED WATER LOOP | Plant Loop Volume [m3] | 1.50695 |
| 239 | Pump:VariableSpeed | CHILLED WATER LOOP PUMP | Design Flow Rate [m3/s] | 1.25579E-002 |
| 240 | Pump:VariableSpeed | CHILLED WATER LOOP PUMP | Design Power Consumption [W] | 4379.04446 |
| 241 | Chiller:Electric:EIR | NREL ZNE READY 2017 CHILLER 0 84TONS 1.1KW/TON | Design Size Reference Chilled Water Flow Rate [m3/s] | 1.25579E-002 |
| 242 | Chiller:Electric:EIR | NREL ZNE READY 2017 CHILLER 0 84TONS 1.1KW/TON | Design Size Reference Capacity [W] |<PHONE_NUMBER>0 |
| 243 | Chiller:Electric:EIR | NREL ZNE READY 2017 CHILLER 0 84TONS 1.1KW/TON | Design Size Reference Condenser Fluid Flow Rate [m3/s] | 33.71811 |
| 244 | PlantLoop | HOT WATER LOOP | Maximum Loop Flow Rate [m3/s] | 3.95199E-003 |
| 245 | PlantLoop | HOT WATER LOOP | Plant Loop Volume [m3] | 0.47424 |
| 246 | Pump:VariableSpeed | HOT WATER LOOP PUMP | Design Flow Rate [m3/s] | 3.95199E-003 |
| 247 | Pump:VariableSpeed | HOT WATER LOOP PUMP | Design Power Consumption [W] | 1190.16470 |
| 248 | Boiler:HotWater | BOILER 617KBTU/HR 0.94 COMBUSTION EFF | Design Size Nominal Capacity [W] |<PHONE_NUMBER>7 |
| 249 | Boiler:HotWater | BOILER 617KBTU/HR 0.94 COMBUSTION EFF | Design Size Design Water Flow Rate [m3/s] | 3.95199E-003 |
| 250 | PlantLoop | MAIN SERVICE WATER LOOP | Maximum Loop Flow Rate [m3/s] | 5.36265E-005 |
| 251 | PlantLoop | MAIN SERVICE WATER LOOP | Plant Loop Volume [m3] | 6.43518E-003 |
| 252 | Pump:ConstantSpeed | SERVICE WATER LOOP PUMP | Design Flow Rate [m3/s] | 5.36265E-005 |
| 253 | Pump:ConstantSpeed | SERVICE WATER LOOP PUMP | Design Power Consumption [W] | 16.14994 |
| 254 | WaterHeater:Mixed | 100GAL NATURAL GAS WATER HEATER - 100KBTU/HR 0.802 THERM EFF 0.808 THERM EFF | Use Side Design Flow Rate [m3/s] | 5.36265E-005 |
| Component Type | Name | Nominal Total Capacity {W} | |
| 1 | Coil:Heating:Water | CORE_BOTTOM ZN REHEAT COIL | 16538.31 |
| 2 | Coil:Heating:Water | CORE_MID ZN REHEAT COIL | 28755.78 |
| 3 | Coil:Heating:Water | CORE_TOP ZN REHEAT COIL | 52348.07 |
| 4 | Coil:Heating:Water | PERIMETER_BOT_ZN_1 ZN REHEAT COIL | 15574.08 |
| 5 | Coil:Heating:Water | PERIMETER_BOT_ZN_2 ZN REHEAT COIL | 10501.30 |
| 6 | Coil:Heating:Water | PERIMETER_BOT_ZN_3 ZN REHEAT COIL | 15462.49 |
| 7 | Coil:Heating:Water | PERIMETER_BOT_ZN_4 ZN REHEAT COIL | 10501.17 |
| 8 | Coil:Heating:Water | PERIMETER_MID_ZN_1 ZN REHEAT COIL | 19328.36 |
| 9 | Coil:Heating:Water | PERIMETER_MID_ZN_2 ZN REHEAT COIL | 12899.61 |
| 10 | Coil:Heating:Water | PERIMETER_MID_ZN_3 ZN REHEAT COIL | 19313.74 |
| 11 | Coil:Heating:Water | PERIMETER_MID_ZN_4 ZN REHEAT COIL | 12899.31 |
| 12 | Coil:Heating:Water | PERIMETER_TOP_ZN_1 ZN REHEAT COIL | 23985.91 |
| 13 | Coil:Heating:Water | PERIMETER_TOP_ZN_2 ZN REHEAT COIL | 15834.27 |
| 14 | Coil:Heating:Water | PERIMETER_TOP_ZN_3 ZN REHEAT COIL | 24002.86 |
| 15 | Coil:Heating:Water | PERIMETER_TOP_ZN_4 ZN REHEAT COIL | 15833.79 |
| 16 | Coil:Heating:Water | 15 ZONE VAV MAIN HTG COIL | 31488.55 |
| Component Type | Name | Nominal Total Capacity {W} | Nominal Sensible Capacity {W} | Nominal Latent Capacity {W} | Nominal Sensible Heat Ratio | Nominal Coil UA Value {W/C} | Nominal Coil Surface Area {m2} | |
| 1 | Coil:Cooling:Water | 15 ZONE VAV CLG COIL | 358174.83 | 245274.96 | 112899.87 | 0.68 | 40581.51 | 411.60 |
| Component Type | Component Name | IPLV in SI Units {W/W} | IPLV in IP Units {Btu/W-h} | |
| 1 | Chiller:Electric:EIR | NREL ZNE READY 2017 CHILLER 0 84TONS 1.1KW/TON | 4.49 | 15.32 |
| Environment Name | Environment Type | Start Date | End Date | Start DayOfWeek | Duration {#days} | Source:Start DayOfWeek | Use Daylight Saving | Use Holidays | Apply Weekend Holiday Rule | Use Rain Values | Use Snow Values | |
| 1 | RUN PERIOD 1 | WeatherFileRunPeriod | 01/01/2006 | 12/31/2006 | Sunday | 365 | Use RunPeriod Specified Day | No | No | No | Yes | Yes |
| Daylight Saving Indicator | Source | Start Date | End Date | |
| 1 | Yes | InputFile | 03/12 | 11/05 |
| NumberofWarmupDays | |
| 1 | 9 |
| Style | Unit Conversion | |
| 1 | HTML | None |
| Zone Name | Environment Type/Name | Average Warmup Temperature Difference {deltaC} | Std Dev Warmup Temperature Difference {deltaC} | Max Temperature Pass/Fail Convergence | Min Temperature Pass/Fail Convergence | Average Warmup Load Difference {W} | Std Dev Warmup Load Difference {W} | Heating Load Pass/Fail Convergence | Cooling Load Pass/Fail Convergence | |
| 1 | CORE_BOTTOM ZN | RunPeriod: RUN PERIOD 1 | 2.4688602767E-002 | 4.7036875704E-002 | Pass | Pass | 3.4809768177E-002 | 0.1830393005 | Pass | Pass |
| 2 | CORE_MID ZN | RunPeriod: RUN PERIOD 1 | 1.9088635902E-002 | 3.0100609641E-002 | Pass | Pass | 3.4822878842E-002 | 0.1829003771 | Pass | Pass |
| 3 | CORE_TOP ZN | RunPeriod: RUN PERIOD 1 | 3.6196101044E-002 | 2.8274437656E-002 | Pass | Pass | 3.4667579049E-002 | 0.1816994793 | Pass | Pass |
| 4 | FIRSTFLOOR_PLENUM ZN | RunPeriod: RUN PERIOD 1 | 1.5488160117E-002 | 9.5404139122E-003 | Pass | Pass | 0.0000000000 | 0.0000000000 | Pass | Pass |
| 5 | MIDFLOOR_PLENUM ZN | RunPeriod: RUN PERIOD 1 | 1.5811392594E-002 | 8.8633550882E-003 | Pass | Pass | 0.0000000000 | 0.0000000000 | Pass | Pass |
| 6 | PERIMETER_BOT_ZN_1 ZN | RunPeriod: RUN PERIOD 1 | 0.1453129994 | 0.1363701116 | Pass | Pass | 4.4689856027E-002 | 0.2446891512 | Pass | Pass |
| 7 | PERIMETER_BOT_ZN_2 ZN | RunPeriod: RUN PERIOD 1 | 9.6719039122E-002 | 0.1176964039 | Pass | Pass | 3.5037206802E-002 | 0.1838517026 | Pass | Pass |
| 8 | PERIMETER_BOT_ZN_3 ZN | RunPeriod: RUN PERIOD 1 | 4.3206277824E-002 | 3.7480522631E-002 | Pass | Pass | 3.4668101613E-002 | 0.1819961627 | Pass | Pass |
| 9 | PERIMETER_BOT_ZN_4 ZN | RunPeriod: RUN PERIOD 1 | 8.4660599855E-002 | 0.1027212603 | Pass | Pass | 3.3662557416E-002 | 0.1754732846 | Pass | Pass |
| 10 | PERIMETER_MID_ZN_1 ZN | RunPeriod: RUN PERIOD 1 | 0.1329764922 | 0.1136743281 | Pass | Pass | 3.4691709880E-002 | 0.1827472888 | Pass | Pass |
| 11 | PERIMETER_MID_ZN_2 ZN | RunPeriod: RUN PERIOD 1 | 9.5332197141E-002 | 0.1148802817 | Pass | Pass | 3.4980662419E-002 | 0.1836610733 | Pass | Pass |
| 12 | PERIMETER_MID_ZN_3 ZN | RunPeriod: RUN PERIOD 1 | 4.2587555942E-002 | 3.7823830838E-002 | Pass | Pass | 3.4647777635E-002 | 0.1817763091 | Pass | Pass |
| 13 | PERIMETER_MID_ZN_4 ZN | RunPeriod: RUN PERIOD 1 | 8.2065313459E-002 | 0.1005571391 | Pass | Pass | 3.3590445722E-002 | 0.1749561038 | Pass | Pass |
| 14 | PERIMETER_TOP_ZN_1 ZN | RunPeriod: RUN PERIOD 1 | 0.1441168283 | 0.1154857231 | Pass | Pass | 3.4588514731E-002 | 0.1821120851 | Pass | Pass |
| 15 | PERIMETER_TOP_ZN_2 ZN | RunPeriod: RUN PERIOD 1 | 9.6579263489E-002 | 0.1076557944 | Pass | Pass | 3.4766868649E-002 | 0.1827236868 | Pass | Pass |
| 16 | PERIMETER_TOP_ZN_3 ZN | RunPeriod: RUN PERIOD 1 | 5.3779744138E-002 | 4.2234203581E-002 | Pass | Pass | 3.4458754185E-002 | 0.1803922842 | Pass | Pass |
| 17 | PERIMETER_TOP_ZN_4 ZN | RunPeriod: RUN PERIOD 1 | 9.5708521781E-002 | 0.1019037412 | Pass | Pass | 3.3381099056E-002 | 0.1730907634 | Pass | Pass |
| 18 | TOPFLOOR_PLENUM ZN | RunPeriod: RUN PERIOD 1 | 9.4306699615E-002 | 7.1507565453E-002 | Pass | Pass | 0.0000000000 | 0.0000000000 | Pass | Pass |
Report: Annual Heat Emissions Summary
For: Entire Facility
Timestamp: 2019-04-09 23:11:28
Heat Emission by Components| Envelope Convection | Zone Exfiltration | Zone Exhaust Air | HVAC Relief Air | HVAC Reject Heat | Total | |
| Heat Emissions [GJ] | 1729.65 | -6.4 | 0.00 | 792.47 | 1925.52 | 4441.29 |
Report: Climatic Data Summary
For: Entire Facility
Timestamp: 2019-04-09 23:11:28
SizingPeriod:DesignDay| Maximum Dry Bulb [C] | Daily Temperature Range [deltaC] | Humidity Value | Humidity Type | Wind Speed [m/s] | Wind Direction | |
| HOUSTON BUSH INTERCONTINENTAL ANN CLG .4% CONDNS DB=>MWB | 36.00 | 10.10 | 24.80 | Wetbulb [C] | 3.50 | 170.00 |
| HOUSTON BUSH INTERCONTINENTAL ANN HTG 99.6% CONDNS DB | -1.60 | 0.00 | -1.60 | Wetbulb [C] | 2.80 | 0.00 |
| Value | |
| None |
Report: Envelope Summary
For: Entire Facility
Timestamp: 2019-04-09 23:11:28
Opaque Exterior| Construction | Reflectance | U-Factor with Film [W/m2-K] | U-Factor no Film [W/m2-K] | Gross Area [m2] | Net Area [m2] | Azimuth [deg] | Tilt [deg] | Cardinal Direction | |
| CORE_BOT_ZN_5_FLOOR | TYPICAL INSULATED CARPETED 8IN SLAB FLOOR | 0.30 | 2.144 | 3.285 | 983.54 | 983.54 | 0.00 | 180.00 | |
| PERIMETER_BOT_PLENUM_WALL_EAST | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-11.9 | 0.30 | 0.477 | 0.514 | 40.57 | 40.57 | 90.00 | 90.00 | E |
| PERIMETER_BOT_PLENUM_WALL_NORTH | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-11.9 | 0.30 | 0.477 | 0.514 | 60.85 | 60.85 | 0.00 | 90.00 | N |
| PERIMETER_BOT_PLENUM_WALL_SOUTH | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-11.9 | 0.30 | 0.477 | 0.514 | 60.85 | 60.85 | 180.00 | 90.00 | S |
| PERIMETER_BOT_PLENUM_WALL_WEST | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-11.9 | 0.30 | 0.477 | 0.514 | 40.57 | 40.57 | 270.00 | 90.00 | W |
| PERIMETER_MID_PLENUM_WALL_EAST | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-11.9 | 0.30 | 0.477 | 0.514 | 40.57 | 40.57 | 90.00 | 90.00 | E |
| PERIMETER_MID_PLENUM_WALL_NORTH | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-11.9 | 0.30 | 0.477 | 0.514 | 60.85 | 60.85 | 0.00 | 90.00 | N |
| PERIMETER_MID_PLENUM_WALL_SOUTH | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-11.9 | 0.30 | 0.477 | 0.514 | 60.85 | 60.85 | 180.00 | 90.00 | S |
| PERIMETER_MID_PLENUM_WALL_WEST | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-11.9 | 0.30 | 0.477 | 0.514 | 40.57 | 40.57 | 270.00 | 90.00 | W |
| PERIMETER_BOT_ZN_1_WALL_SOUTH | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-11.9 | 0.30 | 0.477 | 0.514 | 136.92 | 71.63 | 180.00 | 90.00 | S |
| PERIMETER_BOT_ZN_1_FLOOR | TYPICAL INSULATED CARPETED 8IN SLAB FLOOR | 0.30 | 2.144 | 3.285 | 207.34 | 207.34 | 0.00 | 180.00 | |
| PERIMETER_BOT_ZN_2_WALL_EAST | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-11.9 | 0.30 | 0.477 | 0.514 | 91.28 | 47.75 | 90.00 | 90.00 | E |
| PERIMETER_BOT_ZN_2_FLOOR | TYPICAL INSULATED CARPETED 8IN SLAB FLOOR | 0.30 | 2.144 | 3.285 | 131.26 | 131.26 | 45.00 | 180.00 | |
| PERIMETER_BOT_ZN_3_WALL_NORTH | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-11.9 | 0.30 | 0.477 | 0.514 | 136.92 | 71.63 | 0.00 | 90.00 | N |
| PERIMETER_BOT_ZN_3_FLOOR | TYPICAL INSULATED CARPETED 8IN SLAB FLOOR | 0.30 | 2.144 | 3.285 | 207.34 | 207.34 | 0.00 | 180.00 | |
| PERIMETER_BOT_ZN_4_WALL_WEST | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-11.9 | 0.30 | 0.477 | 0.514 | 91.28 | 47.75 | 270.00 | 90.00 | W |
| PERIMETER_BOT_ZN_4_FLOOR | TYPICAL INSULATED CARPETED 8IN SLAB FLOOR | 0.30 | 2.144 | 3.285 | 131.25 | 131.25 | 270.00 | 180.00 | |
| PERIMETER_MID_ZN_1_WALL_SOUTH | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-11.9 | 0.30 | 0.477 | 0.514 | 136.92 | 71.63 | 180.00 | 90.00 | S |
| PERIMETER_MID_ZN_2_WALL_EAST | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-11.9 | 0.30 | 0.477 | 0.514 | 91.28 | 47.75 | 90.00 | 90.00 | E |
| PERIMETER_MID_ZN_3_WALL_NORTH | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-11.9 | 0.30 | 0.477 | 0.514 | 136.92 | 71.63 | 0.00 | 90.00 | N |
| PERIMETER_MID_ZN_4_WALL_WEST | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-11.9 | 0.30 | 0.477 | 0.514 | 91.28 | 47.75 | 270.00 | 90.00 | W |
| PERIMETER_TOP_ZN_1_WALL_SOUTH | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-11.9 | 0.30 | 0.477 | 0.514 | 136.92 | 71.63 | 180.00 | 90.00 | S |
| PERIMETER_TOP_ZN_2_WALL_EAST | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-11.9 | 0.30 | 0.477 | 0.514 | 91.28 | 47.75 | 90.00 | 90.00 | E |
| PERIMETER_TOP_ZN_3_WALL_NORTH | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-11.9 | 0.30 | 0.477 | 0.514 | 136.92 | 71.63 | 0.00 | 90.00 | N |
| PERIMETER_TOP_ZN_4_WALL_WEST | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-11.9 | 0.30 | 0.477 | 0.514 | 91.28 | 47.75 | 270.00 | 90.00 | W |
| PERIMETER_TOP_PLENUM_WALL_EAST | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-11.9 | 0.30 | 0.477 | 0.514 | 40.57 | 40.57 | 90.00 | 90.00 | E |
| PERIMETER_TOP_PLENUM_WALL_NORTH | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-11.9 | 0.30 | 0.477 | 0.514 | 60.85 | 60.85 | 0.00 | 90.00 | N |
| PERIMETER_TOP_PLENUM_WALL_SOUTH | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-11.9 | 0.30 | 0.477 | 0.514 | 60.85 | 60.85 | 180.00 | 90.00 | S |
| PERIMETER_TOP_PLENUM_WALL_WEST | TYPICAL INSULATED STEEL FRAMED EXTERIOR WALL R-11.9 | 0.30 | 0.477 | 0.514 | 40.57 | 40.57 | 270.00 | 90.00 | W |
| BUILDING_ROOF | TYPICAL IEAD ROOF - HIGHLY REFLECTIVE R-25.64 | 0.55 | 0.221 | 0.228 | 1660.73 | 1660.73 | 0.00 | 0.00 |
| Construction | Glass Area [m2] | Frame Area [m2] | Divider Area [m2] | Area of One Opening [m2] | Area of Multiplied Openings [m2] | Glass U-Factor [W/m2-K] | Glass SHGC | Glass Visible Transmittance | Frame Conductance [W/m2-K] | Divider Conductance [W/m2-K] | Shade Control | Parent Surface | Azimuth [deg] | Tilt [deg] | Cardinal Direction | |
| PERIMETER_BOT_ZN_1_WALL_SOUTH_WINDOW | U 0.60 SHGC 0.25 DBL 2.5MM AIR | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 3.511 | 0.227 | 0.284 | No | PERIMETER_BOT_ZN_1_WALL_SOUTH | 180.00 | 90.00 | S | ||
| PERIMETER_BOT_ZN_2_WALL_EAST_WINDOW | U 0.60 SHGC 0.25 DBL 2.5MM AIR | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 3.511 | 0.227 | 0.284 | No | PERIMETER_BOT_ZN_2_WALL_EAST | 90.00 | 90.00 | E | ||
| PERIMETER_BOT_ZN_3_WALL_NORTH_WINDOW | U 0.60 SHGC 0.25 DBL 2.5MM AIR | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 3.511 | 0.227 | 0.284 | No | PERIMETER_BOT_ZN_3_WALL_NORTH | 0.00 | 90.00 | N | ||
| PERIMETER_BOT_ZN_4_WALL_WEST_WINDOW | U 0.60 SHGC 0.25 DBL 2.5MM AIR | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 3.511 | 0.227 | 0.284 | No | PERIMETER_BOT_ZN_4_WALL_WEST | 270.00 | 90.00 | W | ||
| PERIMETER_MID_ZN_1_WALL_SOUTH_WINDOW | U 0.60 SHGC 0.25 DBL 2.5MM AIR | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 3.511 | 0.227 | 0.284 | No | PERIMETER_MID_ZN_1_WALL_SOUTH | 180.00 | 90.00 | S | ||
| PERIMETER_MID_ZN_2_WALL_EAST_WINDOW | U 0.60 SHGC 0.25 DBL 2.5MM AIR | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 3.511 | 0.227 | 0.284 | No | PERIMETER_MID_ZN_2_WALL_EAST | 90.00 | 90.00 | E | ||
| PERIMETER_MID_ZN_3_WALL_NORTH_WINDOW | U 0.60 SHGC 0.25 DBL 2.5MM AIR | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 3.511 | 0.227 | 0.284 | No | PERIMETER_MID_ZN_3_WALL_NORTH | 0.00 | 90.00 | N | ||
| PERIMETER_MID_ZN_4_WALL_WEST_WINDOW | U 0.60 SHGC 0.25 DBL 2.5MM AIR | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 3.511 | 0.227 | 0.284 | No | PERIMETER_MID_ZN_4_WALL_WEST | 270.00 | 90.00 | W | ||
| PERIMETER_TOP_ZN_1_WALL_SOUTH_WINDOW | U 0.60 SHGC 0.25 DBL 2.5MM AIR | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 3.511 | 0.227 | 0.284 | No | PERIMETER_TOP_ZN_1_WALL_SOUTH | 180.00 | 90.00 | S | ||
| PERIMETER_TOP_ZN_2_WALL_EAST_WINDOW | U 0.60 SHGC 0.25 DBL 2.5MM AIR | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 3.511 | 0.227 | 0.284 | No | PERIMETER_TOP_ZN_2_WALL_EAST | 90.00 | 90.00 | E | ||
| PERIMETER_TOP_ZN_3_WALL_NORTH_WINDOW | U 0.60 SHGC 0.25 DBL 2.5MM AIR | 65.28 | 0.00 | 0.00 | 65.28 | 65.28 | 3.511 | 0.227 | 0.284 | No | PERIMETER_TOP_ZN_3_WALL_NORTH | 0.00 | 90.00 | N | ||
| PERIMETER_TOP_ZN_4_WALL_WEST_WINDOW | U 0.60 SHGC 0.25 DBL 2.5MM AIR | 43.52 | 0.00 | 0.00 | 43.52 | 43.52 | 3.511 | 0.227 | 0.284 | No | PERIMETER_TOP_ZN_4_WALL_WEST | 270.00 | 90.00 | W | ||
| Total or Average | 652.83 | 3.511 | 0.227 | 0.284 | ||||||||||||
| North Total or Average | 195.85 | 3.511 | 0.227 | 0.284 | ||||||||||||
| Non-North Total or Average | 456.98 | 3.511 | 0.227 | 0.284 |
| Construction | Area of One Opening [m2] | Area of Openings [m2] | Glass U-Factor [W/m2-K] | Glass SHGC | Glass Visible Transmittance | Parent Surface | |
| Total or Average | 0.00 | - | - | - |
| Construction | U-Factor with Film [W/m2-K] | U-Factor no Film [W/m2-K] | Gross Area [m2] | Parent Surface | |
| None |
Report: Shading Summary
For: Entire Facility
Timestamp: 2019-04-09 23:11:28
Sunlit Fraction| March 21 9am | March 21 noon | March 21 3pm | June 21 9am | June 21 noon | June 21 3pm | December 21 9am | December 21 noon | December 21 3pm | |
| PERIMETER_BOT_ZN_1_WALL_SOUTH_WINDOW | 1.00 | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 |
| PERIMETER_BOT_ZN_2_WALL_EAST_WINDOW | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 0.00 |
| PERIMETER_BOT_ZN_3_WALL_NORTH_WINDOW | 0.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_BOT_ZN_4_WALL_WEST_WINDOW | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 |
| PERIMETER_MID_ZN_1_WALL_SOUTH_WINDOW | 1.00 | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 |
| PERIMETER_MID_ZN_2_WALL_EAST_WINDOW | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 0.00 |
| PERIMETER_MID_ZN_3_WALL_NORTH_WINDOW | 0.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_MID_ZN_4_WALL_WEST_WINDOW | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 |
| PERIMETER_TOP_ZN_1_WALL_SOUTH_WINDOW | 1.00 | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 |
| PERIMETER_TOP_ZN_2_WALL_EAST_WINDOW | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 0.00 |
| PERIMETER_TOP_ZN_3_WALL_NORTH_WINDOW | 0.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| PERIMETER_TOP_ZN_4_WALL_WEST_WINDOW | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 |
| Name | Type | Shaded Construction | Control | Glare Control | |
| None |
Report: Lighting Summary
For: Entire Facility
Timestamp: 2019-04-09 23:11:28
Interior Lighting| Zone | Lighting Power Density [W/m2] | Zone Area [m2] | Total Power [W] | End Use Subcategory | Schedule Name | Scheduled Hours/Week [hr] | Hours/Week > 1% [hr] | Full Load Hours/Week [hr] | Return Air Fraction | Conditioned (Y/N) | Consumption [GJ] | |
| CORE_BOTTOM ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | CORE_BOTTOM ZN | 8.8264 | 983.54 | 8681.09 | General | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | 49.01 | 168.00 | 49.01 | 0.0000 | Y | 79.86 |
| CORE_MID ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | CORE_MID ZN | 8.8264 | 983.54 | 8681.09 | General | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | 49.01 | 168.00 | 49.01 | 0.0000 | Y | 79.86 |
| CORE_TOP ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | CORE_TOP ZN | 8.8264 | 983.54 | 8681.09 | General | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | 49.01 | 168.00 | 49.01 | 0.0000 | Y | 79.86 |
| PERIMETER_BOT_ZN_1 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | PERIMETER_BOT_ZN_1 ZN | 8.8264 | 207.34 | 1830.05 | General | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | 49.01 | 168.00 | 28.35 | 0.0000 | Y | 9.74 |
| PERIMETER_BOT_ZN_2 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | PERIMETER_BOT_ZN_2 ZN | 8.8264 | 131.26 | 1158.57 | General | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | 49.01 | 168.00 | 28.73 | 0.0000 | Y | 6.25 |
| PERIMETER_BOT_ZN_3 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | PERIMETER_BOT_ZN_3 ZN | 8.8264 | 207.34 | 1830.05 | General | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | 49.01 | 168.00 | 29.02 | 0.0000 | Y | 9.97 |
| PERIMETER_BOT_ZN_4 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | PERIMETER_BOT_ZN_4 ZN | 8.8264 | 131.25 | 1158.50 | General | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | 49.01 | 168.00 | 28.68 | 0.0000 | Y | 6.24 |
| PERIMETER_MID_ZN_1 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | PERIMETER_MID_ZN_1 ZN | 8.8264 | 207.34 | 1830.05 | General | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | 49.01 | 168.00 | 28.30 | 0.0000 | Y | 9.72 |
| PERIMETER_MID_ZN_2 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | PERIMETER_MID_ZN_2 ZN | 8.8264 | 131.26 | 1158.57 | General | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | 49.01 | 168.00 | 28.63 | 0.0000 | Y | 6.23 |
| PERIMETER_MID_ZN_3 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | PERIMETER_MID_ZN_3 ZN | 8.8264 | 207.34 | 1830.05 | General | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | 49.01 | 168.00 | 28.89 | 0.0000 | Y | 9.92 |
| PERIMETER_MID_ZN_4 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | PERIMETER_MID_ZN_4 ZN | 8.8264 | 131.25 | 1158.50 | General | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | 49.01 | 168.00 | 28.58 | 0.0000 | Y | 6.22 |
| PERIMETER_TOP_ZN_1 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | PERIMETER_TOP_ZN_1 ZN | 8.8264 | 207.34 | 1830.05 | General | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | 49.01 | 168.00 | 28.30 | 0.0000 | Y | 9.72 |
| PERIMETER_TOP_ZN_2 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | PERIMETER_TOP_ZN_2 ZN | 8.8264 | 131.26 | 1158.57 | General | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | 49.01 | 168.00 | 28.63 | 0.0000 | Y | 6.23 |
| PERIMETER_TOP_ZN_3 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | PERIMETER_TOP_ZN_3 ZN | 8.8264 | 207.34 | 1830.05 | General | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | 49.01 | 168.00 | 28.89 | 0.0000 | Y | 9.92 |
| PERIMETER_TOP_ZN_4 ZN OFFICE WHOLEBUILDING - MD OFFICE LIGHTS | PERIMETER_TOP_ZN_4 ZN | 8.8264 | 131.25 | 1158.50 | General | OFFICEMEDIUM BLDG_LIGHT_SCH_2013 | 49.01 | 168.00 | 28.58 | 0.0000 | Y | 6.22 |
| Interior Lighting Total | 8.8264 | 4982.19 | 43974.80 | 335.95 |
| Zone | Control Name | Daylighting Method | Control Type | Fraction Controlled | Lighting Installed in Zone [W] | Lighting Controlled [W] | |
| PERIMETER_BOT_ZN_1 DAYLT SENSOR 1 | PERIMETER_BOT_ZN_1 ZN | PERIMETER_BOT_ZN_1 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.38 | 1830.05 | 701.82 |
| PERIMETER_BOT_ZN_1 DAYLT SENSOR 2 | PERIMETER_BOT_ZN_1 ZN | PERIMETER_BOT_ZN_1 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.14 | 1830.05 | 255.29 |
| PERIMETER_BOT_ZN_2 DAYLT SENSOR 1 | PERIMETER_BOT_ZN_2 ZN | PERIMETER_BOT_ZN_2 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.38 | 1158.57 | 444.31 |
| PERIMETER_BOT_ZN_2 DAYLT SENSOR 2 | PERIMETER_BOT_ZN_2 ZN | PERIMETER_BOT_ZN_2 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.14 | 1158.57 | 161.62 |
| PERIMETER_BOT_ZN_3 DAYLT SENSOR 1 | PERIMETER_BOT_ZN_3 ZN | PERIMETER_BOT_ZN_3 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.38 | 1830.05 | 701.82 |
| PERIMETER_BOT_ZN_3 DAYLT SENSOR 2 | PERIMETER_BOT_ZN_3 ZN | PERIMETER_BOT_ZN_3 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.14 | 1830.05 | 255.29 |
| PERIMETER_BOT_ZN_4 DAYLT SENSOR 1 | PERIMETER_BOT_ZN_4 ZN | PERIMETER_BOT_ZN_4 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.38 | 1158.50 | 444.28 |
| PERIMETER_BOT_ZN_4 DAYLT SENSOR 2 | PERIMETER_BOT_ZN_4 ZN | PERIMETER_BOT_ZN_4 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.14 | 1158.50 | 161.61 |
| PERIMETER_MID_ZN_1 DAYLT SENSOR 1 | PERIMETER_MID_ZN_1 ZN | PERIMETER_MID_ZN_1 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.38 | 1830.05 | 701.82 |
| PERIMETER_MID_ZN_1 DAYLT SENSOR 2 | PERIMETER_MID_ZN_1 ZN | PERIMETER_MID_ZN_1 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.14 | 1830.05 | 255.29 |
| PERIMETER_MID_ZN_2 DAYLT SENSOR 1 | PERIMETER_MID_ZN_2 ZN | PERIMETER_MID_ZN_2 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.38 | 1158.57 | 444.31 |
| PERIMETER_MID_ZN_2 DAYLT SENSOR 2 | PERIMETER_MID_ZN_2 ZN | PERIMETER_MID_ZN_2 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.14 | 1158.57 | 161.62 |
| PERIMETER_MID_ZN_3 DAYLT SENSOR 1 | PERIMETER_MID_ZN_3 ZN | PERIMETER_MID_ZN_3 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.38 | 1830.05 | 701.82 |
| PERIMETER_MID_ZN_3 DAYLT SENSOR 2 | PERIMETER_MID_ZN_3 ZN | PERIMETER_MID_ZN_3 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.14 | 1830.05 | 255.29 |
| PERIMETER_MID_ZN_4 DAYLT SENSOR 1 | PERIMETER_MID_ZN_4 ZN | PERIMETER_MID_ZN_4 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.38 | 1158.50 | 444.28 |
| PERIMETER_MID_ZN_4 DAYLT SENSOR 2 | PERIMETER_MID_ZN_4 ZN | PERIMETER_MID_ZN_4 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.14 | 1158.50 | 161.61 |
| PERIMETER_TOP_ZN_1 DAYLT SENSOR 1 | PERIMETER_TOP_ZN_1 ZN | PERIMETER_TOP_ZN_1 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.38 | 1830.05 | 701.82 |
| PERIMETER_TOP_ZN_1 DAYLT SENSOR 2 | PERIMETER_TOP_ZN_1 ZN | PERIMETER_TOP_ZN_1 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.14 | 1830.05 | 255.29 |
| PERIMETER_TOP_ZN_2 DAYLT SENSOR 1 | PERIMETER_TOP_ZN_2 ZN | PERIMETER_TOP_ZN_2 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.38 | 1158.57 | 444.31 |
| PERIMETER_TOP_ZN_2 DAYLT SENSOR 2 | PERIMETER_TOP_ZN_2 ZN | PERIMETER_TOP_ZN_2 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.14 | 1158.57 | 161.62 |
| PERIMETER_TOP_ZN_3 DAYLT SENSOR 1 | PERIMETER_TOP_ZN_3 ZN | PERIMETER_TOP_ZN_3 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.38 | 1830.05 | 701.82 |
| PERIMETER_TOP_ZN_3 DAYLT SENSOR 2 | PERIMETER_TOP_ZN_3 ZN | PERIMETER_TOP_ZN_3 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.14 | 1830.05 | 255.29 |
| PERIMETER_TOP_ZN_4 DAYLT SENSOR 1 | PERIMETER_TOP_ZN_4 ZN | PERIMETER_TOP_ZN_4 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.38 | 1158.50 | 444.28 |
| PERIMETER_TOP_ZN_4 DAYLT SENSOR 2 | PERIMETER_TOP_ZN_4 ZN | PERIMETER_TOP_ZN_4 ZN DAYLIGHTINGCONTROLS | SplitFlux | Stepped | 0.14 | 1158.50 | 161.61 |
| Total Watts | Astronomical Clock/Schedule | Schedule Name | Scheduled Hours/Week [hr] | Hours/Week > 1% [hr] | Full Load Hours/Week [hr] | Consumption [GJ] | |
| NONDIMMING EXTERIOR LIGHTS DEF | 623.03 | AstronomicalClock | - | 41.79 | 41.79 | 4.89 | |
| OCC SENSING EXTERIOR LIGHTS DEF | 7476.45 | AstronomicalClock | - | 83.79 | 71.19 | 99.91 | |
| Exterior Lighting Total | 8099.48 | 104.80 |
Report: Equipment Summary
For: Entire Facility
Timestamp: 2019-04-09 23:11:28
Central Plant| Type | Nominal Capacity [W] | Nominal Efficiency [W/W] | IPLV in SI Units [W/W] | IPLV in IP Units [Btu/W-h] | |
| NREL ZNE READY 2017 CHILLER 0 84TONS 1.1KW/TON | Chiller:Electric:EIR | 295772.86 | 3.29 | 4.49 | 15.32 |
| BOILER 617KBTU/HR 0.94 COMBUSTION EFF | Boiler:HotWater | 180680.03 | 0.93 |
| Type | Design Coil Load [W] | Nominal Total Capacity [W] | Nominal Sensible Capacity [W] | Nominal Latent Capacity [W] | Nominal Sensible Heat Ratio | Nominal Efficiency [W/W] | Nominal Coil UA Value [W/C] | Nominal Coil Surface Area [m2] | |
| 15 ZONE VAV CLG COIL | Coil:Cooling:Water | 295772.86 | 358174.83 | 245274.96 | 112899.87 | 0.68 | - | 40581.51 | 411.60 |
| DX Cooling Coil Type | Standard Rated Net Cooling Capacity [W] | Standard Rated Net COP [W/W] | EER [Btu/W-h] | SEER [Btu/W-h] | IEER [Btu/W-h] | |
| None |
| DX Cooling Coil Type | Rated Net Cooling Capacity Test A [W] | Rated Electric Power Test A [W] | Rated Net Cooling Capacity Test B [W] | Rated Electric Power Test B [W] | Rated Net Cooling Capacity Test C [W] | Rated Electric Power Test C [W] | Rated Net Cooling Capacity Test D [W] | Rated Electric Power Test D [W] | |
| None |
| DX Heating Coil Type | High Temperature Heating (net) Rating Capacity [W] | Low Temperature Heating (net) Rating Capacity [W] | HSPF [Btu/W-h] | Region Number | |
| None |
| Type | Design Coil Load [W] | Nominal Total Capacity [W] | Nominal Efficiency [W/W] | |
| CORE_BOTTOM ZN REHEAT COIL | Coil:Heating:Water | 9090.10 | 16538.31 | - |
| CORE_MID ZN REHEAT COIL | Coil:Heating:Water | 15814.03 | 28755.78 | - |
| CORE_TOP ZN REHEAT COIL | Coil:Heating:Water | 28786.86 | 52348.07 | - |
| PERIMETER_BOT_ZN_1 ZN REHEAT COIL | Coil:Heating:Water | 8564.32 | 15574.08 | - |
| PERIMETER_BOT_ZN_2 ZN REHEAT COIL | Coil:Heating:Water | 5774.75 | 10501.30 | - |
| PERIMETER_BOT_ZN_3 ZN REHEAT COIL | Coil:Heating:Water | 8502.95 | 15462.49 | - |
| PERIMETER_BOT_ZN_4 ZN REHEAT COIL | Coil:Heating:Water | 5774.68 | 10501.17 | - |
| PERIMETER_MID_ZN_1 ZN REHEAT COIL | Coil:Heating:Water | 10628.80 | 19328.36 | - |
| PERIMETER_MID_ZN_2 ZN REHEAT COIL | Coil:Heating:Water | 7093.58 | 12899.61 | - |
| PERIMETER_MID_ZN_3 ZN REHEAT COIL | Coil:Heating:Water | 10620.76 | 19313.74 | - |
| PERIMETER_MID_ZN_4 ZN REHEAT COIL | Coil:Heating:Water | 7093.42 | 12899.31 | - |
| PERIMETER_TOP_ZN_1 ZN REHEAT COIL | Coil:Heating:Water | 13190.00 | 23985.91 | - |
| PERIMETER_TOP_ZN_2 ZN REHEAT COIL | Coil:Heating:Water | 8707.35 | 15834.27 | - |
| PERIMETER_TOP_ZN_3 ZN REHEAT COIL | Coil:Heating:Water | 13199.32 | 24002.86 | - |
| PERIMETER_TOP_ZN_4 ZN REHEAT COIL | Coil:Heating:Water | 8707.09 | 15833.79 | - |
| 15 ZONE VAV MAIN HTG COIL | Coil:Heating:Water | 19132.02 | 31488.55 | - |
| Type | Total Efficiency [W/W] | Delta Pressure [pa] | Max Air Flow Rate [m3/s] | Rated Electric Power [W] | Rated Power Per Max Air Flow Rate [W-s/m3] | Motor Heat In Air Fraction | Fan Energy Index | End Use Subcategory | Design Day Name for Fan Sizing Peak | Date/Time for Fan Sizing Peak | |
| 15 ZONE VAV FAN | Fan:VariableVolume | 0.64 | 996.36 | 13.60 | 21019.62 | 1545.22 | 1.00 | 1.21 | General | HOUSTON BUSH INTERCONTINENTAL ANN CLG .4% CONDNS DB=>MWB | 7/21 15:40:00 |
| Type | Control | Head [pa] | Water Flow [m3/s] | Electric Power [W] | Power Per Water Flow Rate [W-s/m3] | Motor Efficiency [W/W] | End Use Subcategory | |
| CHILLED WATER LOOP PUMP | Pump:VariableSpeed | Intermittent | 249416.25 | 0.012558 | 4379.04 | 348707.11 | 0.92 | General |
| HOT WATER LOOP PUMP | Pump:VariableSpeed | Intermittent | 203190.05 | 0.003952 | 1190.16 | 301156.14 | 0.86 | General |
| SERVICE WATER LOOP PUMP | Pump:ConstantSpeed | Intermittent | 164431.25 | 0.000054 | 16.15 | 301156.14 | 0.70 | General |
| Type | Storage Volume [m3] | Input [W] | Thermal Efficiency [W/W] | Recovery Efficiency [W/W] | Energy Factor | |
| 100GAL NATURAL GAS WATER HEATER - 100KBTU/HR 0.802 THERM EFF 0.808 THERM EFF | WaterHeater:Mixed | 0.38 | 29307.11 | 0.81 | 1.02 | 0.23 |
Report: HVAC Sizing Summary
For: Entire Facility
Timestamp: 2019-04-09 23:11:28
Zone Sensible Cooling| Calculated Design Load [W] | User Design Load [W] | User Design Load per Area [W/m2] | Calculated Design Air Flow [m3/s] | User Design Air Flow [m3/s] | Design Day Name | Date/Time Of Peak {TIMESTAMP} | Thermostat Setpoint Temperature at Peak Load [C] | Indoor Temperature at Peak Load [C] | Indoor Humidity Ratio at Peak Load [kgWater/kgAir] | Outdoor Temperature at Peak Load [C] | Outdoor Humidity Ratio at Peak Load [kgWater/kgAir] | Minimum Outdoor Air Flow Rate [m3/s] | Heat Gain Rate from DOAS [W] | |
| CORE_BOTTOM ZN | 40923.95 | 40923.95 | 41.61 | 2.953 | 2.953 | HOUSTON BUSH INTERCONTINENTAL ANN CLG .4% CONDNS DB=>MWB | 7/21 08:00:00 | 24.00 | 24.00 | 0.00880 | 28.53 | 0.01519 | 0.425 | 0.00 |
| CORE_MID ZN | 29293.99 | 29293.99 | 29.78 | 2.111 | 2.111 | HOUSTON BUSH INTERCONTINENTAL ANN CLG .4% CONDNS DB=>MWB | 7/21 08:00:00 | 24.00 | 24.00 | 0.00892 | 28.53 | 0.01519 | 0.425 | 0.00 |
| CORE_TOP ZN | 30379.51 | 30379.51 | 30.89 | 2.210 | 2.210 | HOUSTON BUSH INTERCONTINENTAL ANN CLG .4% CONDNS DB=>MWB | 7/21 15:00:00 | 24.00 | 24.00 | 0.00890 | 36.00 | 0.01519 | 0.425 | 0.00 |
| PERIMETER_BOT_ZN_1 ZN | 8013.09 | 8013.09 | 38.65 | 0.583 | 0.583 | HOUSTON BUSH INTERCONTINENTAL ANN CLG .4% CONDNS DB=>MWB | 7/21 13:40:00 | 24.00 | 24.00 | 0.00885 | 35.83 | 0.01519 | 0.090 | 0.00 |
| PERIMETER_BOT_ZN_2 ZN | 8690.78 | 8690.78 | 66.21 | 0.632 | 0.632 | HOUSTON BUSH INTERCONTINENTAL ANN CLG .4% CONDNS DB=>MWB | 7/21 09:30:00 | 24.00 | 24.00 | 0.00871 | 31.30 | 0.01519 | 0.057 | 0.00 |
| PERIMETER_BOT_ZN_3 ZN | 7006.16 | 7006.16 | 33.79 | 0.510 | 0.510 | HOUSTON BUSH INTERCONTINENTAL ANN CLG .4% CONDNS DB=>MWB | 7/21 14:50:00 | 24.00 | 24.00 | 0.00890 | 36.00 | 0.01519 | 0.090 | 0.00 |
| PERIMETER_BOT_ZN_4 ZN | 9239.47 | 9239.47 | 70.39 | 0.672 | 0.672 | HOUSTON BUSH INTERCONTINENTAL ANN CLG .4% CONDNS DB=>MWB | 7/21 17:00:00 | 24.00 | 24.00 | 0.00869 | 34.59 | 0.01519 | 0.057 | 0.00 |